device name,device type,product id,shortname,fullname,type [options...] \| (min/max),uom,writeable,discovery entityid v3.4, discovery entityid
BK13/BK15/Smartline/GB1x2,boiler,64,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
BK13/BK15/Smartline/GB1x2,boiler,64,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
BK13/BK15/Smartline/GB1x2,boiler,64,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
BK13/BK15/Smartline/GB1x2,boiler,64,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
BK13/BK15/Smartline/GB1x2,boiler,64,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
BK13/BK15/Smartline/GB1x2,boiler,64,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
BK13/BK15/Smartline/GB1x2,boiler,64,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
BK13/BK15/Smartline/GB1x2,boiler,64,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
BK13/BK15/Smartline/GB1x2,boiler,64,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
BK13/BK15/Smartline/GB1x2,boiler,64,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
BK13/BK15/Smartline/GB1x2,boiler,64,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
BK13/BK15/Smartline/GB1x2,boiler,64,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
BK13/BK15/Smartline/GB1x2,boiler,64,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
BK13/BK15/Smartline/GB1x2,boiler,64,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
BK13/BK15/Smartline/GB1x2,boiler,64,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
BK13/BK15/Smartline/GB1x2,boiler,64,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
BK13/BK15/Smartline/GB1x2,boiler,64,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
BK13/BK15/Smartline/GB1x2,boiler,64,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
BK13/BK15/Smartline/GB1x2,boiler,64,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
BK13/BK15/Smartline/GB1x2,boiler,64,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
BK13/BK15/Smartline/GB1x2,boiler,64,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
BK13/BK15/Smartline/GB1x2,boiler,64,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
BK13/BK15/Smartline/GB1x2,boiler,64,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
BK13/BK15/Smartline/GB1x2,boiler,64,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
BK13/BK15/Smartline/GB1x2,boiler,64,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
BK13/BK15/Smartline/GB1x2,boiler,64,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
BK13/BK15/Smartline/GB1x2,boiler,64,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
BK13/BK15/Smartline/GB1x2,boiler,64,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
BK13/BK15/Smartline/GB1x2,boiler,64,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
BK13/BK15/Smartline/GB1x2,boiler,64,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
BK13/BK15/Smartline/GB1x2,boiler,64,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
BK13/BK15/Smartline/GB1x2,boiler,64,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
BK13/BK15/Smartline/GB1x2,boiler,64,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
BK13/BK15/Smartline/GB1x2,boiler,64,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
BK13/BK15/Smartline/GB1x2,boiler,64,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
BK13/BK15/Smartline/GB1x2,boiler,64,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
BK13/BK15/Smartline/GB1x2,boiler,64,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
BK13/BK15/Smartline/GB1x2,boiler,64,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
BK13/BK15/Smartline/GB1x2,boiler,64,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
BK13/BK15/Smartline/GB1x2,boiler,64,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
BK13/BK15/Smartline/GB1x2,boiler,64,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
BK13/BK15/Smartline/GB1x2,boiler,64,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
BK13/BK15/Smartline/GB1x2,boiler,64,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
BK13/BK15/Smartline/GB1x2,boiler,64,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
BK13/BK15/Smartline/GB1x2,boiler,64,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
BK13/BK15/Smartline/GB1x2,boiler,64,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
BK13/BK15/Smartline/GB1x2,boiler,64,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
BK13/BK15/Smartline/GB1x2,boiler,64,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
BK13/BK15/Smartline/GB1x2,boiler,64,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
BK13/BK15/Smartline/GB1x2,boiler,64,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
BK13/BK15/Smartline/GB1x2,boiler,64,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
BK13/BK15/Smartline/GB1x2,boiler,64,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
BK13/BK15/Smartline/GB1x2,boiler,64,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
BK13/BK15/Smartline/GB1x2,boiler,64,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
BK13/BK15/Smartline/GB1x2,boiler,64,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
BK13/BK15/Smartline/GB1x2,boiler,64,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
BK13/BK15/Smartline/GB1x2,boiler,64,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
BK13/BK15/Smartline/GB1x2,boiler,64,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
BK13/BK15/Smartline/GB1x2,boiler,64,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
BK13/BK15/Smartline/GB1x2,boiler,64,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
BK13/BK15/Smartline/GB1x2,boiler,64,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
BK13/BK15/Smartline/GB1x2,boiler,64,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
BK13/BK15/Smartline/GB1x2,boiler,64,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
BK13/BK15/Smartline/GB1x2,boiler,64,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
BK13/BK15/Smartline/GB1x2,boiler,64,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
BK13/BK15/Smartline/GB1x2,boiler,64,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
BK13/BK15/Smartline/GB1x2,boiler,64,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
BK13/BK15/Smartline/GB1x2,boiler,64,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
BK13/BK15/Smartline/GB1x2,boiler,64,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
BK13/BK15/Smartline/GB1x2,boiler,64,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
BK13/BK15/Smartline/GB1x2,boiler,64,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
BK13/BK15/Smartline/GB1x2,boiler,64,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
BK13/BK15/Smartline/GB1x2,boiler,64,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
BK13/BK15/Smartline/GB1x2,boiler,64,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
BK13/BK15/Smartline/GB1x2,boiler,64,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
BK13/BK15/Smartline/GB1x2,boiler,64,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
BK13/BK15/Smartline/GB1x2,boiler,64,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
BK13/BK15/Smartline/GB1x2,boiler,64,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
BK13/BK15/Smartline/GB1x2,boiler,64,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
BK13/BK15/Smartline/GB1x2,boiler,64,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
BK13/BK15/Smartline/GB1x2,boiler,64,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
BK13/BK15/Smartline/GB1x2,boiler,64,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
BK13/BK15/Smartline/GB1x2,boiler,64,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
GB125/GB135/MC10,boiler,72,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
GB125/GB135/MC10,boiler,72,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
GB125/GB135/MC10,boiler,72,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
GB125/GB135/MC10,boiler,72,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
GB125/GB135/MC10,boiler,72,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
GB125/GB135/MC10,boiler,72,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
GB125/GB135/MC10,boiler,72,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
GB125/GB135/MC10,boiler,72,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
GB125/GB135/MC10,boiler,72,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
GB125/GB135/MC10,boiler,72,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
GB125/GB135/MC10,boiler,72,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
GB125/GB135/MC10,boiler,72,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
GB125/GB135/MC10,boiler,72,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
GB125/GB135/MC10,boiler,72,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
GB125/GB135/MC10,boiler,72,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
GB125/GB135/MC10,boiler,72,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
GB125/GB135/MC10,boiler,72,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
GB125/GB135/MC10,boiler,72,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
GB125/GB135/MC10,boiler,72,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
GB125/GB135/MC10,boiler,72,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
GB125/GB135/MC10,boiler,72,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
GB125/GB135/MC10,boiler,72,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
GB125/GB135/MC10,boiler,72,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
GB125/GB135/MC10,boiler,72,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
GB125/GB135/MC10,boiler,72,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
GB125/GB135/MC10,boiler,72,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
GB125/GB135/MC10,boiler,72,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
GB125/GB135/MC10,boiler,72,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
GB125/GB135/MC10,boiler,72,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
GB125/GB135/MC10,boiler,72,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
GB125/GB135/MC10,boiler,72,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
GB125/GB135/MC10,boiler,72,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
GB125/GB135/MC10,boiler,72,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
GB125/GB135/MC10,boiler,72,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
GB125/GB135/MC10,boiler,72,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
GB125/GB135/MC10,boiler,72,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
GB125/GB135/MC10,boiler,72,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
GB125/GB135/MC10,boiler,72,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
GB125/GB135/MC10,boiler,72,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
GB125/GB135/MC10,boiler,72,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
GB125/GB135/MC10,boiler,72,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
GB125/GB135/MC10,boiler,72,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
GB125/GB135/MC10,boiler,72,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
GB125/GB135/MC10,boiler,72,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
GB125/GB135/MC10,boiler,72,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
GB125/GB135/MC10,boiler,72,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
GB125/GB135/MC10,boiler,72,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
GB125/GB135/MC10,boiler,72,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
GB125/GB135/MC10,boiler,72,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
GB125/GB135/MC10,boiler,72,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
GB125/GB135/MC10,boiler,72,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
GB125/GB135/MC10,boiler,72,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
GB125/GB135/MC10,boiler,72,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
GB125/GB135/MC10,boiler,72,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
GB125/GB135/MC10,boiler,72,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
GB125/GB135/MC10,boiler,72,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
GB125/GB135/MC10,boiler,72,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
GB125/GB135/MC10,boiler,72,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
GB125/GB135/MC10,boiler,72,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
GB125/GB135/MC10,boiler,72,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
GB125/GB135/MC10,boiler,72,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
GB125/GB135/MC10,boiler,72,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
GB125/GB135/MC10,boiler,72,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
GB125/GB135/MC10,boiler,72,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
GB125/GB135/MC10,boiler,72,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
GB125/GB135/MC10,boiler,72,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
GB125/GB135/MC10,boiler,72,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
GB125/GB135/MC10,boiler,72,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
GB125/GB135/MC10,boiler,72,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
GB125/GB135/MC10,boiler,72,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
GB125/GB135/MC10,boiler,72,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
GB125/GB135/MC10,boiler,72,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
GB125/GB135/MC10,boiler,72,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
GB125/GB135/MC10,boiler,72,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
GB125/GB135/MC10,boiler,72,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
GB125/GB135/MC10,boiler,72,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
GB125/GB135/MC10,boiler,72,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
GB125/GB135/MC10,boiler,72,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
GB125/GB135/MC10,boiler,72,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
GB125/GB135/MC10,boiler,72,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
GB125/GB135/MC10,boiler,72,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
GB125/GB135/MC10,boiler,72,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
GB125/GB135/MC10,boiler,72,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
GB125/GB135/MC10,boiler,72,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
GB125/GB135/MC10,boiler,72,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
GB125/GB135/MC10,boiler,72,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
GB125/GB135/MC10,boiler,72,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
GB125/GB135/MC10,boiler,72,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
GB125/GB135/MC10,boiler,72,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
GB125/GB135/MC10,boiler,72,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
GB125/GB135/MC10,boiler,72,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Cascade CM10,boiler,81,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Cascade CM10,boiler,81,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Cascade CM10,boiler,81,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Cascade CM10,boiler,81,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Cascade CM10,boiler,81,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Cascade CM10,boiler,81,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Cascade CM10,boiler,81,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Cascade CM10,boiler,81,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Cascade CM10,boiler,81,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Cascade CM10,boiler,81,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Cascade CM10,boiler,81,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Cascade CM10,boiler,81,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Cascade CM10,boiler,81,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Cascade CM10,boiler,81,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Cascade CM10,boiler,81,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Cascade CM10,boiler,81,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Cascade CM10,boiler,81,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Cascade CM10,boiler,81,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Cascade CM10,boiler,81,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Cascade CM10,boiler,81,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Cascade CM10,boiler,81,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Cascade CM10,boiler,81,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Cascade CM10,boiler,81,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Cascade CM10,boiler,81,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Cascade CM10,boiler,81,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Cascade CM10,boiler,81,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Cascade CM10,boiler,81,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Cascade CM10,boiler,81,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Cascade CM10,boiler,81,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Cascade CM10,boiler,81,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Cascade CM10,boiler,81,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Cascade CM10,boiler,81,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Cascade CM10,boiler,81,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Cascade CM10,boiler,81,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Cascade CM10,boiler,81,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Cascade CM10,boiler,81,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Cascade CM10,boiler,81,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Cascade CM10,boiler,81,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Cascade CM10,boiler,81,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Cascade CM10,boiler,81,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Cascade CM10,boiler,81,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Cascade CM10,boiler,81,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Cascade CM10,boiler,81,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Cascade CM10,boiler,81,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Cascade CM10,boiler,81,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Cascade CM10,boiler,81,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Cascade CM10,boiler,81,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Cascade CM10,boiler,81,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Cascade CM10,boiler,81,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Cascade CM10,boiler,81,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Cascade CM10,boiler,81,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Cascade CM10,boiler,81,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Cascade CM10,boiler,81,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Cascade CM10,boiler,81,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Cascade CM10,boiler,81,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Cascade CM10,boiler,81,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Cascade CM10,boiler,81,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Cascade CM10,boiler,81,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Cascade CM10,boiler,81,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Cascade CM10,boiler,81,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Cascade CM10,boiler,81,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Cascade CM10,boiler,81,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Cascade CM10,boiler,81,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Cascade CM10,boiler,81,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Cascade CM10,boiler,81,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Cascade CM10,boiler,81,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Cascade CM10,boiler,81,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Cascade CM10,boiler,81,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Cascade CM10,boiler,81,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Cascade CM10,boiler,81,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Cascade CM10,boiler,81,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Cascade CM10,boiler,81,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Cascade CM10,boiler,81,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Cascade CM10,boiler,81,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Cascade CM10,boiler,81,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Cascade CM10,boiler,81,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Cascade CM10,boiler,81,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Cascade CM10,boiler,81,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Cascade CM10,boiler,81,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Cascade CM10,boiler,81,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Cascade CM10,boiler,81,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Cascade CM10,boiler,81,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Cascade CM10,boiler,81,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Cascade CM10,boiler,81,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Cascade CM10,boiler,81,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Cascade CM10,boiler,81,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Cascade CM10,boiler,81,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Cascade CM10,boiler,81,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Cascade CM10,boiler,81,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Cascade CM10,boiler,81,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Cascade CM10,boiler,81,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logamax Plus GB022,boiler,84,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Logamax Plus GB022,boiler,84,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Logamax Plus GB022,boiler,84,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Logamax Plus GB022,boiler,84,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Logamax Plus GB022,boiler,84,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Logamax Plus GB022,boiler,84,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Logamax Plus GB022,boiler,84,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Logamax Plus GB022,boiler,84,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Logamax Plus GB022,boiler,84,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Logamax Plus GB022,boiler,84,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Logamax Plus GB022,boiler,84,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Logamax Plus GB022,boiler,84,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Logamax Plus GB022,boiler,84,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Logamax Plus GB022,boiler,84,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Logamax Plus GB022,boiler,84,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Logamax Plus GB022,boiler,84,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Logamax Plus GB022,boiler,84,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Logamax Plus GB022,boiler,84,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Logamax Plus GB022,boiler,84,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Logamax Plus GB022,boiler,84,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Logamax Plus GB022,boiler,84,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Logamax Plus GB022,boiler,84,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Logamax Plus GB022,boiler,84,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Logamax Plus GB022,boiler,84,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Logamax Plus GB022,boiler,84,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Logamax Plus GB022,boiler,84,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Logamax Plus GB022,boiler,84,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Logamax Plus GB022,boiler,84,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Logamax Plus GB022,boiler,84,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Logamax Plus GB022,boiler,84,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Logamax Plus GB022,boiler,84,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Logamax Plus GB022,boiler,84,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Logamax Plus GB022,boiler,84,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Logamax Plus GB022,boiler,84,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Logamax Plus GB022,boiler,84,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Logamax Plus GB022,boiler,84,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Logamax Plus GB022,boiler,84,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Logamax Plus GB022,boiler,84,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Logamax Plus GB022,boiler,84,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Logamax Plus GB022,boiler,84,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Logamax Plus GB022,boiler,84,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Logamax Plus GB022,boiler,84,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Logamax Plus GB022,boiler,84,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Logamax Plus GB022,boiler,84,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Logamax Plus GB022,boiler,84,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Logamax Plus GB022,boiler,84,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Logamax Plus GB022,boiler,84,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Logamax Plus GB022,boiler,84,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Logamax Plus GB022,boiler,84,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Logamax Plus GB022,boiler,84,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Logamax Plus GB022,boiler,84,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Logamax Plus GB022,boiler,84,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Logamax Plus GB022,boiler,84,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Logamax Plus GB022,boiler,84,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Logamax Plus GB022,boiler,84,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Logamax Plus GB022,boiler,84,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Logamax Plus GB022,boiler,84,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Logamax Plus GB022,boiler,84,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Logamax Plus GB022,boiler,84,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Logamax Plus GB022,boiler,84,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Logamax Plus GB022,boiler,84,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Logamax Plus GB022,boiler,84,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Logamax Plus GB022,boiler,84,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Logamax Plus GB022,boiler,84,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Logamax Plus GB022,boiler,84,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Logamax Plus GB022,boiler,84,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Logamax Plus GB022,boiler,84,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Logamax Plus GB022,boiler,84,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Logamax Plus GB022,boiler,84,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Logamax Plus GB022,boiler,84,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Logamax Plus GB022,boiler,84,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Logamax Plus GB022,boiler,84,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Logamax Plus GB022,boiler,84,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Logamax Plus GB022,boiler,84,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Logamax Plus GB022,boiler,84,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Logamax Plus GB022,boiler,84,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Logamax Plus GB022,boiler,84,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Logamax Plus GB022,boiler,84,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Logamax Plus GB022,boiler,84,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Logamax Plus GB022,boiler,84,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Logamax Plus GB022,boiler,84,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Logamax Plus GB022,boiler,84,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Logamax Plus GB022,boiler,84,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Logamax Plus GB022,boiler,84,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Logamax Plus GB022,boiler,84,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Logamax Plus GB022,boiler,84,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Logamax Plus GB022,boiler,84,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Logamax Plus GB022,boiler,84,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Logamax Plus GB022,boiler,84,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Logamax Plus GB022,boiler,84,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Logamax Plus GB022,boiler,84,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Condens 2500/Logamax/Logomatic/Cerapur Top/Greenstar/Generic HT3,boiler,95,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Topline/GB162,boiler,115,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Topline/GB162,boiler,115,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Topline/GB162,boiler,115,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Topline/GB162,boiler,115,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Topline/GB162,boiler,115,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Topline/GB162,boiler,115,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Topline/GB162,boiler,115,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Topline/GB162,boiler,115,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Topline/GB162,boiler,115,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Topline/GB162,boiler,115,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Topline/GB162,boiler,115,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Topline/GB162,boiler,115,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Topline/GB162,boiler,115,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Topline/GB162,boiler,115,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Topline/GB162,boiler,115,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Topline/GB162,boiler,115,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Topline/GB162,boiler,115,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Topline/GB162,boiler,115,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Topline/GB162,boiler,115,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Topline/GB162,boiler,115,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Topline/GB162,boiler,115,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Topline/GB162,boiler,115,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Topline/GB162,boiler,115,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Topline/GB162,boiler,115,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Topline/GB162,boiler,115,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Topline/GB162,boiler,115,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Topline/GB162,boiler,115,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Topline/GB162,boiler,115,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Topline/GB162,boiler,115,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Topline/GB162,boiler,115,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Topline/GB162,boiler,115,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Topline/GB162,boiler,115,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Topline/GB162,boiler,115,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Topline/GB162,boiler,115,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Topline/GB162,boiler,115,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Topline/GB162,boiler,115,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Topline/GB162,boiler,115,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Topline/GB162,boiler,115,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Topline/GB162,boiler,115,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Topline/GB162,boiler,115,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Topline/GB162,boiler,115,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Topline/GB162,boiler,115,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Topline/GB162,boiler,115,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Topline/GB162,boiler,115,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Topline/GB162,boiler,115,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Topline/GB162,boiler,115,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Topline/GB162,boiler,115,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Topline/GB162,boiler,115,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Topline/GB162,boiler,115,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Topline/GB162,boiler,115,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Topline/GB162,boiler,115,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Topline/GB162,boiler,115,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Topline/GB162,boiler,115,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Topline/GB162,boiler,115,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Topline/GB162,boiler,115,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Topline/GB162,boiler,115,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Topline/GB162,boiler,115,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Topline/GB162,boiler,115,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Topline/GB162,boiler,115,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Topline/GB162,boiler,115,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Topline/GB162,boiler,115,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Topline/GB162,boiler,115,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Topline/GB162,boiler,115,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Topline/GB162,boiler,115,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Topline/GB162,boiler,115,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Topline/GB162,boiler,115,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Topline/GB162,boiler,115,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Topline/GB162,boiler,115,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Topline/GB162,boiler,115,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Topline/GB162,boiler,115,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Topline/GB162,boiler,115,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Topline/GB162,boiler,115,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Topline/GB162,boiler,115,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Topline/GB162,boiler,115,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Topline/GB162,boiler,115,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Topline/GB162,boiler,115,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Topline/GB162,boiler,115,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Topline/GB162,boiler,115,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Topline/GB162,boiler,115,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Topline/GB162,boiler,115,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Topline/GB162,boiler,115,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Topline/GB162,boiler,115,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Topline/GB162,boiler,115,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Topline/GB162,boiler,115,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Topline/GB162,boiler,115,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Topline/GB162,boiler,115,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Topline/GB162,boiler,115,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Topline/GB162,boiler,115,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Topline/GB162,boiler,115,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Topline/GB162,boiler,115,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Topline/GB162,boiler,115,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Cascade MCM10,boiler,121,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Cascade MCM10,boiler,121,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Cascade MCM10,boiler,121,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Cascade MCM10,boiler,121,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Cascade MCM10,boiler,121,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Cascade MCM10,boiler,121,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Cascade MCM10,boiler,121,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Cascade MCM10,boiler,121,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Cascade MCM10,boiler,121,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Cascade MCM10,boiler,121,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Cascade MCM10,boiler,121,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Cascade MCM10,boiler,121,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Cascade MCM10,boiler,121,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Cascade MCM10,boiler,121,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Cascade MCM10,boiler,121,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Cascade MCM10,boiler,121,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Cascade MCM10,boiler,121,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Cascade MCM10,boiler,121,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Cascade MCM10,boiler,121,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Cascade MCM10,boiler,121,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Cascade MCM10,boiler,121,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Cascade MCM10,boiler,121,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Cascade MCM10,boiler,121,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Cascade MCM10,boiler,121,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Cascade MCM10,boiler,121,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Cascade MCM10,boiler,121,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Cascade MCM10,boiler,121,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Cascade MCM10,boiler,121,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Cascade MCM10,boiler,121,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Cascade MCM10,boiler,121,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Cascade MCM10,boiler,121,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Cascade MCM10,boiler,121,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Cascade MCM10,boiler,121,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Cascade MCM10,boiler,121,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Cascade MCM10,boiler,121,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Cascade MCM10,boiler,121,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Cascade MCM10,boiler,121,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Cascade MCM10,boiler,121,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Cascade MCM10,boiler,121,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Cascade MCM10,boiler,121,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Cascade MCM10,boiler,121,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Cascade MCM10,boiler,121,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Cascade MCM10,boiler,121,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Cascade MCM10,boiler,121,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Cascade MCM10,boiler,121,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Cascade MCM10,boiler,121,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Cascade MCM10,boiler,121,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Cascade MCM10,boiler,121,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Cascade MCM10,boiler,121,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Cascade MCM10,boiler,121,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Cascade MCM10,boiler,121,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Cascade MCM10,boiler,121,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Cascade MCM10,boiler,121,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Cascade MCM10,boiler,121,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Cascade MCM10,boiler,121,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Cascade MCM10,boiler,121,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Cascade MCM10,boiler,121,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Cascade MCM10,boiler,121,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Cascade MCM10,boiler,121,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Cascade MCM10,boiler,121,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Cascade MCM10,boiler,121,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Cascade MCM10,boiler,121,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Cascade MCM10,boiler,121,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Cascade MCM10,boiler,121,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Cascade MCM10,boiler,121,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Cascade MCM10,boiler,121,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Cascade MCM10,boiler,121,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Cascade MCM10,boiler,121,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Cascade MCM10,boiler,121,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Cascade MCM10,boiler,121,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Cascade MCM10,boiler,121,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Cascade MCM10,boiler,121,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Cascade MCM10,boiler,121,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Cascade MCM10,boiler,121,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Cascade MCM10,boiler,121,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Cascade MCM10,boiler,121,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Cascade MCM10,boiler,121,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Cascade MCM10,boiler,121,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Cascade MCM10,boiler,121,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Cascade MCM10,boiler,121,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Cascade MCM10,boiler,121,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Cascade MCM10,boiler,121,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Cascade MCM10,boiler,121,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Cascade MCM10,boiler,121,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Cascade MCM10,boiler,121,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Cascade MCM10,boiler,121,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Cascade MCM10,boiler,121,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Cascade MCM10,boiler,121,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Cascade MCM10,boiler,121,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Cascade MCM10,boiler,121,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Cascade MCM10,boiler,121,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Proline,boiler,122,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Proline,boiler,122,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Proline,boiler,122,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Proline,boiler,122,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Proline,boiler,122,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Proline,boiler,122,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Proline,boiler,122,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Proline,boiler,122,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Proline,boiler,122,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Proline,boiler,122,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Proline,boiler,122,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Proline,boiler,122,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Proline,boiler,122,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Proline,boiler,122,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Proline,boiler,122,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Proline,boiler,122,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Proline,boiler,122,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Proline,boiler,122,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Proline,boiler,122,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Proline,boiler,122,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Proline,boiler,122,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Proline,boiler,122,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Proline,boiler,122,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Proline,boiler,122,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Proline,boiler,122,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Proline,boiler,122,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Proline,boiler,122,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Proline,boiler,122,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Proline,boiler,122,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Proline,boiler,122,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Proline,boiler,122,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Proline,boiler,122,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Proline,boiler,122,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Proline,boiler,122,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Proline,boiler,122,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Proline,boiler,122,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Proline,boiler,122,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Proline,boiler,122,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Proline,boiler,122,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Proline,boiler,122,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Proline,boiler,122,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Proline,boiler,122,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Proline,boiler,122,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Proline,boiler,122,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Proline,boiler,122,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Proline,boiler,122,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Proline,boiler,122,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Proline,boiler,122,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Proline,boiler,122,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Proline,boiler,122,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Proline,boiler,122,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Proline,boiler,122,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Proline,boiler,122,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Proline,boiler,122,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Proline,boiler,122,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Proline,boiler,122,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Proline,boiler,122,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Proline,boiler,122,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Proline,boiler,122,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Proline,boiler,122,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Proline,boiler,122,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Proline,boiler,122,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Proline,boiler,122,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Proline,boiler,122,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Proline,boiler,122,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Proline,boiler,122,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Proline,boiler,122,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Proline,boiler,122,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Proline,boiler,122,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Proline,boiler,122,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Proline,boiler,122,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Proline,boiler,122,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Proline,boiler,122,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Proline,boiler,122,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Proline,boiler,122,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Proline,boiler,122,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Proline,boiler,122,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Proline,boiler,122,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Proline,boiler,122,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Proline,boiler,122,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Proline,boiler,122,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Proline,boiler,122,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Proline,boiler,122,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Proline,boiler,122,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Proline,boiler,122,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Proline,boiler,122,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Proline,boiler,122,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Proline,boiler,122,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Proline,boiler,122,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Proline,boiler,122,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Proline,boiler,122,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
GBx72/Trendline/Cerapur/Greenstar Si,boiler,123,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
GB212,boiler,131,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
GB212,boiler,131,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
GB212,boiler,131,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
GB212,boiler,131,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
GB212,boiler,131,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
GB212,boiler,131,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
GB212,boiler,131,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
GB212,boiler,131,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
GB212,boiler,131,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
GB212,boiler,131,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
GB212,boiler,131,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
GB212,boiler,131,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
GB212,boiler,131,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
GB212,boiler,131,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
GB212,boiler,131,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
GB212,boiler,131,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
GB212,boiler,131,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
GB212,boiler,131,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
GB212,boiler,131,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
GB212,boiler,131,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
GB212,boiler,131,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
GB212,boiler,131,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
GB212,boiler,131,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
GB212,boiler,131,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
GB212,boiler,131,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
GB212,boiler,131,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
GB212,boiler,131,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
GB212,boiler,131,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
GB212,boiler,131,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
GB212,boiler,131,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
GB212,boiler,131,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
GB212,boiler,131,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
GB212,boiler,131,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
GB212,boiler,131,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
GB212,boiler,131,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
GB212,boiler,131,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
GB212,boiler,131,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
GB212,boiler,131,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
GB212,boiler,131,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
GB212,boiler,131,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
GB212,boiler,131,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
GB212,boiler,131,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
GB212,boiler,131,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
GB212,boiler,131,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
GB212,boiler,131,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
GB212,boiler,131,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
GB212,boiler,131,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
GB212,boiler,131,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
GB212,boiler,131,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
GB212,boiler,131,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
GB212,boiler,131,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
GB212,boiler,131,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
GB212,boiler,131,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
GB212,boiler,131,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
GB212,boiler,131,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
GB212,boiler,131,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
GB212,boiler,131,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
GB212,boiler,131,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
GB212,boiler,131,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
GB212,boiler,131,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
GB212,boiler,131,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
GB212,boiler,131,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
GB212,boiler,131,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
GB212,boiler,131,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
GB212,boiler,131,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
GB212,boiler,131,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
GB212,boiler,131,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
GB212,boiler,131,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
GB212,boiler,131,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
GB212,boiler,131,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
GB212,boiler,131,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
GB212,boiler,131,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
GB212,boiler,131,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
GB212,boiler,131,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
GB212,boiler,131,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
GB212,boiler,131,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
GB212,boiler,131,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
GB212,boiler,131,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
GB212,boiler,131,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
GB212,boiler,131,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
GB212,boiler,131,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
GB212,boiler,131,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
GB212,boiler,131,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
GB212,boiler,131,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
GB212,boiler,131,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
GB212,boiler,131,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
GB212,boiler,131,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
GB212,boiler,131,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
GB212,boiler,131,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
GB212,boiler,131,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
GB212,boiler,131,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
GC7000F,boiler,132,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
GC7000F,boiler,132,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
GC7000F,boiler,132,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
GC7000F,boiler,132,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
GC7000F,boiler,132,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
GC7000F,boiler,132,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
GC7000F,boiler,132,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
GC7000F,boiler,132,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
GC7000F,boiler,132,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
GC7000F,boiler,132,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
GC7000F,boiler,132,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
GC7000F,boiler,132,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
GC7000F,boiler,132,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
GC7000F,boiler,132,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
GC7000F,boiler,132,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
GC7000F,boiler,132,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
GC7000F,boiler,132,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
GC7000F,boiler,132,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
GC7000F,boiler,132,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
GC7000F,boiler,132,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
GC7000F,boiler,132,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
GC7000F,boiler,132,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
GC7000F,boiler,132,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
GC7000F,boiler,132,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
GC7000F,boiler,132,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
GC7000F,boiler,132,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
GC7000F,boiler,132,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
GC7000F,boiler,132,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
GC7000F,boiler,132,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
GC7000F,boiler,132,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
GC7000F,boiler,132,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
GC7000F,boiler,132,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
GC7000F,boiler,132,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
GC7000F,boiler,132,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
GC7000F,boiler,132,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
GC7000F,boiler,132,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
GC7000F,boiler,132,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
GC7000F,boiler,132,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
GC7000F,boiler,132,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
GC7000F,boiler,132,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
GC7000F,boiler,132,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
GC7000F,boiler,132,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
GC7000F,boiler,132,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
GC7000F,boiler,132,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
GC7000F,boiler,132,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
GC7000F,boiler,132,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
GC7000F,boiler,132,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
GC7000F,boiler,132,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
GC7000F,boiler,132,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
GC7000F,boiler,132,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
GC7000F,boiler,132,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
GC7000F,boiler,132,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
GC7000F,boiler,132,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
GC7000F,boiler,132,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
GC7000F,boiler,132,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
GC7000F,boiler,132,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
GC7000F,boiler,132,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
GC7000F,boiler,132,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
GC7000F,boiler,132,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
GC7000F,boiler,132,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
GC7000F,boiler,132,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
GC7000F,boiler,132,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
GC7000F,boiler,132,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
GC7000F,boiler,132,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
GC7000F,boiler,132,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
GC7000F,boiler,132,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
GC7000F,boiler,132,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
GC7000F,boiler,132,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
GC7000F,boiler,132,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
GC7000F,boiler,132,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
GC7000F,boiler,132,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
GC7000F,boiler,132,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
GC7000F,boiler,132,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
GC7000F,boiler,132,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
GC7000F,boiler,132,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
GC7000F,boiler,132,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
GC7000F,boiler,132,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
GC7000F,boiler,132,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
GC7000F,boiler,132,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
GC7000F,boiler,132,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
GC7000F,boiler,132,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
GC7000F,boiler,132,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
GC7000F,boiler,132,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
GC7000F,boiler,132,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
GC7000F,boiler,132,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
GC7000F,boiler,132,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
GC7000F,boiler,132,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
GC7000F,boiler,132,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
GC7000F,boiler,132,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
GC7000F,boiler,132,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
GC7000F,boiler,132,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logano GB125/KB195i/Logamatic MC110,boiler,133,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Logano GB125/KB195i/Logamatic MC110,boiler,133,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Logano GB125/KB195i/Logamatic MC110,boiler,133,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Logano GB125/KB195i/Logamatic MC110,boiler,133,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Logano GB125/KB195i/Logamatic MC110,boiler,133,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Logano GB125/KB195i/Logamatic MC110,boiler,133,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Logano GB125/KB195i/Logamatic MC110,boiler,133,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Logano GB125/KB195i/Logamatic MC110,boiler,133,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Logano GB125/KB195i/Logamatic MC110,boiler,133,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Logano GB125/KB195i/Logamatic MC110,boiler,133,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Logano GB125/KB195i/Logamatic MC110,boiler,133,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Logano GB125/KB195i/Logamatic MC110,boiler,133,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Logano GB125/KB195i/Logamatic MC110,boiler,133,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Logano GB125/KB195i/Logamatic MC110,boiler,133,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Logano GB125/KB195i/Logamatic MC110,boiler,133,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Logano GB125/KB195i/Logamatic MC110,boiler,133,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Logano GB125/KB195i/Logamatic MC110,boiler,133,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Logano GB125/KB195i/Logamatic MC110,boiler,133,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Logano GB125/KB195i/Logamatic MC110,boiler,133,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Logano GB125/KB195i/Logamatic MC110,boiler,133,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Logano GB125/KB195i/Logamatic MC110,boiler,133,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Logano GB125/KB195i/Logamatic MC110,boiler,133,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Logano GB125/KB195i/Logamatic MC110,boiler,133,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Logano GB125/KB195i/Logamatic MC110,boiler,133,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Logano GB125/KB195i/Logamatic MC110,boiler,133,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Logano GB125/KB195i/Logamatic MC110,boiler,133,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Logano GB125/KB195i/Logamatic MC110,boiler,133,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Logano GB125/KB195i/Logamatic MC110,boiler,133,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Logano GB125/KB195i/Logamatic MC110,boiler,133,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Logano GB125/KB195i/Logamatic MC110,boiler,133,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Logano GB125/KB195i/Logamatic MC110,boiler,133,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Logano GB125/KB195i/Logamatic MC110,boiler,133,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Logano GB125/KB195i/Logamatic MC110,boiler,133,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Logano GB125/KB195i/Logamatic MC110,boiler,133,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Logano GB125/KB195i/Logamatic MC110,boiler,133,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Logano GB125/KB195i/Logamatic MC110,boiler,133,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Logano GB125/KB195i/Logamatic MC110,boiler,133,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Logano GB125/KB195i/Logamatic MC110,boiler,133,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Logano GB125/KB195i/Logamatic MC110,boiler,133,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Logano GB125/KB195i/Logamatic MC110,boiler,133,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Greenstar 30Ri Compact,boiler,154,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Greenstar 30Ri Compact,boiler,154,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Greenstar 30Ri Compact,boiler,154,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Greenstar 30Ri Compact,boiler,154,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Greenstar 30Ri Compact,boiler,154,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Greenstar 30Ri Compact,boiler,154,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Greenstar 30Ri Compact,boiler,154,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Greenstar 30Ri Compact,boiler,154,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Greenstar 30Ri Compact,boiler,154,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Greenstar 30Ri Compact,boiler,154,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Greenstar 30Ri Compact,boiler,154,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Greenstar 30Ri Compact,boiler,154,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Greenstar 30Ri Compact,boiler,154,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Greenstar 30Ri Compact,boiler,154,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Greenstar 30Ri Compact,boiler,154,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Greenstar 30Ri Compact,boiler,154,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Greenstar 30Ri Compact,boiler,154,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Greenstar 30Ri Compact,boiler,154,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Greenstar 30Ri Compact,boiler,154,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Greenstar 30Ri Compact,boiler,154,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Greenstar 30Ri Compact,boiler,154,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Greenstar 30Ri Compact,boiler,154,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Greenstar 30Ri Compact,boiler,154,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Greenstar 30Ri Compact,boiler,154,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Greenstar 30Ri Compact,boiler,154,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Greenstar 30Ri Compact,boiler,154,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Greenstar 30Ri Compact,boiler,154,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Greenstar 30Ri Compact,boiler,154,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Greenstar 30Ri Compact,boiler,154,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Greenstar 30Ri Compact,boiler,154,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Greenstar 30Ri Compact,boiler,154,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Greenstar 30Ri Compact,boiler,154,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Greenstar 30Ri Compact,boiler,154,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Greenstar 30Ri Compact,boiler,154,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Greenstar 30Ri Compact,boiler,154,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Greenstar 30Ri Compact,boiler,154,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Greenstar 30Ri Compact,boiler,154,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Greenstar 30Ri Compact,boiler,154,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Greenstar 30Ri Compact,boiler,154,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Greenstar 30Ri Compact,boiler,154,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Greenstar 30Ri Compact,boiler,154,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Greenstar 30Ri Compact,boiler,154,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Greenstar 30Ri Compact,boiler,154,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Greenstar 30Ri Compact,boiler,154,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Greenstar 30Ri Compact,boiler,154,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Greenstar 30Ri Compact,boiler,154,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Greenstar 30Ri Compact,boiler,154,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Greenstar 30Ri Compact,boiler,154,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Greenstar 30Ri Compact,boiler,154,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Greenstar 30Ri Compact,boiler,154,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Greenstar 30Ri Compact,boiler,154,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Greenstar 30Ri Compact,boiler,154,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Greenstar 30Ri Compact,boiler,154,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Greenstar 30Ri Compact,boiler,154,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Greenstar 30Ri Compact,boiler,154,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Greenstar 30Ri Compact,boiler,154,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Greenstar 30Ri Compact,boiler,154,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Greenstar 30Ri Compact,boiler,154,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Greenstar 30Ri Compact,boiler,154,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Greenstar 30Ri Compact,boiler,154,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Greenstar 30Ri Compact,boiler,154,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Greenstar 30Ri Compact,boiler,154,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Greenstar 30Ri Compact,boiler,154,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Greenstar 30Ri Compact,boiler,154,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Greenstar 30Ri Compact,boiler,154,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Greenstar 30Ri Compact,boiler,154,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Greenstar 30Ri Compact,boiler,154,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Greenstar 30Ri Compact,boiler,154,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Greenstar 30Ri Compact,boiler,154,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Greenstar 30Ri Compact,boiler,154,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Greenstar 30Ri Compact,boiler,154,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Greenstar 30Ri Compact,boiler,154,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Greenstar 30Ri Compact,boiler,154,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Greenstar 30Ri Compact,boiler,154,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Greenstar 30Ri Compact,boiler,154,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Greenstar 30Ri Compact,boiler,154,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Greenstar 30Ri Compact,boiler,154,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Greenstar 30Ri Compact,boiler,154,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Greenstar 30Ri Compact,boiler,154,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Greenstar 30Ri Compact,boiler,154,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Greenstar 30Ri Compact,boiler,154,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Greenstar 30Ri Compact,boiler,154,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Greenstar 30Ri Compact,boiler,154,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Greenstar 30Ri Compact,boiler,154,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Greenstar 30Ri Compact,boiler,154,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Greenstar 30Ri Compact,boiler,154,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Greenstar 30Ri Compact,boiler,154,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Greenstar 30Ri Compact,boiler,154,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Greenstar 30Ri Compact,boiler,154,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Greenstar 30Ri Compact,boiler,154,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Greenstar 30Ri Compact,boiler,154,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Cerapur Aero,boiler,167,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Cerapur Aero,boiler,167,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Cerapur Aero,boiler,167,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Cerapur Aero,boiler,167,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Cerapur Aero,boiler,167,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Cerapur Aero,boiler,167,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Cerapur Aero,boiler,167,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Cerapur Aero,boiler,167,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Cerapur Aero,boiler,167,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Cerapur Aero,boiler,167,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Cerapur Aero,boiler,167,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Cerapur Aero,boiler,167,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Cerapur Aero,boiler,167,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Cerapur Aero,boiler,167,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Cerapur Aero,boiler,167,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Cerapur Aero,boiler,167,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Cerapur Aero,boiler,167,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Cerapur Aero,boiler,167,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Cerapur Aero,boiler,167,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Cerapur Aero,boiler,167,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Cerapur Aero,boiler,167,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Cerapur Aero,boiler,167,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Cerapur Aero,boiler,167,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Cerapur Aero,boiler,167,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Cerapur Aero,boiler,167,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Cerapur Aero,boiler,167,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Cerapur Aero,boiler,167,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Cerapur Aero,boiler,167,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Cerapur Aero,boiler,167,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Cerapur Aero,boiler,167,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Cerapur Aero,boiler,167,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Cerapur Aero,boiler,167,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Cerapur Aero,boiler,167,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Cerapur Aero,boiler,167,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Cerapur Aero,boiler,167,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Cerapur Aero,boiler,167,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Cerapur Aero,boiler,167,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Cerapur Aero,boiler,167,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Cerapur Aero,boiler,167,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Cerapur Aero,boiler,167,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Cerapur Aero,boiler,167,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Cerapur Aero,boiler,167,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Cerapur Aero,boiler,167,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Cerapur Aero,boiler,167,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Cerapur Aero,boiler,167,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Cerapur Aero,boiler,167,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Cerapur Aero,boiler,167,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Cerapur Aero,boiler,167,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Cerapur Aero,boiler,167,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Cerapur Aero,boiler,167,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Cerapur Aero,boiler,167,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Cerapur Aero,boiler,167,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Cerapur Aero,boiler,167,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Cerapur Aero,boiler,167,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Cerapur Aero,boiler,167,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Cerapur Aero,boiler,167,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Cerapur Aero,boiler,167,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Cerapur Aero,boiler,167,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Cerapur Aero,boiler,167,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Cerapur Aero,boiler,167,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Cerapur Aero,boiler,167,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Cerapur Aero,boiler,167,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Cerapur Aero,boiler,167,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Cerapur Aero,boiler,167,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Cerapur Aero,boiler,167,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Cerapur Aero,boiler,167,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Cerapur Aero,boiler,167,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Cerapur Aero,boiler,167,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Cerapur Aero,boiler,167,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Cerapur Aero,boiler,167,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Cerapur Aero,boiler,167,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Cerapur Aero,boiler,167,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Cerapur Aero,boiler,167,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Cerapur Aero,boiler,167,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Cerapur Aero,boiler,167,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Cerapur Aero,boiler,167,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Cerapur Aero,boiler,167,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Cerapur Aero,boiler,167,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Cerapur Aero,boiler,167,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Cerapur Aero,boiler,167,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Cerapur Aero,boiler,167,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Cerapur Aero,boiler,167,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Cerapur Aero,boiler,167,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Cerapur Aero,boiler,167,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Cerapur Aero,boiler,167,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Cerapur Aero,boiler,167,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Cerapur Aero,boiler,167,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Cerapur Aero,boiler,167,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Cerapur Aero,boiler,167,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Cerapur Aero,boiler,167,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Cerapur Aero,boiler,167,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Hybrid Heatpump,boiler,168,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Hybrid Heatpump,boiler,168,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Hybrid Heatpump,boiler,168,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Hybrid Heatpump,boiler,168,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Hybrid Heatpump,boiler,168,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Hybrid Heatpump,boiler,168,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Hybrid Heatpump,boiler,168,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Hybrid Heatpump,boiler,168,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Hybrid Heatpump,boiler,168,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Hybrid Heatpump,boiler,168,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Hybrid Heatpump,boiler,168,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Hybrid Heatpump,boiler,168,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Hybrid Heatpump,boiler,168,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Hybrid Heatpump,boiler,168,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Hybrid Heatpump,boiler,168,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Hybrid Heatpump,boiler,168,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Hybrid Heatpump,boiler,168,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Hybrid Heatpump,boiler,168,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Hybrid Heatpump,boiler,168,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Hybrid Heatpump,boiler,168,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Hybrid Heatpump,boiler,168,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Hybrid Heatpump,boiler,168,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Hybrid Heatpump,boiler,168,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Hybrid Heatpump,boiler,168,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Hybrid Heatpump,boiler,168,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Hybrid Heatpump,boiler,168,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Hybrid Heatpump,boiler,168,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Hybrid Heatpump,boiler,168,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Hybrid Heatpump,boiler,168,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Hybrid Heatpump,boiler,168,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Hybrid Heatpump,boiler,168,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Hybrid Heatpump,boiler,168,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Hybrid Heatpump,boiler,168,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Hybrid Heatpump,boiler,168,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Hybrid Heatpump,boiler,168,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Hybrid Heatpump,boiler,168,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Hybrid Heatpump,boiler,168,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Hybrid Heatpump,boiler,168,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Hybrid Heatpump,boiler,168,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Hybrid Heatpump,boiler,168,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Hybrid Heatpump,boiler,168,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Hybrid Heatpump,boiler,168,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Hybrid Heatpump,boiler,168,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Hybrid Heatpump,boiler,168,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Hybrid Heatpump,boiler,168,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Hybrid Heatpump,boiler,168,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Hybrid Heatpump,boiler,168,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Hybrid Heatpump,boiler,168,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Hybrid Heatpump,boiler,168,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Hybrid Heatpump,boiler,168,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Hybrid Heatpump,boiler,168,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Hybrid Heatpump,boiler,168,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Hybrid Heatpump,boiler,168,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Hybrid Heatpump,boiler,168,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Hybrid Heatpump,boiler,168,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Hybrid Heatpump,boiler,168,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Hybrid Heatpump,boiler,168,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Hybrid Heatpump,boiler,168,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Hybrid Heatpump,boiler,168,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Hybrid Heatpump,boiler,168,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Hybrid Heatpump,boiler,168,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Hybrid Heatpump,boiler,168,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Hybrid Heatpump,boiler,168,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Hybrid Heatpump,boiler,168,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Hybrid Heatpump,boiler,168,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Hybrid Heatpump,boiler,168,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Hybrid Heatpump,boiler,168,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Hybrid Heatpump,boiler,168,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Hybrid Heatpump,boiler,168,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Hybrid Heatpump,boiler,168,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Hybrid Heatpump,boiler,168,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Hybrid Heatpump,boiler,168,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Hybrid Heatpump,boiler,168,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Hybrid Heatpump,boiler,168,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Hybrid Heatpump,boiler,168,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Hybrid Heatpump,boiler,168,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Hybrid Heatpump,boiler,168,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Hybrid Heatpump,boiler,168,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Hybrid Heatpump,boiler,168,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Hybrid Heatpump,boiler,168,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Hybrid Heatpump,boiler,168,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Hybrid Heatpump,boiler,168,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Hybrid Heatpump,boiler,168,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Hybrid Heatpump,boiler,168,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Hybrid Heatpump,boiler,168,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Hybrid Heatpump,boiler,168,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Hybrid Heatpump,boiler,168,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Hybrid Heatpump,boiler,168,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Hybrid Heatpump,boiler,168,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Hybrid Heatpump,boiler,168,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Hybrid Heatpump,boiler,168,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logano GB212,boiler,170,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Logano GB212,boiler,170,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Logano GB212,boiler,170,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Logano GB212,boiler,170,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Logano GB212,boiler,170,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Logano GB212,boiler,170,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Logano GB212,boiler,170,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Logano GB212,boiler,170,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Logano GB212,boiler,170,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Logano GB212,boiler,170,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Logano GB212,boiler,170,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Logano GB212,boiler,170,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Logano GB212,boiler,170,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Logano GB212,boiler,170,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Logano GB212,boiler,170,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Logano GB212,boiler,170,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Logano GB212,boiler,170,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Logano GB212,boiler,170,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Logano GB212,boiler,170,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Logano GB212,boiler,170,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Logano GB212,boiler,170,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Logano GB212,boiler,170,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Logano GB212,boiler,170,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Logano GB212,boiler,170,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Logano GB212,boiler,170,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Logano GB212,boiler,170,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Logano GB212,boiler,170,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Logano GB212,boiler,170,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Logano GB212,boiler,170,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Logano GB212,boiler,170,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Logano GB212,boiler,170,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Logano GB212,boiler,170,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Logano GB212,boiler,170,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Logano GB212,boiler,170,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Logano GB212,boiler,170,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Logano GB212,boiler,170,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Logano GB212,boiler,170,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Logano GB212,boiler,170,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Logano GB212,boiler,170,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Logano GB212,boiler,170,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Logano GB212,boiler,170,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Logano GB212,boiler,170,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Logano GB212,boiler,170,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Logano GB212,boiler,170,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Logano GB212,boiler,170,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Logano GB212,boiler,170,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Logano GB212,boiler,170,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Logano GB212,boiler,170,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Logano GB212,boiler,170,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Logano GB212,boiler,170,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Logano GB212,boiler,170,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Logano GB212,boiler,170,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Logano GB212,boiler,170,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Logano GB212,boiler,170,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Logano GB212,boiler,170,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Logano GB212,boiler,170,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Logano GB212,boiler,170,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Logano GB212,boiler,170,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Logano GB212,boiler,170,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Logano GB212,boiler,170,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Logano GB212,boiler,170,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Logano GB212,boiler,170,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Logano GB212,boiler,170,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Logano GB212,boiler,170,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Logano GB212,boiler,170,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Logano GB212,boiler,170,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Logano GB212,boiler,170,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Logano GB212,boiler,170,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Logano GB212,boiler,170,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Logano GB212,boiler,170,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Logano GB212,boiler,170,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Logano GB212,boiler,170,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Logano GB212,boiler,170,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Logano GB212,boiler,170,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Logano GB212,boiler,170,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Logano GB212,boiler,170,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Logano GB212,boiler,170,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Logano GB212,boiler,170,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Logano GB212,boiler,170,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Logano GB212,boiler,170,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Logano GB212,boiler,170,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Logano GB212,boiler,170,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Logano GB212,boiler,170,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Logano GB212,boiler,170,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Logano GB212,boiler,170,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Logano GB212,boiler,170,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Logano GB212,boiler,170,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Logano GB212,boiler,170,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Logano GB212,boiler,170,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Logano GB212,boiler,170,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Logano GB212,boiler,170,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,uptimecontrol,total operating time heat,time (>=0<=17476),minutes,false,sensor.boiler_total_operating_time_heat,sensor.boiler_uptimecontrol
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,uptimecompheating,operating time compressor heating,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_heating,sensor.boiler_uptimecompheating
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,uptimecompcooling,operating time compressor cooling,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_cooling,sensor.boiler_uptimecompcooling
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,uptimecompww,operating time compressor dhw,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_dhw,sensor.boiler_uptimecompww
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,uptimecomppool,operating time compressor pool,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_pool,sensor.boiler_uptimecomppool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,totalcompstarts,total compressor control starts,ulong (>=0<=65533), ,false,sensor.boiler_total_compressor_control_starts,sensor.boiler_totalcompstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatingstarts,heating control starts,ulong (>=0<=65533), ,false,sensor.boiler_heating_control_starts,sensor.boiler_heatingstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,coolingstarts,cooling control starts,ulong (>=0<=65533), ,false,sensor.boiler_cooling_control_starts,sensor.boiler_coolingstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwstarts2,control starts2,ulong (>=0<=65533), ,false,sensor.boiler_control_starts2,sensor.boiler_wwstarts2
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,poolstarts,pool control starts,ulong (>=0<=65533), ,false,sensor.boiler_pool_control_starts,sensor.boiler_poolstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgconstotal,total energy consumption,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_consumption,sensor.boiler_nrgconstotal
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgconscomptotal,total energy consumption compressor,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_consumption_compressor,sensor.boiler_nrgconscomptotal
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgconscompheating,energy consumption compressor heating,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_heating,sensor.boiler_nrgconscompheating
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgconscompww,energy consumption compressor dhw,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_dhw,sensor.boiler_nrgconscompww
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgconscompcooling,energy consumption compressor cooling,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_cooling,sensor.boiler_nrgconscompcooling
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgconscomppool,energy consumption compressor pool,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_pool,sensor.boiler_nrgconscomppool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxelecheatnrgconstotal,total aux elec. heater energy consumption,ulong (>=0<=65533),kWh,false,sensor.boiler_total_aux_elec._heater_energy_consumption,sensor.boiler_auxelecheatnrgconstotal
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxelecheatnrgconsheating,aux elec. heater energy consumption heating,ulong (>=0<=65533),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_heating,sensor.boiler_auxelecheatnrgconsheating
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxelecheatnrgconsww,aux elec. heater energy consumption dhw,ulong (>=0<=65533),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_dhw,sensor.boiler_auxelecheatnrgconsww
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxelecheatnrgconspool,aux elec. heater energy consumption pool,ulong (>=0<=65533),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_pool,sensor.boiler_auxelecheatnrgconspool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgsupptotal,total energy supplied,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied,sensor.boiler_nrgsupptotal
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgsuppheating,total energy supplied heating,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied_heating,sensor.boiler_nrgsuppheating
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgsuppww,total energy warm supplied dhw,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_warm_supplied_dhw,sensor.boiler_nrgsuppww
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgsuppcooling,total energy supplied cooling,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied_cooling,sensor.boiler_nrgsuppcooling
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,nrgsupppool,total energy supplied pool,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied_pool,sensor.boiler_nrgsupppool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hppower,compressor power output,uint (>=0<=25),kW,false,sensor.boiler_compressor_power_output,sensor.boiler_hppower
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpcompon,hp compressor,boolean, ,false,binary_sensor.boiler_hp_compressor,binary_sensor.boiler_hpcompon
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpactivity,compressor activity,enum [none\|heating\|cooling\|hot water\|pool\|unknown\|defrost], ,false,sensor.boiler_compressor_activity,sensor.boiler_hpactivity
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpheatingon,hp heating,boolean, ,false,binary_sensor.boiler_hp_heating,binary_sensor.boiler_hpheatingon
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpcoolingon,hp cooling,boolean, ,false,binary_sensor.boiler_hp_cooling,binary_sensor.boiler_hpcoolingon
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpwwon,hp dhw,boolean, ,false,binary_sensor.boiler_hp_dhw,binary_sensor.boiler_hpwwon
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hppoolon,hp pool,boolean, ,false,binary_sensor.boiler_hp_pool,binary_sensor.boiler_hppoolon
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpbrinepumpspd,brine pump speed,uint (>=0<=100),%,false,sensor.boiler_brine_pump_speed,sensor.boiler_hpbrinepumpspd
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpswitchvalve,switch valve,boolean, ,false,binary_sensor.boiler_switch_valve,binary_sensor.boiler_hpswitchvalve
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpcompspd,compressor speed,uint (>=0<=100),%,false,sensor.boiler_compressor_speed,sensor.boiler_hpcompspd
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpcircspd,circulation pump speed,uint (>=0<=100),%,false,sensor.boiler_circulation_pump_speed,sensor.boiler_hpcircspd
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpbrinein,brine in/evaporator,short (>=-3199<=3199),C,false,sensor.boiler_brine_in/evaporator,sensor.boiler_hpbrinein
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpbrineout,brine out/condenser,short (>=-3199<=3199),C,false,sensor.boiler_brine_out/condenser,sensor.boiler_hpbrineout
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptc0,heat carrier return (TC0),short (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_return_(TC0),sensor.boiler_hptc0
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptc1,heat carrier forward (TC1),short (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_forward_(TC1),sensor.boiler_hptc1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptc3,condenser temperature (TC3),short (>=-3199<=3199),C,false,sensor.boiler_condenser_temperature_(TC3),sensor.boiler_hptc3
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptr1,compressor temperature (TR1),short (>=-3199<=3199),C,false,sensor.boiler_compressor_temperature_(TR1),sensor.boiler_hptr1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptr3,refrigerant temperature liquid side (condenser output) (TR3),short (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.boiler_hptr3
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptr4,evaporator inlet temperature (TR4),short (>=-3199<=3199),C,false,sensor.boiler_evaporator_inlet_temperature_(TR4),sensor.boiler_hptr4
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptr5,compressor inlet temperature (TR5),short (>=-3199<=3199),C,false,sensor.boiler_compressor_inlet_temperature_(TR5),sensor.boiler_hptr5
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptr6,compressor outlet temperature (TR6),short (>=-3199<=3199),C,false,sensor.boiler_compressor_outlet_temperature_(TR6),sensor.boiler_hptr6
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptr7,refrigerant temperature gas side (condenser input) (TR7),short (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_gas_side_(condenser_input)_(TR7),sensor.boiler_hptr7
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hptl2,air inlet temperature (TL2),short (>=-3199<=3199),C,false,sensor.boiler_air_inlet_temperature_(TL2),sensor.boiler_hptl2
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hppl1,low pressure side temperature (PL1),short (>=-3199<=3199),C,false,sensor.boiler_low_pressure_side_temperature_(PL1),sensor.boiler_hppl1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpph1,high pressure side temperature (PH1),short (>=-3199<=3199),C,false,sensor.boiler_high_pressure_side_temperature_(PH1),sensor.boiler_hpph1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,poolsettemp,pool set temperature,uint (>=0<=127),C,true,number.boiler_pool_set_temperature,number.boiler_poolsettemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpin1opt,input 1 options,string, ,true,sensor.boiler_input_1_options,sensor.boiler_hpin1opt
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpin2opt,input 2 options,string, ,true,sensor.boiler_input_2_options,sensor.boiler_hpin2opt
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpin3opt,input 3 options,string, ,true,sensor.boiler_input_3_options,sensor.boiler_hpin3opt
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpin4opt,input 4 options,string, ,true,sensor.boiler_input_4_options,sensor.boiler_hpin4opt
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maxheatcomp,heat limit compressor,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_compressor,select.boiler_maxheatcomp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maxheatheat,heat limit heating,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_heating,select.boiler_maxheatheat
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,maxheatdhw,heat limit dhw,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_dhw,select.boiler_maxheatdhw
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,mandefrost,manual defrost,boolean, ,true,switch.boiler_manual_defrost,switch.boiler_mandefrost
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,pvcooling,Cooling only with PV,boolean, ,true,switch.boiler_Cooling_only_with_PV,switch.boiler_pvcooling
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxheateronly,aux heater only,boolean, ,true,switch.boiler_aux_heater_only,switch.boiler_auxheateronly
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxheateroff,disable aux heater,boolean, ,true,switch.boiler_disable_aux_heater,switch.boiler_auxheateroff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxheaterstatus,aux heater status,boolean, ,false,binary_sensor.boiler_aux_heater_status,binary_sensor.boiler_auxheaterstatus
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxheaterdelay,aux heater on delay,ushort (>=10<=1000),K*min,true,number.boiler_aux_heater_on_delay,number.boiler_auxheaterdelay
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxmaxlimit,aux heater max limit,uint (>=0<=10),K,true,number.boiler_aux_heater_max_limit,number.boiler_auxmaxlimit
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxlimitstart,aux heater limit start,uint (>=0<=10),K,true,number.boiler_aux_heater_limit_start,number.boiler_auxlimitstart
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxheatrmode,aux heater mode,enum [eco\|comfort], ,true,select.boiler_aux_heater_mode,select.boiler_auxheatrmode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hphystheat,on/off hyst heat,ushort (>=50<=1500),K*min,true,number.boiler_on/off_hyst_heat,number.boiler_hphystheat
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hphystcool,on/off hyst cool,ushort (>=50<=1500),K*min,true,number.boiler_on/off_hyst_cool,number.boiler_hphystcool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hphystpool,on/off hyst pool,ushort (>=50<=1500),K*min,true,number.boiler_on/off_hyst_pool,number.boiler_hphystpool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,silentmode,silent mode,enum [off\|auto\|on], ,true,select.boiler_silent_mode,select.boiler_silentmode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,silentfrom,silent mode from,uint (>=0<=3810),minutes,true,number.boiler_silent_mode_from,number.boiler_silentfrom
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,silentto,silent mode to,uint (>=0<=3810),minutes,true,number.boiler_silent_mode_to,number.boiler_silentto
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,mintempsilent,min outside temp for silent mode,int (>=-126<=126),C,true,number.boiler_min_outside_temp_for_silent_mode,number.boiler_mintempsilent
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,tempparmode,outside temp parallel mode,int (>=-126<=126),C,true,number.boiler_outside_temp_parallel_mode,number.boiler_tempparmode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,auxheatmix,aux heater mixing valve,int (>=-100<=100),%,false,sensor.boiler_aux_heater_mixing_valve,sensor.boiler_auxheatmix
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,tempdiffheat,temp diff TC3/TC0 heat,uint (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_heat,number.boiler_tempdiffheat
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,tempdiffcool,temp diff TC3/TC0 cool,uint (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_cool,number.boiler_tempdiffcool
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,vpcooling,valve/pump cooling,boolean, ,true,switch.boiler_valve/pump_cooling,switch.boiler_vpcooling
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,heatcable,heating cable,boolean, ,true,switch.boiler_heating_cable,switch.boiler_heatcable
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,vc0valve,VC0 valve,boolean, ,true,switch.boiler_VC0_valve,switch.boiler_vc0valve
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,primepump,primary heatpump,boolean, ,true,switch.boiler_primary_heatpump,switch.boiler_primepump
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,primepumpmod,primary heatpump modulation,uint (>=0<=100),%,true,number.boiler_primary_heatpump_modulation,number.boiler_primepumpmod
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hp3way,3-way valve,boolean, ,true,switch.boiler_3-way_valve,switch.boiler_hp3way
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,elheatstep1,el. heater step 1,boolean, ,true,switch.boiler_el._heater_step_1,switch.boiler_elheatstep1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,elheatstep2,el. heater step 2,boolean, ,true,switch.boiler_el._heater_step_2,switch.boiler_elheatstep2
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,elheatstep3,el. heater step 3,boolean, ,true,switch.boiler_el._heater_step_3,switch.boiler_elheatstep3
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwalternatingop,alternating operation,boolean, ,true,switch.boiler_alternating_operation,switch.boiler_wwalternatingop
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwaltopprioheat,prioritise heating during dhw,uint (>=20<=120),minutes,true,number.boiler_prioritise_heating_during_dhw,number.boiler_wwaltopprioheat
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwaltopprioww,prioritise dhw during heating,uint (>=30<=120),minutes,true,number.boiler_prioritise_dhw_during_heating,number.boiler_wwaltopprioww
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcomfoff,comfort switch off,uint (>=15<=65),C,true,number.boiler_comfort_switch_off,number.boiler_wwcomfoff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwecooff,eco switch off,uint (>=15<=65),C,true,number.boiler_eco_switch_off,number.boiler_wwecooff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwecoplusoff,eco+ switch off,uint (>=48<=63),C,true,number.boiler_eco+_switch_off,number.boiler_wwecoplusoff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,hpcircpumpww,circulation pump available during dhw,boolean, ,true,switch.boiler_circulation_pump_available_during_dhw,switch.boiler_hpcircpumpww
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Enviline/Compress 6000AW/Hybrid 3000-7000iAW/SupraEco/Geo 5xx/WLW196i/WSW196i,boiler,172,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Geo 5xx,boiler,173,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Geo 5xx,boiler,173,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Geo 5xx,boiler,173,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Geo 5xx,boiler,173,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Geo 5xx,boiler,173,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Geo 5xx,boiler,173,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Geo 5xx,boiler,173,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Geo 5xx,boiler,173,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Geo 5xx,boiler,173,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Geo 5xx,boiler,173,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Geo 5xx,boiler,173,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Geo 5xx,boiler,173,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Geo 5xx,boiler,173,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Geo 5xx,boiler,173,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Geo 5xx,boiler,173,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Geo 5xx,boiler,173,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Geo 5xx,boiler,173,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Geo 5xx,boiler,173,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Geo 5xx,boiler,173,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Geo 5xx,boiler,173,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Geo 5xx,boiler,173,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Geo 5xx,boiler,173,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Geo 5xx,boiler,173,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Geo 5xx,boiler,173,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Geo 5xx,boiler,173,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Geo 5xx,boiler,173,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Geo 5xx,boiler,173,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Geo 5xx,boiler,173,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Geo 5xx,boiler,173,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Geo 5xx,boiler,173,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Geo 5xx,boiler,173,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Geo 5xx,boiler,173,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Geo 5xx,boiler,173,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Geo 5xx,boiler,173,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Geo 5xx,boiler,173,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Geo 5xx,boiler,173,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Geo 5xx,boiler,173,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Geo 5xx,boiler,173,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Geo 5xx,boiler,173,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Geo 5xx,boiler,173,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Geo 5xx,boiler,173,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Geo 5xx,boiler,173,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Geo 5xx,boiler,173,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Geo 5xx,boiler,173,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Geo 5xx,boiler,173,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Geo 5xx,boiler,173,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Geo 5xx,boiler,173,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Geo 5xx,boiler,173,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Geo 5xx,boiler,173,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Geo 5xx,boiler,173,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Geo 5xx,boiler,173,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Geo 5xx,boiler,173,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Geo 5xx,boiler,173,uptimecontrol,total operating time heat,time (>=0<=17476),minutes,false,sensor.boiler_total_operating_time_heat,sensor.boiler_uptimecontrol
Geo 5xx,boiler,173,uptimecompheating,operating time compressor heating,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_heating,sensor.boiler_uptimecompheating
Geo 5xx,boiler,173,uptimecompcooling,operating time compressor cooling,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_cooling,sensor.boiler_uptimecompcooling
Geo 5xx,boiler,173,uptimecompww,operating time compressor dhw,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_dhw,sensor.boiler_uptimecompww
Geo 5xx,boiler,173,uptimecomppool,operating time compressor pool,time (>=0<=17476),minutes,false,sensor.boiler_operating_time_compressor_pool,sensor.boiler_uptimecomppool
Geo 5xx,boiler,173,totalcompstarts,total compressor control starts,ulong (>=0<=65533), ,false,sensor.boiler_total_compressor_control_starts,sensor.boiler_totalcompstarts
Geo 5xx,boiler,173,heatingstarts,heating control starts,ulong (>=0<=65533), ,false,sensor.boiler_heating_control_starts,sensor.boiler_heatingstarts
Geo 5xx,boiler,173,coolingstarts,cooling control starts,ulong (>=0<=65533), ,false,sensor.boiler_cooling_control_starts,sensor.boiler_coolingstarts
Geo 5xx,boiler,173,wwstarts2,control starts2,ulong (>=0<=65533), ,false,sensor.boiler_control_starts2,sensor.boiler_wwstarts2
Geo 5xx,boiler,173,poolstarts,pool control starts,ulong (>=0<=65533), ,false,sensor.boiler_pool_control_starts,sensor.boiler_poolstarts
Geo 5xx,boiler,173,nrgconstotal,total energy consumption,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_consumption,sensor.boiler_nrgconstotal
Geo 5xx,boiler,173,nrgconscomptotal,total energy consumption compressor,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_consumption_compressor,sensor.boiler_nrgconscomptotal
Geo 5xx,boiler,173,nrgconscompheating,energy consumption compressor heating,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_heating,sensor.boiler_nrgconscompheating
Geo 5xx,boiler,173,nrgconscompww,energy consumption compressor dhw,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_dhw,sensor.boiler_nrgconscompww
Geo 5xx,boiler,173,nrgconscompcooling,energy consumption compressor cooling,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_cooling,sensor.boiler_nrgconscompcooling
Geo 5xx,boiler,173,nrgconscomppool,energy consumption compressor pool,ulong (>=0<=65533),kWh,false,sensor.boiler_energy_consumption_compressor_pool,sensor.boiler_nrgconscomppool
Geo 5xx,boiler,173,auxelecheatnrgconstotal,total aux elec. heater energy consumption,ulong (>=0<=65533),kWh,false,sensor.boiler_total_aux_elec._heater_energy_consumption,sensor.boiler_auxelecheatnrgconstotal
Geo 5xx,boiler,173,auxelecheatnrgconsheating,aux elec. heater energy consumption heating,ulong (>=0<=65533),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_heating,sensor.boiler_auxelecheatnrgconsheating
Geo 5xx,boiler,173,auxelecheatnrgconsww,aux elec. heater energy consumption dhw,ulong (>=0<=65533),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_dhw,sensor.boiler_auxelecheatnrgconsww
Geo 5xx,boiler,173,auxelecheatnrgconspool,aux elec. heater energy consumption pool,ulong (>=0<=65533),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_pool,sensor.boiler_auxelecheatnrgconspool
Geo 5xx,boiler,173,nrgsupptotal,total energy supplied,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied,sensor.boiler_nrgsupptotal
Geo 5xx,boiler,173,nrgsuppheating,total energy supplied heating,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied_heating,sensor.boiler_nrgsuppheating
Geo 5xx,boiler,173,nrgsuppww,total energy warm supplied dhw,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_warm_supplied_dhw,sensor.boiler_nrgsuppww
Geo 5xx,boiler,173,nrgsuppcooling,total energy supplied cooling,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied_cooling,sensor.boiler_nrgsuppcooling
Geo 5xx,boiler,173,nrgsupppool,total energy supplied pool,ulong (>=0<=65533),kWh,false,sensor.boiler_total_energy_supplied_pool,sensor.boiler_nrgsupppool
Geo 5xx,boiler,173,hppower,compressor power output,uint (>=0<=25),kW,false,sensor.boiler_compressor_power_output,sensor.boiler_hppower
Geo 5xx,boiler,173,hpcompon,hp compressor,boolean, ,false,binary_sensor.boiler_hp_compressor,binary_sensor.boiler_hpcompon
Geo 5xx,boiler,173,hpactivity,compressor activity,enum [none\|heating\|cooling\|hot water\|pool\|unknown\|defrost], ,false,sensor.boiler_compressor_activity,sensor.boiler_hpactivity
Geo 5xx,boiler,173,hpheatingon,hp heating,boolean, ,false,binary_sensor.boiler_hp_heating,binary_sensor.boiler_hpheatingon
Geo 5xx,boiler,173,hpcoolingon,hp cooling,boolean, ,false,binary_sensor.boiler_hp_cooling,binary_sensor.boiler_hpcoolingon
Geo 5xx,boiler,173,hpwwon,hp dhw,boolean, ,false,binary_sensor.boiler_hp_dhw,binary_sensor.boiler_hpwwon
Geo 5xx,boiler,173,hppoolon,hp pool,boolean, ,false,binary_sensor.boiler_hp_pool,binary_sensor.boiler_hppoolon
Geo 5xx,boiler,173,hpbrinepumpspd,brine pump speed,uint (>=0<=100),%,false,sensor.boiler_brine_pump_speed,sensor.boiler_hpbrinepumpspd
Geo 5xx,boiler,173,hpswitchvalve,switch valve,boolean, ,false,binary_sensor.boiler_switch_valve,binary_sensor.boiler_hpswitchvalve
Geo 5xx,boiler,173,hpcompspd,compressor speed,uint (>=0<=100),%,false,sensor.boiler_compressor_speed,sensor.boiler_hpcompspd
Geo 5xx,boiler,173,hpcircspd,circulation pump speed,uint (>=0<=100),%,false,sensor.boiler_circulation_pump_speed,sensor.boiler_hpcircspd
Geo 5xx,boiler,173,hpbrinein,brine in/evaporator,short (>=-3199<=3199),C,false,sensor.boiler_brine_in/evaporator,sensor.boiler_hpbrinein
Geo 5xx,boiler,173,hpbrineout,brine out/condenser,short (>=-3199<=3199),C,false,sensor.boiler_brine_out/condenser,sensor.boiler_hpbrineout
Geo 5xx,boiler,173,hptc0,heat carrier return (TC0),short (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_return_(TC0),sensor.boiler_hptc0
Geo 5xx,boiler,173,hptc1,heat carrier forward (TC1),short (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_forward_(TC1),sensor.boiler_hptc1
Geo 5xx,boiler,173,hptc3,condenser temperature (TC3),short (>=-3199<=3199),C,false,sensor.boiler_condenser_temperature_(TC3),sensor.boiler_hptc3
Geo 5xx,boiler,173,hptr1,compressor temperature (TR1),short (>=-3199<=3199),C,false,sensor.boiler_compressor_temperature_(TR1),sensor.boiler_hptr1
Geo 5xx,boiler,173,hptr3,refrigerant temperature liquid side (condenser output) (TR3),short (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.boiler_hptr3
Geo 5xx,boiler,173,hptr4,evaporator inlet temperature (TR4),short (>=-3199<=3199),C,false,sensor.boiler_evaporator_inlet_temperature_(TR4),sensor.boiler_hptr4
Geo 5xx,boiler,173,hptr5,compressor inlet temperature (TR5),short (>=-3199<=3199),C,false,sensor.boiler_compressor_inlet_temperature_(TR5),sensor.boiler_hptr5
Geo 5xx,boiler,173,hptr6,compressor outlet temperature (TR6),short (>=-3199<=3199),C,false,sensor.boiler_compressor_outlet_temperature_(TR6),sensor.boiler_hptr6
Geo 5xx,boiler,173,hptr7,refrigerant temperature gas side (condenser input) (TR7),short (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_gas_side_(condenser_input)_(TR7),sensor.boiler_hptr7
Geo 5xx,boiler,173,hptl2,air inlet temperature (TL2),short (>=-3199<=3199),C,false,sensor.boiler_air_inlet_temperature_(TL2),sensor.boiler_hptl2
Geo 5xx,boiler,173,hppl1,low pressure side temperature (PL1),short (>=-3199<=3199),C,false,sensor.boiler_low_pressure_side_temperature_(PL1),sensor.boiler_hppl1
Geo 5xx,boiler,173,hpph1,high pressure side temperature (PH1),short (>=-3199<=3199),C,false,sensor.boiler_high_pressure_side_temperature_(PH1),sensor.boiler_hpph1
Geo 5xx,boiler,173,poolsettemp,pool set temperature,uint (>=0<=127),C,true,number.boiler_pool_set_temperature,number.boiler_poolsettemp
Geo 5xx,boiler,173,hpin1opt,input 1 options,string, ,true,sensor.boiler_input_1_options,sensor.boiler_hpin1opt
Geo 5xx,boiler,173,hpin2opt,input 2 options,string, ,true,sensor.boiler_input_2_options,sensor.boiler_hpin2opt
Geo 5xx,boiler,173,hpin3opt,input 3 options,string, ,true,sensor.boiler_input_3_options,sensor.boiler_hpin3opt
Geo 5xx,boiler,173,hpin4opt,input 4 options,string, ,true,sensor.boiler_input_4_options,sensor.boiler_hpin4opt
Geo 5xx,boiler,173,maxheatcomp,heat limit compressor,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_compressor,select.boiler_maxheatcomp
Geo 5xx,boiler,173,maxheatheat,heat limit heating,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_heating,select.boiler_maxheatheat
Geo 5xx,boiler,173,maxheatdhw,heat limit dhw,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_dhw,select.boiler_maxheatdhw
Geo 5xx,boiler,173,mandefrost,manual defrost,boolean, ,true,switch.boiler_manual_defrost,switch.boiler_mandefrost
Geo 5xx,boiler,173,pvcooling,Cooling only with PV,boolean, ,true,switch.boiler_Cooling_only_with_PV,switch.boiler_pvcooling
Geo 5xx,boiler,173,auxheateronly,aux heater only,boolean, ,true,switch.boiler_aux_heater_only,switch.boiler_auxheateronly
Geo 5xx,boiler,173,auxheateroff,disable aux heater,boolean, ,true,switch.boiler_disable_aux_heater,switch.boiler_auxheateroff
Geo 5xx,boiler,173,auxheaterstatus,aux heater status,boolean, ,false,binary_sensor.boiler_aux_heater_status,binary_sensor.boiler_auxheaterstatus
Geo 5xx,boiler,173,auxheaterdelay,aux heater on delay,ushort (>=10<=1000),K*min,true,number.boiler_aux_heater_on_delay,number.boiler_auxheaterdelay
Geo 5xx,boiler,173,auxmaxlimit,aux heater max limit,uint (>=0<=10),K,true,number.boiler_aux_heater_max_limit,number.boiler_auxmaxlimit
Geo 5xx,boiler,173,auxlimitstart,aux heater limit start,uint (>=0<=10),K,true,number.boiler_aux_heater_limit_start,number.boiler_auxlimitstart
Geo 5xx,boiler,173,auxheatrmode,aux heater mode,enum [eco\|comfort], ,true,select.boiler_aux_heater_mode,select.boiler_auxheatrmode
Geo 5xx,boiler,173,hphystheat,on/off hyst heat,ushort (>=50<=1500),K*min,true,number.boiler_on/off_hyst_heat,number.boiler_hphystheat
Geo 5xx,boiler,173,hphystcool,on/off hyst cool,ushort (>=50<=1500),K*min,true,number.boiler_on/off_hyst_cool,number.boiler_hphystcool
Geo 5xx,boiler,173,hphystpool,on/off hyst pool,ushort (>=50<=1500),K*min,true,number.boiler_on/off_hyst_pool,number.boiler_hphystpool
Geo 5xx,boiler,173,silentmode,silent mode,enum [off\|auto\|on], ,true,select.boiler_silent_mode,select.boiler_silentmode
Geo 5xx,boiler,173,silentfrom,silent mode from,uint (>=0<=3810),minutes,true,number.boiler_silent_mode_from,number.boiler_silentfrom
Geo 5xx,boiler,173,silentto,silent mode to,uint (>=0<=3810),minutes,true,number.boiler_silent_mode_to,number.boiler_silentto
Geo 5xx,boiler,173,mintempsilent,min outside temp for silent mode,int (>=-126<=126),C,true,number.boiler_min_outside_temp_for_silent_mode,number.boiler_mintempsilent
Geo 5xx,boiler,173,tempparmode,outside temp parallel mode,int (>=-126<=126),C,true,number.boiler_outside_temp_parallel_mode,number.boiler_tempparmode
Geo 5xx,boiler,173,auxheatmix,aux heater mixing valve,int (>=-100<=100),%,false,sensor.boiler_aux_heater_mixing_valve,sensor.boiler_auxheatmix
Geo 5xx,boiler,173,tempdiffheat,temp diff TC3/TC0 heat,uint (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_heat,number.boiler_tempdiffheat
Geo 5xx,boiler,173,tempdiffcool,temp diff TC3/TC0 cool,uint (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_cool,number.boiler_tempdiffcool
Geo 5xx,boiler,173,vpcooling,valve/pump cooling,boolean, ,true,switch.boiler_valve/pump_cooling,switch.boiler_vpcooling
Geo 5xx,boiler,173,heatcable,heating cable,boolean, ,true,switch.boiler_heating_cable,switch.boiler_heatcable
Geo 5xx,boiler,173,vc0valve,VC0 valve,boolean, ,true,switch.boiler_VC0_valve,switch.boiler_vc0valve
Geo 5xx,boiler,173,primepump,primary heatpump,boolean, ,true,switch.boiler_primary_heatpump,switch.boiler_primepump
Geo 5xx,boiler,173,primepumpmod,primary heatpump modulation,uint (>=0<=100),%,true,number.boiler_primary_heatpump_modulation,number.boiler_primepumpmod
Geo 5xx,boiler,173,hp3way,3-way valve,boolean, ,true,switch.boiler_3-way_valve,switch.boiler_hp3way
Geo 5xx,boiler,173,elheatstep1,el. heater step 1,boolean, ,true,switch.boiler_el._heater_step_1,switch.boiler_elheatstep1
Geo 5xx,boiler,173,elheatstep2,el. heater step 2,boolean, ,true,switch.boiler_el._heater_step_2,switch.boiler_elheatstep2
Geo 5xx,boiler,173,elheatstep3,el. heater step 3,boolean, ,true,switch.boiler_el._heater_step_3,switch.boiler_elheatstep3
Geo 5xx,boiler,173,wwalternatingop,alternating operation,boolean, ,true,switch.boiler_alternating_operation,switch.boiler_wwalternatingop
Geo 5xx,boiler,173,wwaltopprioheat,prioritise heating during dhw,uint (>=20<=120),minutes,true,number.boiler_prioritise_heating_during_dhw,number.boiler_wwaltopprioheat
Geo 5xx,boiler,173,wwaltopprioww,prioritise dhw during heating,uint (>=30<=120),minutes,true,number.boiler_prioritise_dhw_during_heating,number.boiler_wwaltopprioww
Geo 5xx,boiler,173,wwcomfoff,comfort switch off,uint (>=15<=65),C,true,number.boiler_comfort_switch_off,number.boiler_wwcomfoff
Geo 5xx,boiler,173,wwecooff,eco switch off,uint (>=15<=65),C,true,number.boiler_eco_switch_off,number.boiler_wwecooff
Geo 5xx,boiler,173,wwecoplusoff,eco+ switch off,uint (>=48<=63),C,true,number.boiler_eco+_switch_off,number.boiler_wwecoplusoff
Geo 5xx,boiler,173,hpcircpumpww,circulation pump available during dhw,boolean, ,true,switch.boiler_circulation_pump_available_during_dhw,switch.boiler_hpcircpumpww
Geo 5xx,boiler,173,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Geo 5xx,boiler,173,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Geo 5xx,boiler,173,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Geo 5xx,boiler,173,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Geo 5xx,boiler,173,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Geo 5xx,boiler,173,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Geo 5xx,boiler,173,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Geo 5xx,boiler,173,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Geo 5xx,boiler,173,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Geo 5xx,boiler,173,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Geo 5xx,boiler,173,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Geo 5xx,boiler,173,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Geo 5xx,boiler,173,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Geo 5xx,boiler,173,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Geo 5xx,boiler,173,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Geo 5xx,boiler,173,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Geo 5xx,boiler,173,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Geo 5xx,boiler,173,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Geo 5xx,boiler,173,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Geo 5xx,boiler,173,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Geo 5xx,boiler,173,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Geo 5xx,boiler,173,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Geo 5xx,boiler,173,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Geo 5xx,boiler,173,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Geo 5xx,boiler,173,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Geo 5xx,boiler,173,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Geo 5xx,boiler,173,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Geo 5xx,boiler,173,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Geo 5xx,boiler,173,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Geo 5xx,boiler,173,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Geo 5xx,boiler,173,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Geo 5xx,boiler,173,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Geo 5xx,boiler,173,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Geo 5xx,boiler,173,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Geo 5xx,boiler,173,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Geo 5xx,boiler,173,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Geo 5xx,boiler,173,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Geo 5xx,boiler,173,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Geo 5xx,boiler,173,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Condens 5000i/Greenstar 8000/GC9800IW,boiler,195,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logamax U122/Cerapur,boiler,203,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Logamax U122/Cerapur,boiler,203,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Logamax U122/Cerapur,boiler,203,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Logamax U122/Cerapur,boiler,203,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Logamax U122/Cerapur,boiler,203,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Logamax U122/Cerapur,boiler,203,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Logamax U122/Cerapur,boiler,203,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Logamax U122/Cerapur,boiler,203,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Logamax U122/Cerapur,boiler,203,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Logamax U122/Cerapur,boiler,203,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Logamax U122/Cerapur,boiler,203,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Logamax U122/Cerapur,boiler,203,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Logamax U122/Cerapur,boiler,203,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Logamax U122/Cerapur,boiler,203,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Logamax U122/Cerapur,boiler,203,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Logamax U122/Cerapur,boiler,203,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Logamax U122/Cerapur,boiler,203,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Logamax U122/Cerapur,boiler,203,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Logamax U122/Cerapur,boiler,203,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Logamax U122/Cerapur,boiler,203,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Logamax U122/Cerapur,boiler,203,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Logamax U122/Cerapur,boiler,203,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Logamax U122/Cerapur,boiler,203,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Logamax U122/Cerapur,boiler,203,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Logamax U122/Cerapur,boiler,203,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Logamax U122/Cerapur,boiler,203,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Logamax U122/Cerapur,boiler,203,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Logamax U122/Cerapur,boiler,203,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Logamax U122/Cerapur,boiler,203,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Logamax U122/Cerapur,boiler,203,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Logamax U122/Cerapur,boiler,203,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Logamax U122/Cerapur,boiler,203,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Logamax U122/Cerapur,boiler,203,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Logamax U122/Cerapur,boiler,203,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Logamax U122/Cerapur,boiler,203,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Logamax U122/Cerapur,boiler,203,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Logamax U122/Cerapur,boiler,203,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Logamax U122/Cerapur,boiler,203,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Logamax U122/Cerapur,boiler,203,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Logamax U122/Cerapur,boiler,203,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Logamax U122/Cerapur,boiler,203,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Logamax U122/Cerapur,boiler,203,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Logamax U122/Cerapur,boiler,203,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Logamax U122/Cerapur,boiler,203,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Logamax U122/Cerapur,boiler,203,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Logamax U122/Cerapur,boiler,203,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Logamax U122/Cerapur,boiler,203,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Logamax U122/Cerapur,boiler,203,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Logamax U122/Cerapur,boiler,203,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Logamax U122/Cerapur,boiler,203,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Logamax U122/Cerapur,boiler,203,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Logamax U122/Cerapur,boiler,203,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Logamax U122/Cerapur,boiler,203,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Logamax U122/Cerapur,boiler,203,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Logamax U122/Cerapur,boiler,203,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Logamax U122/Cerapur,boiler,203,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Logamax U122/Cerapur,boiler,203,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Logamax U122/Cerapur,boiler,203,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Logamax U122/Cerapur,boiler,203,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Logamax U122/Cerapur,boiler,203,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Logamax U122/Cerapur,boiler,203,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Logamax U122/Cerapur,boiler,203,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Logamax U122/Cerapur,boiler,203,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Logamax U122/Cerapur,boiler,203,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Logamax U122/Cerapur,boiler,203,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Logamax U122/Cerapur,boiler,203,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Logamax U122/Cerapur,boiler,203,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Logamax U122/Cerapur,boiler,203,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Logamax U122/Cerapur,boiler,203,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Logamax U122/Cerapur,boiler,203,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Logamax U122/Cerapur,boiler,203,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Logamax U122/Cerapur,boiler,203,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Logamax U122/Cerapur,boiler,203,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Logamax U122/Cerapur,boiler,203,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Logamax U122/Cerapur,boiler,203,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Logamax U122/Cerapur,boiler,203,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Logamax U122/Cerapur,boiler,203,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Logamax U122/Cerapur,boiler,203,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Logamax U122/Cerapur,boiler,203,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Logamax U122/Cerapur,boiler,203,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Logamax U122/Cerapur,boiler,203,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Logamax U122/Cerapur,boiler,203,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Logamax U122/Cerapur,boiler,203,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Logamax U122/Cerapur,boiler,203,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Logamax U122/Cerapur,boiler,203,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Logamax U122/Cerapur,boiler,203,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Logamax U122/Cerapur,boiler,203,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Logamax U122/Cerapur,boiler,203,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Logamax U122/Cerapur,boiler,203,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Logamax U122/Cerapur,boiler,203,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Logamax U122/Cerapur,boiler,203,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Ecomline Excellent,boiler,206,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Ecomline Excellent,boiler,206,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Ecomline Excellent,boiler,206,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Ecomline Excellent,boiler,206,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Ecomline Excellent,boiler,206,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Ecomline Excellent,boiler,206,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Ecomline Excellent,boiler,206,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Ecomline Excellent,boiler,206,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Ecomline Excellent,boiler,206,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Ecomline Excellent,boiler,206,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Ecomline Excellent,boiler,206,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Ecomline Excellent,boiler,206,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Ecomline Excellent,boiler,206,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Ecomline Excellent,boiler,206,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Ecomline Excellent,boiler,206,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Ecomline Excellent,boiler,206,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Ecomline Excellent,boiler,206,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Ecomline Excellent,boiler,206,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Ecomline Excellent,boiler,206,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Ecomline Excellent,boiler,206,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Ecomline Excellent,boiler,206,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Ecomline Excellent,boiler,206,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Ecomline Excellent,boiler,206,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Ecomline Excellent,boiler,206,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Ecomline Excellent,boiler,206,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Ecomline Excellent,boiler,206,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Ecomline Excellent,boiler,206,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Ecomline Excellent,boiler,206,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Ecomline Excellent,boiler,206,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Ecomline Excellent,boiler,206,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Ecomline Excellent,boiler,206,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Ecomline Excellent,boiler,206,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Ecomline Excellent,boiler,206,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Ecomline Excellent,boiler,206,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Ecomline Excellent,boiler,206,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Ecomline Excellent,boiler,206,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Ecomline Excellent,boiler,206,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Ecomline Excellent,boiler,206,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Ecomline Excellent,boiler,206,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Ecomline Excellent,boiler,206,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Ecomline Excellent,boiler,206,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Ecomline Excellent,boiler,206,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Ecomline Excellent,boiler,206,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Ecomline Excellent,boiler,206,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Ecomline Excellent,boiler,206,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Ecomline Excellent,boiler,206,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Ecomline Excellent,boiler,206,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Ecomline Excellent,boiler,206,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Ecomline Excellent,boiler,206,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Ecomline Excellent,boiler,206,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Ecomline Excellent,boiler,206,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Ecomline Excellent,boiler,206,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Ecomline Excellent,boiler,206,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Ecomline Excellent,boiler,206,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Ecomline Excellent,boiler,206,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Ecomline Excellent,boiler,206,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Ecomline Excellent,boiler,206,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Ecomline Excellent,boiler,206,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Ecomline Excellent,boiler,206,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Ecomline Excellent,boiler,206,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Ecomline Excellent,boiler,206,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Ecomline Excellent,boiler,206,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Ecomline Excellent,boiler,206,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Ecomline Excellent,boiler,206,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Ecomline Excellent,boiler,206,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Ecomline Excellent,boiler,206,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Ecomline Excellent,boiler,206,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Ecomline Excellent,boiler,206,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Ecomline Excellent,boiler,206,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Ecomline Excellent,boiler,206,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Ecomline Excellent,boiler,206,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Ecomline Excellent,boiler,206,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Ecomline Excellent,boiler,206,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Ecomline Excellent,boiler,206,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Ecomline Excellent,boiler,206,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Ecomline Excellent,boiler,206,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Ecomline Excellent,boiler,206,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Ecomline Excellent,boiler,206,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Ecomline Excellent,boiler,206,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Ecomline Excellent,boiler,206,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Ecomline Excellent,boiler,206,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Ecomline Excellent,boiler,206,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Ecomline Excellent,boiler,206,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Ecomline Excellent,boiler,206,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Ecomline Excellent,boiler,206,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Ecomline Excellent,boiler,206,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Ecomline Excellent,boiler,206,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Ecomline Excellent,boiler,206,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Ecomline Excellent,boiler,206,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Ecomline Excellent,boiler,206,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Ecomline Excellent,boiler,206,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Logamax Plus/GB192/Condens GC9000/Greenstar ErP,boiler,208,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Cascade MC400,boiler,210,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Cascade MC400,boiler,210,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Cascade MC400,boiler,210,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Cascade MC400,boiler,210,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Cascade MC400,boiler,210,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Cascade MC400,boiler,210,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Cascade MC400,boiler,210,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Cascade MC400,boiler,210,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Cascade MC400,boiler,210,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Cascade MC400,boiler,210,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Cascade MC400,boiler,210,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Cascade MC400,boiler,210,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Cascade MC400,boiler,210,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Cascade MC400,boiler,210,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Cascade MC400,boiler,210,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Cascade MC400,boiler,210,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Cascade MC400,boiler,210,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Cascade MC400,boiler,210,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Cascade MC400,boiler,210,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Cascade MC400,boiler,210,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Cascade MC400,boiler,210,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Cascade MC400,boiler,210,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Cascade MC400,boiler,210,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Cascade MC400,boiler,210,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Cascade MC400,boiler,210,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Cascade MC400,boiler,210,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Cascade MC400,boiler,210,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Cascade MC400,boiler,210,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Cascade MC400,boiler,210,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Cascade MC400,boiler,210,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Cascade MC400,boiler,210,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Cascade MC400,boiler,210,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Cascade MC400,boiler,210,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Cascade MC400,boiler,210,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Cascade MC400,boiler,210,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Cascade MC400,boiler,210,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Cascade MC400,boiler,210,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Cascade MC400,boiler,210,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Cascade MC400,boiler,210,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Cascade MC400,boiler,210,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Cascade MC400,boiler,210,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Cascade MC400,boiler,210,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Cascade MC400,boiler,210,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Cascade MC400,boiler,210,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Cascade MC400,boiler,210,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Cascade MC400,boiler,210,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Cascade MC400,boiler,210,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Cascade MC400,boiler,210,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Cascade MC400,boiler,210,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Cascade MC400,boiler,210,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Cascade MC400,boiler,210,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Cascade MC400,boiler,210,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Cascade MC400,boiler,210,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Cascade MC400,boiler,210,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Cascade MC400,boiler,210,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Cascade MC400,boiler,210,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Cascade MC400,boiler,210,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Cascade MC400,boiler,210,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Cascade MC400,boiler,210,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Cascade MC400,boiler,210,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Cascade MC400,boiler,210,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Cascade MC400,boiler,210,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Cascade MC400,boiler,210,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Cascade MC400,boiler,210,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Cascade MC400,boiler,210,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Cascade MC400,boiler,210,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Cascade MC400,boiler,210,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Cascade MC400,boiler,210,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Cascade MC400,boiler,210,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Cascade MC400,boiler,210,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Cascade MC400,boiler,210,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Cascade MC400,boiler,210,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Cascade MC400,boiler,210,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Cascade MC400,boiler,210,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Cascade MC400,boiler,210,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Cascade MC400,boiler,210,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Cascade MC400,boiler,210,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Cascade MC400,boiler,210,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Cascade MC400,boiler,210,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Cascade MC400,boiler,210,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Cascade MC400,boiler,210,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Cascade MC400,boiler,210,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Cascade MC400,boiler,210,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Cascade MC400,boiler,210,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Cascade MC400,boiler,210,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Cascade MC400,boiler,210,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Cascade MC400,boiler,210,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Cascade MC400,boiler,210,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Cascade MC400,boiler,210,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Cascade MC400,boiler,210,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Cascade MC400,boiler,210,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
EasyControl Adapter,boiler,211,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
EasyControl Adapter,boiler,211,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
EasyControl Adapter,boiler,211,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
EasyControl Adapter,boiler,211,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
EasyControl Adapter,boiler,211,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
EasyControl Adapter,boiler,211,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
EasyControl Adapter,boiler,211,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
EasyControl Adapter,boiler,211,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
EasyControl Adapter,boiler,211,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
EasyControl Adapter,boiler,211,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
EasyControl Adapter,boiler,211,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
EasyControl Adapter,boiler,211,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
EasyControl Adapter,boiler,211,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
EasyControl Adapter,boiler,211,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
EasyControl Adapter,boiler,211,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
EasyControl Adapter,boiler,211,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
EasyControl Adapter,boiler,211,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
EasyControl Adapter,boiler,211,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
EasyControl Adapter,boiler,211,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
EasyControl Adapter,boiler,211,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
EasyControl Adapter,boiler,211,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
EasyControl Adapter,boiler,211,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
EasyControl Adapter,boiler,211,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
EasyControl Adapter,boiler,211,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
EasyControl Adapter,boiler,211,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
EasyControl Adapter,boiler,211,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
EasyControl Adapter,boiler,211,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
EasyControl Adapter,boiler,211,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
EasyControl Adapter,boiler,211,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
EasyControl Adapter,boiler,211,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
EasyControl Adapter,boiler,211,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
EasyControl Adapter,boiler,211,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
EasyControl Adapter,boiler,211,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
EasyControl Adapter,boiler,211,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
EasyControl Adapter,boiler,211,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
EasyControl Adapter,boiler,211,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
EasyControl Adapter,boiler,211,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
EasyControl Adapter,boiler,211,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
EasyControl Adapter,boiler,211,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
EasyControl Adapter,boiler,211,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
EasyControl Adapter,boiler,211,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
EasyControl Adapter,boiler,211,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
EasyControl Adapter,boiler,211,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
EasyControl Adapter,boiler,211,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
EasyControl Adapter,boiler,211,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
EasyControl Adapter,boiler,211,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
EasyControl Adapter,boiler,211,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
EasyControl Adapter,boiler,211,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
EasyControl Adapter,boiler,211,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
EasyControl Adapter,boiler,211,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
EasyControl Adapter,boiler,211,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
EasyControl Adapter,boiler,211,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
EasyControl Adapter,boiler,211,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
EasyControl Adapter,boiler,211,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
EasyControl Adapter,boiler,211,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
EasyControl Adapter,boiler,211,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
EasyControl Adapter,boiler,211,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
EasyControl Adapter,boiler,211,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
EasyControl Adapter,boiler,211,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
EasyControl Adapter,boiler,211,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
EasyControl Adapter,boiler,211,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
EasyControl Adapter,boiler,211,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
EasyControl Adapter,boiler,211,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
EasyControl Adapter,boiler,211,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
EasyControl Adapter,boiler,211,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
EasyControl Adapter,boiler,211,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
EasyControl Adapter,boiler,211,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
EasyControl Adapter,boiler,211,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
EasyControl Adapter,boiler,211,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
EasyControl Adapter,boiler,211,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
EasyControl Adapter,boiler,211,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
EasyControl Adapter,boiler,211,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
EasyControl Adapter,boiler,211,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
EasyControl Adapter,boiler,211,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
EasyControl Adapter,boiler,211,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
EasyControl Adapter,boiler,211,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
EasyControl Adapter,boiler,211,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
EasyControl Adapter,boiler,211,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
EasyControl Adapter,boiler,211,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
EasyControl Adapter,boiler,211,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
EasyControl Adapter,boiler,211,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
EasyControl Adapter,boiler,211,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
EasyControl Adapter,boiler,211,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
EasyControl Adapter,boiler,211,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
EasyControl Adapter,boiler,211,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
EasyControl Adapter,boiler,211,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
EasyControl Adapter,boiler,211,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
EasyControl Adapter,boiler,211,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
EasyControl Adapter,boiler,211,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
EasyControl Adapter,boiler,211,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
EasyControl Adapter,boiler,211,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Greenstar HIU,boiler,219,keepwarmtemp,keep warm temperature,uint (>=0<=254),C,true,number.boiler_keep_warm_temperature,number.boiler_keepwarmtemp
Greenstar HIU,boiler,219,setreturntemp,set temp return,uint (>=0<=254),C,true,number.boiler_set_temp_return,number.boiler_setreturntemp
Greenstar HIU,boiler,219,cwflowrate,cold water flow rate,ushort (>=0<=31999),l/min,false,sensor.boiler_cold_water_flow_rate,sensor.boiler_cwflowrate
Greenstar HIU,boiler,219,netflowtemp,heat network flow temp,ushort (>=0<=31999),C,false,sensor.boiler_heat_network_flow_temp,sensor.boiler_netflowtemp
Greenstar HIU,boiler,219,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Greenstar HIU,boiler,219,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Greenstar HIU,boiler,219,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Greenstar HIU,boiler,219,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Greenstar HIU,boiler,219,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Greenstar HIU,boiler,219,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Greenstar HIU,boiler,219,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Greenstar HIU,boiler,219,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Greenstar HIU,boiler,219,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Greenstar HIU,boiler,219,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Greenstar HIU,boiler,219,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Greenstar HIU,boiler,219,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Greenstar HIU,boiler,219,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Greenstar HIU,boiler,219,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Greenstar HIU,boiler,219,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Greenstar HIU,boiler,219,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Greenstar HIU,boiler,219,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Greenstar HIU,boiler,219,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Greenstar HIU,boiler,219,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Greenstar HIU,boiler,219,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Greenstar HIU,boiler,219,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Greenstar HIU,boiler,219,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Greenstar HIU,boiler,219,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Greenstar HIU,boiler,219,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Greenstar HIU,boiler,219,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Greenstar HIU,boiler,219,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Greenstar HIU,boiler,219,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Greenstar HIU,boiler,219,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Greenstar HIU,boiler,219,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Greenstar HIU,boiler,219,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Greenstar HIU,boiler,219,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Greenstar HIU,boiler,219,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Greenstar HIU,boiler,219,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Greenstar HIU,boiler,219,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Greenstar HIU,boiler,219,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Greenstar HIU,boiler,219,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Greenstar HIU,boiler,219,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Greenstar HIU,boiler,219,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Greenstar HIU,boiler,219,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Greenstar HIU,boiler,219,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Greenstar HIU,boiler,219,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Greenstar HIU,boiler,219,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Greenstar HIU,boiler,219,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Greenstar HIU,boiler,219,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Greenstar HIU,boiler,219,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Greenstar HIU,boiler,219,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Greenstar HIU,boiler,219,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Greenstar HIU,boiler,219,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Greenstar HIU,boiler,219,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Greenstar HIU,boiler,219,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Greenstar HIU,boiler,219,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Greenstar HIU,boiler,219,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Greenstar HIU,boiler,219,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Greenstar HIU,boiler,219,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Greenstar HIU,boiler,219,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Greenstar HIU,boiler,219,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Greenstar HIU,boiler,219,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Greenstar HIU,boiler,219,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Greenstar HIU,boiler,219,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Greenstar HIU,boiler,219,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Greenstar HIU,boiler,219,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Greenstar HIU,boiler,219,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Greenstar HIU,boiler,219,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Greenstar HIU,boiler,219,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Greenstar HIU,boiler,219,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Greenstar HIU,boiler,219,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Greenstar HIU,boiler,219,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Greenstar HIU,boiler,219,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Greenstar HIU,boiler,219,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Greenstar HIU,boiler,219,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Greenstar HIU,boiler,219,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Greenstar HIU,boiler,219,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Greenstar HIU,boiler,219,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Greenstar HIU,boiler,219,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Greenstar HIU,boiler,219,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Greenstar HIU,boiler,219,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Greenstar HIU,boiler,219,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Greenstar HIU,boiler,219,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Greenstar HIU,boiler,219,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Greenstar HIU,boiler,219,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Greenstar HIU,boiler,219,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Greenstar HIU,boiler,219,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Greenstar HIU,boiler,219,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Greenstar HIU,boiler,219,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Greenstar HIU,boiler,219,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Greenstar HIU,boiler,219,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Greenstar HIU,boiler,219,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Greenstar HIU,boiler,219,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Greenstar HIU,boiler,219,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Greenstar HIU,boiler,219,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Greenstar HIU,boiler,219,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logamax Plus GB122/Condense 2300,boiler,234,reset,Reset,cmd [-\|maintenance\|error], ,true,sensor.boiler_Reset,sensor.boiler_reset
Logamax Plus GB122/Condense 2300,boiler,234,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive
Logamax Plus GB122/Condense 2300,boiler,234,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive
Logamax Plus GB122/Condense 2300,boiler,234,selflowtemp,selected flow temperature,uint (>=0<=254),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp
Logamax Plus GB122/Condense 2300,boiler,234,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod
Logamax Plus GB122/Condense 2300,boiler,234,outdoortemp,outside temperature,short (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp
Logamax Plus GB122/Condense 2300,boiler,234,curflowtemp,current flow temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp
Logamax Plus GB122/Condense 2300,boiler,234,rettemp,return temperature,ushort (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp
Logamax Plus GB122/Condense 2300,boiler,234,switchtemp,mixing switch temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp
Logamax Plus GB122/Condense 2300,boiler,234,syspress,system pressure,uint (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress
Logamax Plus GB122/Condense 2300,boiler,234,boiltemp,actual boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp
Logamax Plus GB122/Condense 2300,boiler,234,exhausttemp,exhaust temperature,ushort (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp
Logamax Plus GB122/Condense 2300,boiler,234,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas
Logamax Plus GB122/Condense 2300,boiler,234,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2
Logamax Plus GB122/Condense 2300,boiler,234,flamecurr,flame current,ushort (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr
Logamax Plus GB122/Condense 2300,boiler,234,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump
Logamax Plus GB122/Condense 2300,boiler,234,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork
Logamax Plus GB122/Condense 2300,boiler,234,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork
Logamax Plus GB122/Condense 2300,boiler,234,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat
Logamax Plus GB122/Condense 2300,boiler,234,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated
Logamax Plus GB122/Condense 2300,boiler,234,heatingtemp,heating temperature,uint (>=0<=254),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp
Logamax Plus GB122/Condense 2300,boiler,234,pumpmodmax,boiler pump max power,uint (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax
Logamax Plus GB122/Condense 2300,boiler,234,pumpmodmin,boiler pump min power,uint (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin
Logamax Plus GB122/Condense 2300,boiler,234,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode
Logamax Plus GB122/Condense 2300,boiler,234,pumpdelay,pump delay,uint (>=0<=254),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay
Logamax Plus GB122/Condense 2300,boiler,234,burnminperiod,burner min period,uint (>=0<=254),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod
Logamax Plus GB122/Condense 2300,boiler,234,burnminpower,burner min power,uint (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower
Logamax Plus GB122/Condense 2300,boiler,234,burnmaxpower,burner max power,uint (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower
Logamax Plus GB122/Condense 2300,boiler,234,boilhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston
Logamax Plus GB122/Condense 2300,boiler,234,boilhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff
Logamax Plus GB122/Condense 2300,boiler,234,boil2hyston,hysteresis stage 2 on temperature,int (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston
Logamax Plus GB122/Condense 2300,boiler,234,boil2hystoff,hysteresis stage 2 off temperature,int (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff
Logamax Plus GB122/Condense 2300,boiler,234,setflowtemp,set flow temperature,uint (>=0<=254),C,false,sensor.boiler_set_flow_temperature,sensor.boiler_setflowtemp
Logamax Plus GB122/Condense 2300,boiler,234,setburnpow,burner set power,uint (>=0<=100),%,false,sensor.boiler_burner_set_power,sensor.boiler_setburnpow
Logamax Plus GB122/Condense 2300,boiler,234,absburnpow,burner current power (absolute),uint (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow
Logamax Plus GB122/Condense 2300,boiler,234,selburnpow,burner selected max power,uint (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow
Logamax Plus GB122/Condense 2300,boiler,234,curburnpow,burner current power,uint (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow
Logamax Plus GB122/Condense 2300,boiler,234,burnstarts,burner starts,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts
Logamax Plus GB122/Condense 2300,boiler,234,burnworkmin,total burner operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin
Logamax Plus GB122/Condense 2300,boiler,234,burn2workmin,burner stage 2 operating time,time (>=0<=65533),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin
Logamax Plus GB122/Condense 2300,boiler,234,heatworkmin,total heat operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin
Logamax Plus GB122/Condense 2300,boiler,234,heatstarts,burner starts heating,ulong (>=0<=65533), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts
Logamax Plus GB122/Condense 2300,boiler,234,ubauptime,total UBA operating time,time (>=0<=65533),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime
Logamax Plus GB122/Condense 2300,boiler,234,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode
Logamax Plus GB122/Condense 2300,boiler,234,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode
Logamax Plus GB122/Condense 2300,boiler,234,servicecodenumber,service code number,ushort (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber
Logamax Plus GB122/Condense 2300,boiler,234,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage
Logamax Plus GB122/Condense 2300,boiler,234,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance
Logamax Plus GB122/Condense 2300,boiler,234,maintenancetime,time to next maintenance,ushort (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime
Logamax Plus GB122/Condense 2300,boiler,234,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate
Logamax Plus GB122/Condense 2300,boiler,234,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops
Logamax Plus GB122/Condense 2300,boiler,234,emergencytemp,emergency temperature,uint (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp
Logamax Plus GB122/Condense 2300,boiler,234,wwtapactivated,turn on/off,boolean, ,true,switch.boiler_turn_on/off,switch.boiler_wwtapactivated
Logamax Plus GB122/Condense 2300,boiler,234,wwsettemp,set temperature,uint (>=0<=254),C,false,sensor.boiler_set_temperature,sensor.boiler_wwsettemp
Logamax Plus GB122/Condense 2300,boiler,234,wwseltemp,selected temperature,uint (>=0<=254),C,true,number.boiler_selected_temperature,number.boiler_wwseltemp
Logamax Plus GB122/Condense 2300,boiler,234,wwseltemplow,selected lower temperature,uint (>=0<=254),C,true,number.boiler_selected_lower_temperature,number.boiler_wwseltemplow
Logamax Plus GB122/Condense 2300,boiler,234,wwseltempoff,selected temperature for off,uint (>=0<=254),C,false,sensor.boiler_selected_temperature_for_off,sensor.boiler_wwseltempoff
Logamax Plus GB122/Condense 2300,boiler,234,wwseltempsingle,single charge temperature,uint (>=0<=254),C,true,number.boiler_single_charge_temperature,number.boiler_wwseltempsingle
Logamax Plus GB122/Condense 2300,boiler,234,wwsolartemp,solar boiler temperature,ushort (>=0<=3199),C,false,sensor.boiler_solar_boiler_temperature,sensor.boiler_wwsolartemp
Logamax Plus GB122/Condense 2300,boiler,234,wwtype,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_type,sensor.boiler_wwtype
Logamax Plus GB122/Condense 2300,boiler,234,wwcomfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_comfort,select.boiler_wwcomfort
Logamax Plus GB122/Condense 2300,boiler,234,wwcomfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_comfort_mode,select.boiler_wwcomfort1
Logamax Plus GB122/Condense 2300,boiler,234,wwflowtempoffset,flow temperature offset,uint (>=0<=100),C,true,number.boiler_flow_temperature_offset,number.boiler_wwflowtempoffset
Logamax Plus GB122/Condense 2300,boiler,234,wwchargeoptimization,charge optimization,boolean, ,true,switch.boiler_charge_optimization,switch.boiler_wwchargeoptimization
Logamax Plus GB122/Condense 2300,boiler,234,wwmaxpower,max power,uint (>=0<=254),%,true,number.boiler_max_power,number.boiler_wwmaxpower
Logamax Plus GB122/Condense 2300,boiler,234,wwmaxtemp,maximum temperature,uint (>=0<=70),C,true,number.boiler_maximum_temperature,number.boiler_wwmaxtemp
Logamax Plus GB122/Condense 2300,boiler,234,wwcircpump,circulation pump available,boolean, ,true,switch.boiler_circulation_pump_available,switch.boiler_wwcircpump
Logamax Plus GB122/Condense 2300,boiler,234,wwchargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_charging_type,sensor.boiler_wwchargetype
Logamax Plus GB122/Condense 2300,boiler,234,wwhyston,hysteresis on temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_on_temperature,number.boiler_wwhyston
Logamax Plus GB122/Condense 2300,boiler,234,wwhystoff,hysteresis off temperature,int (>=-126<=126),C,true,number.boiler_hysteresis_off_temperature,number.boiler_wwhystoff
Logamax Plus GB122/Condense 2300,boiler,234,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.boiler_disinfection_temperature,number.boiler_wwdisinfectiontemp
Logamax Plus GB122/Condense 2300,boiler,234,wwcircmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_circulation_pump_mode,select.boiler_wwcircmode
Logamax Plus GB122/Condense 2300,boiler,234,wwcirc,circulation active,boolean, ,true,switch.boiler_circulation_active,switch.boiler_wwcirc
Logamax Plus GB122/Condense 2300,boiler,234,wwcurtemp,current intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_intern_temperature,sensor.boiler_wwcurtemp
Logamax Plus GB122/Condense 2300,boiler,234,wwcurtemp2,current extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_current_extern_temperature,sensor.boiler_wwcurtemp2
Logamax Plus GB122/Condense 2300,boiler,234,wwcurflow,current tap water flow,uint (>=0<=25),l/min,false,sensor.boiler_current_tap_water_flow,sensor.boiler_wwcurflow
Logamax Plus GB122/Condense 2300,boiler,234,wwstoragetemp1,storage intern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_intern_temperature,sensor.boiler_wwstoragetemp1
Logamax Plus GB122/Condense 2300,boiler,234,wwstoragetemp2,storage extern temperature,ushort (>=0<=3199),C,false,sensor.boiler_storage_extern_temperature,sensor.boiler_wwstoragetemp2
Logamax Plus GB122/Condense 2300,boiler,234,wwactivated,activated,boolean, ,true,switch.boiler_activated,switch.boiler_wwactivated
Logamax Plus GB122/Condense 2300,boiler,234,wwonetime,one time charging,boolean, ,true,switch.boiler_one_time_charging,switch.boiler_wwonetime
Logamax Plus GB122/Condense 2300,boiler,234,wwdisinfecting,disinfecting,boolean, ,true,switch.boiler_disinfecting,switch.boiler_wwdisinfecting
Logamax Plus GB122/Condense 2300,boiler,234,wwcharging,charging,boolean, ,false,binary_sensor.boiler_charging,binary_sensor.boiler_wwcharging
Logamax Plus GB122/Condense 2300,boiler,234,wwrecharging,recharging,boolean, ,false,binary_sensor.boiler_recharging,binary_sensor.boiler_wwrecharging
Logamax Plus GB122/Condense 2300,boiler,234,wwtempok,temperature ok,boolean, ,false,binary_sensor.boiler_temperature_ok,binary_sensor.boiler_wwtempok
Logamax Plus GB122/Condense 2300,boiler,234,wwactive,active,boolean, ,false,binary_sensor.boiler_active,binary_sensor.boiler_wwactive
Logamax Plus GB122/Condense 2300,boiler,234,ww3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_3-way_valve_active,binary_sensor.boiler_ww3wayvalve
Logamax Plus GB122/Condense 2300,boiler,234,wwsetpumppower,set pump power,uint (>=0<=100),%,false,sensor.boiler_set_pump_power,sensor.boiler_wwsetpumppower
Logamax Plus GB122/Condense 2300,boiler,234,wwmixertemp,mixer temperature,ushort (>=0<=3199),C,false,sensor.boiler_mixer_temperature,sensor.boiler_wwmixertemp
Logamax Plus GB122/Condense 2300,boiler,234,wwcylmiddletemp,cylinder middle temperature (TS3),ushort (>=0<=3199),C,false,sensor.boiler_cylinder_middle_temperature_(TS3),sensor.boiler_wwcylmiddletemp
Logamax Plus GB122/Condense 2300,boiler,234,wwstarts,starts,ulong (>=0<=65533), ,false,sensor.boiler_starts,sensor.boiler_wwstarts
Logamax Plus GB122/Condense 2300,boiler,234,wwworkm,active time,time (>=0<=65533),minutes,false,sensor.boiler_active_time,sensor.boiler_wwworkm
Logamatic TC100/Moduline Easy,thermostat,202,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Logamatic TC100/Moduline Easy,thermostat,202,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Logamatic TC100/Moduline Easy,thermostat,202,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
Logamatic TC100/Moduline Easy,thermostat,202,seltemp,selected room temperature,short (>=-319<=319),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp
Logamatic TC100/Moduline Easy,thermostat,202,currtemp,current room temperature,short (>=-319<=319),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Logamatic TC100/Moduline Easy,thermostat,202,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
EasyControl CT200,thermostat,203,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
EasyControl CT200,thermostat,203,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
EasyControl CT200,thermostat,203,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
EasyControl CT200,thermostat,203,seltemp,selected room temperature,short (>=-319<=319),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp
EasyControl CT200,thermostat,203,currtemp,current room temperature,short (>=-319<=319),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
EasyControl CT200,thermostat,203,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
UI800,thermostat,4,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
UI800,thermostat,4,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
UI800,thermostat,4,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
UI800,thermostat,4,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
UI800,thermostat,4,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry
UI800,thermostat,4,dampedoutdoortemp,damped outdoor temperature,short (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
UI800,thermostat,4,floordrytemp,floor drying temperature,uint (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp
UI800,thermostat,4,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
UI800,thermostat,4,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
UI800,thermostat,4,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
UI800,thermostat,4,wwsettemp,set temperature,uint (>=0<=254),C,true,number.thermostat_set_temperature,number.thermostat_wwsettemp
UI800,thermostat,4,wwmode,mode,enum [off\|normal\|comfort\|auto\|own prog\|eco], ,true,select.thermostat_mode,select.thermostat_wwmode
UI800,thermostat,4,wwsettemplow,set low temperature,uint (>=0<=254),C,true,number.thermostat_set_low_temperature,number.thermostat_wwsettemplow
UI800,thermostat,4,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
UI800,thermostat,4,wwchargeduration,charge duration,uint (>=0<=3810),minutes,true,number.thermostat_charge_duration,number.thermostat_wwchargeduration
UI800,thermostat,4,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
UI800,thermostat,4,wwextra1,circuit 1 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_1_extra,sensor.thermostat_wwextra1
UI800,thermostat,4,wwextra2,circuit 2 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_2_extra,sensor.thermostat_wwextra2
UI800,thermostat,4,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
UI800,thermostat,4,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
UI800,thermostat,4,wwdisinfecttime,disinfection time,uint (>=0<=1431),minutes,true,number.thermostat_disinfection_time,number.thermostat_wwdisinfecttime
UI800,thermostat,4,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
UI800,thermostat,4,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
UI800,thermostat,4,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
UI800,thermostat,4,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
UI800,thermostat,4,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
UI800,thermostat,4,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
UI800,thermostat,4,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
UI800,thermostat,4,pvenableww,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenableww
UI800,thermostat,4,pvraiseheat,raise heating with PV,int (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat
UI800,thermostat,4,pvlowercool,lower cooling with PV,int (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool
UI800,thermostat,4,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
UI800,thermostat,4,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
UI800,thermostat,4,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
UI800,thermostat,4,mode,mode,enum [manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
UI800,thermostat,4,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
UI800,thermostat,4,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
UI800,thermostat,4,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
UI800,thermostat,4,comforttemp,comfort temperature,uint (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp
UI800,thermostat,4,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
UI800,thermostat,4,designtemp,design temperature,uint (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
UI800,thermostat,4,offsettemp,offset temperature,int (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
UI800,thermostat,4,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
UI800,thermostat,4,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
UI800,thermostat,4,roominfluence,room influence,uint (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
UI800,thermostat,4,roominflfactor,room influence factor,uint (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor
UI800,thermostat,4,curroominfl,current room influence,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl
UI800,thermostat,4,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
UI800,thermostat,4,nofrosttemp,nofrost temperature,int (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
UI800,thermostat,4,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
UI800,thermostat,4,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
UI800,thermostat,4,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode
UI800,thermostat,4,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode
UI800,thermostat,4,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
UI800,thermostat,4,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate
UI800,thermostat,4,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
UI800,thermostat,4,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
UI800,thermostat,4,tempautotemp,temporary set temperature automode,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
UI800,thermostat,4,remoteseltemp,temporary set temperature from remote,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp
UI800,thermostat,4,fastheatup,fast heatup,uint (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup
UI800,thermostat,4,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization
UI800,thermostat,4,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
UI800,thermostat,4,noreducetemp,no reduce below temperature,int (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
UI800,thermostat,4,reducetemp,off/reduce switch temperature,int (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
UI800,thermostat,4,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
UI800,thermostat,4,cooling,cooling,boolean, ,true,switch.thermostat_hc1_cooling,switch.thermostat_hc1_cooling
UI800,thermostat,4,coolingon,cooling,boolean, ,false,binary_sensor.thermostat_hc1_cooling,binary_sensor.thermostat_hc1_coolingon
UI800,thermostat,4,hpmode,HP Mode,enum [heating\|cooling\|heating&cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode
UI800,thermostat,4,dewoffset,dew point offset,uint (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset
UI800,thermostat,4,roomtempdiff,room temp difference,uint (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff
UI800,thermostat,4,hpminflowtemp,HP min. flow temp.,uint (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp
RC10,thermostat,65,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC10,thermostat,65,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC10,thermostat,65,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC10,thermostat,65,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC10,thermostat,65,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC10,thermostat,65,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC10,thermostat,65,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC10,thermostat,65,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC10,thermostat,65,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC10,thermostat,65,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
RC10,thermostat,65,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
RC10,thermostat,65,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC10,thermostat,65,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC10,thermostat,65,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC10,thermostat,65,tempautotemp,temporary set temperature automode,uint (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC10,thermostat,65,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC10,thermostat,65,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC10,thermostat,65,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC10,thermostat,65,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
RC30,thermostat,67,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC30,thermostat,67,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC30,thermostat,67,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC30,thermostat,67,display,display,enum [internal temperature\|internal setpoint\|external temperature\|burner temperature\|ww temperature\|functioning mode\|time\|date\|smoke temperature], ,true,select.thermostat_display,select.thermostat_display
RC30,thermostat,67,language,language,enum [german\|dutch\|french\|italian], ,false,sensor.thermostat_language,sensor.thermostat_language
RC30,thermostat,67,clockoffset,clock offset,int (>=-126<=126),seconds,true,number.thermostat_clock_offset,number.thermostat_clockoffset
RC30,thermostat,67,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
RC30,thermostat,67,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC30,thermostat,67,inttemp1,temperature sensor 1,short (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1
RC30,thermostat,67,inttemp2,temperature sensor 2,short (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2
RC30,thermostat,67,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
RC30,thermostat,67,dampedoutdoortemp,damped outdoor temperature,int (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
RC30,thermostat,67,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
RC30,thermostat,67,wwmode,mode,enum [off\|on\|auto], ,true,select.thermostat_mode,select.thermostat_wwmode
RC30,thermostat,67,wwcircmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
RC30,thermostat,67,wwprogmode,program,enum [std prog\|own prog], ,true,select.thermostat_program,select.thermostat_wwprogmode
RC30,thermostat,67,wwcircprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_circulation_program,select.thermostat_wwcircprog
RC30,thermostat,67,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
RC30,thermostat,67,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
RC30,thermostat,67,wwdisinfecthour,disinfection hour,uint (>=0<=23), ,true,number.thermostat_disinfection_hour,number.thermostat_wwdisinfecthour
RC30,thermostat,67,wwmaxtemp,maximum temperature,uint (>=0<=254),C,true,number.thermostat_maximum_temperature,number.thermostat_wwmaxtemp
RC30,thermostat,67,wwonetimekey,one time key function,boolean, ,true,switch.thermostat_one_time_key_function,switch.thermostat_wwonetimekey
RC30,thermostat,67,wwswitchtime,program switchtime,string, ,true,sensor.thermostat_program_switchtime,sensor.thermostat_wwswitchtime
RC30,thermostat,67,wwcircswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_circulation_program_switchtime,sensor.thermostat_wwcircswitchtime
RC30,thermostat,67,wwholidays,holiday dates,string, ,true,sensor.thermostat_holiday_dates,sensor.thermostat_wwholidays
RC30,thermostat,67,wwvacations,vacation dates,string, ,true,sensor.thermostat_vacation_dates,sensor.thermostat_wwvacations
RC30,thermostat,67,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC30,thermostat,67,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC30,thermostat,67,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC30,thermostat,67,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC30,thermostat,67,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC30,thermostat,67,daytemp,day temperature,uint (>=5<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
RC30,thermostat,67,nighttemp,night temperature,uint (>=5<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
RC30,thermostat,67,designtemp,design temperature,uint (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
RC30,thermostat,67,offsettemp,offset temperature,int (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
RC30,thermostat,67,holidaytemp,holiday temperature,uint (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp
RC30,thermostat,67,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
RC30,thermostat,67,summertemp,summer temperature,uint (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC30,thermostat,67,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC30,thermostat,67,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode
RC30,thermostat,67,nofrosttemp,nofrost temperature,int (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
RC30,thermostat,67,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
RC30,thermostat,67,roominfluence,room influence,uint (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
RC30,thermostat,67,minflowtemp,min flow temperature,uint (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC30,thermostat,67,maxflowtemp,max flow temperature,uint (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC30,thermostat,67,flowtempoffset,flow temperature offset for mixer,uint (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset
RC30,thermostat,67,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC30,thermostat,67,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
RC30,thermostat,67,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
RC30,thermostat,67,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
RC30,thermostat,67,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays
RC30,thermostat,67,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations
RC30,thermostat,67,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC30,thermostat,67,pause,pause time,uint (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause
RC30,thermostat,67,party,party time,uint (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party
RC30,thermostat,67,tempautotemp,temporary set temperature automode,uint (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC30,thermostat,67,noreducetemp,no reduce below temperature,int (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
RC30,thermostat,67,reducetemp,off/reduce switch temperature,int (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
RC30,thermostat,67,vacreducetemp,vacations off/reduce switch temperature,int (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp
RC30,thermostat,67,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode
RC30,thermostat,67,remotetemp,room temperature from remote,short (>=-3199<=3199),C,true,number.thermostat_hc1_room_temperature_from_remote,number.thermostat_hc1_remotetemp
RC30,thermostat,67,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
RC30,thermostat,67,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1
RC30,thermostat,67,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2
RC20/Moduline 300,thermostat,77,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC20/Moduline 300,thermostat,77,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC20/Moduline 300,thermostat,77,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC20/Moduline 300,thermostat,77,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC20/Moduline 300,thermostat,77,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC20/Moduline 300,thermostat,77,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC20/Moduline 300,thermostat,77,mode,mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC20/Moduline 300,thermostat,77,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
RC20/Moduline 300,thermostat,77,offtemp,temperature when mode is off,uint (>=0<=127),C,true,number.thermostat_hc1_temperature_when_mode_is_off,number.thermostat_hc1_offtemp
RC20/Moduline 300,thermostat,77,daytemp2,day temperature T2,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T2,number.thermostat_hc1_daytemp2
RC20/Moduline 300,thermostat,77,daytemp3,day temperature T3,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T3,number.thermostat_hc1_daytemp3
RC20/Moduline 300,thermostat,77,daytemp4,day temperature T4,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T4,number.thermostat_hc1_daytemp4
RC20/Moduline 300,thermostat,77,nighttemp,night temperature T1,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature_T1,number.thermostat_hc1_nighttemp
RC20/Moduline 300,thermostat,77,switchtime,program switchtime,string, ,true,sensor.thermostat_hc1_program_switchtime,sensor.thermostat_hc1_switchtime
Moduline 400,thermostat,78,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Moduline 400,thermostat,78,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Moduline 400,thermostat,78,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
Moduline 400,thermostat,78,clockoffset,clock offset,int (>=-126<=126),seconds,true,number.thermostat_clock_offset,number.thermostat_clockoffset
Moduline 400,thermostat,78,autodst,automatic change daylight saving time,boolean, ,true,switch.thermostat_automatic_change_daylight_saving_time,switch.thermostat_autodst
Moduline 400,thermostat,78,language,language,enum [german\|dutch], ,true,select.thermostat_language,select.thermostat_language
Moduline 400,thermostat,78,backlight,key backlight,boolean, ,true,switch.thermostat_key_backlight,switch.thermostat_backlight
Moduline 400,thermostat,78,brightness,screen brightness,int (>=-15<=15), ,true,number.thermostat_screen_brightness,number.thermostat_brightness
Moduline 400,thermostat,78,mixingvalves,mixing valves,uint (>=0<=2), ,true,number.thermostat_mixing_valves,number.thermostat_mixingvalves
Moduline 400,thermostat,78,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
Moduline 400,thermostat,78,heatingpid,heating PID,enum [fast\|medium\|slow], ,true,select.thermostat_heating_PID,select.thermostat_heatingpid
Moduline 400,thermostat,78,preheating,preheating in the clock program,boolean, ,true,switch.thermostat_preheating_in_the_clock_program,switch.thermostat_preheating
Moduline 400,thermostat,78,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
Moduline 400,thermostat,78,wwmode,mode,enum [on\|off\|auto], ,true,select.thermostat_mode,select.thermostat_wwmode
Moduline 400,thermostat,78,wwwhenmodeoff,when thermostat mode off,boolean, ,true,switch.thermostat_when_thermostat_mode_off,switch.thermostat_wwwhenmodeoff
Moduline 400,thermostat,78,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
Moduline 400,thermostat,78,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
Moduline 400,thermostat,78,wwdisinfecthour,disinfection hour,uint (>=0<=23), ,true,number.thermostat_disinfection_hour,number.thermostat_wwdisinfecthour
Moduline 400,thermostat,78,wwholidays,holiday dates,string, ,true,sensor.thermostat_holiday_dates,sensor.thermostat_wwholidays
Moduline 400,thermostat,78,wwvacations,vacation dates,string, ,true,sensor.thermostat_vacation_dates,sensor.thermostat_wwvacations
Moduline 400,thermostat,78,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
Moduline 400,thermostat,78,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Moduline 400,thermostat,78,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
Moduline 400,thermostat,78,mode,mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
Moduline 400,thermostat,78,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays
Moduline 400,thermostat,78,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations
Moduline 400,thermostat,78,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
Moduline 400,thermostat,78,pause,pause time,uint (>=0<=254),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause
Moduline 400,thermostat,78,party,party time,uint (>=0<=254),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party
Moduline 400,thermostat,78,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1
Moduline 400,thermostat,78,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
Moduline 400,thermostat,78,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
Moduline 400,thermostat,78,holidaytemp,holiday temperature,uint (>=0<=127),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp
Moduline 400,thermostat,78,nighttemp,night temperature T1,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature_T1,number.thermostat_hc1_nighttemp
Moduline 400,thermostat,78,daytemp2,day temperature T2,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T2,number.thermostat_hc1_daytemp2
Moduline 400,thermostat,78,daytemp3,day temperature T3,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T3,number.thermostat_hc1_daytemp3
Moduline 400,thermostat,78,daytemp4,day temperature T4,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T4,number.thermostat_hc1_daytemp4
Moduline 400,thermostat,78,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
Moduline 400,thermostat,78,offtemp,temperature when mode is off,uint (>=0<=127),C,true,number.thermostat_hc1_temperature_when_mode_is_off,number.thermostat_hc1_offtemp
RC10/Moduline 100,thermostat,79,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC10/Moduline 100,thermostat,79,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC10/Moduline 100,thermostat,79,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
RC10/Moduline 100,thermostat,79,heatingpid,heating PID,enum [fast\|medium\|slow], ,true,select.thermostat_heating_PID,select.thermostat_heatingpid
RC10/Moduline 100,thermostat,79,backlight,key backlight,boolean, ,true,switch.thermostat_key_backlight,switch.thermostat_backlight
RC10/Moduline 100,thermostat,79,wwmode,mode,enum [on\|off\|auto], ,true,select.thermostat_mode,select.thermostat_wwmode
RC10/Moduline 100,thermostat,79,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC10/Moduline 100,thermostat,79,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC10/Moduline 100,thermostat,79,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC10/Moduline 100,thermostat,79,mode,mode,enum [nofrost\|night\|day], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC10/Moduline 100,thermostat,79,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
RC10/Moduline 100,thermostat,79,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
RC10/Moduline 100,thermostat,79,reducehours,duration for nighttemp,uint (>=0<=254),hours,true,number.thermostat_hc1_duration_for_nighttemp,number.thermostat_hc1_reducehours
RC10/Moduline 100,thermostat,79,reduceminutes,remaining time for nightmode,ushort (>=0<=31999),minutes,false,sensor.thermostat_hc1_remaining_time_for_nightmode,sensor.thermostat_hc1_reduceminutes
Moduline 200,thermostat,80,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Moduline 200,thermostat,80,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Moduline 200,thermostat,80,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
Moduline 200,thermostat,80,heatingpid,heating PID,enum [fast\|medium\|slow], ,true,select.thermostat_heating_PID,select.thermostat_heatingpid
Moduline 200,thermostat,80,backlight,key backlight,boolean, ,true,switch.thermostat_key_backlight,switch.thermostat_backlight
Moduline 200,thermostat,80,wwmode,mode,enum [on\|off\|auto], ,true,select.thermostat_mode,select.thermostat_wwmode
Moduline 200,thermostat,80,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
Moduline 200,thermostat,80,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Moduline 200,thermostat,80,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
Moduline 200,thermostat,80,mode,mode,enum [nofrost\|night\|day], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
Moduline 200,thermostat,80,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
Moduline 200,thermostat,80,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
Moduline 200,thermostat,80,reducehours,duration for nighttemp,uint (>=0<=254),hours,true,number.thermostat_hc1_duration_for_nighttemp,number.thermostat_hc1_reducehours
Moduline 200,thermostat,80,reduceminutes,remaining time for nightmode,ushort (>=0<=31999),minutes,false,sensor.thermostat_hc1_remaining_time_for_nightmode,sensor.thermostat_hc1_reduceminutes
RC35,thermostat,86,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC35,thermostat,86,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC35,thermostat,86,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
RC35,thermostat,86,intoffset,internal temperature offset,int (>=-5<=5),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
RC35,thermostat,86,minexttemp,minimal external temperature,int (>=-30<=0),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC35,thermostat,86,inttemp1,temperature sensor 1,short (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1
RC35,thermostat,86,inttemp2,temperature sensor 2,short (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2
RC35,thermostat,86,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
RC35,thermostat,86,dampedoutdoortemp,damped outdoor temperature,int (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
RC35,thermostat,86,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
RC35,thermostat,86,wwmode,mode,enum [off\|on\|auto], ,true,select.thermostat_mode,select.thermostat_wwmode
RC35,thermostat,86,wwcircmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
RC35,thermostat,86,wwprogmode,program,enum [std prog\|own prog], ,true,select.thermostat_program,select.thermostat_wwprogmode
RC35,thermostat,86,wwcircprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_circulation_program,select.thermostat_wwcircprog
RC35,thermostat,86,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
RC35,thermostat,86,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
RC35,thermostat,86,wwdisinfecthour,disinfection hour,uint (>=0<=23), ,true,number.thermostat_disinfection_hour,number.thermostat_wwdisinfecthour
RC35,thermostat,86,wwmaxtemp,maximum temperature,uint (>=60<=80),C,true,number.thermostat_maximum_temperature,number.thermostat_wwmaxtemp
RC35,thermostat,86,wwonetimekey,one time key function,boolean, ,true,switch.thermostat_one_time_key_function,switch.thermostat_wwonetimekey
RC35,thermostat,86,wwswitchtime,program switchtime,string, ,true,sensor.thermostat_program_switchtime,sensor.thermostat_wwswitchtime
RC35,thermostat,86,wwcircswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_circulation_program_switchtime,sensor.thermostat_wwcircswitchtime
RC35,thermostat,86,wwholidays,holiday dates,string, ,true,sensor.thermostat_holiday_dates,sensor.thermostat_wwholidays
RC35,thermostat,86,wwvacations,vacation dates,string, ,true,sensor.thermostat_vacation_dates,sensor.thermostat_wwvacations
RC35,thermostat,86,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC35,thermostat,86,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC35,thermostat,86,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC35,thermostat,86,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC35,thermostat,86,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC35,thermostat,86,daytemp,day temperature,uint (>=5<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
RC35,thermostat,86,nighttemp,night temperature,uint (>=5<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
RC35,thermostat,86,designtemp,design temperature,uint (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
RC35,thermostat,86,offsettemp,offset temperature,int (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
RC35,thermostat,86,holidaytemp,holiday temperature,uint (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp
RC35,thermostat,86,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
RC35,thermostat,86,summertemp,summer temperature,uint (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC35,thermostat,86,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC35,thermostat,86,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode
RC35,thermostat,86,nofrosttemp,nofrost temperature,int (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
RC35,thermostat,86,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
RC35,thermostat,86,roominfluence,room influence,uint (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
RC35,thermostat,86,minflowtemp,min flow temperature,uint (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC35,thermostat,86,maxflowtemp,max flow temperature,uint (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC35,thermostat,86,flowtempoffset,flow temperature offset for mixer,uint (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset
RC35,thermostat,86,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC35,thermostat,86,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
RC35,thermostat,86,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
RC35,thermostat,86,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
RC35,thermostat,86,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays
RC35,thermostat,86,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations
RC35,thermostat,86,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC35,thermostat,86,pause,pause time,uint (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause
RC35,thermostat,86,party,party time,uint (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party
RC35,thermostat,86,tempautotemp,temporary set temperature automode,uint (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC35,thermostat,86,noreducetemp,no reduce below temperature,int (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
RC35,thermostat,86,reducetemp,off/reduce switch temperature,int (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
RC35,thermostat,86,vacreducetemp,vacations off/reduce switch temperature,int (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp
RC35,thermostat,86,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode
RC35,thermostat,86,remotetemp,room temperature from remote,short (>=-3199<=3199),C,true,number.thermostat_hc1_room_temperature_from_remote,number.thermostat_hc1_remotetemp
RC35,thermostat,86,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
RC35,thermostat,86,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1
RC35,thermostat,86,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2
RC10/Moduline 100,thermostat,90,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC10/Moduline 100,thermostat,90,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC10/Moduline 100,thermostat,90,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC10/Moduline 100,thermostat,90,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC10/Moduline 100,thermostat,90,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC10/Moduline 100,thermostat,90,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC10/Moduline 100,thermostat,90,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC10/Moduline 100,thermostat,90,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC10/Moduline 100,thermostat,90,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC10/Moduline 100,thermostat,90,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
RC10/Moduline 100,thermostat,90,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
RC10/Moduline 100,thermostat,90,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC10/Moduline 100,thermostat,90,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC10/Moduline 100,thermostat,90,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC10/Moduline 100,thermostat,90,tempautotemp,temporary set temperature automode,uint (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC10/Moduline 100,thermostat,90,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC10/Moduline 100,thermostat,90,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC10/Moduline 100,thermostat,90,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC10/Moduline 100,thermostat,90,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
RC20RF,thermostat,93,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC20RF,thermostat,93,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC20RF,thermostat,93,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC20RF,thermostat,93,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC20RF,thermostat,93,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC20RF,thermostat,93,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC20RF,thermostat,93,mode,mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC20RF,thermostat,93,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
RC20RF,thermostat,93,offtemp,temperature when mode is off,uint (>=0<=127),C,true,number.thermostat_hc1_temperature_when_mode_is_off,number.thermostat_hc1_offtemp
RC20RF,thermostat,93,daytemp2,day temperature T2,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T2,number.thermostat_hc1_daytemp2
RC20RF,thermostat,93,daytemp3,day temperature T3,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T3,number.thermostat_hc1_daytemp3
RC20RF,thermostat,93,daytemp4,day temperature T4,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T4,number.thermostat_hc1_daytemp4
RC20RF,thermostat,93,nighttemp,night temperature T1,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature_T1,number.thermostat_hc1_nighttemp
RC20RF,thermostat,93,switchtime,program switchtime,string, ,true,sensor.thermostat_hc1_program_switchtime,sensor.thermostat_hc1_switchtime
RFM20 Remote,thermostat,94,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RFM20 Remote,thermostat,94,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RFM20 Remote,thermostat,94,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RFM20 Remote,thermostat,94,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RFM20 Remote,thermostat,94,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RFM20 Remote,thermostat,94,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC25,thermostat,151,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC25,thermostat,151,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC25,thermostat,151,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC25,thermostat,151,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC25,thermostat,151,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC25,thermostat,151,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC25,thermostat,151,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC25,thermostat,151,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC25,thermostat,151,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC25,thermostat,151,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
RC25,thermostat,151,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
RC25,thermostat,151,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC25,thermostat,151,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC25,thermostat,151,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC25,thermostat,151,tempautotemp,temporary set temperature automode,uint (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC25,thermostat,151,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC25,thermostat,151,summertemp,summer temperature,uint (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC25,thermostat,151,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC200/CW100,thermostat,157,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC200/CW100,thermostat,157,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC200/CW100,thermostat,157,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
RC200/CW100,thermostat,157,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
RC200/CW100,thermostat,157,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry
RC200/CW100,thermostat,157,dampedoutdoortemp,damped outdoor temperature,short (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
RC200/CW100,thermostat,157,floordrytemp,floor drying temperature,uint (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp
RC200/CW100,thermostat,157,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
RC200/CW100,thermostat,157,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC200/CW100,thermostat,157,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
RC200/CW100,thermostat,157,wwsettemp,set temperature,uint (>=0<=254),C,true,number.thermostat_set_temperature,number.thermostat_wwsettemp
RC200/CW100,thermostat,157,wwmode,mode,enum [off\|normal\|comfort\|auto\|own prog\|eco], ,true,select.thermostat_mode,select.thermostat_wwmode
RC200/CW100,thermostat,157,wwsettemplow,set low temperature,uint (>=0<=254),C,true,number.thermostat_set_low_temperature,number.thermostat_wwsettemplow
RC200/CW100,thermostat,157,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
RC200/CW100,thermostat,157,wwchargeduration,charge duration,uint (>=0<=3810),minutes,true,number.thermostat_charge_duration,number.thermostat_wwchargeduration
RC200/CW100,thermostat,157,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
RC200/CW100,thermostat,157,wwextra1,circuit 1 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_1_extra,sensor.thermostat_wwextra1
RC200/CW100,thermostat,157,wwextra2,circuit 2 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_2_extra,sensor.thermostat_wwextra2
RC200/CW100,thermostat,157,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
RC200/CW100,thermostat,157,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
RC200/CW100,thermostat,157,wwdisinfecttime,disinfection time,uint (>=0<=1431),minutes,true,number.thermostat_disinfection_time,number.thermostat_wwdisinfecttime
RC200/CW100,thermostat,157,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
RC200/CW100,thermostat,157,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
RC200/CW100,thermostat,157,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
RC200/CW100,thermostat,157,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
RC200/CW100,thermostat,157,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
RC200/CW100,thermostat,157,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
RC200/CW100,thermostat,157,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
RC200/CW100,thermostat,157,pvenableww,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenableww
RC200/CW100,thermostat,157,pvraiseheat,raise heating with PV,int (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat
RC200/CW100,thermostat,157,pvlowercool,lower cooling with PV,int (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool
RC200/CW100,thermostat,157,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC200/CW100,thermostat,157,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC200/CW100,thermostat,157,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC200/CW100,thermostat,157,mode,mode,enum [manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC200/CW100,thermostat,157,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC200/CW100,thermostat,157,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
RC200/CW100,thermostat,157,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
RC200/CW100,thermostat,157,comforttemp,comfort temperature,uint (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp
RC200/CW100,thermostat,157,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC200/CW100,thermostat,157,designtemp,design temperature,uint (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
RC200/CW100,thermostat,157,offsettemp,offset temperature,int (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
RC200/CW100,thermostat,157,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC200/CW100,thermostat,157,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC200/CW100,thermostat,157,roominfluence,room influence,uint (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
RC200/CW100,thermostat,157,roominflfactor,room influence factor,uint (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor
RC200/CW100,thermostat,157,curroominfl,current room influence,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl
RC200/CW100,thermostat,157,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
RC200/CW100,thermostat,157,nofrosttemp,nofrost temperature,int (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
RC200/CW100,thermostat,157,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
RC200/CW100,thermostat,157,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC200/CW100,thermostat,157,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode
RC200/CW100,thermostat,157,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode
RC200/CW100,thermostat,157,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC200/CW100,thermostat,157,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate
RC200/CW100,thermostat,157,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
RC200/CW100,thermostat,157,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC200/CW100,thermostat,157,tempautotemp,temporary set temperature automode,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC200/CW100,thermostat,157,remoteseltemp,temporary set temperature from remote,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp
RC200/CW100,thermostat,157,fastheatup,fast heatup,uint (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup
RC200/CW100,thermostat,157,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization
RC200/CW100,thermostat,157,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
RC200/CW100,thermostat,157,noreducetemp,no reduce below temperature,int (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
RC200/CW100,thermostat,157,reducetemp,off/reduce switch temperature,int (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
RC200/CW100,thermostat,157,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
RC200/CW100,thermostat,157,cooling,cooling,boolean, ,true,switch.thermostat_hc1_cooling,switch.thermostat_hc1_cooling
RC200/CW100,thermostat,157,coolingon,cooling,boolean, ,false,binary_sensor.thermostat_hc1_cooling,binary_sensor.thermostat_hc1_coolingon
RC200/CW100,thermostat,157,hpmode,HP Mode,enum [heating\|cooling\|heating&cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode
RC200/CW100,thermostat,157,dewoffset,dew point offset,uint (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset
RC200/CW100,thermostat,157,roomtempdiff,room temp difference,uint (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff
RC200/CW100,thermostat,157,hpminflowtemp,HP min. flow temp.,uint (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,dampedoutdoortemp,damped outdoor temperature,short (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,floordrytemp,floor drying temperature,uint (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwsettemp,set temperature,uint (>=0<=254),C,true,number.thermostat_set_temperature,number.thermostat_wwsettemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwmode,mode,enum [off\|normal\|comfort\|auto\|own prog\|eco], ,true,select.thermostat_mode,select.thermostat_wwmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwsettemplow,set low temperature,uint (>=0<=254),C,true,number.thermostat_set_low_temperature,number.thermostat_wwsettemplow
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwchargeduration,charge duration,uint (>=0<=3810),minutes,true,number.thermostat_charge_duration,number.thermostat_wwchargeduration
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwextra1,circuit 1 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_1_extra,sensor.thermostat_wwextra1
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwextra2,circuit 2 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_2_extra,sensor.thermostat_wwextra2
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwdisinfecttime,disinfection time,uint (>=0<=1431),minutes,true,number.thermostat_disinfection_time,number.thermostat_wwdisinfecttime
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,pvenableww,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenableww
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,pvraiseheat,raise heating with PV,int (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,pvlowercool,lower cooling with PV,int (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,mode,mode,enum [manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,comforttemp,comfort temperature,uint (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,designtemp,design temperature,uint (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,offsettemp,offset temperature,int (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,roominfluence,room influence,uint (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,roominflfactor,room influence factor,uint (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,curroominfl,current room influence,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,nofrosttemp,nofrost temperature,int (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,tempautotemp,temporary set temperature automode,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,remoteseltemp,temporary set temperature from remote,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,fastheatup,fast heatup,uint (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,noreducetemp,no reduce below temperature,int (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,reducetemp,off/reduce switch temperature,int (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,cooling,cooling,boolean, ,true,switch.thermostat_hc1_cooling,switch.thermostat_hc1_cooling
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,coolingon,cooling,boolean, ,false,binary_sensor.thermostat_hc1_cooling,binary_sensor.thermostat_hc1_coolingon
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,hpmode,HP Mode,enum [heating\|cooling\|heating&cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,dewoffset,dew point offset,uint (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,roomtempdiff,room temp difference,uint (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff
RC300/RC310/Moduline 3000/1010H/CW400/Sense II/HPC410,thermostat,158,hpminflowtemp,HP min. flow temp.,uint (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp
RC100/Moduline 1000/1010,thermostat,165,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC100/Moduline 1000/1010,thermostat,165,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC100/Moduline 1000/1010,thermostat,165,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
RC100/Moduline 1000/1010,thermostat,165,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
RC100/Moduline 1000/1010,thermostat,165,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry
RC100/Moduline 1000/1010,thermostat,165,dampedoutdoortemp,damped outdoor temperature,short (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
RC100/Moduline 1000/1010,thermostat,165,floordrytemp,floor drying temperature,uint (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp
RC100/Moduline 1000/1010,thermostat,165,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
RC100/Moduline 1000/1010,thermostat,165,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
RC100/Moduline 1000/1010,thermostat,165,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
RC100/Moduline 1000/1010,thermostat,165,wwsettemp,set temperature,uint (>=0<=254),C,true,number.thermostat_set_temperature,number.thermostat_wwsettemp
RC100/Moduline 1000/1010,thermostat,165,wwmode,mode,enum [off\|normal\|comfort\|auto\|own prog\|eco], ,true,select.thermostat_mode,select.thermostat_wwmode
RC100/Moduline 1000/1010,thermostat,165,wwsettemplow,set low temperature,uint (>=0<=254),C,true,number.thermostat_set_low_temperature,number.thermostat_wwsettemplow
RC100/Moduline 1000/1010,thermostat,165,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
RC100/Moduline 1000/1010,thermostat,165,wwchargeduration,charge duration,uint (>=0<=3810),minutes,true,number.thermostat_charge_duration,number.thermostat_wwchargeduration
RC100/Moduline 1000/1010,thermostat,165,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
RC100/Moduline 1000/1010,thermostat,165,wwextra1,circuit 1 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_1_extra,sensor.thermostat_wwextra1
RC100/Moduline 1000/1010,thermostat,165,wwextra2,circuit 2 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_2_extra,sensor.thermostat_wwextra2
RC100/Moduline 1000/1010,thermostat,165,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
RC100/Moduline 1000/1010,thermostat,165,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
RC100/Moduline 1000/1010,thermostat,165,wwdisinfecttime,disinfection time,uint (>=0<=1431),minutes,true,number.thermostat_disinfection_time,number.thermostat_wwdisinfecttime
RC100/Moduline 1000/1010,thermostat,165,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
RC100/Moduline 1000/1010,thermostat,165,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
RC100/Moduline 1000/1010,thermostat,165,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
RC100/Moduline 1000/1010,thermostat,165,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
RC100/Moduline 1000/1010,thermostat,165,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
RC100/Moduline 1000/1010,thermostat,165,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
RC100/Moduline 1000/1010,thermostat,165,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
RC100/Moduline 1000/1010,thermostat,165,pvenableww,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenableww
RC100/Moduline 1000/1010,thermostat,165,pvraiseheat,raise heating with PV,int (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat
RC100/Moduline 1000/1010,thermostat,165,pvlowercool,lower cooling with PV,int (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool
RC100/Moduline 1000/1010,thermostat,165,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC100/Moduline 1000/1010,thermostat,165,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC100/Moduline 1000/1010,thermostat,165,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC100/Moduline 1000/1010,thermostat,165,mode,mode,enum [manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
RC100/Moduline 1000/1010,thermostat,165,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
RC100/Moduline 1000/1010,thermostat,165,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
RC100/Moduline 1000/1010,thermostat,165,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
RC100/Moduline 1000/1010,thermostat,165,comforttemp,comfort temperature,uint (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp
RC100/Moduline 1000/1010,thermostat,165,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
RC100/Moduline 1000/1010,thermostat,165,designtemp,design temperature,uint (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
RC100/Moduline 1000/1010,thermostat,165,offsettemp,offset temperature,int (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
RC100/Moduline 1000/1010,thermostat,165,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
RC100/Moduline 1000/1010,thermostat,165,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
RC100/Moduline 1000/1010,thermostat,165,roominfluence,room influence,uint (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
RC100/Moduline 1000/1010,thermostat,165,roominflfactor,room influence factor,uint (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor
RC100/Moduline 1000/1010,thermostat,165,curroominfl,current room influence,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl
RC100/Moduline 1000/1010,thermostat,165,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
RC100/Moduline 1000/1010,thermostat,165,nofrosttemp,nofrost temperature,int (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
RC100/Moduline 1000/1010,thermostat,165,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
RC100/Moduline 1000/1010,thermostat,165,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
RC100/Moduline 1000/1010,thermostat,165,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode
RC100/Moduline 1000/1010,thermostat,165,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode
RC100/Moduline 1000/1010,thermostat,165,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
RC100/Moduline 1000/1010,thermostat,165,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate
RC100/Moduline 1000/1010,thermostat,165,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
RC100/Moduline 1000/1010,thermostat,165,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
RC100/Moduline 1000/1010,thermostat,165,tempautotemp,temporary set temperature automode,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
RC100/Moduline 1000/1010,thermostat,165,remoteseltemp,temporary set temperature from remote,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp
RC100/Moduline 1000/1010,thermostat,165,fastheatup,fast heatup,uint (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup
RC100/Moduline 1000/1010,thermostat,165,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization
RC100/Moduline 1000/1010,thermostat,165,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
RC100/Moduline 1000/1010,thermostat,165,noreducetemp,no reduce below temperature,int (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
RC100/Moduline 1000/1010,thermostat,165,reducetemp,off/reduce switch temperature,int (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
RC100/Moduline 1000/1010,thermostat,165,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
RC100/Moduline 1000/1010,thermostat,165,cooling,cooling,boolean, ,true,switch.thermostat_hc1_cooling,switch.thermostat_hc1_cooling
RC100/Moduline 1000/1010,thermostat,165,coolingon,cooling,boolean, ,false,binary_sensor.thermostat_hc1_cooling,binary_sensor.thermostat_hc1_coolingon
RC100/Moduline 1000/1010,thermostat,165,hpmode,HP Mode,enum [heating\|cooling\|heating&cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode
RC100/Moduline 1000/1010,thermostat,165,dewoffset,dew point offset,uint (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset
RC100/Moduline 1000/1010,thermostat,165,roomtempdiff,room temp difference,uint (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff
RC100/Moduline 1000/1010,thermostat,165,hpminflowtemp,HP min. flow temp.,uint (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp
Rego 2000/3000,thermostat,172,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Rego 2000/3000,thermostat,172,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Rego 2000/3000,thermostat,172,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
Rego 2000/3000,thermostat,172,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
Rego 2000/3000,thermostat,172,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry
Rego 2000/3000,thermostat,172,dampedoutdoortemp,damped outdoor temperature,short (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
Rego 2000/3000,thermostat,172,floordrytemp,floor drying temperature,uint (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp
Rego 2000/3000,thermostat,172,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
Rego 2000/3000,thermostat,172,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
Rego 2000/3000,thermostat,172,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
Rego 2000/3000,thermostat,172,wwsettemp,set temperature,uint (>=0<=254),C,true,number.thermostat_set_temperature,number.thermostat_wwsettemp
Rego 2000/3000,thermostat,172,wwmode,mode,enum [off\|normal\|comfort\|auto\|own prog\|eco], ,true,select.thermostat_mode,select.thermostat_wwmode
Rego 2000/3000,thermostat,172,wwsettemplow,set low temperature,uint (>=0<=254),C,true,number.thermostat_set_low_temperature,number.thermostat_wwsettemplow
Rego 2000/3000,thermostat,172,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
Rego 2000/3000,thermostat,172,wwchargeduration,charge duration,uint (>=0<=3810),minutes,true,number.thermostat_charge_duration,number.thermostat_wwchargeduration
Rego 2000/3000,thermostat,172,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
Rego 2000/3000,thermostat,172,wwextra1,circuit 1 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_1_extra,sensor.thermostat_wwextra1
Rego 2000/3000,thermostat,172,wwextra2,circuit 2 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_2_extra,sensor.thermostat_wwextra2
Rego 2000/3000,thermostat,172,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
Rego 2000/3000,thermostat,172,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
Rego 2000/3000,thermostat,172,wwdisinfecttime,disinfection time,uint (>=0<=1431),minutes,true,number.thermostat_disinfection_time,number.thermostat_wwdisinfecttime
Rego 2000/3000,thermostat,172,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
Rego 2000/3000,thermostat,172,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
Rego 2000/3000,thermostat,172,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
Rego 2000/3000,thermostat,172,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
Rego 2000/3000,thermostat,172,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
Rego 2000/3000,thermostat,172,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
Rego 2000/3000,thermostat,172,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
Rego 2000/3000,thermostat,172,pvenableww,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenableww
Rego 2000/3000,thermostat,172,pvraiseheat,raise heating with PV,int (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat
Rego 2000/3000,thermostat,172,pvlowercool,lower cooling with PV,int (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool
Rego 2000/3000,thermostat,172,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
Rego 2000/3000,thermostat,172,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Rego 2000/3000,thermostat,172,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
Rego 2000/3000,thermostat,172,mode,mode,enum [manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
Rego 2000/3000,thermostat,172,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
Rego 2000/3000,thermostat,172,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
Rego 2000/3000,thermostat,172,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
Rego 2000/3000,thermostat,172,comforttemp,comfort temperature,uint (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp
Rego 2000/3000,thermostat,172,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
Rego 2000/3000,thermostat,172,designtemp,design temperature,uint (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
Rego 2000/3000,thermostat,172,offsettemp,offset temperature,int (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
Rego 2000/3000,thermostat,172,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
Rego 2000/3000,thermostat,172,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
Rego 2000/3000,thermostat,172,roominfluence,room influence,uint (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
Rego 2000/3000,thermostat,172,roominflfactor,room influence factor,uint (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor
Rego 2000/3000,thermostat,172,curroominfl,current room influence,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl
Rego 2000/3000,thermostat,172,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
Rego 2000/3000,thermostat,172,nofrosttemp,nofrost temperature,int (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
Rego 2000/3000,thermostat,172,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
Rego 2000/3000,thermostat,172,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
Rego 2000/3000,thermostat,172,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode
Rego 2000/3000,thermostat,172,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode
Rego 2000/3000,thermostat,172,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
Rego 2000/3000,thermostat,172,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate
Rego 2000/3000,thermostat,172,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
Rego 2000/3000,thermostat,172,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
Rego 2000/3000,thermostat,172,tempautotemp,temporary set temperature automode,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
Rego 2000/3000,thermostat,172,remoteseltemp,temporary set temperature from remote,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp
Rego 2000/3000,thermostat,172,fastheatup,fast heatup,uint (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup
Rego 2000/3000,thermostat,172,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization
Rego 2000/3000,thermostat,172,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
Rego 2000/3000,thermostat,172,noreducetemp,no reduce below temperature,int (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
Rego 2000/3000,thermostat,172,reducetemp,off/reduce switch temperature,int (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
Rego 2000/3000,thermostat,172,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
Rego 2000/3000,thermostat,172,cooling,cooling,boolean, ,true,switch.thermostat_hc1_cooling,switch.thermostat_hc1_cooling
Rego 2000/3000,thermostat,172,coolingon,cooling,boolean, ,false,binary_sensor.thermostat_hc1_cooling,binary_sensor.thermostat_hc1_coolingon
Rego 2000/3000,thermostat,172,hpmode,HP Mode,enum [heating\|cooling\|heating&cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode
Rego 2000/3000,thermostat,172,dewoffset,dew point offset,uint (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset
Rego 2000/3000,thermostat,172,roomtempdiff,room temp difference,uint (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff
Rego 2000/3000,thermostat,172,hpminflowtemp,HP min. flow temp.,uint (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp
Comfort RF,thermostat,215,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Comfort RF,thermostat,215,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Comfort RF,thermostat,215,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
Comfort RF,thermostat,215,seltemp,selected room temperature,short (>=-15999<=15999),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp
Comfort RF,thermostat,215,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Comfort RF,thermostat,215,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
Comfort RF,thermostat,215,mode,mode,enum [auto\|off], ,false,sensor.thermostat_hc1_mode,sensor.thermostat_hc1_mode
Comfort RF,thermostat,215,modetype,mode type,enum [off\|on], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
Comfort RF,thermostat,215,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
CRF200S,thermostat,216,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
CRF200S,thermostat,216,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
CRF200S,thermostat,216,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
CRF200S,thermostat,216,seltemp,selected room temperature,short (>=-15999<=15999),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp
CRF200S,thermostat,216,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
CRF200S,thermostat,216,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
CRF200S,thermostat,216,mode,mode,enum [auto\|off], ,false,sensor.thermostat_hc1_mode,sensor.thermostat_hc1_mode
CRF200S,thermostat,216,modetype,mode type,enum [off\|on], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
CRF200S,thermostat,216,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
Comfort+2RF,thermostat,246,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Comfort+2RF,thermostat,246,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Comfort+2RF,thermostat,246,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
Comfort+2RF,thermostat,246,seltemp,selected room temperature,short (>=-15999<=15999),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp
Comfort+2RF,thermostat,246,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Comfort+2RF,thermostat,246,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
Comfort+2RF,thermostat,246,mode,mode,enum [auto\|off], ,false,sensor.thermostat_hc1_mode,sensor.thermostat_hc1_mode
Comfort+2RF,thermostat,246,modetype,mode type,enum [off\|on], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
Comfort+2RF,thermostat,246,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
Rego 3000/UI800,thermostat,253,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
Rego 3000/UI800,thermostat,253,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
Rego 3000/UI800,thermostat,253,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
Rego 3000/UI800,thermostat,253,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
Rego 3000/UI800,thermostat,253,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry
Rego 3000/UI800,thermostat,253,dampedoutdoortemp,damped outdoor temperature,short (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
Rego 3000/UI800,thermostat,253,floordrytemp,floor drying temperature,uint (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp
Rego 3000/UI800,thermostat,253,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
Rego 3000/UI800,thermostat,253,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
Rego 3000/UI800,thermostat,253,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
Rego 3000/UI800,thermostat,253,wwsettemp,set temperature,uint (>=0<=254),C,true,number.thermostat_set_temperature,number.thermostat_wwsettemp
Rego 3000/UI800,thermostat,253,wwmode,mode,enum [off\|normal\|comfort\|auto\|own prog\|eco], ,true,select.thermostat_mode,select.thermostat_wwmode
Rego 3000/UI800,thermostat,253,wwsettemplow,set low temperature,uint (>=0<=254),C,true,number.thermostat_set_low_temperature,number.thermostat_wwsettemplow
Rego 3000/UI800,thermostat,253,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
Rego 3000/UI800,thermostat,253,wwchargeduration,charge duration,uint (>=0<=3810),minutes,true,number.thermostat_charge_duration,number.thermostat_wwchargeduration
Rego 3000/UI800,thermostat,253,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
Rego 3000/UI800,thermostat,253,wwextra1,circuit 1 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_1_extra,sensor.thermostat_wwextra1
Rego 3000/UI800,thermostat,253,wwextra2,circuit 2 extra,uint (>=0<=254),C,false,sensor.thermostat_circuit_2_extra,sensor.thermostat_wwextra2
Rego 3000/UI800,thermostat,253,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
Rego 3000/UI800,thermostat,253,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
Rego 3000/UI800,thermostat,253,wwdisinfecttime,disinfection time,uint (>=0<=1431),minutes,true,number.thermostat_disinfection_time,number.thermostat_wwdisinfecttime
Rego 3000/UI800,thermostat,253,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
Rego 3000/UI800,thermostat,253,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
Rego 3000/UI800,thermostat,253,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
Rego 3000/UI800,thermostat,253,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
Rego 3000/UI800,thermostat,253,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
Rego 3000/UI800,thermostat,253,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
Rego 3000/UI800,thermostat,253,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
Rego 3000/UI800,thermostat,253,pvenableww,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenableww
Rego 3000/UI800,thermostat,253,pvraiseheat,raise heating with PV,int (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat
Rego 3000/UI800,thermostat,253,pvlowercool,lower cooling with PV,int (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool
Rego 3000/UI800,thermostat,253,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
Rego 3000/UI800,thermostat,253,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
Rego 3000/UI800,thermostat,253,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
Rego 3000/UI800,thermostat,253,mode,mode,enum [manual\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
Rego 3000/UI800,thermostat,253,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
Rego 3000/UI800,thermostat,253,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
Rego 3000/UI800,thermostat,253,manualtemp,manual temperature,uint (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp
Rego 3000/UI800,thermostat,253,comforttemp,comfort temperature,uint (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp
Rego 3000/UI800,thermostat,253,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
Rego 3000/UI800,thermostat,253,designtemp,design temperature,uint (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
Rego 3000/UI800,thermostat,253,offsettemp,offset temperature,int (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
Rego 3000/UI800,thermostat,253,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
Rego 3000/UI800,thermostat,253,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
Rego 3000/UI800,thermostat,253,roominfluence,room influence,uint (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
Rego 3000/UI800,thermostat,253,roominflfactor,room influence factor,uint (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor
Rego 3000/UI800,thermostat,253,curroominfl,current room influence,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl
Rego 3000/UI800,thermostat,253,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
Rego 3000/UI800,thermostat,253,nofrosttemp,nofrost temperature,int (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
Rego 3000/UI800,thermostat,253,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
Rego 3000/UI800,thermostat,253,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
Rego 3000/UI800,thermostat,253,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode
Rego 3000/UI800,thermostat,253,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode
Rego 3000/UI800,thermostat,253,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
Rego 3000/UI800,thermostat,253,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate
Rego 3000/UI800,thermostat,253,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
Rego 3000/UI800,thermostat,253,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
Rego 3000/UI800,thermostat,253,tempautotemp,temporary set temperature automode,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
Rego 3000/UI800,thermostat,253,remoteseltemp,temporary set temperature from remote,int (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp
Rego 3000/UI800,thermostat,253,fastheatup,fast heatup,uint (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup
Rego 3000/UI800,thermostat,253,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization
Rego 3000/UI800,thermostat,253,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
Rego 3000/UI800,thermostat,253,noreducetemp,no reduce below temperature,int (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
Rego 3000/UI800,thermostat,253,reducetemp,off/reduce switch temperature,int (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
Rego 3000/UI800,thermostat,253,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
Rego 3000/UI800,thermostat,253,cooling,cooling,boolean, ,true,switch.thermostat_hc1_cooling,switch.thermostat_hc1_cooling
Rego 3000/UI800,thermostat,253,coolingon,cooling,boolean, ,false,binary_sensor.thermostat_hc1_cooling,binary_sensor.thermostat_hc1_coolingon
Rego 3000/UI800,thermostat,253,hpmode,HP Mode,enum [heating\|cooling\|heating&cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode
Rego 3000/UI800,thermostat,253,dewoffset,dew point offset,uint (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset
Rego 3000/UI800,thermostat,253,roomtempdiff,room temp difference,uint (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff
Rego 3000/UI800,thermostat,253,hpminflowtemp,HP min. flow temp.,uint (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp
ES72/RC20,thermostat,66,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
ES72/RC20,thermostat,66,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
ES72/RC20,thermostat,66,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
ES72/RC20,thermostat,66,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
ES72/RC20,thermostat,66,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
ES72/RC20,thermostat,66,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
ES72/RC20,thermostat,66,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
ES72/RC20,thermostat,66,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
ES72/RC20,thermostat,66,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
ES72/RC20,thermostat,66,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
ES72/RC20,thermostat,66,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
ES72/RC20,thermostat,66,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
ES72/RC20,thermostat,66,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
ES72/RC20,thermostat,66,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
ES72/RC20,thermostat,66,tempautotemp,temporary set temperature automode,uint (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
ES72/RC20,thermostat,66,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
ES72/RC20,thermostat,66,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
ES72/RC20,thermostat,66,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
ES72/RC20,thermostat,66,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
ES73,thermostat,76,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
ES73,thermostat,76,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
ES73,thermostat,76,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
ES73,thermostat,76,display,display,enum [internal temperature\|internal setpoint\|external temperature\|burner temperature\|ww temperature\|functioning mode\|time\|date\|smoke temperature], ,true,select.thermostat_display,select.thermostat_display
ES73,thermostat,76,language,language,enum [german\|dutch\|french\|italian], ,false,sensor.thermostat_language,sensor.thermostat_language
ES73,thermostat,76,clockoffset,clock offset,int (>=-126<=126),seconds,true,number.thermostat_clock_offset,number.thermostat_clockoffset
ES73,thermostat,76,intoffset,internal temperature offset,int (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset
ES73,thermostat,76,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
ES73,thermostat,76,inttemp1,temperature sensor 1,short (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1
ES73,thermostat,76,inttemp2,temperature sensor 2,short (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2
ES73,thermostat,76,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping
ES73,thermostat,76,dampedoutdoortemp,damped outdoor temperature,int (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp
ES73,thermostat,76,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building
ES73,thermostat,76,wwmode,mode,enum [off\|on\|auto], ,true,select.thermostat_mode,select.thermostat_wwmode
ES73,thermostat,76,wwcircmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_circulation_pump_mode,select.thermostat_wwcircmode
ES73,thermostat,76,wwprogmode,program,enum [std prog\|own prog], ,true,select.thermostat_program,select.thermostat_wwprogmode
ES73,thermostat,76,wwcircprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_circulation_program,select.thermostat_wwcircprog
ES73,thermostat,76,wwdisinfecting,disinfecting,boolean, ,true,switch.thermostat_disinfecting,switch.thermostat_wwdisinfecting
ES73,thermostat,76,wwdisinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_disinfection_day,select.thermostat_wwdisinfectday
ES73,thermostat,76,wwdisinfecthour,disinfection hour,uint (>=0<=23), ,true,number.thermostat_disinfection_hour,number.thermostat_wwdisinfecthour
ES73,thermostat,76,wwmaxtemp,maximum temperature,uint (>=0<=254),C,true,number.thermostat_maximum_temperature,number.thermostat_wwmaxtemp
ES73,thermostat,76,wwonetimekey,one time key function,boolean, ,true,switch.thermostat_one_time_key_function,switch.thermostat_wwonetimekey
ES73,thermostat,76,wwswitchtime,program switchtime,string, ,true,sensor.thermostat_program_switchtime,sensor.thermostat_wwswitchtime
ES73,thermostat,76,wwcircswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_circulation_program_switchtime,sensor.thermostat_wwcircswitchtime
ES73,thermostat,76,wwholidays,holiday dates,string, ,true,sensor.thermostat_holiday_dates,sensor.thermostat_wwholidays
ES73,thermostat,76,wwvacations,vacation dates,string, ,true,sensor.thermostat_vacation_dates,sensor.thermostat_wwvacations
ES73,thermostat,76,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
ES73,thermostat,76,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
ES73,thermostat,76,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
ES73,thermostat,76,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
ES73,thermostat,76,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
ES73,thermostat,76,daytemp,day temperature,uint (>=5<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
ES73,thermostat,76,nighttemp,night temperature,uint (>=5<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
ES73,thermostat,76,designtemp,design temperature,uint (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp
ES73,thermostat,76,offsettemp,offset temperature,int (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp
ES73,thermostat,76,holidaytemp,holiday temperature,uint (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp
ES73,thermostat,76,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
ES73,thermostat,76,summertemp,summer temperature,uint (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
ES73,thermostat,76,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
ES73,thermostat,76,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode
ES73,thermostat,76,nofrosttemp,nofrost temperature,int (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
ES73,thermostat,76,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode
ES73,thermostat,76,roominfluence,room influence,uint (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence
ES73,thermostat,76,minflowtemp,min flow temperature,uint (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
ES73,thermostat,76,maxflowtemp,max flow temperature,uint (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
ES73,thermostat,76,flowtempoffset,flow temperature offset for mixer,uint (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset
ES73,thermostat,76,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
ES73,thermostat,76,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode
ES73,thermostat,76,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode
ES73,thermostat,76,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
ES73,thermostat,76,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays
ES73,thermostat,76,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations
ES73,thermostat,76,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
ES73,thermostat,76,pause,pause time,uint (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause
ES73,thermostat,76,party,party time,uint (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party
ES73,thermostat,76,tempautotemp,temporary set temperature automode,uint (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
ES73,thermostat,76,noreducetemp,no reduce below temperature,int (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp
ES73,thermostat,76,reducetemp,off/reduce switch temperature,int (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp
ES73,thermostat,76,vacreducetemp,vacations off/reduce switch temperature,int (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp
ES73,thermostat,76,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode
ES73,thermostat,76,remotetemp,room temperature from remote,short (>=-3199<=3199),C,true,number.thermostat_hc1_room_temperature_from_remote,number.thermostat_hc1_remotetemp
ES73,thermostat,76,wwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_wwprio
ES73,thermostat,76,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1
ES73,thermostat,76,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2
ES72/RC20,thermostat,113,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
ES72/RC20,thermostat,113,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
ES72/RC20,thermostat,113,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
ES72/RC20,thermostat,113,minexttemp,minimal external temperature,int (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp
ES72/RC20,thermostat,113,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
ES72/RC20,thermostat,113,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
ES72/RC20,thermostat,113,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
ES72/RC20,thermostat,113,mode,mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
ES72/RC20,thermostat,113,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
ES72/RC20,thermostat,113,daytemp,day temperature,uint (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp
ES72/RC20,thermostat,113,nighttemp,night temperature,uint (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp
ES72/RC20,thermostat,113,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
ES72/RC20,thermostat,113,minflowtemp,min flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp
ES72/RC20,thermostat,113,maxflowtemp,max flow temperature,uint (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp
ES72/RC20,thermostat,113,tempautotemp,temporary set temperature automode,uint (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp
ES72/RC20,thermostat,113,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype
ES72/RC20,thermostat,113,summertemp,summer temperature,uint (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp
ES72/RC20,thermostat,113,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode
ES72/RC20,thermostat,113,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FW100,thermostat,105,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FW100,thermostat,105,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FW100,thermostat,105,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
FW100,thermostat,105,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FW100,thermostat,105,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FW100,thermostat,105,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FW100,thermostat,105,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FW100,thermostat,105,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FW100,thermostat,105,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FW100,thermostat,105,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FW100,thermostat,105,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FW100,thermostat,105,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FW100,thermostat,105,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FW100,thermostat,105,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FW100,thermostat,105,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FW100,thermostat,105,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FW100,thermostat,105,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FW100,thermostat,105,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FW100,thermostat,105,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FW100,thermostat,105,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FW100,thermostat,105,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FW100,thermostat,105,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FW100,thermostat,105,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FW100,thermostat,105,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FW200,thermostat,106,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FW200,thermostat,106,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FW200,thermostat,106,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
FW200,thermostat,106,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FW200,thermostat,106,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FW200,thermostat,106,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FW200,thermostat,106,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FW200,thermostat,106,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FW200,thermostat,106,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FW200,thermostat,106,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FW200,thermostat,106,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FW200,thermostat,106,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FW200,thermostat,106,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FW200,thermostat,106,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FW200,thermostat,106,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FW200,thermostat,106,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FW200,thermostat,106,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FW200,thermostat,106,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FW200,thermostat,106,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FW200,thermostat,106,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FW200,thermostat,106,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FW200,thermostat,106,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FW200,thermostat,106,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FW200,thermostat,106,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FR100,thermostat,107,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FR100,thermostat,107,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FR100,thermostat,107,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
FR100,thermostat,107,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FR100,thermostat,107,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FR100,thermostat,107,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FR100,thermostat,107,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FR100,thermostat,107,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FR100,thermostat,107,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FR100,thermostat,107,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FR100,thermostat,107,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FR100,thermostat,107,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FR100,thermostat,107,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FR100,thermostat,107,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FR100,thermostat,107,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FR100,thermostat,107,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FR100,thermostat,107,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FR100,thermostat,107,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FR100,thermostat,107,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FR100,thermostat,107,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FR100,thermostat,107,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FR100,thermostat,107,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FR100,thermostat,107,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FR100,thermostat,107,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FR110,thermostat,108,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FR110,thermostat,108,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FR110,thermostat,108,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
FR110,thermostat,108,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FR110,thermostat,108,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FR110,thermostat,108,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FR110,thermostat,108,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FR110,thermostat,108,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FR110,thermostat,108,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FR110,thermostat,108,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FR110,thermostat,108,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FR110,thermostat,108,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FR110,thermostat,108,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FR110,thermostat,108,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FR110,thermostat,108,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FR110,thermostat,108,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FR110,thermostat,108,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FR110,thermostat,108,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FR110,thermostat,108,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FR110,thermostat,108,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FR110,thermostat,108,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FR110,thermostat,108,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FR110,thermostat,108,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FR110,thermostat,108,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FB10,thermostat,109,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FB10,thermostat,109,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FB10,thermostat,109,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
FB10,thermostat,109,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FB10,thermostat,109,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FB10,thermostat,109,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FB10,thermostat,109,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FB10,thermostat,109,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FB10,thermostat,109,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FB10,thermostat,109,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FB10,thermostat,109,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FB10,thermostat,109,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FB10,thermostat,109,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FB10,thermostat,109,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FB10,thermostat,109,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FB10,thermostat,109,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FB10,thermostat,109,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FB10,thermostat,109,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FB10,thermostat,109,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FB10,thermostat,109,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FB10,thermostat,109,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FB10,thermostat,109,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FB10,thermostat,109,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FB10,thermostat,109,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FB100,thermostat,110,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FB100,thermostat,110,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FB100,thermostat,110,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
FB100,thermostat,110,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FB100,thermostat,110,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FB100,thermostat,110,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FB100,thermostat,110,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FB100,thermostat,110,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FB100,thermostat,110,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FB100,thermostat,110,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FB100,thermostat,110,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FB100,thermostat,110,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FB100,thermostat,110,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FB100,thermostat,110,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FB100,thermostat,110,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FB100,thermostat,110,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FB100,thermostat,110,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FB100,thermostat,110,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FB100,thermostat,110,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FB100,thermostat,110,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FB100,thermostat,110,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FB100,thermostat,110,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FB100,thermostat,110,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FB100,thermostat,110,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FR10,thermostat,111,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FR10,thermostat,111,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FR10,thermostat,111,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
FR10,thermostat,111,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FR10,thermostat,111,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FR10,thermostat,111,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FR10,thermostat,111,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FR10,thermostat,111,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FR10,thermostat,111,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FR10,thermostat,111,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FR10,thermostat,111,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FR10,thermostat,111,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FR10,thermostat,111,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FR10,thermostat,111,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FR10,thermostat,111,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FR10,thermostat,111,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FR10,thermostat,111,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FR10,thermostat,111,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FR10,thermostat,111,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FR10,thermostat,111,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FR10,thermostat,111,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FR10,thermostat,111,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FR10,thermostat,111,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FR10,thermostat,111,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FW500,thermostat,116,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FW500,thermostat,116,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FW500,thermostat,116,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
FW500,thermostat,116,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FW500,thermostat,116,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FW500,thermostat,116,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FW500,thermostat,116,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FW500,thermostat,116,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FW500,thermostat,116,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FW500,thermostat,116,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FW500,thermostat,116,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FW500,thermostat,116,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FW500,thermostat,116,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FW500,thermostat,116,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FW500,thermostat,116,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FW500,thermostat,116,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FW500,thermostat,116,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FW500,thermostat,116,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FW500,thermostat,116,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FW500,thermostat,116,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FW500,thermostat,116,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FW500,thermostat,116,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FW500,thermostat,116,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FW500,thermostat,116,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FR50,thermostat,147,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FR50,thermostat,147,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FR50,thermostat,147,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
FR50,thermostat,147,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FR50,thermostat,147,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FR50,thermostat,147,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FR50,thermostat,147,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FR50,thermostat,147,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FR50,thermostat,147,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FR50,thermostat,147,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FR50,thermostat,147,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FR50,thermostat,147,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FR50,thermostat,147,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FR50,thermostat,147,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FR50,thermostat,147,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FR50,thermostat,147,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FR50,thermostat,147,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FR50,thermostat,147,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FR50,thermostat,147,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FR50,thermostat,147,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FR50,thermostat,147,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FR50,thermostat,147,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FR50,thermostat,147,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FR50,thermostat,147,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FR120,thermostat,191,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FR120,thermostat,191,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FR120,thermostat,191,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
FR120,thermostat,191,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FR120,thermostat,191,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FR120,thermostat,191,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FR120,thermostat,191,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FR120,thermostat,191,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FR120,thermostat,191,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FR120,thermostat,191,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FR120,thermostat,191,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FR120,thermostat,191,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FR120,thermostat,191,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FR120,thermostat,191,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FR120,thermostat,191,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FR120,thermostat,191,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FR120,thermostat,191,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FR120,thermostat,191,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FR120,thermostat,191,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FR120,thermostat,191,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FR120,thermostat,191,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FR120,thermostat,191,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FR120,thermostat,191,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FR120,thermostat,191,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
FW120,thermostat,192,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
FW120,thermostat,192,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
FW120,thermostat,192,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime
FW120,thermostat,192,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy
FW120,thermostat,192,switchovertemp,outside switchover temperature,int (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp
FW120,thermostat,192,energycostratio,energy cost ratio,uint (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio
FW120,thermostat,192,fossilefactor,fossile energy factor,uint (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor
FW120,thermostat,192,electricfactor,electric energy factor,uint (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor
FW120,thermostat,192,delayboiler,delay boiler support,uint (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler
FW120,thermostat,192,tempdiffboiler,temp diff boiler support,uint (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler
FW120,thermostat,192,wwcharge,charge,boolean, ,true,switch.thermostat_charge,switch.thermostat_wwcharge
FW120,thermostat,192,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
FW120,thermostat,192,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
FW120,thermostat,192,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
FW120,thermostat,192,mode,mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_mode,select.thermostat_hc1_mode
FW120,thermostat,192,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype
FW120,thermostat,192,heattemp,heat temperature,uint (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp
FW120,thermostat,192,ecotemp,eco temperature,uint (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp
FW120,thermostat,192,nofrosttemp,nofrost temperature,int (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp
FW120,thermostat,192,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control
FW120,thermostat,192,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program
FW120,thermostat,192,remotetemp,room temperature from remote,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp
FW120,thermostat,192,targetflowtemp,target flow temperature,uint (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp
FW120,thermostat,192,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor
RT800,thermostat,3,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RT800,thermostat,3,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RT800,thermostat,3,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RT800,thermostat,3,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RT800,thermostat,3,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RT800,thermostat,3,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
RC100H,thermostat,200,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
RC100H,thermostat,200,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
RC100H,thermostat,200,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
RC100H,thermostat,200,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
RC100H,thermostat,200,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
RC100H,thermostat,200,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
TR120RF/CR20RF,thermostat,249,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode
TR120RF/CR20RF,thermostat,249,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode
TR120RF/CR20RF,thermostat,249,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime
TR120RF/CR20RF,thermostat,249,seltemp,selected room temperature,short (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp
TR120RF/CR20RF,thermostat,249,currtemp,current room temperature,short (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp
TR120RF/CR20RF,thermostat,249,haclimate,Discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_Discovery_current_room_temperature,sensor.thermostat_hc1_haclimate
MM10,mixer,69,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc
MM10,mixer,69,valvestatus,mixing valve actuator (VC1),int (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus
MM10,mixer,69,flowsettemp,setpoint flow temperature,uint (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp
MM10,mixer,69,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus
MM10,mixer,69,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated
MM10,mixer,69,valvesettime,time to set valve,uint (>=10<=120),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime
IPM,mixer,100,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc
IPM,mixer,100,valvestatus,mixing valve actuator (VC1),int (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus
IPM,mixer,100,flowsettemp,setpoint flow temperature,uint (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp
IPM,mixer,100,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus
IPM,mixer,100,flowtempvf,flow temperature in header (T0/Vf),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_in_header_(T0/Vf),sensor.mixer_hc1_flowtempvf
IPM,mixer,102,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc
IPM,mixer,102,valvestatus,mixing valve actuator (VC1),int (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus
IPM,mixer,102,flowsettemp,setpoint flow temperature,uint (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp
IPM,mixer,102,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus
IPM,mixer,102,flowtempvf,flow temperature in header (T0/Vf),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_in_header_(T0/Vf),sensor.mixer_hc1_flowtempvf
MM50,mixer,159,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc
MM50,mixer,159,valvestatus,mixing valve actuator (VC1),int (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus
MM50,mixer,159,flowsettemp,setpoint flow temperature,uint (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp
MM50,mixer,159,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus
MM100,mixer,160,wwtemp,current temperature,ushort (>=0<=3199),C,false,sensor.mixer_wwc1_current_temperature,sensor.mixer_wwc1_wwtemp
MM100,mixer,160,pumpstatus,pump status in assigned wwc (PC1),boolean, ,false,binary_sensor.mixer_wwc1_pump_status_in_assigned_wwc_(PC1),binary_sensor.mixer_wwc1_pumpstatus
MM100,mixer,160,wwtempstatus,temperature switch in assigned wwc (MC1),int (>=-126<=126), ,false,sensor.mixer_wwc1_temperature_switch_in_assigned_wwc_(MC1),sensor.mixer_wwc1_wwtempstatus
MM100,mixer,160,wwmaxtemp,maximum temperature,uint (>=0<=254),C,true,number.mixer_wwc1_maximum_temperature,number.mixer_wwc1_wwmaxtemp
MM100,mixer,160,wwdifftemp,start differential temperature,int (>=-126<=126),C,true,number.mixer_wwc1_start_differential_temperature,number.mixer_wwc1_wwdifftemp
MM100,mixer,160,wwdisinfectiontemp,disinfection temperature,uint (>=0<=254),C,true,number.mixer_wwc1_disinfection_temperature,number.mixer_wwc1_wwdisinfectiontemp
MM100,mixer,160,wwredtemp,reduced temperature,uint (>=0<=254),C,true,number.mixer_wwc1_reduced_temperature,number.mixer_wwc1_wwredtemp
MM100,mixer,160,wwrequiredtemp,required temperature,uint (>=0<=254),C,true,number.mixer_wwc1_required_temperature,number.mixer_wwc1_wwrequiredtemp
MM100,mixer,160,wwcircpump,circulation pump available,boolean, ,true,switch.mixer_circulation_pump_available,switch.mixer_wwcircpump
MM100,mixer,160,wwcircmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.mixer_wwc1_circulation_pump_mode,select.mixer_wwc1_wwcircmode
MM200,mixer,161,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc
MM200,mixer,161,valvestatus,mixing valve actuator (VC1),int (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus
MM200,mixer,161,flowsettemp,setpoint flow temperature,uint (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp
MM200,mixer,161,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus
MZ100,mixer,193,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc
MZ100,mixer,193,valvestatus,mixing valve actuator (VC1),int (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus
MZ100,mixer,193,flowsettemp,setpoint flow temperature,uint (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp
MZ100,mixer,193,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus
MP100,mixer,204,pooltemp,pool temperature,short (>=-3199<=3199),C,false,sensor.mixer_pool_temperature,sensor.mixer_pooltemp
MP100,mixer,204,poolshuntstatus,pool shunt status opening/closing,enum [stopped\|opening\|closing\|open\|close], ,false,sensor.mixer_pool_shunt_status_opening/closing,sensor.mixer_poolshuntstatus
MP100,mixer,204,poolshunt,pool shunt open/close (0% = pool / 100% = heat),uint (>=0<=100),%,false,sensor.mixer_pool_shunt_open/close_(0%_=_pool_/_100%_=_heat),sensor.mixer_poolshunt
SM10,solar,73,collectortemp,collector temperature (TS1),short (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp
SM10,solar,73,cylbottomtemp,cylinder bottom temperature (TS2),short (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp
SM10,solar,73,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump
SM10,solar,73,pumpworktime,pump working time,time (>=0<=65533),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime
SM10,solar,73,cylmaxtemp,maximum cylinder temperature,uint (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp
SM10,solar,73,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM10,solar,73,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM10,solar,73,solarpumpmod,pump modulation (PS1),uint (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod
SM10,solar,73,pumpminmod,minimum pump modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod
SM10,solar,73,turnondiff,pump turn on difference,uint (>=0<=254),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff
SM10,solar,73,turnoffdiff,pump turn off difference,uint (>=0<=254),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff
SM10,solar,73,solarpower,actual solar power,short (>=-31999<=31999),W,false,sensor.solar_actual_solar_power,sensor.solar_solarpower
SM10,solar,73,energylasthour,energy last hour,ulong (>=0<=39321),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour
SM10,solar,73,maxflow,maximum solar flow,uint (>=0<=25),l/min,true,number.solar_maximum_solar_flow,number.solar_maxflow
SM10,solar,73,wwmintemp,minimum temperature,uint (>=0<=254),C,true,number.solar_minimum_temperature,number.solar_wwmintemp
SM10,solar,73,solarenabled,solarmodule enabled,boolean, ,true,switch.solar_solarmodule_enabled,switch.solar_solarenabled
ISM1,solar,101,collectortemp,collector temperature (TS1),short (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp
ISM1,solar,101,cylbottomtemp,cylinder bottom temperature (TS2),short (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp
ISM1,solar,101,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump
ISM1,solar,101,pumpworktime,pump working time,time (>=0<=65533),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime
ISM1,solar,101,cylmaxtemp,maximum cylinder temperature,uint (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp
ISM1,solar,101,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
ISM1,solar,101,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
ISM1,solar,101,cylmiddletemp,cylinder middle temperature (TS3),short (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp
ISM1,solar,101,retheatassist,return temperature heat assistance (TS4),short (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist
ISM1,solar,101,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve
ISM1,solar,101,energylasthour,energy last hour,ulong (>=0<=39321),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour
ISM2,solar,103,collectortemp,collector temperature (TS1),short (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp
ISM2,solar,103,cylbottomtemp,cylinder bottom temperature (TS2),short (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp
ISM2,solar,103,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump
ISM2,solar,103,pumpworktime,pump working time,time (>=0<=65533),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime
ISM2,solar,103,cylmaxtemp,maximum cylinder temperature,uint (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp
ISM2,solar,103,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
ISM2,solar,103,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
ISM2,solar,103,cylmiddletemp,cylinder middle temperature (TS3),short (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp
ISM2,solar,103,retheatassist,return temperature heat assistance (TS4),short (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist
ISM2,solar,103,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve
ISM2,solar,103,energylasthour,energy last hour,ulong (>=0<=39321),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour
SM50,solar,162,collectortemp,collector temperature (TS1),short (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp
SM50,solar,162,cylbottomtemp,cylinder bottom temperature (TS2),short (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp
SM50,solar,162,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump
SM50,solar,162,pumpworktime,pump working time,time (>=0<=65533),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime
SM50,solar,162,cylmaxtemp,maximum cylinder temperature,uint (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp
SM50,solar,162,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM50,solar,162,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM50,solar,162,solarpumpmod,pump modulation (PS1),uint (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod
SM50,solar,162,pumpminmod,minimum pump modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod
SM50,solar,162,turnondiff,pump turn on difference,uint (>=0<=25),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff
SM50,solar,162,turnoffdiff,pump turn off difference,uint (>=0<=25),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff
SM50,solar,162,collector2temp,collector 2 temperature (TS7),short (>=-3199<=3199),C,false,sensor.solar_collector_2_temperature_(TS7),sensor.solar_collector2temp
SM50,solar,162,cylmiddletemp,cylinder middle temperature (TS3),short (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp
SM50,solar,162,retheatassist,return temperature heat assistance (TS4),short (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist
SM50,solar,162,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve
SM50,solar,162,heatassistpower,heat assistance valve power (M1),uint (>=0<=100),%,false,sensor.solar_heat_assistance_valve_power_(M1),sensor.solar_heatassistpower
SM50,solar,162,solarpump2,pump 2 (PS4),boolean, ,false,binary_sensor.solar_pump_2_(PS4),binary_sensor.solar_solarpump2
SM50,solar,162,solarpump2mod,pump 2 modulation (PS4),uint (>=0<=100),%,false,sensor.solar_pump_2_modulation_(PS4),sensor.solar_solarpump2mod
SM50,solar,162,cyl2bottomtemp,second cylinder bottom temperature (TS5),short (>=-3199<=3199),C,false,sensor.solar_second_cylinder_bottom_temperature_(TS5),sensor.solar_cyl2bottomtemp
SM50,solar,162,heatexchangertemp,heat exchanger temperature (TS6),short (>=-3199<=3199),C,false,sensor.solar_heat_exchanger_temperature_(TS6),sensor.solar_heatexchangertemp
SM50,solar,162,cylpumpmod,cylinder pump modulation (PS5),uint (>=0<=100),%,false,sensor.solar_cylinder_pump_modulation_(PS5),sensor.solar_cylpumpmod
SM50,solar,162,valvestatus,valve status,boolean, ,false,binary_sensor.solar_valve_status,binary_sensor.solar_valvestatus
SM50,solar,162,vs1status,valve status VS1,boolean, ,false,binary_sensor.solar_valve_status_VS1,binary_sensor.solar_vs1status
SM50,solar,162,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM50,solar,162,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM50,solar,162,collectormaxtemp,maximum collector temperature,uint (>=0<=254),C,true,number.solar_maximum_collector_temperature,number.solar_collectormaxtemp
SM50,solar,162,collectormintemp,minimum collector temperature,uint (>=0<=254),C,true,number.solar_minimum_collector_temperature,number.solar_collectormintemp
SM50,solar,162,energylasthour,energy last hour,ulong (>=0<=39321),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour
SM50,solar,162,energytoday,total energy today,ulong (>=0<=65533),Wh,false,sensor.solar_total_energy_today,sensor.solar_energytoday
SM50,solar,162,energytotal,total energy,ulong (>=0<=39321),kWh,false,sensor.solar_total_energy,sensor.solar_energytotal
SM50,solar,162,pump2worktime,pump 2 working time,time (>=0<=65533),minutes,false,sensor.solar_pump_2_working_time,sensor.solar_pump2worktime
SM50,solar,162,m1worktime,differential control working time,time (>=0<=65533),minutes,false,sensor.solar_differential_control_working_time,sensor.solar_m1worktime
SM50,solar,162,heattransfersystem,heattransfer system,boolean, ,true,switch.solar_heattransfer_system,switch.solar_heattransfersystem
SM50,solar,162,externalcyl,external cylinder,boolean, ,true,switch.solar_external_cylinder,switch.solar_externalcyl
SM50,solar,162,thermaldisinfect,thermal disinfection,boolean, ,true,switch.solar_thermal_disinfection,switch.solar_thermaldisinfect
SM50,solar,162,heatmetering,heatmetering,boolean, ,true,switch.solar_heatmetering,switch.solar_heatmetering
SM50,solar,162,activated,activated,boolean, ,true,switch.solar_activated,switch.solar_activated
SM50,solar,162,solarpumpmode,pump mode,enum [constant\|pwm\|analog], ,true,select.solar_pump_mode,select.solar_solarpumpmode
SM50,solar,162,pumpkick,pump kick,boolean, ,true,switch.solar_pump_kick,switch.solar_pumpkick
SM50,solar,162,plainwatermode,plain water mode,boolean, ,true,switch.solar_plain_water_mode,switch.solar_plainwatermode
SM50,solar,162,doublematchflow,doublematchflow,boolean, ,true,switch.solar_doublematchflow,switch.solar_doublematchflow
SM50,solar,162,pump2minmod,minimum pump 2 modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_2_modulation,number.solar_pump2minmod
SM50,solar,162,turnondiff2,pump 2 turn on difference,uint (>=0<=25),C,true,number.solar_pump_2_turn_on_difference,number.solar_turnondiff2
SM50,solar,162,turnoffdiff2,pump 2 turn off difference,uint (>=0<=25),C,true,number.solar_pump_2_turn_off_difference,number.solar_turnoffdiff2
SM50,solar,162,pump2kick,pump kick 2,boolean, ,true,switch.solar_pump_kick_2,switch.solar_pump2kick
SM50,solar,162,climatezone,climate zone,uint (>=0<=254), ,true,number.solar_climate_zone,number.solar_climatezone
SM50,solar,162,collector1area,collector 1 area,ushort (>=0<=3199),m²,true,number.solar_collector_1_area,number.solar_collector1area
SM50,solar,162,collector1type,collector 1 type,enum [flat\|vacuum], ,true,select.solar_collector_1_type,select.solar_collector1type
SM50,solar,162,collector2area,collector 2 area,ushort (>=0<=3199),m²,true,number.solar_collector_2_area,number.solar_collector2area
SM50,solar,162,collector2type,collector 2 type,enum [flat\|vacuum], ,true,select.solar_collector_2_type,select.solar_collector2type
SM50,solar,162,cylpriority,cylinder priority,enum [cyl 1\|cyl 2], ,true,select.solar_cylinder_priority,select.solar_cylpriority
SM50,solar,162,heatcntflowtemp,heat counter flow temperature,ushort (>=0<=3199),C,false,sensor.solar_heat_counter_flow_temperature,sensor.solar_heatcntflowtemp
SM50,solar,162,heatcntrettemp,heat counter return temperature,ushort (>=0<=3199),C,false,sensor.solar_heat_counter_return_temperature,sensor.solar_heatcntrettemp
SM50,solar,162,heatcnt,heat counter impulses,uint (>=0<=254), ,false,sensor.solar_heat_counter_impulses,sensor.solar_heatcnt
SM50,solar,162,swapflowtemp,swap flow temperature (TS14),ushort (>=0<=3199),C,false,sensor.solar_swap_flow_temperature_(TS14),sensor.solar_swapflowtemp
SM50,solar,162,swaprettemp,swap return temperature (TS15),ushort (>=0<=3199),C,false,sensor.solar_swap_return_temperature_(TS15),sensor.solar_swaprettemp
SM100/MS100,solar,163,collectortemp,collector temperature (TS1),short (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp
SM100/MS100,solar,163,cylbottomtemp,cylinder bottom temperature (TS2),short (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp
SM100/MS100,solar,163,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump
SM100/MS100,solar,163,pumpworktime,pump working time,time (>=0<=65533),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime
SM100/MS100,solar,163,cylmaxtemp,maximum cylinder temperature,uint (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp
SM100/MS100,solar,163,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM100/MS100,solar,163,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM100/MS100,solar,163,solarpumpmod,pump modulation (PS1),uint (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod
SM100/MS100,solar,163,pumpminmod,minimum pump modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod
SM100/MS100,solar,163,turnondiff,pump turn on difference,uint (>=0<=25),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff
SM100/MS100,solar,163,turnoffdiff,pump turn off difference,uint (>=0<=25),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff
SM100/MS100,solar,163,collector2temp,collector 2 temperature (TS7),short (>=-3199<=3199),C,false,sensor.solar_collector_2_temperature_(TS7),sensor.solar_collector2temp
SM100/MS100,solar,163,cylmiddletemp,cylinder middle temperature (TS3),short (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp
SM100/MS100,solar,163,retheatassist,return temperature heat assistance (TS4),short (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist
SM100/MS100,solar,163,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve
SM100/MS100,solar,163,heatassistpower,heat assistance valve power (M1),uint (>=0<=100),%,false,sensor.solar_heat_assistance_valve_power_(M1),sensor.solar_heatassistpower
SM100/MS100,solar,163,solarpump2,pump 2 (PS4),boolean, ,false,binary_sensor.solar_pump_2_(PS4),binary_sensor.solar_solarpump2
SM100/MS100,solar,163,solarpump2mod,pump 2 modulation (PS4),uint (>=0<=100),%,false,sensor.solar_pump_2_modulation_(PS4),sensor.solar_solarpump2mod
SM100/MS100,solar,163,cyl2bottomtemp,second cylinder bottom temperature (TS5),short (>=-3199<=3199),C,false,sensor.solar_second_cylinder_bottom_temperature_(TS5),sensor.solar_cyl2bottomtemp
SM100/MS100,solar,163,heatexchangertemp,heat exchanger temperature (TS6),short (>=-3199<=3199),C,false,sensor.solar_heat_exchanger_temperature_(TS6),sensor.solar_heatexchangertemp
SM100/MS100,solar,163,cylpumpmod,cylinder pump modulation (PS5),uint (>=0<=100),%,false,sensor.solar_cylinder_pump_modulation_(PS5),sensor.solar_cylpumpmod
SM100/MS100,solar,163,valvestatus,valve status,boolean, ,false,binary_sensor.solar_valve_status,binary_sensor.solar_valvestatus
SM100/MS100,solar,163,vs1status,valve status VS1,boolean, ,false,binary_sensor.solar_valve_status_VS1,binary_sensor.solar_vs1status
SM100/MS100,solar,163,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM100/MS100,solar,163,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM100/MS100,solar,163,collectormaxtemp,maximum collector temperature,uint (>=0<=254),C,true,number.solar_maximum_collector_temperature,number.solar_collectormaxtemp
SM100/MS100,solar,163,collectormintemp,minimum collector temperature,uint (>=0<=254),C,true,number.solar_minimum_collector_temperature,number.solar_collectormintemp
SM100/MS100,solar,163,energylasthour,energy last hour,ulong (>=0<=39321),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour
SM100/MS100,solar,163,energytoday,total energy today,ulong (>=0<=65533),Wh,false,sensor.solar_total_energy_today,sensor.solar_energytoday
SM100/MS100,solar,163,energytotal,total energy,ulong (>=0<=39321),kWh,false,sensor.solar_total_energy,sensor.solar_energytotal
SM100/MS100,solar,163,pump2worktime,pump 2 working time,time (>=0<=65533),minutes,false,sensor.solar_pump_2_working_time,sensor.solar_pump2worktime
SM100/MS100,solar,163,m1worktime,differential control working time,time (>=0<=65533),minutes,false,sensor.solar_differential_control_working_time,sensor.solar_m1worktime
SM100/MS100,solar,163,heattransfersystem,heattransfer system,boolean, ,true,switch.solar_heattransfer_system,switch.solar_heattransfersystem
SM100/MS100,solar,163,externalcyl,external cylinder,boolean, ,true,switch.solar_external_cylinder,switch.solar_externalcyl
SM100/MS100,solar,163,thermaldisinfect,thermal disinfection,boolean, ,true,switch.solar_thermal_disinfection,switch.solar_thermaldisinfect
SM100/MS100,solar,163,heatmetering,heatmetering,boolean, ,true,switch.solar_heatmetering,switch.solar_heatmetering
SM100/MS100,solar,163,activated,activated,boolean, ,true,switch.solar_activated,switch.solar_activated
SM100/MS100,solar,163,solarpumpmode,pump mode,enum [constant\|pwm\|analog], ,true,select.solar_pump_mode,select.solar_solarpumpmode
SM100/MS100,solar,163,pumpkick,pump kick,boolean, ,true,switch.solar_pump_kick,switch.solar_pumpkick
SM100/MS100,solar,163,plainwatermode,plain water mode,boolean, ,true,switch.solar_plain_water_mode,switch.solar_plainwatermode
SM100/MS100,solar,163,doublematchflow,doublematchflow,boolean, ,true,switch.solar_doublematchflow,switch.solar_doublematchflow
SM100/MS100,solar,163,pump2minmod,minimum pump 2 modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_2_modulation,number.solar_pump2minmod
SM100/MS100,solar,163,turnondiff2,pump 2 turn on difference,uint (>=0<=25),C,true,number.solar_pump_2_turn_on_difference,number.solar_turnondiff2
SM100/MS100,solar,163,turnoffdiff2,pump 2 turn off difference,uint (>=0<=25),C,true,number.solar_pump_2_turn_off_difference,number.solar_turnoffdiff2
SM100/MS100,solar,163,pump2kick,pump kick 2,boolean, ,true,switch.solar_pump_kick_2,switch.solar_pump2kick
SM100/MS100,solar,163,climatezone,climate zone,uint (>=0<=254), ,true,number.solar_climate_zone,number.solar_climatezone
SM100/MS100,solar,163,collector1area,collector 1 area,ushort (>=0<=3199),m²,true,number.solar_collector_1_area,number.solar_collector1area
SM100/MS100,solar,163,collector1type,collector 1 type,enum [flat\|vacuum], ,true,select.solar_collector_1_type,select.solar_collector1type
SM100/MS100,solar,163,collector2area,collector 2 area,ushort (>=0<=3199),m²,true,number.solar_collector_2_area,number.solar_collector2area
SM100/MS100,solar,163,collector2type,collector 2 type,enum [flat\|vacuum], ,true,select.solar_collector_2_type,select.solar_collector2type
SM100/MS100,solar,163,cylpriority,cylinder priority,enum [cyl 1\|cyl 2], ,true,select.solar_cylinder_priority,select.solar_cylpriority
SM100/MS100,solar,163,heatcntflowtemp,heat counter flow temperature,ushort (>=0<=3199),C,false,sensor.solar_heat_counter_flow_temperature,sensor.solar_heatcntflowtemp
SM100/MS100,solar,163,heatcntrettemp,heat counter return temperature,ushort (>=0<=3199),C,false,sensor.solar_heat_counter_return_temperature,sensor.solar_heatcntrettemp
SM100/MS100,solar,163,heatcnt,heat counter impulses,uint (>=0<=254), ,false,sensor.solar_heat_counter_impulses,sensor.solar_heatcnt
SM100/MS100,solar,163,swapflowtemp,swap flow temperature (TS14),ushort (>=0<=3199),C,false,sensor.solar_swap_flow_temperature_(TS14),sensor.solar_swapflowtemp
SM100/MS100,solar,163,swaprettemp,swap return temperature (TS15),ushort (>=0<=3199),C,false,sensor.solar_swap_return_temperature_(TS15),sensor.solar_swaprettemp
SM200/MS200,solar,164,collectortemp,collector temperature (TS1),short (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp
SM200/MS200,solar,164,cylbottomtemp,cylinder bottom temperature (TS2),short (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp
SM200/MS200,solar,164,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump
SM200/MS200,solar,164,pumpworktime,pump working time,time (>=0<=65533),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime
SM200/MS200,solar,164,cylmaxtemp,maximum cylinder temperature,uint (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp
SM200/MS200,solar,164,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM200/MS200,solar,164,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM200/MS200,solar,164,solarpumpmod,pump modulation (PS1),uint (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod
SM200/MS200,solar,164,pumpminmod,minimum pump modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod
SM200/MS200,solar,164,turnondiff,pump turn on difference,uint (>=0<=25),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff
SM200/MS200,solar,164,turnoffdiff,pump turn off difference,uint (>=0<=25),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff
SM200/MS200,solar,164,collector2temp,collector 2 temperature (TS7),short (>=-3199<=3199),C,false,sensor.solar_collector_2_temperature_(TS7),sensor.solar_collector2temp
SM200/MS200,solar,164,cylmiddletemp,cylinder middle temperature (TS3),short (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp
SM200/MS200,solar,164,retheatassist,return temperature heat assistance (TS4),short (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist
SM200/MS200,solar,164,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve
SM200/MS200,solar,164,heatassistpower,heat assistance valve power (M1),uint (>=0<=100),%,false,sensor.solar_heat_assistance_valve_power_(M1),sensor.solar_heatassistpower
SM200/MS200,solar,164,solarpump2,pump 2 (PS4),boolean, ,false,binary_sensor.solar_pump_2_(PS4),binary_sensor.solar_solarpump2
SM200/MS200,solar,164,solarpump2mod,pump 2 modulation (PS4),uint (>=0<=100),%,false,sensor.solar_pump_2_modulation_(PS4),sensor.solar_solarpump2mod
SM200/MS200,solar,164,cyl2bottomtemp,second cylinder bottom temperature (TS5),short (>=-3199<=3199),C,false,sensor.solar_second_cylinder_bottom_temperature_(TS5),sensor.solar_cyl2bottomtemp
SM200/MS200,solar,164,heatexchangertemp,heat exchanger temperature (TS6),short (>=-3199<=3199),C,false,sensor.solar_heat_exchanger_temperature_(TS6),sensor.solar_heatexchangertemp
SM200/MS200,solar,164,cylpumpmod,cylinder pump modulation (PS5),uint (>=0<=100),%,false,sensor.solar_cylinder_pump_modulation_(PS5),sensor.solar_cylpumpmod
SM200/MS200,solar,164,valvestatus,valve status,boolean, ,false,binary_sensor.solar_valve_status,binary_sensor.solar_valvestatus
SM200/MS200,solar,164,vs1status,valve status VS1,boolean, ,false,binary_sensor.solar_valve_status_VS1,binary_sensor.solar_vs1status
SM200/MS200,solar,164,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated
SM200/MS200,solar,164,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown
SM200/MS200,solar,164,collectormaxtemp,maximum collector temperature,uint (>=0<=254),C,true,number.solar_maximum_collector_temperature,number.solar_collectormaxtemp
SM200/MS200,solar,164,collectormintemp,minimum collector temperature,uint (>=0<=254),C,true,number.solar_minimum_collector_temperature,number.solar_collectormintemp
SM200/MS200,solar,164,energylasthour,energy last hour,ulong (>=0<=39321),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour
SM200/MS200,solar,164,energytoday,total energy today,ulong (>=0<=65533),Wh,false,sensor.solar_total_energy_today,sensor.solar_energytoday
SM200/MS200,solar,164,energytotal,total energy,ulong (>=0<=39321),kWh,false,sensor.solar_total_energy,sensor.solar_energytotal
SM200/MS200,solar,164,pump2worktime,pump 2 working time,time (>=0<=65533),minutes,false,sensor.solar_pump_2_working_time,sensor.solar_pump2worktime
SM200/MS200,solar,164,m1worktime,differential control working time,time (>=0<=65533),minutes,false,sensor.solar_differential_control_working_time,sensor.solar_m1worktime
SM200/MS200,solar,164,heattransfersystem,heattransfer system,boolean, ,true,switch.solar_heattransfer_system,switch.solar_heattransfersystem
SM200/MS200,solar,164,externalcyl,external cylinder,boolean, ,true,switch.solar_external_cylinder,switch.solar_externalcyl
SM200/MS200,solar,164,thermaldisinfect,thermal disinfection,boolean, ,true,switch.solar_thermal_disinfection,switch.solar_thermaldisinfect
SM200/MS200,solar,164,heatmetering,heatmetering,boolean, ,true,switch.solar_heatmetering,switch.solar_heatmetering
SM200/MS200,solar,164,activated,activated,boolean, ,true,switch.solar_activated,switch.solar_activated
SM200/MS200,solar,164,solarpumpmode,pump mode,enum [constant\|pwm\|analog], ,true,select.solar_pump_mode,select.solar_solarpumpmode
SM200/MS200,solar,164,pumpkick,pump kick,boolean, ,true,switch.solar_pump_kick,switch.solar_pumpkick
SM200/MS200,solar,164,plainwatermode,plain water mode,boolean, ,true,switch.solar_plain_water_mode,switch.solar_plainwatermode
SM200/MS200,solar,164,doublematchflow,doublematchflow,boolean, ,true,switch.solar_doublematchflow,switch.solar_doublematchflow
SM200/MS200,solar,164,pump2minmod,minimum pump 2 modulation,uint (>=0<=100),%,true,number.solar_minimum_pump_2_modulation,number.solar_pump2minmod
SM200/MS200,solar,164,turnondiff2,pump 2 turn on difference,uint (>=0<=25),C,true,number.solar_pump_2_turn_on_difference,number.solar_turnondiff2
SM200/MS200,solar,164,turnoffdiff2,pump 2 turn off difference,uint (>=0<=25),C,true,number.solar_pump_2_turn_off_difference,number.solar_turnoffdiff2
SM200/MS200,solar,164,pump2kick,pump kick 2,boolean, ,true,switch.solar_pump_kick_2,switch.solar_pump2kick
SM200/MS200,solar,164,climatezone,climate zone,uint (>=0<=254), ,true,number.solar_climate_zone,number.solar_climatezone
SM200/MS200,solar,164,collector1area,collector 1 area,ushort (>=0<=3199),m²,true,number.solar_collector_1_area,number.solar_collector1area
SM200/MS200,solar,164,collector1type,collector 1 type,enum [flat\|vacuum], ,true,select.solar_collector_1_type,select.solar_collector1type
SM200/MS200,solar,164,collector2area,collector 2 area,ushort (>=0<=3199),m²,true,number.solar_collector_2_area,number.solar_collector2area
SM200/MS200,solar,164,collector2type,collector 2 type,enum [flat\|vacuum], ,true,select.solar_collector_2_type,select.solar_collector2type
SM200/MS200,solar,164,cylpriority,cylinder priority,enum [cyl 1\|cyl 2], ,true,select.solar_cylinder_priority,select.solar_cylpriority
SM200/MS200,solar,164,heatcntflowtemp,heat counter flow temperature,ushort (>=0<=3199),C,false,sensor.solar_heat_counter_flow_temperature,sensor.solar_heatcntflowtemp
SM200/MS200,solar,164,heatcntrettemp,heat counter return temperature,ushort (>=0<=3199),C,false,sensor.solar_heat_counter_return_temperature,sensor.solar_heatcntrettemp
SM200/MS200,solar,164,heatcnt,heat counter impulses,uint (>=0<=254), ,false,sensor.solar_heat_counter_impulses,sensor.solar_heatcnt
SM200/MS200,solar,164,swapflowtemp,swap flow temperature (TS14),ushort (>=0<=3199),C,false,sensor.solar_swap_flow_temperature_(TS14),sensor.solar_swapflowtemp
SM200/MS200,solar,164,swaprettemp,swap return temperature (TS15),ushort (>=0<=3199),C,false,sensor.solar_swap_return_temperature_(TS15),sensor.solar_swaprettemp
HP Module,heatpump,252,airhumidity,relative air humidity,uint (>=0<=100),%,false,sensor.heatpump_relative_air_humidity,sensor.heatpump_airhumidity
HP Module,heatpump,252,dewtemperature,dew point temperature,uint (>=0<=254),C,false,sensor.heatpump_dew_point_temperature,sensor.heatpump_dewtemperature
HP Module,heatpump,252,curflowtemp,current flow temperature,short (>=-3199<=3199),C,false,sensor.heatpump_current_flow_temperature,sensor.heatpump_curflowtemp
HP Module,heatpump,252,rettemp,return temperature,short (>=-3199<=3199),C,false,sensor.heatpump_return_temperature,sensor.heatpump_rettemp
HP Module,heatpump,252,sysrettemp,system return temperature,short (>=-3199<=3199),C,false,sensor.heatpump_system_return_temperature,sensor.heatpump_sysrettemp
HP Module,heatpump,252,hpta4,drain pan temp (TA4),short (>=-3199<=3199),C,false,sensor.heatpump_drain_pan_temp_(TA4),sensor.heatpump_hpta4
HP Module,heatpump,252,hptr1,compressor temperature (TR1),short (>=-3199<=3199),C,false,sensor.heatpump_compressor_temperature_(TR1),sensor.heatpump_hptr1
HP Module,heatpump,252,hptr3,refrigerant temperature liquid side (condenser output) (TR3),short (>=-3199<=3199),C,false,sensor.heatpump_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.heatpump_hptr3
HP Module,heatpump,252,hptr4,evaporator inlet temperature (TR4),short (>=-3199<=3199),C,false,sensor.heatpump_evaporator_inlet_temperature_(TR4),sensor.heatpump_hptr4
HP Module,heatpump,252,hptr5,compressor inlet temperature (TR5),short (>=-3199<=3199),C,false,sensor.heatpump_compressor_inlet_temperature_(TR5),sensor.heatpump_hptr5
HP Module,heatpump,252,hptr6,compressor outlet temperature (TR6),short (>=-3199<=3199),C,false,sensor.heatpump_compressor_outlet_temperature_(TR6),sensor.heatpump_hptr6
HP Module,heatpump,252,hptl2,air inlet temperature (TL2),short (>=-3199<=3199),C,false,sensor.heatpump_air_inlet_temperature_(TL2),sensor.heatpump_hptl2
HP Module,heatpump,252,hppl1,low pressure side temperature (PL1),short (>=-3199<=3199),C,false,sensor.heatpump_low_pressure_side_temperature_(PL1),sensor.heatpump_hppl1
HP Module,heatpump,252,hpph1,high pressure side temperature (PH1),short (>=-3199<=3199),C,false,sensor.heatpump_high_pressure_side_temperature_(PH1),sensor.heatpump_hpph1
HP Module,heatpump,252,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.heatpump_heating_pump_modulation,sensor.heatpump_heatingpumpmod
HP Module,heatpump,252,hpcompspd,compressor speed,uint (>=0<=100),%,false,sensor.heatpump_compressor_speed,sensor.heatpump_hpcompspd
HP Module,heatpump,252,hybridstrategy,hybrid control strategy,enum [cost optimized\|co2 optimized\|outside temperature alt.\|outside temperature parallel\|heatpump prefered\|boiler only], ,true,select.heatpump_hybrid_control_strategy,select.heatpump_hybridstrategy
HP Module,heatpump,252,lownoisemode,low noise mode,enum [off\|reduced output\|switch off hp\|perm. reduced], ,true,select.heatpump_low_noise_mode,select.heatpump_lownoisemode
HP Module,heatpump,252,lownoisestart,low noise starttime,uint (>=0<=23), ,true,number.heatpump_low_noise_starttime,number.heatpump_lownoisestart
HP Module,heatpump,252,lownoisestop,low noise stoptime,uint (>=0<=23), ,true,number.heatpump_low_noise_stoptime,number.heatpump_lownoisestop
HP Module,heatpump,252,hybriddhw,hybrid DHW,enum [eco\|high comfort], ,true,select.heatpump_hybrid_DHW,select.heatpump_hybriddhw
HP Module,heatpump,252,energypricegas,energy price gas,uint (>=0<=254), ,true,number.heatpump_energy_price_gas,number.heatpump_energypricegas
HP Module,heatpump,252,energypriceel,energy price electric,uint (>=0<=254), ,true,number.heatpump_energy_price_electric,number.heatpump_energypriceel
HP Module,heatpump,252,energyfeedpv,feed in PV,uint (>=0<=254), ,true,number.heatpump_feed_in_PV,number.heatpump_energyfeedpv
HP Module,heatpump,252,switchovertemp,outside switchover temperature,int (>=-126<=126), ,true,number.heatpump_outside_switchover_temperature,number.heatpump_switchovertemp
HP Module,heatpump,252,airpurgemode,air purge mode,boolean, ,true,switch.heatpump_air_purge_mode,switch.heatpump_airpurgemode
HP Module,heatpump,252,heatpumpoutput,heatpump output,uint (>=0<=100),%,true,number.heatpump_heatpump_output,number.heatpump_heatpumpoutput
HP Module,heatpump,252,coolingcircuit,cooling circuit,boolean, ,true,switch.heatpump_cooling_circuit,switch.heatpump_coolingcircuit
HP Module,heatpump,252,compstartmod,compressor start modulation,uint (>=0<=100),%,true,number.heatpump_compressor_start_modulation,number.heatpump_compstartmod
HP Module,heatpump,252,heatdrainpan,heat drain pan,boolean, ,true,switch.heatpump_heat_drain_pan,switch.heatpump_heatdrainpan
HP Module,heatpump,252,heatcable,heating cable,boolean, ,true,switch.heatpump_heating_cable,switch.heatpump_heatcable
Hybrid Manager HM200,heatpump,248,airhumidity,relative air humidity,uint (>=0<=100),%,false,sensor.heatpump_relative_air_humidity,sensor.heatpump_airhumidity
Hybrid Manager HM200,heatpump,248,dewtemperature,dew point temperature,uint (>=0<=254),C,false,sensor.heatpump_dew_point_temperature,sensor.heatpump_dewtemperature
Hybrid Manager HM200,heatpump,248,curflowtemp,current flow temperature,short (>=-3199<=3199),C,false,sensor.heatpump_current_flow_temperature,sensor.heatpump_curflowtemp
Hybrid Manager HM200,heatpump,248,rettemp,return temperature,short (>=-3199<=3199),C,false,sensor.heatpump_return_temperature,sensor.heatpump_rettemp
Hybrid Manager HM200,heatpump,248,sysrettemp,system return temperature,short (>=-3199<=3199),C,false,sensor.heatpump_system_return_temperature,sensor.heatpump_sysrettemp
Hybrid Manager HM200,heatpump,248,hpta4,drain pan temp (TA4),short (>=-3199<=3199),C,false,sensor.heatpump_drain_pan_temp_(TA4),sensor.heatpump_hpta4
Hybrid Manager HM200,heatpump,248,hptr1,compressor temperature (TR1),short (>=-3199<=3199),C,false,sensor.heatpump_compressor_temperature_(TR1),sensor.heatpump_hptr1
Hybrid Manager HM200,heatpump,248,hptr3,refrigerant temperature liquid side (condenser output) (TR3),short (>=-3199<=3199),C,false,sensor.heatpump_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.heatpump_hptr3
Hybrid Manager HM200,heatpump,248,hptr4,evaporator inlet temperature (TR4),short (>=-3199<=3199),C,false,sensor.heatpump_evaporator_inlet_temperature_(TR4),sensor.heatpump_hptr4
Hybrid Manager HM200,heatpump,248,hptr5,compressor inlet temperature (TR5),short (>=-3199<=3199),C,false,sensor.heatpump_compressor_inlet_temperature_(TR5),sensor.heatpump_hptr5
Hybrid Manager HM200,heatpump,248,hptr6,compressor outlet temperature (TR6),short (>=-3199<=3199),C,false,sensor.heatpump_compressor_outlet_temperature_(TR6),sensor.heatpump_hptr6
Hybrid Manager HM200,heatpump,248,hptl2,air inlet temperature (TL2),short (>=-3199<=3199),C,false,sensor.heatpump_air_inlet_temperature_(TL2),sensor.heatpump_hptl2
Hybrid Manager HM200,heatpump,248,hppl1,low pressure side temperature (PL1),short (>=-3199<=3199),C,false,sensor.heatpump_low_pressure_side_temperature_(PL1),sensor.heatpump_hppl1
Hybrid Manager HM200,heatpump,248,hpph1,high pressure side temperature (PH1),short (>=-3199<=3199),C,false,sensor.heatpump_high_pressure_side_temperature_(PH1),sensor.heatpump_hpph1
Hybrid Manager HM200,heatpump,248,heatingpumpmod,heating pump modulation,uint (>=0<=100),%,false,sensor.heatpump_heating_pump_modulation,sensor.heatpump_heatingpumpmod
Hybrid Manager HM200,heatpump,248,hpcompspd,compressor speed,uint (>=0<=100),%,false,sensor.heatpump_compressor_speed,sensor.heatpump_hpcompspd
Hybrid Manager HM200,heatpump,248,hybridstrategy,hybrid control strategy,enum [cost optimized\|co2 optimized\|outside temperature alt.\|outside temperature parallel\|heatpump prefered\|boiler only], ,true,select.heatpump_hybrid_control_strategy,select.heatpump_hybridstrategy
Hybrid Manager HM200,heatpump,248,lownoisemode,low noise mode,enum [off\|reduced output\|switch off hp\|perm. reduced], ,true,select.heatpump_low_noise_mode,select.heatpump_lownoisemode
Hybrid Manager HM200,heatpump,248,lownoisestart,low noise starttime,uint (>=0<=23), ,true,number.heatpump_low_noise_starttime,number.heatpump_lownoisestart
Hybrid Manager HM200,heatpump,248,lownoisestop,low noise stoptime,uint (>=0<=23), ,true,number.heatpump_low_noise_stoptime,number.heatpump_lownoisestop
Hybrid Manager HM200,heatpump,248,hybriddhw,hybrid DHW,enum [eco\|high comfort], ,true,select.heatpump_hybrid_DHW,select.heatpump_hybriddhw
Hybrid Manager HM200,heatpump,248,energypricegas,energy price gas,uint (>=0<=254), ,true,number.heatpump_energy_price_gas,number.heatpump_energypricegas
Hybrid Manager HM200,heatpump,248,energypriceel,energy price electric,uint (>=0<=254), ,true,number.heatpump_energy_price_electric,number.heatpump_energypriceel
Hybrid Manager HM200,heatpump,248,energyfeedpv,feed in PV,uint (>=0<=254), ,true,number.heatpump_feed_in_PV,number.heatpump_energyfeedpv
Hybrid Manager HM200,heatpump,248,switchovertemp,outside switchover temperature,int (>=-126<=126), ,true,number.heatpump_outside_switchover_temperature,number.heatpump_switchovertemp
Hybrid Manager HM200,heatpump,248,airpurgemode,air purge mode,boolean, ,true,switch.heatpump_air_purge_mode,switch.heatpump_airpurgemode
Hybrid Manager HM200,heatpump,248,heatpumpoutput,heatpump output,uint (>=0<=100),%,true,number.heatpump_heatpump_output,number.heatpump_heatpumpoutput
Hybrid Manager HM200,heatpump,248,coolingcircuit,cooling circuit,boolean, ,true,switch.heatpump_cooling_circuit,switch.heatpump_coolingcircuit
Hybrid Manager HM200,heatpump,248,compstartmod,compressor start modulation,uint (>=0<=100),%,true,number.heatpump_compressor_start_modulation,number.heatpump_compstartmod
Hybrid Manager HM200,heatpump,248,heatdrainpan,heat drain pan,boolean, ,true,switch.heatpump_heat_drain_pan,switch.heatpump_heatdrainpan
Hybrid Manager HM200,heatpump,248,heatcable,heating cable,boolean, ,true,switch.heatpump_heating_cable,switch.heatpump_heatcable
WM10,switch,71,activated,activated,boolean, ,false,binary_sensor.switch_activated,binary_sensor.switch_activated
WM10,switch,71,flowtemphc,flow temperature (TC1),ushort (>=0<=3199),C,false,sensor.switch_flow_temperature_(TC1),sensor.switch_flowtemphc
WM10,switch,71,status,status,int (>=-126<=126), ,false,sensor.switch_status,sensor.switch_status
Rego 3000,controller,240,datetime,date/time,string, ,false,sensor.controller_date/time,sensor.controller_datetime
Logavent HRV176,ventilation,231,outfresh,outdoor fresh air,short (>=-3199<=3199),C,false,sensor.ventilation_outdoor_fresh_air,sensor.ventilation_outfresh
Logavent HRV176,ventilation,231,infresh,indoor fresh air,short (>=-3199<=3199),C,false,sensor.ventilation_indoor_fresh_air,sensor.ventilation_infresh
Logavent HRV176,ventilation,231,outexhaust,outdoor exhaust air,short (>=-3199<=3199),C,false,sensor.ventilation_outdoor_exhaust_air,sensor.ventilation_outexhaust
Logavent HRV176,ventilation,231,inexhaust,indoor exhaust air,short (>=-3199<=3199),C,false,sensor.ventilation_indoor_exhaust_air,sensor.ventilation_inexhaust
Logavent HRV176,ventilation,231,ventinspeed,in blower speed,uint (>=0<=100),%,false,sensor.ventilation_in_blower_speed,sensor.ventilation_ventinspeed
Logavent HRV176,ventilation,231,ventoutspeed,out blower speed,uint (>=0<=100),%,false,sensor.ventilation_out_blower_speed,sensor.ventilation_ventoutspeed
Logavent HRV176,ventilation,231,ventmode,ventilation mode,enum [auto\|off\|L1\|L2\|L3\|L4\|demand\|sleep\|intense\|bypass\|party\|fireplace], ,true,select.ventilation_ventilation_mode,select.ventilation_ventmode
Logavent HRV176,ventilation,231,airquality,air quality (voc),ushort (>=0<=31999), ,false,sensor.ventilation_air_quality_(voc),sensor.ventilation_airquality
