device name,device type,product id,shortname,fullname,type [options...] \| (min/max),uom,writeable,discovery entityid v3.4,discovery entityid,modbus unit identifier,modbus block,modbus scale factor,modbus offset,modbus count
"CS*800i, Logatherm WLW*",boiler,8,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"CS*800i, Logatherm WLW*",boiler,8,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"CS*800i, Logatherm WLW*",boiler,8,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"CS*800i, Logatherm WLW*",boiler,8,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"CS*800i, Logatherm WLW*",boiler,8,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"CS*800i, Logatherm WLW*",boiler,8,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"CS*800i, Logatherm WLW*",boiler,8,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"CS*800i, Logatherm WLW*",boiler,8,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"CS*800i, Logatherm WLW*",boiler,8,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"CS*800i, Logatherm WLW*",boiler,8,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"CS*800i, Logatherm WLW*",boiler,8,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"CS*800i, Logatherm WLW*",boiler,8,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"CS*800i, Logatherm WLW*",boiler,8,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"CS*800i, Logatherm WLW*",boiler,8,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"CS*800i, Logatherm WLW*",boiler,8,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"CS*800i, Logatherm WLW*",boiler,8,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"CS*800i, Logatherm WLW*",boiler,8,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"CS*800i, Logatherm WLW*",boiler,8,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"CS*800i, Logatherm WLW*",boiler,8,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"CS*800i, Logatherm WLW*",boiler,8,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"CS*800i, Logatherm WLW*",boiler,8,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"CS*800i, Logatherm WLW*",boiler,8,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"CS*800i, Logatherm WLW*",boiler,8,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"CS*800i, Logatherm WLW*",boiler,8,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"CS*800i, Logatherm WLW*",boiler,8,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"CS*800i, Logatherm WLW*",boiler,8,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"CS*800i, Logatherm WLW*",boiler,8,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"CS*800i, Logatherm WLW*",boiler,8,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"CS*800i, Logatherm WLW*",boiler,8,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"CS*800i, Logatherm WLW*",boiler,8,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"CS*800i, Logatherm WLW*",boiler,8,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"CS*800i, Logatherm WLW*",boiler,8,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"CS*800i, Logatherm WLW*",boiler,8,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"CS*800i, Logatherm WLW*",boiler,8,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"CS*800i, Logatherm WLW*",boiler,8,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"CS*800i, Logatherm WLW*",boiler,8,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"CS*800i, Logatherm WLW*",boiler,8,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"CS*800i, Logatherm WLW*",boiler,8,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"CS*800i, Logatherm WLW*",boiler,8,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"CS*800i, Logatherm WLW*",boiler,8,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"CS*800i, Logatherm WLW*",boiler,8,nrg,energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_dhw_energy,sensor.boiler_dhw_nrg,5,9,1/100,0,2
"CS*800i, Logatherm WLW*",boiler,8,nrgheat,energy heating,uint24 (>=0<=167772),kWh,false,sensor.boiler_energy_heating,sensor.boiler_nrgheat,5,0,1/100,81,2
"CS*800i, Logatherm WLW*",boiler,8,nrgcool,energy cooling,uint24 (>=0<=167772),kWh,false,sensor.boiler_energy_cooling,sensor.boiler_nrgcool,5,0,1/100,83,2
"CS*800i, Logatherm WLW*",boiler,8,metertotal,meter total,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_total,sensor.boiler_metertotal,5,0,1/100,85,2
"CS*800i, Logatherm WLW*",boiler,8,metercomp,meter compressor,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_compressor,sensor.boiler_metercomp,5,0,1/100,87,2
"CS*800i, Logatherm WLW*",boiler,8,metereheat,meter e-heater,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_e-heater,sensor.boiler_metereheat,5,0,1/100,89,2
"CS*800i, Logatherm WLW*",boiler,8,meterheat,meter heating,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/100,91,2
"CS*800i, Logatherm WLW*",boiler,8,metercool,meter cooling,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_cooling,sensor.boiler_metercool,5,0,1/100,93,2
"CS*800i, Logatherm WLW*",boiler,8,meter,meter,uint24 (>=0<=167772),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/100,2,2
"CS*800i, Logatherm WLW*",boiler,8,uptimetotal,heatpump total uptime,time (>=0<=279620),minutes,false,sensor.boiler_heatpump_total_uptime,sensor.boiler_uptimetotal,5,0,1/60,95,2
"CS*800i, Logatherm WLW*",boiler,8,uptimecontrol,total operating time heat,time (>=0<=279620),minutes,false,sensor.boiler_total_operating_time_heat,sensor.boiler_uptimecontrol,5,0,1/60,97,2
"CS*800i, Logatherm WLW*",boiler,8,uptimecompheating,operating time compressor heating,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_heating,sensor.boiler_uptimecompheating,5,0,1/60,99,2
"CS*800i, Logatherm WLW*",boiler,8,uptimecompcooling,operating time compressor cooling,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_cooling,sensor.boiler_uptimecompcooling,5,0,1/60,101,2
"CS*800i, Logatherm WLW*",boiler,8,uptimecomp,operating time compressor,time (>=0<=279620),minutes,false,sensor.boiler_dhw_operating_time_compressor,sensor.boiler_dhw_uptimecomp,5,9,1/60,4,2
"CS*800i, Logatherm WLW*",boiler,8,uptimecomppool,operating time compressor pool,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_pool,sensor.boiler_uptimecomppool,5,0,1/60,103,2
"CS*800i, Logatherm WLW*",boiler,8,totalcompstarts,total compressor control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_total_compressor_control_starts,sensor.boiler_totalcompstarts,5,0,1,105,2
"CS*800i, Logatherm WLW*",boiler,8,heatingstarts,heating control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_heating_control_starts,sensor.boiler_heatingstarts,5,0,1,107,2
"CS*800i, Logatherm WLW*",boiler,8,coolingstarts,cooling control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_cooling_control_starts,sensor.boiler_coolingstarts,5,0,1,109,2
"CS*800i, Logatherm WLW*",boiler,8,startshp,starts hp,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts_hp,sensor.boiler_dhw_startshp,5,9,1,6,2
"CS*800i, Logatherm WLW*",boiler,8,poolstarts,pool control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_pool_control_starts,sensor.boiler_poolstarts,5,0,1,111,2
"CS*800i, Logatherm WLW*",boiler,8,nrgconstotal,total energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_consumption,sensor.boiler_nrgconstotal,5,0,1,113,2
"CS*800i, Logatherm WLW*",boiler,8,nrgconscomptotal,total energy consumption compressor,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_consumption_compressor,sensor.boiler_nrgconscomptotal,5,0,1,115,2
"CS*800i, Logatherm WLW*",boiler,8,nrgconscompheating,energy consumption compressor heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_heating,sensor.boiler_nrgconscompheating,5,0,1,117,2
"CS*800i, Logatherm WLW*",boiler,8,nrgconscomp,energy consumption compressor,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_energy_consumption_compressor,sensor.boiler_dhw_nrgconscomp,5,9,1,8,2
"CS*800i, Logatherm WLW*",boiler,8,nrgconscompcooling,energy consumption compressor cooling,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_cooling,sensor.boiler_nrgconscompcooling,5,0,1,119,2
"CS*800i, Logatherm WLW*",boiler,8,nrgconscomppool,energy consumption compressor pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_pool,sensor.boiler_nrgconscomppool,5,0,1,121,2
"CS*800i, Logatherm WLW*",boiler,8,auxelecheatnrgconstotal,total aux elec. heater energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_aux_elec._heater_energy_consumption,sensor.boiler_auxelecheatnrgconstotal,5,0,1,123,2
"CS*800i, Logatherm WLW*",boiler,8,auxelecheatnrgconsheating,aux elec. heater energy consumption heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_heating,sensor.boiler_auxelecheatnrgconsheating,5,0,1,125,2
"CS*800i, Logatherm WLW*",boiler,8,auxelecheatnrgcons,aux elec. heater energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_aux_elec._heater_energy_consumption,sensor.boiler_dhw_auxelecheatnrgcons,5,9,1,10,2
"CS*800i, Logatherm WLW*",boiler,8,auxelecheatnrgconspool,aux elec. heater energy consumption pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_pool,sensor.boiler_auxelecheatnrgconspool,5,0,1,127,2
"CS*800i, Logatherm WLW*",boiler,8,nrgsupptotal,total energy supplied,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied,sensor.boiler_nrgsupptotal,5,0,1,129,2
"CS*800i, Logatherm WLW*",boiler,8,nrgsuppheating,total energy supplied heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_heating,sensor.boiler_nrgsuppheating,5,0,1,131,2
"CS*800i, Logatherm WLW*",boiler,8,nrgsupp,total energy warm supplied,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_total_energy_warm_supplied,sensor.boiler_dhw_nrgsupp,5,9,1,12,2
"CS*800i, Logatherm WLW*",boiler,8,nrgsuppcooling,total energy supplied cooling,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_cooling,sensor.boiler_nrgsuppcooling,5,0,1,133,2
"CS*800i, Logatherm WLW*",boiler,8,nrgsupppool,total energy supplied pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_pool,sensor.boiler_nrgsupppool,5,0,1,135,2
"CS*800i, Logatherm WLW*",boiler,8,hppower,compressor power output,uint8 (>=0<=25),kW,false,sensor.boiler_compressor_power_output,sensor.boiler_hppower,5,0,1/10,137,1
"CS*800i, Logatherm WLW*",boiler,8,hpmaxpower,compressor max power,uint8 (>=0<=100),%,true,number.boiler_compressor_max_power,number.boiler_hpmaxpower,5,0,1,138,1
"CS*800i, Logatherm WLW*",boiler,8,pvmaxcomp,pv compressor max power,uint8 (>=0<=25),kW,true,number.boiler_pv_compressor_max_power,number.boiler_pvmaxcomp,5,0,1/10,139,1
"CS*800i, Logatherm WLW*",boiler,8,powerreduction,power reduction,uint8 (>=30<=60),%,true,number.boiler_power_reduction,number.boiler_powerreduction,5,0,10,140,1
"CS*800i, Logatherm WLW*",boiler,8,hpsetdiffpress,set differential pressure,uint8 (>=150<=750),mbar,true,number.boiler_set_differential_pressure,number.boiler_hpsetdiffpress,5,0,50,141,1
"CS*800i, Logatherm WLW*",boiler,8,hpcompon,hp compressor,boolean, ,false,binary_sensor.boiler_hp_compressor,binary_sensor.boiler_hpcompon,5,0,1,142,1
"CS*800i, Logatherm WLW*",boiler,8,hpactivity,compressor activity,enum [none\|heating\|cooling\|hot water\|pool\|unknown\|defrost], ,false,sensor.boiler_compressor_activity,sensor.boiler_hpactivity,5,0,1,143,1
"CS*800i, Logatherm WLW*",boiler,8,hpbrinepumpspd,brine pump speed,uint8 (>=0<=100),%,false,sensor.boiler_brine_pump_speed,sensor.boiler_hpbrinepumpspd,5,0,1,144,1
"CS*800i, Logatherm WLW*",boiler,8,hpswitchvalve,switch valve,boolean, ,false,binary_sensor.boiler_switch_valve,binary_sensor.boiler_hpswitchvalve,5,0,1,145,1
"CS*800i, Logatherm WLW*",boiler,8,hpcompspd,compressor speed,uint8 (>=0<=100),%,false,sensor.boiler_compressor_speed,sensor.boiler_hpcompspd,5,0,1,146,1
"CS*800i, Logatherm WLW*",boiler,8,hpcircspd,circulation pump speed,uint8 (>=0<=100),%,false,sensor.boiler_circulation_pump_speed,sensor.boiler_hpcircspd,5,0,1,147,1
"CS*800i, Logatherm WLW*",boiler,8,hpbrinein,brine in/evaporator,int16 (>=-3199<=3199),C,false,sensor.boiler_brine_in/evaporator,sensor.boiler_hpbrinein,5,0,1/10,148,1
"CS*800i, Logatherm WLW*",boiler,8,hpbrineout,brine out/condenser,int16 (>=-3199<=3199),C,false,sensor.boiler_brine_out/condenser,sensor.boiler_hpbrineout,5,0,1/10,149,1
"CS*800i, Logatherm WLW*",boiler,8,hptc0,heat carrier return (TC0),int16 (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_return_(TC0),sensor.boiler_hptc0,5,0,1/10,150,1
"CS*800i, Logatherm WLW*",boiler,8,hptc1,heat carrier forward (TC1),int16 (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_forward_(TC1),sensor.boiler_hptc1,5,0,1/10,151,1
"CS*800i, Logatherm WLW*",boiler,8,hptc3,condenser temperature (TC3),int16 (>=-3199<=3199),C,false,sensor.boiler_condenser_temperature_(TC3),sensor.boiler_hptc3,5,0,1/10,152,1
"CS*800i, Logatherm WLW*",boiler,8,hptr1,compressor temperature (TR1),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_temperature_(TR1),sensor.boiler_hptr1,5,0,1/10,153,1
"CS*800i, Logatherm WLW*",boiler,8,hptr3,refrigerant temperature liquid side (condenser output) (TR3),int16 (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.boiler_hptr3,5,0,1/10,154,1
"CS*800i, Logatherm WLW*",boiler,8,hptr4,evaporator inlet temperature (TR4),int16 (>=-3199<=3199),C,false,sensor.boiler_evaporator_inlet_temperature_(TR4),sensor.boiler_hptr4,5,0,1/10,155,1
"CS*800i, Logatherm WLW*",boiler,8,hptr5,compressor inlet temperature (TR5),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_inlet_temperature_(TR5),sensor.boiler_hptr5,5,0,1/10,156,1
"CS*800i, Logatherm WLW*",boiler,8,hptr6,compressor outlet temperature (TR6),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_outlet_temperature_(TR6),sensor.boiler_hptr6,5,0,1/10,157,1
"CS*800i, Logatherm WLW*",boiler,8,hptr7,refrigerant temperature gas side (condenser input) (TR7),int16 (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_gas_side_(condenser_input)_(TR7),sensor.boiler_hptr7,5,0,1/10,158,1
"CS*800i, Logatherm WLW*",boiler,8,hptl2,air inlet temperature (TL2),int16 (>=-3199<=3199),C,false,sensor.boiler_air_inlet_temperature_(TL2),sensor.boiler_hptl2,5,0,1/10,159,1
"CS*800i, Logatherm WLW*",boiler,8,hppl1,low pressure side temperature (PL1),int16 (>=-3199<=3199),C,false,sensor.boiler_low_pressure_side_temperature_(PL1),sensor.boiler_hppl1,5,0,1/10,160,1
"CS*800i, Logatherm WLW*",boiler,8,hpph1,high pressure side temperature (PH1),int16 (>=-3199<=3199),C,false,sensor.boiler_high_pressure_side_temperature_(PH1),sensor.boiler_hpph1,5,0,1/10,161,1
"CS*800i, Logatherm WLW*",boiler,8,hpta4,drain pan temp (TA4),int16 (>=-3199<=3199),C,false,sensor.boiler_drain_pan_temp_(TA4),sensor.boiler_hpta4,5,0,1/10,162,1
"CS*800i, Logatherm WLW*",boiler,8,hptw1,reservoir temp (TW1),int16 (>=-3199<=3199),C,false,sensor.boiler_reservoir_temp_(TW1),sensor.boiler_hptw1,5,0,1/10,163,1
"CS*800i, Logatherm WLW*",boiler,8,poolsettemp,pool set temperature,uint8 (>=0<=127),C,true,number.boiler_pool_set_temperature,number.boiler_poolsettemp,5,0,1/2,164,1
"CS*800i, Logatherm WLW*",boiler,8,hp4way,4-way valve (VR4),enum [cooling & defrost\|heating & dhw], ,false,sensor.boiler_4-way_valve_(VR4),sensor.boiler_hp4way,5,0,1,165,1
"CS*800i, Logatherm WLW*",boiler,8,hpin1,input 1 state,boolean, ,false,binary_sensor.boiler_input_1_state,binary_sensor.boiler_hpin1,5,0,1,166,1
"CS*800i, Logatherm WLW*",boiler,8,hpin1opt,input 1 options,string, ,true,sensor.boiler_input_1_options,sensor.boiler_hpin1opt,5,0,1,167,8
"CS*800i, Logatherm WLW*",boiler,8,hpin2,input 2 state,boolean, ,false,binary_sensor.boiler_input_2_state,binary_sensor.boiler_hpin2,5,0,1,175,1
"CS*800i, Logatherm WLW*",boiler,8,hpin2opt,input 2 options,string, ,true,sensor.boiler_input_2_options,sensor.boiler_hpin2opt,5,0,1,176,8
"CS*800i, Logatherm WLW*",boiler,8,hpin3,input 3 state,boolean, ,false,binary_sensor.boiler_input_3_state,binary_sensor.boiler_hpin3,5,0,1,184,1
"CS*800i, Logatherm WLW*",boiler,8,hpin3opt,input 3 options,string, ,true,sensor.boiler_input_3_options,sensor.boiler_hpin3opt,5,0,1,185,8
"CS*800i, Logatherm WLW*",boiler,8,hpin4,input 4 state,boolean, ,false,binary_sensor.boiler_input_4_state,binary_sensor.boiler_hpin4,5,0,1,193,1
"CS*800i, Logatherm WLW*",boiler,8,hpin4opt,input 4 options,string, ,true,sensor.boiler_input_4_options,sensor.boiler_hpin4opt,5,0,1,194,8
"CS*800i, Logatherm WLW*",boiler,8,maxheatcomp,heat limit compressor,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_compressor,select.boiler_maxheatcomp,5,0,1,202,1
"CS*800i, Logatherm WLW*",boiler,8,maxheatheat,heat limit heating,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_heating,select.boiler_maxheatheat,5,0,1,203,1
"CS*800i, Logatherm WLW*",boiler,8,maxheat,heat limit,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_dhw_heat_limit,select.boiler_dhw_maxheat,5,9,1,14,1
"CS*800i, Logatherm WLW*",boiler,8,mandefrost,manual defrost,boolean, ,true,switch.boiler_manual_defrost,switch.boiler_mandefrost,5,0,1,204,1
"CS*800i, Logatherm WLW*",boiler,8,pvcooling,cooling only with PV,boolean, ,true,switch.boiler_cooling_only_with_PV,switch.boiler_pvcooling,5,0,1,205,1
"CS*800i, Logatherm WLW*",boiler,8,auxheateronly,aux heater only,boolean, ,true,switch.boiler_aux_heater_only,switch.boiler_auxheateronly,5,0,1,206,1
"CS*800i, Logatherm WLW*",boiler,8,auxheateroff,disable aux heater,boolean, ,true,switch.boiler_disable_aux_heater,switch.boiler_auxheateroff,5,0,1,207,1
"CS*800i, Logatherm WLW*",boiler,8,auxheaterstatus,aux heater status,boolean, ,false,binary_sensor.boiler_aux_heater_status,binary_sensor.boiler_auxheaterstatus,5,0,1,208,1
"CS*800i, Logatherm WLW*",boiler,8,auxheaterlevel,aux heater level,uint8 (>=0<=100),%,false,sensor.boiler_aux_heater_level,sensor.boiler_auxheaterlevel,5,0,1,209,1
"CS*800i, Logatherm WLW*",boiler,8,auxheaterdelay,aux heater on delay,uint16 (>=10<=1000),K*min,true,number.boiler_aux_heater_on_delay,number.boiler_auxheaterdelay,5,0,10,210,1
"CS*800i, Logatherm WLW*",boiler,8,auxmaxlimit,aux heater max limit,uint8 (>=0<=10),K,true,number.boiler_aux_heater_max_limit,number.boiler_auxmaxlimit,5,0,1/10,211,1
"CS*800i, Logatherm WLW*",boiler,8,auxlimitstart,aux heater limit start,uint8 (>=0<=10),K,true,number.boiler_aux_heater_limit_start,number.boiler_auxlimitstart,5,0,1/10,212,1
"CS*800i, Logatherm WLW*",boiler,8,auxheatrmode,aux heater mode,enum [eco\|comfort], ,true,select.boiler_aux_heater_mode,select.boiler_auxheatrmode,5,0,1,213,1
"CS*800i, Logatherm WLW*",boiler,8,hphystheat,on/off hyst heat,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_heat,number.boiler_hphystheat,5,0,5,214,1
"CS*800i, Logatherm WLW*",boiler,8,hphystcool,on/off hyst cool,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_cool,number.boiler_hphystcool,5,0,5,215,1
"CS*800i, Logatherm WLW*",boiler,8,hphystpool,on/off hyst pool,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_pool,number.boiler_hphystpool,5,0,5,216,1
"CS*800i, Logatherm WLW*",boiler,8,silentmode,silent mode,enum [off\|auto\|on], ,true,select.boiler_silent_mode,select.boiler_silentmode,5,0,1,217,1
"CS*800i, Logatherm WLW*",boiler,8,silentfrom,silent mode from,uint8 (>=0<=3810),minutes,true,number.boiler_silent_mode_from,number.boiler_silentfrom,5,0,15,218,1
"CS*800i, Logatherm WLW*",boiler,8,silentto,silent mode to,uint8 (>=0<=3810),minutes,true,number.boiler_silent_mode_to,number.boiler_silentto,5,0,15,219,1
"CS*800i, Logatherm WLW*",boiler,8,mintempsilent,min outside temp for silent mode,int8 (>=-126<=126),C,true,number.boiler_min_outside_temp_for_silent_mode,number.boiler_mintempsilent,5,0,1,220,1
"CS*800i, Logatherm WLW*",boiler,8,tempparmode,outside temp parallel mode,int8 (>=-126<=126),C,true,number.boiler_outside_temp_parallel_mode,number.boiler_tempparmode,5,0,1,221,1
"CS*800i, Logatherm WLW*",boiler,8,auxheatmix,aux heater mixing valve,int8 (>=-100<=100),%,false,sensor.boiler_aux_heater_mixing_valve,sensor.boiler_auxheatmix,5,0,1,222,1
"CS*800i, Logatherm WLW*",boiler,8,tempdiffheat,temp diff TC3/TC0 heat,uint8 (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_heat,number.boiler_tempdiffheat,5,0,1/10,223,1
"CS*800i, Logatherm WLW*",boiler,8,tempdiffcool,temp diff TC3/TC0 cool,uint8 (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_cool,number.boiler_tempdiffcool,5,0,1/10,224,1
"CS*800i, Logatherm WLW*",boiler,8,vpcooling,valve/pump cooling,boolean, ,true,switch.boiler_valve/pump_cooling,switch.boiler_vpcooling,5,0,1,225,1
"CS*800i, Logatherm WLW*",boiler,8,heatcable,heating cable,boolean, ,true,switch.boiler_heating_cable,switch.boiler_heatcable,5,0,1,226,1
"CS*800i, Logatherm WLW*",boiler,8,vc0valve,VC0 valve,boolean, ,true,switch.boiler_VC0_valve,switch.boiler_vc0valve,5,0,1,227,1
"CS*800i, Logatherm WLW*",boiler,8,primepump,primary heatpump,boolean, ,true,switch.boiler_primary_heatpump,switch.boiler_primepump,5,0,1,228,1
"CS*800i, Logatherm WLW*",boiler,8,primepumpmod,primary heatpump modulation,uint8 (>=0<=100),%,true,number.boiler_primary_heatpump_modulation,number.boiler_primepumpmod,5,0,1,229,1
"CS*800i, Logatherm WLW*",boiler,8,hp3way,3-way valve,boolean, ,true,switch.boiler_3-way_valve,switch.boiler_hp3way,5,0,1,230,1
"CS*800i, Logatherm WLW*",boiler,8,elheatstep1,el. heater step 1,boolean, ,true,switch.boiler_el._heater_step_1,switch.boiler_elheatstep1,5,0,1,231,1
"CS*800i, Logatherm WLW*",boiler,8,elheatstep2,el. heater step 2,boolean, ,true,switch.boiler_el._heater_step_2,switch.boiler_elheatstep2,5,0,1,232,1
"CS*800i, Logatherm WLW*",boiler,8,elheatstep3,el. heater step 3,boolean, ,true,switch.boiler_el._heater_step_3,switch.boiler_elheatstep3,5,0,1,233,1
"CS*800i, Logatherm WLW*",boiler,8,hpea0,condensate reservoir heating (EA0),boolean, ,false,binary_sensor.boiler_condensate_reservoir_heating_(EA0),binary_sensor.boiler_hpea0,5,0,1,234,1
"CS*800i, Logatherm WLW*",boiler,8,hppumpmode,primary heatpump mode,enum [auto\|continuous], ,true,select.boiler_primary_heatpump_mode,select.boiler_hppumpmode,5,0,1,235,1
"CS*800i, Logatherm WLW*",boiler,8,fan,fan,uint8 (>=20<=100),%,true,number.boiler_fan,number.boiler_fan,5,0,1,236,1
"CS*800i, Logatherm WLW*",boiler,8,shutdown,shutdown,cmd [off\|on], ,true,sensor.boiler_shutdown,sensor.boiler_shutdown,5,0,1,237,1
"CS*800i, Logatherm WLW*",boiler,8,hpcurrpower,compressor current power,uint16 (>=0<=31999),W,false,sensor.boiler_compressor_current_power,sensor.boiler_hpcurrpower,5,0,1,238,1
"CS*800i, Logatherm WLW*",boiler,8,hppowerlimit,power limit,uint16 (>=0<=31999),W,true,number.boiler_power_limit,number.boiler_hppowerlimit,5,0,1,239,1
"CS*800i, Logatherm WLW*",boiler,8,pc0flow,Flow PC0,int16 (>=-31999<=31999),l/h,false,sensor.boiler_Flow_PC0,sensor.boiler_pc0flow,5,0,1,240,1
"CS*800i, Logatherm WLW*",boiler,8,pc1flow,Flow PC1,int16 (>=-31999<=31999),l/h,false,sensor.boiler_Flow_PC1,sensor.boiler_pc1flow,5,0,1,241,1
"CS*800i, Logatherm WLW*",boiler,8,pc1on,PC1,boolean, ,false,binary_sensor.boiler_PC1,binary_sensor.boiler_pc1on,5,0,1,242,1
"CS*800i, Logatherm WLW*",boiler,8,pc1rate,PC1 rate,uint8 (>=0<=100),%,false,sensor.boiler_PC1_rate,sensor.boiler_pc1rate,5,0,1,243,1
"CS*800i, Logatherm WLW*",boiler,8,alternatingop,alternating operation,boolean, ,true,switch.boiler_dhw_alternating_operation,switch.boiler_dhw_alternatingop,5,9,1,15,1
"CS*800i, Logatherm WLW*",boiler,8,altopprioheat,prioritise heating during dhw,uint8 (>=20<=120),minutes,true,number.boiler_dhw_prioritise_heating_during_dhw,number.boiler_dhw_altopprioheat,5,9,1,16,1
"CS*800i, Logatherm WLW*",boiler,8,altopprio,prioritise dhw during heating,uint8 (>=30<=120),minutes,true,number.boiler_dhw_prioritise_dhw_during_heating,number.boiler_dhw_altopprio,5,9,1,17,1
"CS*800i, Logatherm WLW*",boiler,8,comfoff,comfort switch off,uint8 (>=15<=65),C,true,number.boiler_dhw_comfort_switch_off,number.boiler_dhw_comfoff,5,9,1,18,1
"CS*800i, Logatherm WLW*",boiler,8,ecooff,eco switch off,uint8 (>=15<=65),C,true,number.boiler_dhw_eco_switch_off,number.boiler_dhw_ecooff,5,9,1,19,1
"CS*800i, Logatherm WLW*",boiler,8,ecoplusoff,eco+ switch off,uint8 (>=48<=63),C,true,number.boiler_dhw_eco+_switch_off,number.boiler_dhw_ecoplusoff,5,9,1,20,1
"CS*800i, Logatherm WLW*",boiler,8,comfdiff,comfort diff,uint8 (>=6<=12),K,true,number.boiler_dhw_comfort_diff,number.boiler_dhw_comfdiff,5,9,1,21,1
"CS*800i, Logatherm WLW*",boiler,8,ecodiff,eco diff,uint8 (>=6<=12),K,true,number.boiler_dhw_eco_diff,number.boiler_dhw_ecodiff,5,9,1,22,1
"CS*800i, Logatherm WLW*",boiler,8,ecoplusdiff,eco+ diff,uint8 (>=6<=12),K,true,number.boiler_dhw_eco+_diff,number.boiler_dhw_ecoplusdiff,5,9,1,23,1
"CS*800i, Logatherm WLW*",boiler,8,comfstop,comfort stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_comfort_stop_temp,number.boiler_dhw_comfstop,5,9,1,24,1
"CS*800i, Logatherm WLW*",boiler,8,ecostop,eco stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_eco_stop_temp,number.boiler_dhw_ecostop,5,9,1,25,1
"CS*800i, Logatherm WLW*",boiler,8,ecoplusstop,eco+ stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_eco+_stop_temp,number.boiler_dhw_ecoplusstop,5,9,1,26,1
"CS*800i, Logatherm WLW*",boiler,8,hpcircpump,circulation pump available during dhw,boolean, ,true,switch.boiler_dhw_circulation_pump_available_during_dhw,switch.boiler_dhw_hpcircpump,5,9,1,27,1
"CS*800i, Logatherm WLW*",boiler,8,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"CS*800i, Logatherm WLW*",boiler,8,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"CS*800i, Logatherm WLW*",boiler,8,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"CS*800i, Logatherm WLW*",boiler,8,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"CS*800i, Logatherm WLW*",boiler,8,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"CS*800i, Logatherm WLW*",boiler,8,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"CS*800i, Logatherm WLW*",boiler,8,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"CS*800i, Logatherm WLW*",boiler,8,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"CS*800i, Logatherm WLW*",boiler,8,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"CS*800i, Logatherm WLW*",boiler,8,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"CS*800i, Logatherm WLW*",boiler,8,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"CS*800i, Logatherm WLW*",boiler,8,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"CS*800i, Logatherm WLW*",boiler,8,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"CS*800i, Logatherm WLW*",boiler,8,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"CS*800i, Logatherm WLW*",boiler,8,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"CS*800i, Logatherm WLW*",boiler,8,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"CS*800i, Logatherm WLW*",boiler,8,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"CS*800i, Logatherm WLW*",boiler,8,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"CS*800i, Logatherm WLW*",boiler,8,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"CS*800i, Logatherm WLW*",boiler,8,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"CS*800i, Logatherm WLW*",boiler,8,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"CS*800i, Logatherm WLW*",boiler,8,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"CS*800i, Logatherm WLW*",boiler,8,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"CS*800i, Logatherm WLW*",boiler,8,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"CS*800i, Logatherm WLW*",boiler,8,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"CS*800i, Logatherm WLW*",boiler,8,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"CS*800i, Logatherm WLW*",boiler,8,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"CS*800i, Logatherm WLW*",boiler,8,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"CS*800i, Logatherm WLW*",boiler,8,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"CS*800i, Logatherm WLW*",boiler,8,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"CS*800i, Logatherm WLW*",boiler,8,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"CS*800i, Logatherm WLW*",boiler,8,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"CS*800i, Logatherm WLW*",boiler,8,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"CS*800i, Logatherm WLW*",boiler,8,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"CS*800i, Logatherm WLW*",boiler,8,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"CS*800i, Logatherm WLW*",boiler,8,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"CS*800i, Logatherm WLW*",boiler,8,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"CS*800i, Logatherm WLW*",boiler,8,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"CS*800i, Logatherm WLW*",boiler,8,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"C1200W",boiler,12,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"C1200W",boiler,12,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"C1200W",boiler,12,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"C1200W",boiler,12,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"C1200W",boiler,12,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"C1200W",boiler,12,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"C1200W",boiler,12,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"C1200W",boiler,12,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"C1200W",boiler,12,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"C1200W",boiler,12,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"C1200W",boiler,12,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"C1200W",boiler,12,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"C1200W",boiler,12,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"C1200W",boiler,12,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"C1200W",boiler,12,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"C1200W",boiler,12,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"C1200W",boiler,12,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"C1200W",boiler,12,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"C1200W",boiler,12,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"C1200W",boiler,12,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"C1200W",boiler,12,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"C1200W",boiler,12,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"C1200W",boiler,12,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"C1200W",boiler,12,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"C1200W",boiler,12,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"C1200W",boiler,12,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"C1200W",boiler,12,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"C1200W",boiler,12,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"C1200W",boiler,12,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"C1200W",boiler,12,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"C1200W",boiler,12,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"C1200W",boiler,12,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"C1200W",boiler,12,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"C1200W",boiler,12,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"C1200W",boiler,12,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"C1200W",boiler,12,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"C1200W",boiler,12,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"C1200W",boiler,12,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"C1200W",boiler,12,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"C1200W",boiler,12,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"C1200W",boiler,12,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"C1200W",boiler,12,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"C1200W",boiler,12,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"C1200W",boiler,12,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"C1200W",boiler,12,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"C1200W",boiler,12,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"C1200W",boiler,12,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"C1200W",boiler,12,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"C1200W",boiler,12,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"C1200W",boiler,12,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"C1200W",boiler,12,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"C1200W",boiler,12,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"C1200W",boiler,12,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"C1200W",boiler,12,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"C1200W",boiler,12,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"C1200W",boiler,12,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"C1200W",boiler,12,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"C1200W",boiler,12,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"C1200W",boiler,12,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"C1200W",boiler,12,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"C1200W",boiler,12,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"C1200W",boiler,12,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"C1200W",boiler,12,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"C1200W",boiler,12,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"C1200W",boiler,12,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"C1200W",boiler,12,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"C1200W",boiler,12,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"C1200W",boiler,12,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"C1200W",boiler,12,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"C1200W",boiler,12,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"C1200W",boiler,12,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"C1200W",boiler,12,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"C1200W",boiler,12,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"C1200W",boiler,12,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"C1200W",boiler,12,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"C1200W",boiler,12,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"C1200W",boiler,12,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"C1200W",boiler,12,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"C1200W",boiler,12,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"C1200W",boiler,12,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"C1200W",boiler,12,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"C1200W",boiler,12,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"C1200W",boiler,12,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"C1200W",boiler,12,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"C1200W",boiler,12,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"C1200W",boiler,12,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"C1200W",boiler,12,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"C1200W",boiler,12,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"C1200W",boiler,12,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"C1200W",boiler,12,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"C1200W",boiler,12,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"C1200W",boiler,12,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"C1200W",boiler,12,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"C1200W",boiler,12,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"C1200W",boiler,12,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"C1200W",boiler,12,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"C1200W",boiler,12,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"C1200W",boiler,12,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"C1200W",boiler,12,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"C1200W",boiler,12,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"C1200W",boiler,12,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"C1200W",boiler,12,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"C1200W",boiler,12,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"C1200W",boiler,12,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"C1200W",boiler,12,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"C1200W",boiler,12,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"C1200W",boiler,12,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"C1200W",boiler,12,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"C1200W",boiler,12,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"C1200W",boiler,12,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"BK13/BK15, Smartline, GB1*2",boiler,64,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"BK13/BK15, Smartline, GB1*2",boiler,64,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"BK13/BK15, Smartline, GB1*2",boiler,64,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"BK13/BK15, Smartline, GB1*2",boiler,64,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"BK13/BK15, Smartline, GB1*2",boiler,64,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"BK13/BK15, Smartline, GB1*2",boiler,64,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"BK13/BK15, Smartline, GB1*2",boiler,64,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"BK13/BK15, Smartline, GB1*2",boiler,64,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"BK13/BK15, Smartline, GB1*2",boiler,64,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"BK13/BK15, Smartline, GB1*2",boiler,64,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"BK13/BK15, Smartline, GB1*2",boiler,64,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"BK13/BK15, Smartline, GB1*2",boiler,64,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"BK13/BK15, Smartline, GB1*2",boiler,64,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"BK13/BK15, Smartline, GB1*2",boiler,64,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"BK13/BK15, Smartline, GB1*2",boiler,64,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"BK13/BK15, Smartline, GB1*2",boiler,64,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"BK13/BK15, Smartline, GB1*2",boiler,64,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"BK13/BK15, Smartline, GB1*2",boiler,64,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"BK13/BK15, Smartline, GB1*2",boiler,64,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"BK13/BK15, Smartline, GB1*2",boiler,64,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"BK13/BK15, Smartline, GB1*2",boiler,64,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"BK13/BK15, Smartline, GB1*2",boiler,64,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"BK13/BK15, Smartline, GB1*2",boiler,64,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"BK13/BK15, Smartline, GB1*2",boiler,64,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"BK13/BK15, Smartline, GB1*2",boiler,64,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"BK13/BK15, Smartline, GB1*2",boiler,64,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"BK13/BK15, Smartline, GB1*2",boiler,64,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"BK13/BK15, Smartline, GB1*2",boiler,64,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"BK13/BK15, Smartline, GB1*2",boiler,64,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"BK13/BK15, Smartline, GB1*2",boiler,64,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"BK13/BK15, Smartline, GB1*2",boiler,64,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"BK13/BK15, Smartline, GB1*2",boiler,64,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"BK13/BK15, Smartline, GB1*2",boiler,64,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"BK13/BK15, Smartline, GB1*2",boiler,64,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"BK13/BK15, Smartline, GB1*2",boiler,64,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"BK13/BK15, Smartline, GB1*2",boiler,64,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"BK13/BK15, Smartline, GB1*2",boiler,64,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"BK13/BK15, Smartline, GB1*2",boiler,64,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"BK13/BK15, Smartline, GB1*2",boiler,64,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"BK13/BK15, Smartline, GB1*2",boiler,64,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"BK13/BK15, Smartline, GB1*2",boiler,64,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"BK13/BK15, Smartline, GB1*2",boiler,64,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"BK13/BK15, Smartline, GB1*2",boiler,64,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"BK13/BK15, Smartline, GB1*2",boiler,64,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"BK13/BK15, Smartline, GB1*2",boiler,64,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"BK13/BK15, Smartline, GB1*2",boiler,64,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"BK13/BK15, Smartline, GB1*2",boiler,64,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"BK13/BK15, Smartline, GB1*2",boiler,64,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"BK13/BK15, Smartline, GB1*2",boiler,64,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"BK13/BK15, Smartline, GB1*2",boiler,64,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"BK13/BK15, Smartline, GB1*2",boiler,64,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"BK13/BK15, Smartline, GB1*2",boiler,64,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"BK13/BK15, Smartline, GB1*2",boiler,64,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"BK13/BK15, Smartline, GB1*2",boiler,64,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"BK13/BK15, Smartline, GB1*2",boiler,64,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"BK13/BK15, Smartline, GB1*2",boiler,64,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"BK13/BK15, Smartline, GB1*2",boiler,64,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"BK13/BK15, Smartline, GB1*2",boiler,64,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"BK13/BK15, Smartline, GB1*2",boiler,64,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"BK13/BK15, Smartline, GB1*2",boiler,64,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"BK13/BK15, Smartline, GB1*2",boiler,64,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"BK13/BK15, Smartline, GB1*2",boiler,64,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"BK13/BK15, Smartline, GB1*2",boiler,64,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"BK13/BK15, Smartline, GB1*2",boiler,64,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"BK13/BK15, Smartline, GB1*2",boiler,64,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"BK13/BK15, Smartline, GB1*2",boiler,64,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"BK13/BK15, Smartline, GB1*2",boiler,64,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"BK13/BK15, Smartline, GB1*2",boiler,64,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"BK13/BK15, Smartline, GB1*2",boiler,64,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"BK13/BK15, Smartline, GB1*2",boiler,64,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"BK13/BK15, Smartline, GB1*2",boiler,64,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"BK13/BK15, Smartline, GB1*2",boiler,64,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"BK13/BK15, Smartline, GB1*2",boiler,64,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"BK13/BK15, Smartline, GB1*2",boiler,64,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"BK13/BK15, Smartline, GB1*2",boiler,64,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"BK13/BK15, Smartline, GB1*2",boiler,64,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"BK13/BK15, Smartline, GB1*2",boiler,64,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"BK13/BK15, Smartline, GB1*2",boiler,64,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"BK13/BK15, Smartline, GB1*2",boiler,64,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"BK13/BK15, Smartline, GB1*2",boiler,64,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"BK13/BK15, Smartline, GB1*2",boiler,64,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"BK13/BK15, Smartline, GB1*2",boiler,64,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"BK13/BK15, Smartline, GB1*2",boiler,64,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"BK13/BK15, Smartline, GB1*2",boiler,64,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"BK13/BK15, Smartline, GB1*2",boiler,64,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"BK13/BK15, Smartline, GB1*2",boiler,64,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"BK13/BK15, Smartline, GB1*2",boiler,64,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"BK13/BK15, Smartline, GB1*2",boiler,64,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"BK13/BK15, Smartline, GB1*2",boiler,64,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"BK13/BK15, Smartline, GB1*2",boiler,64,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"BK13/BK15, Smartline, GB1*2",boiler,64,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"BK13/BK15, Smartline, GB1*2",boiler,64,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"BK13/BK15, Smartline, GB1*2",boiler,64,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"BK13/BK15, Smartline, GB1*2",boiler,64,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"BK13/BK15, Smartline, GB1*2",boiler,64,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"BK13/BK15, Smartline, GB1*2",boiler,64,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"BK13/BK15, Smartline, GB1*2",boiler,64,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logano GB1*5, Logamatic MC10",boiler,72,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logano GB1*5, Logamatic MC10",boiler,72,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logano GB1*5, Logamatic MC10",boiler,72,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logano GB1*5, Logamatic MC10",boiler,72,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logano GB1*5, Logamatic MC10",boiler,72,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logano GB1*5, Logamatic MC10",boiler,72,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logano GB1*5, Logamatic MC10",boiler,72,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logano GB1*5, Logamatic MC10",boiler,72,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logano GB1*5, Logamatic MC10",boiler,72,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logano GB1*5, Logamatic MC10",boiler,72,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logano GB1*5, Logamatic MC10",boiler,72,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logano GB1*5, Logamatic MC10",boiler,72,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logano GB1*5, Logamatic MC10",boiler,72,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logano GB1*5, Logamatic MC10",boiler,72,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logano GB1*5, Logamatic MC10",boiler,72,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logano GB1*5, Logamatic MC10",boiler,72,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logano GB1*5, Logamatic MC10",boiler,72,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logano GB1*5, Logamatic MC10",boiler,72,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logano GB1*5, Logamatic MC10",boiler,72,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logano GB1*5, Logamatic MC10",boiler,72,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logano GB1*5, Logamatic MC10",boiler,72,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logano GB1*5, Logamatic MC10",boiler,72,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logano GB1*5, Logamatic MC10",boiler,72,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logano GB1*5, Logamatic MC10",boiler,72,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logano GB1*5, Logamatic MC10",boiler,72,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logano GB1*5, Logamatic MC10",boiler,72,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logano GB1*5, Logamatic MC10",boiler,72,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logano GB1*5, Logamatic MC10",boiler,72,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logano GB1*5, Logamatic MC10",boiler,72,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logano GB1*5, Logamatic MC10",boiler,72,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logano GB1*5, Logamatic MC10",boiler,72,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logano GB1*5, Logamatic MC10",boiler,72,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logano GB1*5, Logamatic MC10",boiler,72,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logano GB1*5, Logamatic MC10",boiler,72,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logano GB1*5, Logamatic MC10",boiler,72,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logano GB1*5, Logamatic MC10",boiler,72,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logano GB1*5, Logamatic MC10",boiler,72,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logano GB1*5, Logamatic MC10",boiler,72,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logano GB1*5, Logamatic MC10",boiler,72,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logano GB1*5, Logamatic MC10",boiler,72,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logano GB1*5, Logamatic MC10",boiler,72,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logano GB1*5, Logamatic MC10",boiler,72,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logano GB1*5, Logamatic MC10",boiler,72,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logano GB1*5, Logamatic MC10",boiler,72,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logano GB1*5, Logamatic MC10",boiler,72,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logano GB1*5, Logamatic MC10",boiler,72,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logano GB1*5, Logamatic MC10",boiler,72,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logano GB1*5, Logamatic MC10",boiler,72,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logano GB1*5, Logamatic MC10",boiler,72,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logano GB1*5, Logamatic MC10",boiler,72,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logano GB1*5, Logamatic MC10",boiler,72,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logano GB1*5, Logamatic MC10",boiler,72,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logano GB1*5, Logamatic MC10",boiler,72,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logano GB1*5, Logamatic MC10",boiler,72,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logano GB1*5, Logamatic MC10",boiler,72,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logano GB1*5, Logamatic MC10",boiler,72,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logano GB1*5, Logamatic MC10",boiler,72,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logano GB1*5, Logamatic MC10",boiler,72,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logano GB1*5, Logamatic MC10",boiler,72,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logano GB1*5, Logamatic MC10",boiler,72,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logano GB1*5, Logamatic MC10",boiler,72,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logano GB1*5, Logamatic MC10",boiler,72,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logano GB1*5, Logamatic MC10",boiler,72,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logano GB1*5, Logamatic MC10",boiler,72,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logano GB1*5, Logamatic MC10",boiler,72,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logano GB1*5, Logamatic MC10",boiler,72,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logano GB1*5, Logamatic MC10",boiler,72,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logano GB1*5, Logamatic MC10",boiler,72,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logano GB1*5, Logamatic MC10",boiler,72,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logano GB1*5, Logamatic MC10",boiler,72,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logano GB1*5, Logamatic MC10",boiler,72,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logano GB1*5, Logamatic MC10",boiler,72,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logano GB1*5, Logamatic MC10",boiler,72,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logano GB1*5, Logamatic MC10",boiler,72,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logano GB1*5, Logamatic MC10",boiler,72,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logano GB1*5, Logamatic MC10",boiler,72,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logano GB1*5, Logamatic MC10",boiler,72,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logano GB1*5, Logamatic MC10",boiler,72,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logano GB1*5, Logamatic MC10",boiler,72,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logano GB1*5, Logamatic MC10",boiler,72,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logano GB1*5, Logamatic MC10",boiler,72,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logano GB1*5, Logamatic MC10",boiler,72,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logano GB1*5, Logamatic MC10",boiler,72,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logano GB1*5, Logamatic MC10",boiler,72,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logano GB1*5, Logamatic MC10",boiler,72,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logano GB1*5, Logamatic MC10",boiler,72,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logano GB1*5, Logamatic MC10",boiler,72,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logano GB1*5, Logamatic MC10",boiler,72,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logano GB1*5, Logamatic MC10",boiler,72,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logano GB1*5, Logamatic MC10",boiler,72,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logano GB1*5, Logamatic MC10",boiler,72,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logano GB1*5, Logamatic MC10",boiler,72,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logano GB1*5, Logamatic MC10",boiler,72,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logano GB1*5, Logamatic MC10",boiler,72,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logano GB1*5, Logamatic MC10",boiler,72,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logano GB1*5, Logamatic MC10",boiler,72,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logano GB1*5, Logamatic MC10",boiler,72,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logano GB1*5, Logamatic MC10",boiler,72,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logano GB1*5, Logamatic MC10",boiler,72,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logano GB1*5, Logamatic MC10",boiler,72,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logano GB1*5, Logamatic MC10",boiler,72,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logano GB1*5, Logamatic MC10",boiler,72,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logano GB1*5, Logamatic MC10",boiler,72,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logano GB1*5, Logamatic MC10",boiler,72,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Cascade CM10",boiler,81,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Cascade CM10",boiler,81,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Cascade CM10",boiler,81,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Cascade CM10",boiler,81,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Cascade CM10",boiler,81,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Cascade CM10",boiler,81,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Cascade CM10",boiler,81,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Cascade CM10",boiler,81,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Cascade CM10",boiler,81,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Cascade CM10",boiler,81,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Cascade CM10",boiler,81,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Cascade CM10",boiler,81,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Cascade CM10",boiler,81,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Cascade CM10",boiler,81,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Cascade CM10",boiler,81,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Cascade CM10",boiler,81,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Cascade CM10",boiler,81,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Cascade CM10",boiler,81,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Cascade CM10",boiler,81,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Cascade CM10",boiler,81,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Cascade CM10",boiler,81,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Cascade CM10",boiler,81,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Cascade CM10",boiler,81,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Cascade CM10",boiler,81,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Cascade CM10",boiler,81,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Cascade CM10",boiler,81,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Cascade CM10",boiler,81,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Cascade CM10",boiler,81,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Cascade CM10",boiler,81,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Cascade CM10",boiler,81,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Cascade CM10",boiler,81,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Cascade CM10",boiler,81,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Cascade CM10",boiler,81,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Cascade CM10",boiler,81,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Cascade CM10",boiler,81,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Cascade CM10",boiler,81,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Cascade CM10",boiler,81,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Cascade CM10",boiler,81,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Cascade CM10",boiler,81,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Cascade CM10",boiler,81,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Cascade CM10",boiler,81,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Cascade CM10",boiler,81,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Cascade CM10",boiler,81,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Cascade CM10",boiler,81,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Cascade CM10",boiler,81,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Cascade CM10",boiler,81,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Cascade CM10",boiler,81,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Cascade CM10",boiler,81,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Cascade CM10",boiler,81,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Cascade CM10",boiler,81,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Cascade CM10",boiler,81,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Cascade CM10",boiler,81,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Cascade CM10",boiler,81,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Cascade CM10",boiler,81,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Cascade CM10",boiler,81,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Cascade CM10",boiler,81,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Cascade CM10",boiler,81,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Cascade CM10",boiler,81,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Cascade CM10",boiler,81,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Cascade CM10",boiler,81,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Cascade CM10",boiler,81,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Cascade CM10",boiler,81,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Cascade CM10",boiler,81,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Cascade CM10",boiler,81,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Cascade CM10",boiler,81,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Cascade CM10",boiler,81,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Cascade CM10",boiler,81,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Cascade CM10",boiler,81,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Cascade CM10",boiler,81,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Cascade CM10",boiler,81,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Cascade CM10",boiler,81,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Cascade CM10",boiler,81,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Cascade CM10",boiler,81,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Cascade CM10",boiler,81,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Cascade CM10",boiler,81,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Cascade CM10",boiler,81,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Cascade CM10",boiler,81,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Cascade CM10",boiler,81,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Cascade CM10",boiler,81,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Cascade CM10",boiler,81,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Cascade CM10",boiler,81,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Cascade CM10",boiler,81,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Cascade CM10",boiler,81,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Cascade CM10",boiler,81,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Cascade CM10",boiler,81,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Cascade CM10",boiler,81,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Cascade CM10",boiler,81,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Cascade CM10",boiler,81,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Cascade CM10",boiler,81,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Cascade CM10",boiler,81,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Cascade CM10",boiler,81,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Cascade CM10",boiler,81,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Cascade CM10",boiler,81,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Cascade CM10",boiler,81,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Cascade CM10",boiler,81,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Cascade CM10",boiler,81,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Cascade CM10",boiler,81,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Cascade CM10",boiler,81,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Cascade CM10",boiler,81,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Cascade CM10",boiler,81,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Cascade CM10",boiler,81,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Cascade CM10",boiler,81,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Cascade CM10",boiler,81,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Cascade CM10",boiler,81,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Cascade CM10",boiler,81,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Cascade CM10",boiler,81,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Cascade CM10",boiler,81,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Cascade CM10",boiler,81,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Cascade CM10",boiler,81,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Cascade CM10",boiler,81,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logamax Plus GB022",boiler,84,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logamax Plus GB022",boiler,84,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logamax Plus GB022",boiler,84,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logamax Plus GB022",boiler,84,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logamax Plus GB022",boiler,84,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logamax Plus GB022",boiler,84,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logamax Plus GB022",boiler,84,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logamax Plus GB022",boiler,84,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logamax Plus GB022",boiler,84,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logamax Plus GB022",boiler,84,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logamax Plus GB022",boiler,84,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logamax Plus GB022",boiler,84,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logamax Plus GB022",boiler,84,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logamax Plus GB022",boiler,84,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logamax Plus GB022",boiler,84,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logamax Plus GB022",boiler,84,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logamax Plus GB022",boiler,84,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logamax Plus GB022",boiler,84,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logamax Plus GB022",boiler,84,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logamax Plus GB022",boiler,84,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logamax Plus GB022",boiler,84,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logamax Plus GB022",boiler,84,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logamax Plus GB022",boiler,84,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logamax Plus GB022",boiler,84,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logamax Plus GB022",boiler,84,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logamax Plus GB022",boiler,84,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logamax Plus GB022",boiler,84,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logamax Plus GB022",boiler,84,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logamax Plus GB022",boiler,84,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logamax Plus GB022",boiler,84,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logamax Plus GB022",boiler,84,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logamax Plus GB022",boiler,84,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logamax Plus GB022",boiler,84,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logamax Plus GB022",boiler,84,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logamax Plus GB022",boiler,84,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logamax Plus GB022",boiler,84,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logamax Plus GB022",boiler,84,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logamax Plus GB022",boiler,84,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logamax Plus GB022",boiler,84,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logamax Plus GB022",boiler,84,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logamax Plus GB022",boiler,84,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logamax Plus GB022",boiler,84,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logamax Plus GB022",boiler,84,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logamax Plus GB022",boiler,84,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logamax Plus GB022",boiler,84,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logamax Plus GB022",boiler,84,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logamax Plus GB022",boiler,84,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logamax Plus GB022",boiler,84,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logamax Plus GB022",boiler,84,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logamax Plus GB022",boiler,84,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logamax Plus GB022",boiler,84,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logamax Plus GB022",boiler,84,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logamax Plus GB022",boiler,84,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logamax Plus GB022",boiler,84,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logamax Plus GB022",boiler,84,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logamax Plus GB022",boiler,84,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logamax Plus GB022",boiler,84,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logamax Plus GB022",boiler,84,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logamax Plus GB022",boiler,84,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logamax Plus GB022",boiler,84,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logamax Plus GB022",boiler,84,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logamax Plus GB022",boiler,84,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logamax Plus GB022",boiler,84,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logamax Plus GB022",boiler,84,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logamax Plus GB022",boiler,84,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logamax Plus GB022",boiler,84,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logamax Plus GB022",boiler,84,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logamax Plus GB022",boiler,84,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logamax Plus GB022",boiler,84,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logamax Plus GB022",boiler,84,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logamax Plus GB022",boiler,84,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logamax Plus GB022",boiler,84,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logamax Plus GB022",boiler,84,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logamax Plus GB022",boiler,84,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logamax Plus GB022",boiler,84,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logamax Plus GB022",boiler,84,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logamax Plus GB022",boiler,84,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logamax Plus GB022",boiler,84,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logamax Plus GB022",boiler,84,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logamax Plus GB022",boiler,84,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logamax Plus GB022",boiler,84,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logamax Plus GB022",boiler,84,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logamax Plus GB022",boiler,84,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logamax Plus GB022",boiler,84,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logamax Plus GB022",boiler,84,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logamax Plus GB022",boiler,84,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logamax Plus GB022",boiler,84,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logamax Plus GB022",boiler,84,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logamax Plus GB022",boiler,84,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logamax Plus GB022",boiler,84,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logamax Plus GB022",boiler,84,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logamax Plus GB022",boiler,84,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logamax Plus GB022",boiler,84,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logamax Plus GB022",boiler,84,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logamax Plus GB022",boiler,84,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logamax Plus GB022",boiler,84,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logamax Plus GB022",boiler,84,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logamax Plus GB022",boiler,84,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logamax Plus GB022",boiler,84,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logamax Plus GB022",boiler,84,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logamax Plus GB022",boiler,84,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logamax Plus GB022",boiler,84,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logamax Plus GB022",boiler,84,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logamax Plus GB022",boiler,84,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logamax Plus GB022",boiler,84,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logamax Plus GB022",boiler,84,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logamax Plus GB022",boiler,84,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logamax Plus GB022",boiler,84,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logamax Plus GB022",boiler,84,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logamax Plus GB022",boiler,84,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Condens, Logamax/Logomatic, Cerapur Top, Greenstar, Generic HT3",boiler,95,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Topline, GB162",boiler,115,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Topline, GB162",boiler,115,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Topline, GB162",boiler,115,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Topline, GB162",boiler,115,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Topline, GB162",boiler,115,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Topline, GB162",boiler,115,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Topline, GB162",boiler,115,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Topline, GB162",boiler,115,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Topline, GB162",boiler,115,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Topline, GB162",boiler,115,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Topline, GB162",boiler,115,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Topline, GB162",boiler,115,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Topline, GB162",boiler,115,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Topline, GB162",boiler,115,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Topline, GB162",boiler,115,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Topline, GB162",boiler,115,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Topline, GB162",boiler,115,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Topline, GB162",boiler,115,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Topline, GB162",boiler,115,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Topline, GB162",boiler,115,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Topline, GB162",boiler,115,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Topline, GB162",boiler,115,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Topline, GB162",boiler,115,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Topline, GB162",boiler,115,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Topline, GB162",boiler,115,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Topline, GB162",boiler,115,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Topline, GB162",boiler,115,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Topline, GB162",boiler,115,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Topline, GB162",boiler,115,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Topline, GB162",boiler,115,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Topline, GB162",boiler,115,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Topline, GB162",boiler,115,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Topline, GB162",boiler,115,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Topline, GB162",boiler,115,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Topline, GB162",boiler,115,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Topline, GB162",boiler,115,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Topline, GB162",boiler,115,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Topline, GB162",boiler,115,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Topline, GB162",boiler,115,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Topline, GB162",boiler,115,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Topline, GB162",boiler,115,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Topline, GB162",boiler,115,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Topline, GB162",boiler,115,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Topline, GB162",boiler,115,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Topline, GB162",boiler,115,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Topline, GB162",boiler,115,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Topline, GB162",boiler,115,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Topline, GB162",boiler,115,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Topline, GB162",boiler,115,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Topline, GB162",boiler,115,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Topline, GB162",boiler,115,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Topline, GB162",boiler,115,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Topline, GB162",boiler,115,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Topline, GB162",boiler,115,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Topline, GB162",boiler,115,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Topline, GB162",boiler,115,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Topline, GB162",boiler,115,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Topline, GB162",boiler,115,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Topline, GB162",boiler,115,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Topline, GB162",boiler,115,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Topline, GB162",boiler,115,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Topline, GB162",boiler,115,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Topline, GB162",boiler,115,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Topline, GB162",boiler,115,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Topline, GB162",boiler,115,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Topline, GB162",boiler,115,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Topline, GB162",boiler,115,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Topline, GB162",boiler,115,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Topline, GB162",boiler,115,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Topline, GB162",boiler,115,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Topline, GB162",boiler,115,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Topline, GB162",boiler,115,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Topline, GB162",boiler,115,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Topline, GB162",boiler,115,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Topline, GB162",boiler,115,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Topline, GB162",boiler,115,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Topline, GB162",boiler,115,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Topline, GB162",boiler,115,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Topline, GB162",boiler,115,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Topline, GB162",boiler,115,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Topline, GB162",boiler,115,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Topline, GB162",boiler,115,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Topline, GB162",boiler,115,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Topline, GB162",boiler,115,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Topline, GB162",boiler,115,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Topline, GB162",boiler,115,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Topline, GB162",boiler,115,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Topline, GB162",boiler,115,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Topline, GB162",boiler,115,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Topline, GB162",boiler,115,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Topline, GB162",boiler,115,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Topline, GB162",boiler,115,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Topline, GB162",boiler,115,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Topline, GB162",boiler,115,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Topline, GB162",boiler,115,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Topline, GB162",boiler,115,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Topline, GB162",boiler,115,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Topline, GB162",boiler,115,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Topline, GB162",boiler,115,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Topline, GB162",boiler,115,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Topline, GB162",boiler,115,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Topline, GB162",boiler,115,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Topline, GB162",boiler,115,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Topline, GB162",boiler,115,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Topline, GB162",boiler,115,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Topline, GB162",boiler,115,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Topline, GB162",boiler,115,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Topline, GB162",boiler,115,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Topline, GB162",boiler,115,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Topline, GB162",boiler,115,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Cascade MCM10",boiler,121,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Cascade MCM10",boiler,121,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Cascade MCM10",boiler,121,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Cascade MCM10",boiler,121,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Cascade MCM10",boiler,121,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Cascade MCM10",boiler,121,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Cascade MCM10",boiler,121,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Cascade MCM10",boiler,121,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Cascade MCM10",boiler,121,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Cascade MCM10",boiler,121,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Cascade MCM10",boiler,121,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Cascade MCM10",boiler,121,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Cascade MCM10",boiler,121,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Cascade MCM10",boiler,121,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Cascade MCM10",boiler,121,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Cascade MCM10",boiler,121,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Cascade MCM10",boiler,121,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Cascade MCM10",boiler,121,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Cascade MCM10",boiler,121,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Cascade MCM10",boiler,121,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Cascade MCM10",boiler,121,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Cascade MCM10",boiler,121,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Cascade MCM10",boiler,121,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Cascade MCM10",boiler,121,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Cascade MCM10",boiler,121,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Cascade MCM10",boiler,121,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Cascade MCM10",boiler,121,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Cascade MCM10",boiler,121,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Cascade MCM10",boiler,121,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Cascade MCM10",boiler,121,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Cascade MCM10",boiler,121,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Cascade MCM10",boiler,121,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Cascade MCM10",boiler,121,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Cascade MCM10",boiler,121,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Cascade MCM10",boiler,121,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Cascade MCM10",boiler,121,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Cascade MCM10",boiler,121,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Cascade MCM10",boiler,121,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Cascade MCM10",boiler,121,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Cascade MCM10",boiler,121,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Cascade MCM10",boiler,121,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Cascade MCM10",boiler,121,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Cascade MCM10",boiler,121,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Cascade MCM10",boiler,121,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Cascade MCM10",boiler,121,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Cascade MCM10",boiler,121,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Cascade MCM10",boiler,121,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Cascade MCM10",boiler,121,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Cascade MCM10",boiler,121,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Cascade MCM10",boiler,121,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Cascade MCM10",boiler,121,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Cascade MCM10",boiler,121,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Cascade MCM10",boiler,121,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Cascade MCM10",boiler,121,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Cascade MCM10",boiler,121,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Cascade MCM10",boiler,121,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Cascade MCM10",boiler,121,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Cascade MCM10",boiler,121,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Cascade MCM10",boiler,121,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Cascade MCM10",boiler,121,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Cascade MCM10",boiler,121,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Cascade MCM10",boiler,121,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Cascade MCM10",boiler,121,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Cascade MCM10",boiler,121,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Cascade MCM10",boiler,121,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Cascade MCM10",boiler,121,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Cascade MCM10",boiler,121,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Cascade MCM10",boiler,121,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Cascade MCM10",boiler,121,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Cascade MCM10",boiler,121,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Cascade MCM10",boiler,121,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Cascade MCM10",boiler,121,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Cascade MCM10",boiler,121,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Cascade MCM10",boiler,121,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Cascade MCM10",boiler,121,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Cascade MCM10",boiler,121,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Cascade MCM10",boiler,121,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Cascade MCM10",boiler,121,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Cascade MCM10",boiler,121,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Cascade MCM10",boiler,121,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Cascade MCM10",boiler,121,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Cascade MCM10",boiler,121,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Cascade MCM10",boiler,121,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Cascade MCM10",boiler,121,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Cascade MCM10",boiler,121,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Cascade MCM10",boiler,121,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Cascade MCM10",boiler,121,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Cascade MCM10",boiler,121,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Cascade MCM10",boiler,121,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Cascade MCM10",boiler,121,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Cascade MCM10",boiler,121,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Cascade MCM10",boiler,121,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Cascade MCM10",boiler,121,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Cascade MCM10",boiler,121,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Cascade MCM10",boiler,121,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Cascade MCM10",boiler,121,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Cascade MCM10",boiler,121,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Cascade MCM10",boiler,121,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Cascade MCM10",boiler,121,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Cascade MCM10",boiler,121,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Cascade MCM10",boiler,121,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Cascade MCM10",boiler,121,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Cascade MCM10",boiler,121,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Cascade MCM10",boiler,121,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Cascade MCM10",boiler,121,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Cascade MCM10",boiler,121,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Cascade MCM10",boiler,121,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Cascade MCM10",boiler,121,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Cascade MCM10",boiler,121,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Cascade MCM10",boiler,121,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Proline",boiler,122,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Proline",boiler,122,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Proline",boiler,122,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Proline",boiler,122,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Proline",boiler,122,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Proline",boiler,122,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Proline",boiler,122,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Proline",boiler,122,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Proline",boiler,122,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Proline",boiler,122,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Proline",boiler,122,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Proline",boiler,122,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Proline",boiler,122,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Proline",boiler,122,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Proline",boiler,122,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Proline",boiler,122,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Proline",boiler,122,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Proline",boiler,122,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Proline",boiler,122,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Proline",boiler,122,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Proline",boiler,122,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Proline",boiler,122,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Proline",boiler,122,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Proline",boiler,122,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Proline",boiler,122,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Proline",boiler,122,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Proline",boiler,122,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Proline",boiler,122,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Proline",boiler,122,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Proline",boiler,122,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Proline",boiler,122,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Proline",boiler,122,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Proline",boiler,122,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Proline",boiler,122,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Proline",boiler,122,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Proline",boiler,122,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Proline",boiler,122,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Proline",boiler,122,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Proline",boiler,122,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Proline",boiler,122,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Proline",boiler,122,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Proline",boiler,122,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Proline",boiler,122,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Proline",boiler,122,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Proline",boiler,122,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Proline",boiler,122,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Proline",boiler,122,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Proline",boiler,122,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Proline",boiler,122,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Proline",boiler,122,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Proline",boiler,122,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Proline",boiler,122,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Proline",boiler,122,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Proline",boiler,122,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Proline",boiler,122,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Proline",boiler,122,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Proline",boiler,122,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Proline",boiler,122,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Proline",boiler,122,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Proline",boiler,122,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Proline",boiler,122,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Proline",boiler,122,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Proline",boiler,122,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Proline",boiler,122,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Proline",boiler,122,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Proline",boiler,122,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Proline",boiler,122,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Proline",boiler,122,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Proline",boiler,122,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Proline",boiler,122,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Proline",boiler,122,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Proline",boiler,122,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Proline",boiler,122,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Proline",boiler,122,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Proline",boiler,122,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Proline",boiler,122,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Proline",boiler,122,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Proline",boiler,122,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Proline",boiler,122,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Proline",boiler,122,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Proline",boiler,122,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Proline",boiler,122,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Proline",boiler,122,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Proline",boiler,122,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Proline",boiler,122,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Proline",boiler,122,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Proline",boiler,122,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Proline",boiler,122,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Proline",boiler,122,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Proline",boiler,122,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Proline",boiler,122,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Proline",boiler,122,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Proline",boiler,122,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Proline",boiler,122,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Proline",boiler,122,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Proline",boiler,122,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Proline",boiler,122,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Proline",boiler,122,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Proline",boiler,122,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Proline",boiler,122,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Proline",boiler,122,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Proline",boiler,122,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Proline",boiler,122,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Proline",boiler,122,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Proline",boiler,122,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Proline",boiler,122,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Proline",boiler,122,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Proline",boiler,122,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Proline",boiler,122,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Proline",boiler,122,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"GB*72, Trendline, Cerapur, Greenstar Si",boiler,123,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"GB212",boiler,131,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"GB212",boiler,131,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"GB212",boiler,131,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"GB212",boiler,131,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"GB212",boiler,131,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"GB212",boiler,131,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"GB212",boiler,131,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"GB212",boiler,131,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"GB212",boiler,131,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"GB212",boiler,131,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"GB212",boiler,131,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"GB212",boiler,131,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"GB212",boiler,131,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"GB212",boiler,131,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"GB212",boiler,131,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"GB212",boiler,131,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"GB212",boiler,131,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"GB212",boiler,131,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"GB212",boiler,131,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"GB212",boiler,131,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"GB212",boiler,131,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"GB212",boiler,131,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"GB212",boiler,131,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"GB212",boiler,131,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"GB212",boiler,131,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"GB212",boiler,131,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"GB212",boiler,131,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"GB212",boiler,131,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"GB212",boiler,131,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"GB212",boiler,131,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"GB212",boiler,131,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"GB212",boiler,131,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"GB212",boiler,131,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"GB212",boiler,131,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"GB212",boiler,131,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"GB212",boiler,131,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"GB212",boiler,131,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"GB212",boiler,131,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"GB212",boiler,131,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"GB212",boiler,131,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"GB212",boiler,131,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"GB212",boiler,131,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"GB212",boiler,131,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"GB212",boiler,131,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"GB212",boiler,131,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"GB212",boiler,131,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"GB212",boiler,131,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"GB212",boiler,131,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"GB212",boiler,131,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"GB212",boiler,131,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"GB212",boiler,131,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"GB212",boiler,131,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"GB212",boiler,131,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"GB212",boiler,131,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"GB212",boiler,131,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"GB212",boiler,131,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"GB212",boiler,131,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"GB212",boiler,131,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"GB212",boiler,131,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"GB212",boiler,131,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"GB212",boiler,131,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"GB212",boiler,131,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"GB212",boiler,131,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"GB212",boiler,131,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"GB212",boiler,131,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"GB212",boiler,131,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"GB212",boiler,131,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"GB212",boiler,131,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"GB212",boiler,131,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"GB212",boiler,131,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"GB212",boiler,131,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"GB212",boiler,131,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"GB212",boiler,131,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"GB212",boiler,131,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"GB212",boiler,131,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"GB212",boiler,131,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"GB212",boiler,131,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"GB212",boiler,131,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"GB212",boiler,131,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"GB212",boiler,131,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"GB212",boiler,131,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"GB212",boiler,131,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"GB212",boiler,131,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"GB212",boiler,131,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"GB212",boiler,131,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"GB212",boiler,131,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"GB212",boiler,131,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"GB212",boiler,131,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"GB212",boiler,131,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"GB212",boiler,131,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"GB212",boiler,131,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"GB212",boiler,131,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"GB212",boiler,131,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"GB212",boiler,131,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"GB212",boiler,131,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"GB212",boiler,131,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"GB212",boiler,131,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"GB212",boiler,131,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"GB212",boiler,131,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"GB212",boiler,131,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"GB212",boiler,131,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"GB212",boiler,131,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"GB212",boiler,131,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"GB212",boiler,131,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"GB212",boiler,131,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"GB212",boiler,131,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"GB212",boiler,131,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"GB212",boiler,131,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"GB212",boiler,131,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"GB212",boiler,131,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"GC7000F",boiler,132,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"GC7000F",boiler,132,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"GC7000F",boiler,132,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"GC7000F",boiler,132,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"GC7000F",boiler,132,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"GC7000F",boiler,132,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"GC7000F",boiler,132,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"GC7000F",boiler,132,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"GC7000F",boiler,132,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"GC7000F",boiler,132,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"GC7000F",boiler,132,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"GC7000F",boiler,132,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"GC7000F",boiler,132,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"GC7000F",boiler,132,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"GC7000F",boiler,132,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"GC7000F",boiler,132,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"GC7000F",boiler,132,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"GC7000F",boiler,132,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"GC7000F",boiler,132,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"GC7000F",boiler,132,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"GC7000F",boiler,132,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"GC7000F",boiler,132,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"GC7000F",boiler,132,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"GC7000F",boiler,132,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"GC7000F",boiler,132,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"GC7000F",boiler,132,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"GC7000F",boiler,132,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"GC7000F",boiler,132,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"GC7000F",boiler,132,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"GC7000F",boiler,132,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"GC7000F",boiler,132,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"GC7000F",boiler,132,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"GC7000F",boiler,132,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"GC7000F",boiler,132,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"GC7000F",boiler,132,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"GC7000F",boiler,132,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"GC7000F",boiler,132,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"GC7000F",boiler,132,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"GC7000F",boiler,132,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"GC7000F",boiler,132,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"GC7000F",boiler,132,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"GC7000F",boiler,132,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"GC7000F",boiler,132,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"GC7000F",boiler,132,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"GC7000F",boiler,132,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"GC7000F",boiler,132,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"GC7000F",boiler,132,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"GC7000F",boiler,132,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"GC7000F",boiler,132,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"GC7000F",boiler,132,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"GC7000F",boiler,132,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"GC7000F",boiler,132,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"GC7000F",boiler,132,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"GC7000F",boiler,132,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"GC7000F",boiler,132,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"GC7000F",boiler,132,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"GC7000F",boiler,132,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"GC7000F",boiler,132,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"GC7000F",boiler,132,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"GC7000F",boiler,132,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"GC7000F",boiler,132,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"GC7000F",boiler,132,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"GC7000F",boiler,132,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"GC7000F",boiler,132,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"GC7000F",boiler,132,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"GC7000F",boiler,132,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"GC7000F",boiler,132,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"GC7000F",boiler,132,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"GC7000F",boiler,132,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"GC7000F",boiler,132,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"GC7000F",boiler,132,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"GC7000F",boiler,132,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"GC7000F",boiler,132,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"GC7000F",boiler,132,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"GC7000F",boiler,132,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"GC7000F",boiler,132,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"GC7000F",boiler,132,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"GC7000F",boiler,132,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"GC7000F",boiler,132,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"GC7000F",boiler,132,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"GC7000F",boiler,132,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"GC7000F",boiler,132,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"GC7000F",boiler,132,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"GC7000F",boiler,132,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"GC7000F",boiler,132,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"GC7000F",boiler,132,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"GC7000F",boiler,132,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"GC7000F",boiler,132,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"GC7000F",boiler,132,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"GC7000F",boiler,132,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"GC7000F",boiler,132,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"GC7000F",boiler,132,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"GC7000F",boiler,132,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"GC7000F",boiler,132,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"GC7000F",boiler,132,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"GC7000F",boiler,132,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"GC7000F",boiler,132,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"GC7000F",boiler,132,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"GC7000F",boiler,132,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"GC7000F",boiler,132,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"GC7000F",boiler,132,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"GC7000F",boiler,132,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"GC7000F",boiler,132,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"GC7000F",boiler,132,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"GC7000F",boiler,132,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"GC7000F",boiler,132,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"GC7000F",boiler,132,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"GC7000F",boiler,132,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"GC7000F",boiler,132,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"GC7000F",boiler,132,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logano GB125/KB195i, Logamatic MC110",boiler,133,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logano GB125/KB195i, Logamatic MC110",boiler,133,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logano GB125/KB195i, Logamatic MC110",boiler,133,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Greenstar 30Ri Compact",boiler,154,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Greenstar 30Ri Compact",boiler,154,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Greenstar 30Ri Compact",boiler,154,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Greenstar 30Ri Compact",boiler,154,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Greenstar 30Ri Compact",boiler,154,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Greenstar 30Ri Compact",boiler,154,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Greenstar 30Ri Compact",boiler,154,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Greenstar 30Ri Compact",boiler,154,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Greenstar 30Ri Compact",boiler,154,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Greenstar 30Ri Compact",boiler,154,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Greenstar 30Ri Compact",boiler,154,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Greenstar 30Ri Compact",boiler,154,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Greenstar 30Ri Compact",boiler,154,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Greenstar 30Ri Compact",boiler,154,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Greenstar 30Ri Compact",boiler,154,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Greenstar 30Ri Compact",boiler,154,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Greenstar 30Ri Compact",boiler,154,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Greenstar 30Ri Compact",boiler,154,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Greenstar 30Ri Compact",boiler,154,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Greenstar 30Ri Compact",boiler,154,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Greenstar 30Ri Compact",boiler,154,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Greenstar 30Ri Compact",boiler,154,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Greenstar 30Ri Compact",boiler,154,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Greenstar 30Ri Compact",boiler,154,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Greenstar 30Ri Compact",boiler,154,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Greenstar 30Ri Compact",boiler,154,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Greenstar 30Ri Compact",boiler,154,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Greenstar 30Ri Compact",boiler,154,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Greenstar 30Ri Compact",boiler,154,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Greenstar 30Ri Compact",boiler,154,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Greenstar 30Ri Compact",boiler,154,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Greenstar 30Ri Compact",boiler,154,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Greenstar 30Ri Compact",boiler,154,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Greenstar 30Ri Compact",boiler,154,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Greenstar 30Ri Compact",boiler,154,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Greenstar 30Ri Compact",boiler,154,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Greenstar 30Ri Compact",boiler,154,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Greenstar 30Ri Compact",boiler,154,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Greenstar 30Ri Compact",boiler,154,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Greenstar 30Ri Compact",boiler,154,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Greenstar 30Ri Compact",boiler,154,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Greenstar 30Ri Compact",boiler,154,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Greenstar 30Ri Compact",boiler,154,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Greenstar 30Ri Compact",boiler,154,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Greenstar 30Ri Compact",boiler,154,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Greenstar 30Ri Compact",boiler,154,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Greenstar 30Ri Compact",boiler,154,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Greenstar 30Ri Compact",boiler,154,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Greenstar 30Ri Compact",boiler,154,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Greenstar 30Ri Compact",boiler,154,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Greenstar 30Ri Compact",boiler,154,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Greenstar 30Ri Compact",boiler,154,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Greenstar 30Ri Compact",boiler,154,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Greenstar 30Ri Compact",boiler,154,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Greenstar 30Ri Compact",boiler,154,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Greenstar 30Ri Compact",boiler,154,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Greenstar 30Ri Compact",boiler,154,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Greenstar 30Ri Compact",boiler,154,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Greenstar 30Ri Compact",boiler,154,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Greenstar 30Ri Compact",boiler,154,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Greenstar 30Ri Compact",boiler,154,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Greenstar 30Ri Compact",boiler,154,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Greenstar 30Ri Compact",boiler,154,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Greenstar 30Ri Compact",boiler,154,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Greenstar 30Ri Compact",boiler,154,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Greenstar 30Ri Compact",boiler,154,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Greenstar 30Ri Compact",boiler,154,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Greenstar 30Ri Compact",boiler,154,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Greenstar 30Ri Compact",boiler,154,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Greenstar 30Ri Compact",boiler,154,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Greenstar 30Ri Compact",boiler,154,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Greenstar 30Ri Compact",boiler,154,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Greenstar 30Ri Compact",boiler,154,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Greenstar 30Ri Compact",boiler,154,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Greenstar 30Ri Compact",boiler,154,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Greenstar 30Ri Compact",boiler,154,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Greenstar 30Ri Compact",boiler,154,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Greenstar 30Ri Compact",boiler,154,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Greenstar 30Ri Compact",boiler,154,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Greenstar 30Ri Compact",boiler,154,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Greenstar 30Ri Compact",boiler,154,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Greenstar 30Ri Compact",boiler,154,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Greenstar 30Ri Compact",boiler,154,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Greenstar 30Ri Compact",boiler,154,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Greenstar 30Ri Compact",boiler,154,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Greenstar 30Ri Compact",boiler,154,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Greenstar 30Ri Compact",boiler,154,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Greenstar 30Ri Compact",boiler,154,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Greenstar 30Ri Compact",boiler,154,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Greenstar 30Ri Compact",boiler,154,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Greenstar 30Ri Compact",boiler,154,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Greenstar 30Ri Compact",boiler,154,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Greenstar 30Ri Compact",boiler,154,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Greenstar 30Ri Compact",boiler,154,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Greenstar 30Ri Compact",boiler,154,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Greenstar 30Ri Compact",boiler,154,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Greenstar 30Ri Compact",boiler,154,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Greenstar 30Ri Compact",boiler,154,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Greenstar 30Ri Compact",boiler,154,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Greenstar 30Ri Compact",boiler,154,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Greenstar 30Ri Compact",boiler,154,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Greenstar 30Ri Compact",boiler,154,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Greenstar 30Ri Compact",boiler,154,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Greenstar 30Ri Compact",boiler,154,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Greenstar 30Ri Compact",boiler,154,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Greenstar 30Ri Compact",boiler,154,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Greenstar 30Ri Compact",boiler,154,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Greenstar 30Ri Compact",boiler,154,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Greenstar 30Ri Compact",boiler,154,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Greenstar 30Ri Compact",boiler,154,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Cerapur Aero",boiler,167,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Cerapur Aero",boiler,167,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Cerapur Aero",boiler,167,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Cerapur Aero",boiler,167,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Cerapur Aero",boiler,167,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Cerapur Aero",boiler,167,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Cerapur Aero",boiler,167,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Cerapur Aero",boiler,167,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Cerapur Aero",boiler,167,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Cerapur Aero",boiler,167,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Cerapur Aero",boiler,167,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Cerapur Aero",boiler,167,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Cerapur Aero",boiler,167,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Cerapur Aero",boiler,167,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Cerapur Aero",boiler,167,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Cerapur Aero",boiler,167,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Cerapur Aero",boiler,167,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Cerapur Aero",boiler,167,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Cerapur Aero",boiler,167,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Cerapur Aero",boiler,167,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Cerapur Aero",boiler,167,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Cerapur Aero",boiler,167,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Cerapur Aero",boiler,167,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Cerapur Aero",boiler,167,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Cerapur Aero",boiler,167,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Cerapur Aero",boiler,167,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Cerapur Aero",boiler,167,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Cerapur Aero",boiler,167,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Cerapur Aero",boiler,167,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Cerapur Aero",boiler,167,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Cerapur Aero",boiler,167,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Cerapur Aero",boiler,167,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Cerapur Aero",boiler,167,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Cerapur Aero",boiler,167,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Cerapur Aero",boiler,167,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Cerapur Aero",boiler,167,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Cerapur Aero",boiler,167,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Cerapur Aero",boiler,167,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Cerapur Aero",boiler,167,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Cerapur Aero",boiler,167,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Cerapur Aero",boiler,167,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Cerapur Aero",boiler,167,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Cerapur Aero",boiler,167,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Cerapur Aero",boiler,167,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Cerapur Aero",boiler,167,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Cerapur Aero",boiler,167,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Cerapur Aero",boiler,167,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Cerapur Aero",boiler,167,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Cerapur Aero",boiler,167,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Cerapur Aero",boiler,167,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Cerapur Aero",boiler,167,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Cerapur Aero",boiler,167,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Cerapur Aero",boiler,167,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Cerapur Aero",boiler,167,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Cerapur Aero",boiler,167,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Cerapur Aero",boiler,167,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Cerapur Aero",boiler,167,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Cerapur Aero",boiler,167,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Cerapur Aero",boiler,167,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Cerapur Aero",boiler,167,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Cerapur Aero",boiler,167,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Cerapur Aero",boiler,167,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Cerapur Aero",boiler,167,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Cerapur Aero",boiler,167,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Cerapur Aero",boiler,167,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Cerapur Aero",boiler,167,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Cerapur Aero",boiler,167,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Cerapur Aero",boiler,167,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Cerapur Aero",boiler,167,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Cerapur Aero",boiler,167,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Cerapur Aero",boiler,167,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Cerapur Aero",boiler,167,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Cerapur Aero",boiler,167,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Cerapur Aero",boiler,167,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Cerapur Aero",boiler,167,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Cerapur Aero",boiler,167,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Cerapur Aero",boiler,167,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Cerapur Aero",boiler,167,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Cerapur Aero",boiler,167,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Cerapur Aero",boiler,167,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Cerapur Aero",boiler,167,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Cerapur Aero",boiler,167,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Cerapur Aero",boiler,167,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Cerapur Aero",boiler,167,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Cerapur Aero",boiler,167,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Cerapur Aero",boiler,167,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Cerapur Aero",boiler,167,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Cerapur Aero",boiler,167,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Cerapur Aero",boiler,167,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Cerapur Aero",boiler,167,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Cerapur Aero",boiler,167,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Cerapur Aero",boiler,167,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Cerapur Aero",boiler,167,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Cerapur Aero",boiler,167,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Cerapur Aero",boiler,167,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Cerapur Aero",boiler,167,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Cerapur Aero",boiler,167,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Cerapur Aero",boiler,167,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Cerapur Aero",boiler,167,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Cerapur Aero",boiler,167,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Cerapur Aero",boiler,167,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Cerapur Aero",boiler,167,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Cerapur Aero",boiler,167,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Cerapur Aero",boiler,167,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Cerapur Aero",boiler,167,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Cerapur Aero",boiler,167,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Cerapur Aero",boiler,167,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Cerapur Aero",boiler,167,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Cerapur Aero",boiler,167,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Cerapur Aero",boiler,167,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Hybrid Heatpump",boiler,168,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Hybrid Heatpump",boiler,168,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Hybrid Heatpump",boiler,168,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Hybrid Heatpump",boiler,168,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Hybrid Heatpump",boiler,168,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Hybrid Heatpump",boiler,168,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Hybrid Heatpump",boiler,168,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Hybrid Heatpump",boiler,168,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Hybrid Heatpump",boiler,168,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Hybrid Heatpump",boiler,168,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Hybrid Heatpump",boiler,168,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Hybrid Heatpump",boiler,168,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Hybrid Heatpump",boiler,168,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Hybrid Heatpump",boiler,168,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Hybrid Heatpump",boiler,168,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Hybrid Heatpump",boiler,168,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Hybrid Heatpump",boiler,168,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Hybrid Heatpump",boiler,168,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Hybrid Heatpump",boiler,168,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Hybrid Heatpump",boiler,168,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Hybrid Heatpump",boiler,168,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Hybrid Heatpump",boiler,168,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Hybrid Heatpump",boiler,168,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Hybrid Heatpump",boiler,168,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Hybrid Heatpump",boiler,168,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Hybrid Heatpump",boiler,168,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Hybrid Heatpump",boiler,168,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Hybrid Heatpump",boiler,168,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Hybrid Heatpump",boiler,168,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Hybrid Heatpump",boiler,168,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Hybrid Heatpump",boiler,168,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Hybrid Heatpump",boiler,168,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Hybrid Heatpump",boiler,168,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Hybrid Heatpump",boiler,168,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Hybrid Heatpump",boiler,168,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Hybrid Heatpump",boiler,168,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Hybrid Heatpump",boiler,168,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Hybrid Heatpump",boiler,168,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Hybrid Heatpump",boiler,168,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Hybrid Heatpump",boiler,168,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Hybrid Heatpump",boiler,168,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Hybrid Heatpump",boiler,168,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Hybrid Heatpump",boiler,168,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Hybrid Heatpump",boiler,168,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Hybrid Heatpump",boiler,168,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Hybrid Heatpump",boiler,168,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Hybrid Heatpump",boiler,168,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Hybrid Heatpump",boiler,168,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Hybrid Heatpump",boiler,168,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Hybrid Heatpump",boiler,168,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Hybrid Heatpump",boiler,168,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Hybrid Heatpump",boiler,168,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Hybrid Heatpump",boiler,168,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Hybrid Heatpump",boiler,168,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Hybrid Heatpump",boiler,168,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Hybrid Heatpump",boiler,168,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Hybrid Heatpump",boiler,168,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Hybrid Heatpump",boiler,168,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Hybrid Heatpump",boiler,168,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Hybrid Heatpump",boiler,168,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Hybrid Heatpump",boiler,168,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Hybrid Heatpump",boiler,168,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Hybrid Heatpump",boiler,168,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Hybrid Heatpump",boiler,168,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Hybrid Heatpump",boiler,168,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Hybrid Heatpump",boiler,168,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Hybrid Heatpump",boiler,168,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Hybrid Heatpump",boiler,168,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Hybrid Heatpump",boiler,168,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Hybrid Heatpump",boiler,168,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Hybrid Heatpump",boiler,168,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Hybrid Heatpump",boiler,168,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Hybrid Heatpump",boiler,168,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Hybrid Heatpump",boiler,168,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Hybrid Heatpump",boiler,168,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Hybrid Heatpump",boiler,168,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Hybrid Heatpump",boiler,168,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Hybrid Heatpump",boiler,168,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Hybrid Heatpump",boiler,168,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Hybrid Heatpump",boiler,168,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Hybrid Heatpump",boiler,168,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Hybrid Heatpump",boiler,168,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Hybrid Heatpump",boiler,168,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Hybrid Heatpump",boiler,168,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Hybrid Heatpump",boiler,168,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Hybrid Heatpump",boiler,168,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Hybrid Heatpump",boiler,168,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Hybrid Heatpump",boiler,168,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Hybrid Heatpump",boiler,168,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Hybrid Heatpump",boiler,168,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Hybrid Heatpump",boiler,168,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Hybrid Heatpump",boiler,168,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Hybrid Heatpump",boiler,168,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Hybrid Heatpump",boiler,168,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Hybrid Heatpump",boiler,168,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Hybrid Heatpump",boiler,168,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Hybrid Heatpump",boiler,168,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Hybrid Heatpump",boiler,168,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Hybrid Heatpump",boiler,168,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Hybrid Heatpump",boiler,168,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Hybrid Heatpump",boiler,168,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Hybrid Heatpump",boiler,168,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Hybrid Heatpump",boiler,168,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Hybrid Heatpump",boiler,168,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Hybrid Heatpump",boiler,168,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Hybrid Heatpump",boiler,168,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Hybrid Heatpump",boiler,168,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Hybrid Heatpump",boiler,168,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Hybrid Heatpump",boiler,168,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Hybrid Heatpump",boiler,168,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logano GB212",boiler,170,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logano GB212",boiler,170,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logano GB212",boiler,170,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logano GB212",boiler,170,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logano GB212",boiler,170,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logano GB212",boiler,170,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logano GB212",boiler,170,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logano GB212",boiler,170,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logano GB212",boiler,170,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logano GB212",boiler,170,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logano GB212",boiler,170,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logano GB212",boiler,170,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logano GB212",boiler,170,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logano GB212",boiler,170,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logano GB212",boiler,170,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logano GB212",boiler,170,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logano GB212",boiler,170,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logano GB212",boiler,170,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logano GB212",boiler,170,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logano GB212",boiler,170,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logano GB212",boiler,170,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logano GB212",boiler,170,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logano GB212",boiler,170,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logano GB212",boiler,170,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logano GB212",boiler,170,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logano GB212",boiler,170,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logano GB212",boiler,170,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logano GB212",boiler,170,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logano GB212",boiler,170,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logano GB212",boiler,170,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logano GB212",boiler,170,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logano GB212",boiler,170,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logano GB212",boiler,170,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logano GB212",boiler,170,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logano GB212",boiler,170,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logano GB212",boiler,170,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logano GB212",boiler,170,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logano GB212",boiler,170,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logano GB212",boiler,170,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logano GB212",boiler,170,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logano GB212",boiler,170,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logano GB212",boiler,170,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logano GB212",boiler,170,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logano GB212",boiler,170,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logano GB212",boiler,170,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logano GB212",boiler,170,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logano GB212",boiler,170,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logano GB212",boiler,170,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logano GB212",boiler,170,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logano GB212",boiler,170,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logano GB212",boiler,170,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logano GB212",boiler,170,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logano GB212",boiler,170,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logano GB212",boiler,170,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logano GB212",boiler,170,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logano GB212",boiler,170,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logano GB212",boiler,170,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logano GB212",boiler,170,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logano GB212",boiler,170,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logano GB212",boiler,170,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logano GB212",boiler,170,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logano GB212",boiler,170,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logano GB212",boiler,170,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logano GB212",boiler,170,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logano GB212",boiler,170,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logano GB212",boiler,170,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logano GB212",boiler,170,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logano GB212",boiler,170,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logano GB212",boiler,170,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logano GB212",boiler,170,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logano GB212",boiler,170,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logano GB212",boiler,170,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logano GB212",boiler,170,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logano GB212",boiler,170,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logano GB212",boiler,170,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logano GB212",boiler,170,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logano GB212",boiler,170,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logano GB212",boiler,170,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logano GB212",boiler,170,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logano GB212",boiler,170,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logano GB212",boiler,170,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logano GB212",boiler,170,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logano GB212",boiler,170,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logano GB212",boiler,170,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logano GB212",boiler,170,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logano GB212",boiler,170,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logano GB212",boiler,170,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logano GB212",boiler,170,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logano GB212",boiler,170,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logano GB212",boiler,170,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logano GB212",boiler,170,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logano GB212",boiler,170,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logano GB212",boiler,170,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logano GB212",boiler,170,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logano GB212",boiler,170,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logano GB212",boiler,170,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logano GB212",boiler,170,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logano GB212",boiler,170,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logano GB212",boiler,170,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logano GB212",boiler,170,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logano GB212",boiler,170,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logano GB212",boiler,170,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logano GB212",boiler,170,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logano GB212",boiler,170,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logano GB212",boiler,170,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logano GB212",boiler,170,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logano GB212",boiler,170,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logano GB212",boiler,170,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logano GB212",boiler,170,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logano GB212",boiler,170,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrg,energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_dhw_energy,sensor.boiler_dhw_nrg,5,9,1/100,0,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgheat,energy heating,uint24 (>=0<=167772),kWh,false,sensor.boiler_energy_heating,sensor.boiler_nrgheat,5,0,1/100,81,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgcool,energy cooling,uint24 (>=0<=167772),kWh,false,sensor.boiler_energy_cooling,sensor.boiler_nrgcool,5,0,1/100,83,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,metertotal,meter total,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_total,sensor.boiler_metertotal,5,0,1/100,85,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,metercomp,meter compressor,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_compressor,sensor.boiler_metercomp,5,0,1/100,87,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,metereheat,meter e-heater,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_e-heater,sensor.boiler_metereheat,5,0,1/100,89,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,meterheat,meter heating,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/100,91,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,metercool,meter cooling,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_cooling,sensor.boiler_metercool,5,0,1/100,93,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,meter,meter,uint24 (>=0<=167772),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/100,2,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,uptimetotal,heatpump total uptime,time (>=0<=279620),minutes,false,sensor.boiler_heatpump_total_uptime,sensor.boiler_uptimetotal,5,0,1/60,95,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,uptimecontrol,total operating time heat,time (>=0<=279620),minutes,false,sensor.boiler_total_operating_time_heat,sensor.boiler_uptimecontrol,5,0,1/60,97,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,uptimecompheating,operating time compressor heating,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_heating,sensor.boiler_uptimecompheating,5,0,1/60,99,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,uptimecompcooling,operating time compressor cooling,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_cooling,sensor.boiler_uptimecompcooling,5,0,1/60,101,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,uptimecomp,operating time compressor,time (>=0<=279620),minutes,false,sensor.boiler_dhw_operating_time_compressor,sensor.boiler_dhw_uptimecomp,5,9,1/60,4,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,uptimecomppool,operating time compressor pool,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_pool,sensor.boiler_uptimecomppool,5,0,1/60,103,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,totalcompstarts,total compressor control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_total_compressor_control_starts,sensor.boiler_totalcompstarts,5,0,1,105,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatingstarts,heating control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_heating_control_starts,sensor.boiler_heatingstarts,5,0,1,107,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,coolingstarts,cooling control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_cooling_control_starts,sensor.boiler_coolingstarts,5,0,1,109,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,startshp,starts hp,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts_hp,sensor.boiler_dhw_startshp,5,9,1,6,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,poolstarts,pool control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_pool_control_starts,sensor.boiler_poolstarts,5,0,1,111,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgconstotal,total energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_consumption,sensor.boiler_nrgconstotal,5,0,1,113,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgconscomptotal,total energy consumption compressor,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_consumption_compressor,sensor.boiler_nrgconscomptotal,5,0,1,115,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgconscompheating,energy consumption compressor heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_heating,sensor.boiler_nrgconscompheating,5,0,1,117,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgconscomp,energy consumption compressor,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_energy_consumption_compressor,sensor.boiler_dhw_nrgconscomp,5,9,1,8,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgconscompcooling,energy consumption compressor cooling,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_cooling,sensor.boiler_nrgconscompcooling,5,0,1,119,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgconscomppool,energy consumption compressor pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_pool,sensor.boiler_nrgconscomppool,5,0,1,121,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxelecheatnrgconstotal,total aux elec. heater energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_aux_elec._heater_energy_consumption,sensor.boiler_auxelecheatnrgconstotal,5,0,1,123,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxelecheatnrgconsheating,aux elec. heater energy consumption heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_heating,sensor.boiler_auxelecheatnrgconsheating,5,0,1,125,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxelecheatnrgcons,aux elec. heater energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_aux_elec._heater_energy_consumption,sensor.boiler_dhw_auxelecheatnrgcons,5,9,1,10,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxelecheatnrgconspool,aux elec. heater energy consumption pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_pool,sensor.boiler_auxelecheatnrgconspool,5,0,1,127,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgsupptotal,total energy supplied,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied,sensor.boiler_nrgsupptotal,5,0,1,129,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgsuppheating,total energy supplied heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_heating,sensor.boiler_nrgsuppheating,5,0,1,131,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgsupp,total energy warm supplied,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_total_energy_warm_supplied,sensor.boiler_dhw_nrgsupp,5,9,1,12,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgsuppcooling,total energy supplied cooling,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_cooling,sensor.boiler_nrgsuppcooling,5,0,1,133,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,nrgsupppool,total energy supplied pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_pool,sensor.boiler_nrgsupppool,5,0,1,135,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hppower,compressor power output,uint8 (>=0<=25),kW,false,sensor.boiler_compressor_power_output,sensor.boiler_hppower,5,0,1/10,137,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpmaxpower,compressor max power,uint8 (>=0<=100),%,true,number.boiler_compressor_max_power,number.boiler_hpmaxpower,5,0,1,138,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pvmaxcomp,pv compressor max power,uint8 (>=0<=25),kW,true,number.boiler_pv_compressor_max_power,number.boiler_pvmaxcomp,5,0,1/10,139,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,powerreduction,power reduction,uint8 (>=30<=60),%,true,number.boiler_power_reduction,number.boiler_powerreduction,5,0,10,140,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpsetdiffpress,set differential pressure,uint8 (>=150<=750),mbar,true,number.boiler_set_differential_pressure,number.boiler_hpsetdiffpress,5,0,50,141,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpcompon,hp compressor,boolean, ,false,binary_sensor.boiler_hp_compressor,binary_sensor.boiler_hpcompon,5,0,1,142,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpactivity,compressor activity,enum [none\|heating\|cooling\|hot water\|pool\|unknown\|defrost], ,false,sensor.boiler_compressor_activity,sensor.boiler_hpactivity,5,0,1,143,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpbrinepumpspd,brine pump speed,uint8 (>=0<=100),%,false,sensor.boiler_brine_pump_speed,sensor.boiler_hpbrinepumpspd,5,0,1,144,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpswitchvalve,switch valve,boolean, ,false,binary_sensor.boiler_switch_valve,binary_sensor.boiler_hpswitchvalve,5,0,1,145,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpcompspd,compressor speed,uint8 (>=0<=100),%,false,sensor.boiler_compressor_speed,sensor.boiler_hpcompspd,5,0,1,146,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpcircspd,circulation pump speed,uint8 (>=0<=100),%,false,sensor.boiler_circulation_pump_speed,sensor.boiler_hpcircspd,5,0,1,147,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpbrinein,brine in/evaporator,int16 (>=-3199<=3199),C,false,sensor.boiler_brine_in/evaporator,sensor.boiler_hpbrinein,5,0,1/10,148,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpbrineout,brine out/condenser,int16 (>=-3199<=3199),C,false,sensor.boiler_brine_out/condenser,sensor.boiler_hpbrineout,5,0,1/10,149,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptc0,heat carrier return (TC0),int16 (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_return_(TC0),sensor.boiler_hptc0,5,0,1/10,150,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptc1,heat carrier forward (TC1),int16 (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_forward_(TC1),sensor.boiler_hptc1,5,0,1/10,151,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptc3,condenser temperature (TC3),int16 (>=-3199<=3199),C,false,sensor.boiler_condenser_temperature_(TC3),sensor.boiler_hptc3,5,0,1/10,152,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptr1,compressor temperature (TR1),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_temperature_(TR1),sensor.boiler_hptr1,5,0,1/10,153,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptr3,refrigerant temperature liquid side (condenser output) (TR3),int16 (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.boiler_hptr3,5,0,1/10,154,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptr4,evaporator inlet temperature (TR4),int16 (>=-3199<=3199),C,false,sensor.boiler_evaporator_inlet_temperature_(TR4),sensor.boiler_hptr4,5,0,1/10,155,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptr5,compressor inlet temperature (TR5),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_inlet_temperature_(TR5),sensor.boiler_hptr5,5,0,1/10,156,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptr6,compressor outlet temperature (TR6),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_outlet_temperature_(TR6),sensor.boiler_hptr6,5,0,1/10,157,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptr7,refrigerant temperature gas side (condenser input) (TR7),int16 (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_gas_side_(condenser_input)_(TR7),sensor.boiler_hptr7,5,0,1/10,158,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptl2,air inlet temperature (TL2),int16 (>=-3199<=3199),C,false,sensor.boiler_air_inlet_temperature_(TL2),sensor.boiler_hptl2,5,0,1/10,159,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hppl1,low pressure side temperature (PL1),int16 (>=-3199<=3199),C,false,sensor.boiler_low_pressure_side_temperature_(PL1),sensor.boiler_hppl1,5,0,1/10,160,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpph1,high pressure side temperature (PH1),int16 (>=-3199<=3199),C,false,sensor.boiler_high_pressure_side_temperature_(PH1),sensor.boiler_hpph1,5,0,1/10,161,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpta4,drain pan temp (TA4),int16 (>=-3199<=3199),C,false,sensor.boiler_drain_pan_temp_(TA4),sensor.boiler_hpta4,5,0,1/10,162,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hptw1,reservoir temp (TW1),int16 (>=-3199<=3199),C,false,sensor.boiler_reservoir_temp_(TW1),sensor.boiler_hptw1,5,0,1/10,163,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,poolsettemp,pool set temperature,uint8 (>=0<=127),C,true,number.boiler_pool_set_temperature,number.boiler_poolsettemp,5,0,1/2,164,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hp4way,4-way valve (VR4),enum [cooling & defrost\|heating & dhw], ,false,sensor.boiler_4-way_valve_(VR4),sensor.boiler_hp4way,5,0,1,165,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin1,input 1 state,boolean, ,false,binary_sensor.boiler_input_1_state,binary_sensor.boiler_hpin1,5,0,1,166,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin1opt,input 1 options,string, ,true,sensor.boiler_input_1_options,sensor.boiler_hpin1opt,5,0,1,167,8
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin2,input 2 state,boolean, ,false,binary_sensor.boiler_input_2_state,binary_sensor.boiler_hpin2,5,0,1,175,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin2opt,input 2 options,string, ,true,sensor.boiler_input_2_options,sensor.boiler_hpin2opt,5,0,1,176,8
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin3,input 3 state,boolean, ,false,binary_sensor.boiler_input_3_state,binary_sensor.boiler_hpin3,5,0,1,184,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin3opt,input 3 options,string, ,true,sensor.boiler_input_3_options,sensor.boiler_hpin3opt,5,0,1,185,8
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin4,input 4 state,boolean, ,false,binary_sensor.boiler_input_4_state,binary_sensor.boiler_hpin4,5,0,1,193,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpin4opt,input 4 options,string, ,true,sensor.boiler_input_4_options,sensor.boiler_hpin4opt,5,0,1,194,8
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maxheatcomp,heat limit compressor,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_compressor,select.boiler_maxheatcomp,5,0,1,202,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maxheatheat,heat limit heating,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_heating,select.boiler_maxheatheat,5,0,1,203,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maxheat,heat limit,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_dhw_heat_limit,select.boiler_dhw_maxheat,5,9,1,14,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,mandefrost,manual defrost,boolean, ,true,switch.boiler_manual_defrost,switch.boiler_mandefrost,5,0,1,204,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pvcooling,cooling only with PV,boolean, ,true,switch.boiler_cooling_only_with_PV,switch.boiler_pvcooling,5,0,1,205,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheateronly,aux heater only,boolean, ,true,switch.boiler_aux_heater_only,switch.boiler_auxheateronly,5,0,1,206,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheateroff,disable aux heater,boolean, ,true,switch.boiler_disable_aux_heater,switch.boiler_auxheateroff,5,0,1,207,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheaterstatus,aux heater status,boolean, ,false,binary_sensor.boiler_aux_heater_status,binary_sensor.boiler_auxheaterstatus,5,0,1,208,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheaterlevel,aux heater level,uint8 (>=0<=100),%,false,sensor.boiler_aux_heater_level,sensor.boiler_auxheaterlevel,5,0,1,209,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheaterdelay,aux heater on delay,uint16 (>=10<=1000),K*min,true,number.boiler_aux_heater_on_delay,number.boiler_auxheaterdelay,5,0,10,210,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxmaxlimit,aux heater max limit,uint8 (>=0<=10),K,true,number.boiler_aux_heater_max_limit,number.boiler_auxmaxlimit,5,0,1/10,211,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxlimitstart,aux heater limit start,uint8 (>=0<=10),K,true,number.boiler_aux_heater_limit_start,number.boiler_auxlimitstart,5,0,1/10,212,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheatrmode,aux heater mode,enum [eco\|comfort], ,true,select.boiler_aux_heater_mode,select.boiler_auxheatrmode,5,0,1,213,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hphystheat,on/off hyst heat,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_heat,number.boiler_hphystheat,5,0,5,214,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hphystcool,on/off hyst cool,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_cool,number.boiler_hphystcool,5,0,5,215,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hphystpool,on/off hyst pool,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_pool,number.boiler_hphystpool,5,0,5,216,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,silentmode,silent mode,enum [off\|auto\|on], ,true,select.boiler_silent_mode,select.boiler_silentmode,5,0,1,217,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,silentfrom,silent mode from,uint8 (>=0<=3810),minutes,true,number.boiler_silent_mode_from,number.boiler_silentfrom,5,0,15,218,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,silentto,silent mode to,uint8 (>=0<=3810),minutes,true,number.boiler_silent_mode_to,number.boiler_silentto,5,0,15,219,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,mintempsilent,min outside temp for silent mode,int8 (>=-126<=126),C,true,number.boiler_min_outside_temp_for_silent_mode,number.boiler_mintempsilent,5,0,1,220,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tempparmode,outside temp parallel mode,int8 (>=-126<=126),C,true,number.boiler_outside_temp_parallel_mode,number.boiler_tempparmode,5,0,1,221,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,auxheatmix,aux heater mixing valve,int8 (>=-100<=100),%,false,sensor.boiler_aux_heater_mixing_valve,sensor.boiler_auxheatmix,5,0,1,222,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tempdiffheat,temp diff TC3/TC0 heat,uint8 (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_heat,number.boiler_tempdiffheat,5,0,1/10,223,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tempdiffcool,temp diff TC3/TC0 cool,uint8 (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_cool,number.boiler_tempdiffcool,5,0,1/10,224,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,vpcooling,valve/pump cooling,boolean, ,true,switch.boiler_valve/pump_cooling,switch.boiler_vpcooling,5,0,1,225,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,heatcable,heating cable,boolean, ,true,switch.boiler_heating_cable,switch.boiler_heatcable,5,0,1,226,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,vc0valve,VC0 valve,boolean, ,true,switch.boiler_VC0_valve,switch.boiler_vc0valve,5,0,1,227,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,primepump,primary heatpump,boolean, ,true,switch.boiler_primary_heatpump,switch.boiler_primepump,5,0,1,228,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,primepumpmod,primary heatpump modulation,uint8 (>=0<=100),%,true,number.boiler_primary_heatpump_modulation,number.boiler_primepumpmod,5,0,1,229,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hp3way,3-way valve,boolean, ,true,switch.boiler_3-way_valve,switch.boiler_hp3way,5,0,1,230,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,elheatstep1,el. heater step 1,boolean, ,true,switch.boiler_el._heater_step_1,switch.boiler_elheatstep1,5,0,1,231,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,elheatstep2,el. heater step 2,boolean, ,true,switch.boiler_el._heater_step_2,switch.boiler_elheatstep2,5,0,1,232,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,elheatstep3,el. heater step 3,boolean, ,true,switch.boiler_el._heater_step_3,switch.boiler_elheatstep3,5,0,1,233,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpea0,condensate reservoir heating (EA0),boolean, ,false,binary_sensor.boiler_condensate_reservoir_heating_(EA0),binary_sensor.boiler_hpea0,5,0,1,234,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hppumpmode,primary heatpump mode,enum [auto\|continuous], ,true,select.boiler_primary_heatpump_mode,select.boiler_hppumpmode,5,0,1,235,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,fan,fan,uint8 (>=20<=100),%,true,number.boiler_fan,number.boiler_fan,5,0,1,236,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,shutdown,shutdown,cmd [off\|on], ,true,sensor.boiler_shutdown,sensor.boiler_shutdown,5,0,1,237,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpcurrpower,compressor current power,uint16 (>=0<=31999),W,false,sensor.boiler_compressor_current_power,sensor.boiler_hpcurrpower,5,0,1,238,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hppowerlimit,power limit,uint16 (>=0<=31999),W,true,number.boiler_power_limit,number.boiler_hppowerlimit,5,0,1,239,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pc0flow,Flow PC0,int16 (>=-31999<=31999),l/h,false,sensor.boiler_Flow_PC0,sensor.boiler_pc0flow,5,0,1,240,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pc1flow,Flow PC1,int16 (>=-31999<=31999),l/h,false,sensor.boiler_Flow_PC1,sensor.boiler_pc1flow,5,0,1,241,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pc1on,PC1,boolean, ,false,binary_sensor.boiler_PC1,binary_sensor.boiler_pc1on,5,0,1,242,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,pc1rate,PC1 rate,uint8 (>=0<=100),%,false,sensor.boiler_PC1_rate,sensor.boiler_pc1rate,5,0,1,243,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,alternatingop,alternating operation,boolean, ,true,switch.boiler_dhw_alternating_operation,switch.boiler_dhw_alternatingop,5,9,1,15,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,altopprioheat,prioritise heating during dhw,uint8 (>=20<=120),minutes,true,number.boiler_dhw_prioritise_heating_during_dhw,number.boiler_dhw_altopprioheat,5,9,1,16,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,altopprio,prioritise dhw during heating,uint8 (>=30<=120),minutes,true,number.boiler_dhw_prioritise_dhw_during_heating,number.boiler_dhw_altopprio,5,9,1,17,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,comfoff,comfort switch off,uint8 (>=15<=65),C,true,number.boiler_dhw_comfort_switch_off,number.boiler_dhw_comfoff,5,9,1,18,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ecooff,eco switch off,uint8 (>=15<=65),C,true,number.boiler_dhw_eco_switch_off,number.boiler_dhw_ecooff,5,9,1,19,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ecoplusoff,eco+ switch off,uint8 (>=48<=63),C,true,number.boiler_dhw_eco+_switch_off,number.boiler_dhw_ecoplusoff,5,9,1,20,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,comfdiff,comfort diff,uint8 (>=6<=12),K,true,number.boiler_dhw_comfort_diff,number.boiler_dhw_comfdiff,5,9,1,21,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ecodiff,eco diff,uint8 (>=6<=12),K,true,number.boiler_dhw_eco_diff,number.boiler_dhw_ecodiff,5,9,1,22,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ecoplusdiff,eco+ diff,uint8 (>=6<=12),K,true,number.boiler_dhw_eco+_diff,number.boiler_dhw_ecoplusdiff,5,9,1,23,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,comfstop,comfort stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_comfort_stop_temp,number.boiler_dhw_comfstop,5,9,1,24,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ecostop,eco stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_eco_stop_temp,number.boiler_dhw_ecostop,5,9,1,25,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,ecoplusstop,eco+ stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_eco+_stop_temp,number.boiler_dhw_ecoplusstop,5,9,1,26,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hpcircpump,circulation pump available during dhw,boolean, ,true,switch.boiler_dhw_circulation_pump_available_during_dhw,switch.boiler_dhw_hpcircpump,5,9,1,27,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Enviline, Compress 6000AW, Hybrid 3000-7000iAW, SupraEco/Geo 5xx, WLW196i/WSW196i",boiler,172,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Geo 5xx",boiler,173,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Geo 5xx",boiler,173,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Geo 5xx",boiler,173,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Geo 5xx",boiler,173,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Geo 5xx",boiler,173,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Geo 5xx",boiler,173,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Geo 5xx",boiler,173,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Geo 5xx",boiler,173,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Geo 5xx",boiler,173,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Geo 5xx",boiler,173,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Geo 5xx",boiler,173,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Geo 5xx",boiler,173,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Geo 5xx",boiler,173,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Geo 5xx",boiler,173,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Geo 5xx",boiler,173,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Geo 5xx",boiler,173,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Geo 5xx",boiler,173,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Geo 5xx",boiler,173,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Geo 5xx",boiler,173,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Geo 5xx",boiler,173,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Geo 5xx",boiler,173,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Geo 5xx",boiler,173,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Geo 5xx",boiler,173,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Geo 5xx",boiler,173,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Geo 5xx",boiler,173,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Geo 5xx",boiler,173,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Geo 5xx",boiler,173,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Geo 5xx",boiler,173,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Geo 5xx",boiler,173,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Geo 5xx",boiler,173,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Geo 5xx",boiler,173,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Geo 5xx",boiler,173,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Geo 5xx",boiler,173,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Geo 5xx",boiler,173,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Geo 5xx",boiler,173,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Geo 5xx",boiler,173,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Geo 5xx",boiler,173,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Geo 5xx",boiler,173,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Geo 5xx",boiler,173,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Geo 5xx",boiler,173,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Geo 5xx",boiler,173,nrg,energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_dhw_energy,sensor.boiler_dhw_nrg,5,9,1/100,0,2
"Geo 5xx",boiler,173,nrgheat,energy heating,uint24 (>=0<=167772),kWh,false,sensor.boiler_energy_heating,sensor.boiler_nrgheat,5,0,1/100,81,2
"Geo 5xx",boiler,173,nrgcool,energy cooling,uint24 (>=0<=167772),kWh,false,sensor.boiler_energy_cooling,sensor.boiler_nrgcool,5,0,1/100,83,2
"Geo 5xx",boiler,173,metertotal,meter total,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_total,sensor.boiler_metertotal,5,0,1/100,85,2
"Geo 5xx",boiler,173,metercomp,meter compressor,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_compressor,sensor.boiler_metercomp,5,0,1/100,87,2
"Geo 5xx",boiler,173,metereheat,meter e-heater,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_e-heater,sensor.boiler_metereheat,5,0,1/100,89,2
"Geo 5xx",boiler,173,meterheat,meter heating,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/100,91,2
"Geo 5xx",boiler,173,metercool,meter cooling,uint24 (>=0<=167772),kWh,false,sensor.boiler_meter_cooling,sensor.boiler_metercool,5,0,1/100,93,2
"Geo 5xx",boiler,173,meter,meter,uint24 (>=0<=167772),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/100,2,2
"Geo 5xx",boiler,173,uptimetotal,heatpump total uptime,time (>=0<=279620),minutes,false,sensor.boiler_heatpump_total_uptime,sensor.boiler_uptimetotal,5,0,1/60,95,2
"Geo 5xx",boiler,173,uptimecontrol,total operating time heat,time (>=0<=279620),minutes,false,sensor.boiler_total_operating_time_heat,sensor.boiler_uptimecontrol,5,0,1/60,97,2
"Geo 5xx",boiler,173,uptimecompheating,operating time compressor heating,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_heating,sensor.boiler_uptimecompheating,5,0,1/60,99,2
"Geo 5xx",boiler,173,uptimecompcooling,operating time compressor cooling,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_cooling,sensor.boiler_uptimecompcooling,5,0,1/60,101,2
"Geo 5xx",boiler,173,uptimecomp,operating time compressor,time (>=0<=279620),minutes,false,sensor.boiler_dhw_operating_time_compressor,sensor.boiler_dhw_uptimecomp,5,9,1/60,4,2
"Geo 5xx",boiler,173,uptimecomppool,operating time compressor pool,time (>=0<=279620),minutes,false,sensor.boiler_operating_time_compressor_pool,sensor.boiler_uptimecomppool,5,0,1/60,103,2
"Geo 5xx",boiler,173,totalcompstarts,total compressor control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_total_compressor_control_starts,sensor.boiler_totalcompstarts,5,0,1,105,2
"Geo 5xx",boiler,173,heatingstarts,heating control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_heating_control_starts,sensor.boiler_heatingstarts,5,0,1,107,2
"Geo 5xx",boiler,173,coolingstarts,cooling control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_cooling_control_starts,sensor.boiler_coolingstarts,5,0,1,109,2
"Geo 5xx",boiler,173,startshp,starts hp,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts_hp,sensor.boiler_dhw_startshp,5,9,1,6,2
"Geo 5xx",boiler,173,poolstarts,pool control starts,uint24 (>=0<=16777213), ,false,sensor.boiler_pool_control_starts,sensor.boiler_poolstarts,5,0,1,111,2
"Geo 5xx",boiler,173,nrgconstotal,total energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_consumption,sensor.boiler_nrgconstotal,5,0,1,113,2
"Geo 5xx",boiler,173,nrgconscomptotal,total energy consumption compressor,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_consumption_compressor,sensor.boiler_nrgconscomptotal,5,0,1,115,2
"Geo 5xx",boiler,173,nrgconscompheating,energy consumption compressor heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_heating,sensor.boiler_nrgconscompheating,5,0,1,117,2
"Geo 5xx",boiler,173,nrgconscomp,energy consumption compressor,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_energy_consumption_compressor,sensor.boiler_dhw_nrgconscomp,5,9,1,8,2
"Geo 5xx",boiler,173,nrgconscompcooling,energy consumption compressor cooling,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_cooling,sensor.boiler_nrgconscompcooling,5,0,1,119,2
"Geo 5xx",boiler,173,nrgconscomppool,energy consumption compressor pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_energy_consumption_compressor_pool,sensor.boiler_nrgconscomppool,5,0,1,121,2
"Geo 5xx",boiler,173,auxelecheatnrgconstotal,total aux elec. heater energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_aux_elec._heater_energy_consumption,sensor.boiler_auxelecheatnrgconstotal,5,0,1,123,2
"Geo 5xx",boiler,173,auxelecheatnrgconsheating,aux elec. heater energy consumption heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_heating,sensor.boiler_auxelecheatnrgconsheating,5,0,1,125,2
"Geo 5xx",boiler,173,auxelecheatnrgcons,aux elec. heater energy consumption,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_aux_elec._heater_energy_consumption,sensor.boiler_dhw_auxelecheatnrgcons,5,9,1,10,2
"Geo 5xx",boiler,173,auxelecheatnrgconspool,aux elec. heater energy consumption pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_aux_elec._heater_energy_consumption_pool,sensor.boiler_auxelecheatnrgconspool,5,0,1,127,2
"Geo 5xx",boiler,173,nrgsupptotal,total energy supplied,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied,sensor.boiler_nrgsupptotal,5,0,1,129,2
"Geo 5xx",boiler,173,nrgsuppheating,total energy supplied heating,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_heating,sensor.boiler_nrgsuppheating,5,0,1,131,2
"Geo 5xx",boiler,173,nrgsupp,total energy warm supplied,uint24 (>=0<=16777213),kWh,false,sensor.boiler_dhw_total_energy_warm_supplied,sensor.boiler_dhw_nrgsupp,5,9,1,12,2
"Geo 5xx",boiler,173,nrgsuppcooling,total energy supplied cooling,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_cooling,sensor.boiler_nrgsuppcooling,5,0,1,133,2
"Geo 5xx",boiler,173,nrgsupppool,total energy supplied pool,uint24 (>=0<=16777213),kWh,false,sensor.boiler_total_energy_supplied_pool,sensor.boiler_nrgsupppool,5,0,1,135,2
"Geo 5xx",boiler,173,hppower,compressor power output,uint8 (>=0<=25),kW,false,sensor.boiler_compressor_power_output,sensor.boiler_hppower,5,0,1/10,137,1
"Geo 5xx",boiler,173,hpmaxpower,compressor max power,uint8 (>=0<=100),%,true,number.boiler_compressor_max_power,number.boiler_hpmaxpower,5,0,1,138,1
"Geo 5xx",boiler,173,pvmaxcomp,pv compressor max power,uint8 (>=0<=25),kW,true,number.boiler_pv_compressor_max_power,number.boiler_pvmaxcomp,5,0,1/10,139,1
"Geo 5xx",boiler,173,powerreduction,power reduction,uint8 (>=30<=60),%,true,number.boiler_power_reduction,number.boiler_powerreduction,5,0,10,140,1
"Geo 5xx",boiler,173,hpsetdiffpress,set differential pressure,uint8 (>=150<=750),mbar,true,number.boiler_set_differential_pressure,number.boiler_hpsetdiffpress,5,0,50,141,1
"Geo 5xx",boiler,173,hpcompon,hp compressor,boolean, ,false,binary_sensor.boiler_hp_compressor,binary_sensor.boiler_hpcompon,5,0,1,142,1
"Geo 5xx",boiler,173,hpactivity,compressor activity,enum [none\|heating\|cooling\|hot water\|pool\|unknown\|defrost], ,false,sensor.boiler_compressor_activity,sensor.boiler_hpactivity,5,0,1,143,1
"Geo 5xx",boiler,173,hpbrinepumpspd,brine pump speed,uint8 (>=0<=100),%,false,sensor.boiler_brine_pump_speed,sensor.boiler_hpbrinepumpspd,5,0,1,144,1
"Geo 5xx",boiler,173,hpswitchvalve,switch valve,boolean, ,false,binary_sensor.boiler_switch_valve,binary_sensor.boiler_hpswitchvalve,5,0,1,145,1
"Geo 5xx",boiler,173,hpcompspd,compressor speed,uint8 (>=0<=100),%,false,sensor.boiler_compressor_speed,sensor.boiler_hpcompspd,5,0,1,146,1
"Geo 5xx",boiler,173,hpcircspd,circulation pump speed,uint8 (>=0<=100),%,false,sensor.boiler_circulation_pump_speed,sensor.boiler_hpcircspd,5,0,1,147,1
"Geo 5xx",boiler,173,hpbrinein,brine in/evaporator,int16 (>=-3199<=3199),C,false,sensor.boiler_brine_in/evaporator,sensor.boiler_hpbrinein,5,0,1/10,148,1
"Geo 5xx",boiler,173,hpbrineout,brine out/condenser,int16 (>=-3199<=3199),C,false,sensor.boiler_brine_out/condenser,sensor.boiler_hpbrineout,5,0,1/10,149,1
"Geo 5xx",boiler,173,hptc0,heat carrier return (TC0),int16 (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_return_(TC0),sensor.boiler_hptc0,5,0,1/10,150,1
"Geo 5xx",boiler,173,hptc1,heat carrier forward (TC1),int16 (>=-3199<=3199),C,false,sensor.boiler_heat_carrier_forward_(TC1),sensor.boiler_hptc1,5,0,1/10,151,1
"Geo 5xx",boiler,173,hptc3,condenser temperature (TC3),int16 (>=-3199<=3199),C,false,sensor.boiler_condenser_temperature_(TC3),sensor.boiler_hptc3,5,0,1/10,152,1
"Geo 5xx",boiler,173,hptr1,compressor temperature (TR1),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_temperature_(TR1),sensor.boiler_hptr1,5,0,1/10,153,1
"Geo 5xx",boiler,173,hptr3,refrigerant temperature liquid side (condenser output) (TR3),int16 (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.boiler_hptr3,5,0,1/10,154,1
"Geo 5xx",boiler,173,hptr4,evaporator inlet temperature (TR4),int16 (>=-3199<=3199),C,false,sensor.boiler_evaporator_inlet_temperature_(TR4),sensor.boiler_hptr4,5,0,1/10,155,1
"Geo 5xx",boiler,173,hptr5,compressor inlet temperature (TR5),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_inlet_temperature_(TR5),sensor.boiler_hptr5,5,0,1/10,156,1
"Geo 5xx",boiler,173,hptr6,compressor outlet temperature (TR6),int16 (>=-3199<=3199),C,false,sensor.boiler_compressor_outlet_temperature_(TR6),sensor.boiler_hptr6,5,0,1/10,157,1
"Geo 5xx",boiler,173,hptr7,refrigerant temperature gas side (condenser input) (TR7),int16 (>=-3199<=3199),C,false,sensor.boiler_refrigerant_temperature_gas_side_(condenser_input)_(TR7),sensor.boiler_hptr7,5,0,1/10,158,1
"Geo 5xx",boiler,173,hptl2,air inlet temperature (TL2),int16 (>=-3199<=3199),C,false,sensor.boiler_air_inlet_temperature_(TL2),sensor.boiler_hptl2,5,0,1/10,159,1
"Geo 5xx",boiler,173,hppl1,low pressure side temperature (PL1),int16 (>=-3199<=3199),C,false,sensor.boiler_low_pressure_side_temperature_(PL1),sensor.boiler_hppl1,5,0,1/10,160,1
"Geo 5xx",boiler,173,hpph1,high pressure side temperature (PH1),int16 (>=-3199<=3199),C,false,sensor.boiler_high_pressure_side_temperature_(PH1),sensor.boiler_hpph1,5,0,1/10,161,1
"Geo 5xx",boiler,173,hpta4,drain pan temp (TA4),int16 (>=-3199<=3199),C,false,sensor.boiler_drain_pan_temp_(TA4),sensor.boiler_hpta4,5,0,1/10,162,1
"Geo 5xx",boiler,173,hptw1,reservoir temp (TW1),int16 (>=-3199<=3199),C,false,sensor.boiler_reservoir_temp_(TW1),sensor.boiler_hptw1,5,0,1/10,163,1
"Geo 5xx",boiler,173,poolsettemp,pool set temperature,uint8 (>=0<=127),C,true,number.boiler_pool_set_temperature,number.boiler_poolsettemp,5,0,1/2,164,1
"Geo 5xx",boiler,173,hp4way,4-way valve (VR4),enum [cooling & defrost\|heating & dhw], ,false,sensor.boiler_4-way_valve_(VR4),sensor.boiler_hp4way,5,0,1,165,1
"Geo 5xx",boiler,173,hpin1,input 1 state,boolean, ,false,binary_sensor.boiler_input_1_state,binary_sensor.boiler_hpin1,5,0,1,166,1
"Geo 5xx",boiler,173,hpin1opt,input 1 options,string, ,true,sensor.boiler_input_1_options,sensor.boiler_hpin1opt,5,0,1,167,8
"Geo 5xx",boiler,173,hpin2,input 2 state,boolean, ,false,binary_sensor.boiler_input_2_state,binary_sensor.boiler_hpin2,5,0,1,175,1
"Geo 5xx",boiler,173,hpin2opt,input 2 options,string, ,true,sensor.boiler_input_2_options,sensor.boiler_hpin2opt,5,0,1,176,8
"Geo 5xx",boiler,173,hpin3,input 3 state,boolean, ,false,binary_sensor.boiler_input_3_state,binary_sensor.boiler_hpin3,5,0,1,184,1
"Geo 5xx",boiler,173,hpin3opt,input 3 options,string, ,true,sensor.boiler_input_3_options,sensor.boiler_hpin3opt,5,0,1,185,8
"Geo 5xx",boiler,173,hpin4,input 4 state,boolean, ,false,binary_sensor.boiler_input_4_state,binary_sensor.boiler_hpin4,5,0,1,193,1
"Geo 5xx",boiler,173,hpin4opt,input 4 options,string, ,true,sensor.boiler_input_4_options,sensor.boiler_hpin4opt,5,0,1,194,8
"Geo 5xx",boiler,173,maxheatcomp,heat limit compressor,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_compressor,select.boiler_maxheatcomp,5,0,1,202,1
"Geo 5xx",boiler,173,maxheatheat,heat limit heating,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_heat_limit_heating,select.boiler_maxheatheat,5,0,1,203,1
"Geo 5xx",boiler,173,maxheat,heat limit,enum [0 kW\|2 kW\|3 kW\|4 kW\|6 kW\|9 kW], ,true,select.boiler_dhw_heat_limit,select.boiler_dhw_maxheat,5,9,1,14,1
"Geo 5xx",boiler,173,mandefrost,manual defrost,boolean, ,true,switch.boiler_manual_defrost,switch.boiler_mandefrost,5,0,1,204,1
"Geo 5xx",boiler,173,pvcooling,cooling only with PV,boolean, ,true,switch.boiler_cooling_only_with_PV,switch.boiler_pvcooling,5,0,1,205,1
"Geo 5xx",boiler,173,auxheateronly,aux heater only,boolean, ,true,switch.boiler_aux_heater_only,switch.boiler_auxheateronly,5,0,1,206,1
"Geo 5xx",boiler,173,auxheateroff,disable aux heater,boolean, ,true,switch.boiler_disable_aux_heater,switch.boiler_auxheateroff,5,0,1,207,1
"Geo 5xx",boiler,173,auxheaterstatus,aux heater status,boolean, ,false,binary_sensor.boiler_aux_heater_status,binary_sensor.boiler_auxheaterstatus,5,0,1,208,1
"Geo 5xx",boiler,173,auxheaterlevel,aux heater level,uint8 (>=0<=100),%,false,sensor.boiler_aux_heater_level,sensor.boiler_auxheaterlevel,5,0,1,209,1
"Geo 5xx",boiler,173,auxheaterdelay,aux heater on delay,uint16 (>=10<=1000),K*min,true,number.boiler_aux_heater_on_delay,number.boiler_auxheaterdelay,5,0,10,210,1
"Geo 5xx",boiler,173,auxmaxlimit,aux heater max limit,uint8 (>=0<=10),K,true,number.boiler_aux_heater_max_limit,number.boiler_auxmaxlimit,5,0,1/10,211,1
"Geo 5xx",boiler,173,auxlimitstart,aux heater limit start,uint8 (>=0<=10),K,true,number.boiler_aux_heater_limit_start,number.boiler_auxlimitstart,5,0,1/10,212,1
"Geo 5xx",boiler,173,auxheatrmode,aux heater mode,enum [eco\|comfort], ,true,select.boiler_aux_heater_mode,select.boiler_auxheatrmode,5,0,1,213,1
"Geo 5xx",boiler,173,hphystheat,on/off hyst heat,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_heat,number.boiler_hphystheat,5,0,5,214,1
"Geo 5xx",boiler,173,hphystcool,on/off hyst cool,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_cool,number.boiler_hphystcool,5,0,5,215,1
"Geo 5xx",boiler,173,hphystpool,on/off hyst pool,uint16 (>=50<=1500),K*min,true,number.boiler_on/off_hyst_pool,number.boiler_hphystpool,5,0,5,216,1
"Geo 5xx",boiler,173,silentmode,silent mode,enum [off\|auto\|on], ,true,select.boiler_silent_mode,select.boiler_silentmode,5,0,1,217,1
"Geo 5xx",boiler,173,silentfrom,silent mode from,uint8 (>=0<=3810),minutes,true,number.boiler_silent_mode_from,number.boiler_silentfrom,5,0,15,218,1
"Geo 5xx",boiler,173,silentto,silent mode to,uint8 (>=0<=3810),minutes,true,number.boiler_silent_mode_to,number.boiler_silentto,5,0,15,219,1
"Geo 5xx",boiler,173,mintempsilent,min outside temp for silent mode,int8 (>=-126<=126),C,true,number.boiler_min_outside_temp_for_silent_mode,number.boiler_mintempsilent,5,0,1,220,1
"Geo 5xx",boiler,173,tempparmode,outside temp parallel mode,int8 (>=-126<=126),C,true,number.boiler_outside_temp_parallel_mode,number.boiler_tempparmode,5,0,1,221,1
"Geo 5xx",boiler,173,auxheatmix,aux heater mixing valve,int8 (>=-100<=100),%,false,sensor.boiler_aux_heater_mixing_valve,sensor.boiler_auxheatmix,5,0,1,222,1
"Geo 5xx",boiler,173,tempdiffheat,temp diff TC3/TC0 heat,uint8 (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_heat,number.boiler_tempdiffheat,5,0,1/10,223,1
"Geo 5xx",boiler,173,tempdiffcool,temp diff TC3/TC0 cool,uint8 (>=2<=10),K,true,number.boiler_temp_diff_TC3/TC0_cool,number.boiler_tempdiffcool,5,0,1/10,224,1
"Geo 5xx",boiler,173,vpcooling,valve/pump cooling,boolean, ,true,switch.boiler_valve/pump_cooling,switch.boiler_vpcooling,5,0,1,225,1
"Geo 5xx",boiler,173,heatcable,heating cable,boolean, ,true,switch.boiler_heating_cable,switch.boiler_heatcable,5,0,1,226,1
"Geo 5xx",boiler,173,vc0valve,VC0 valve,boolean, ,true,switch.boiler_VC0_valve,switch.boiler_vc0valve,5,0,1,227,1
"Geo 5xx",boiler,173,primepump,primary heatpump,boolean, ,true,switch.boiler_primary_heatpump,switch.boiler_primepump,5,0,1,228,1
"Geo 5xx",boiler,173,primepumpmod,primary heatpump modulation,uint8 (>=0<=100),%,true,number.boiler_primary_heatpump_modulation,number.boiler_primepumpmod,5,0,1,229,1
"Geo 5xx",boiler,173,hp3way,3-way valve,boolean, ,true,switch.boiler_3-way_valve,switch.boiler_hp3way,5,0,1,230,1
"Geo 5xx",boiler,173,elheatstep1,el. heater step 1,boolean, ,true,switch.boiler_el._heater_step_1,switch.boiler_elheatstep1,5,0,1,231,1
"Geo 5xx",boiler,173,elheatstep2,el. heater step 2,boolean, ,true,switch.boiler_el._heater_step_2,switch.boiler_elheatstep2,5,0,1,232,1
"Geo 5xx",boiler,173,elheatstep3,el. heater step 3,boolean, ,true,switch.boiler_el._heater_step_3,switch.boiler_elheatstep3,5,0,1,233,1
"Geo 5xx",boiler,173,hpea0,condensate reservoir heating (EA0),boolean, ,false,binary_sensor.boiler_condensate_reservoir_heating_(EA0),binary_sensor.boiler_hpea0,5,0,1,234,1
"Geo 5xx",boiler,173,hppumpmode,primary heatpump mode,enum [auto\|continuous], ,true,select.boiler_primary_heatpump_mode,select.boiler_hppumpmode,5,0,1,235,1
"Geo 5xx",boiler,173,fan,fan,uint8 (>=20<=100),%,true,number.boiler_fan,number.boiler_fan,5,0,1,236,1
"Geo 5xx",boiler,173,shutdown,shutdown,cmd [off\|on], ,true,sensor.boiler_shutdown,sensor.boiler_shutdown,5,0,1,237,1
"Geo 5xx",boiler,173,hpcurrpower,compressor current power,uint16 (>=0<=31999),W,false,sensor.boiler_compressor_current_power,sensor.boiler_hpcurrpower,5,0,1,238,1
"Geo 5xx",boiler,173,hppowerlimit,power limit,uint16 (>=0<=31999),W,true,number.boiler_power_limit,number.boiler_hppowerlimit,5,0,1,239,1
"Geo 5xx",boiler,173,pc0flow,Flow PC0,int16 (>=-31999<=31999),l/h,false,sensor.boiler_Flow_PC0,sensor.boiler_pc0flow,5,0,1,240,1
"Geo 5xx",boiler,173,pc1flow,Flow PC1,int16 (>=-31999<=31999),l/h,false,sensor.boiler_Flow_PC1,sensor.boiler_pc1flow,5,0,1,241,1
"Geo 5xx",boiler,173,pc1on,PC1,boolean, ,false,binary_sensor.boiler_PC1,binary_sensor.boiler_pc1on,5,0,1,242,1
"Geo 5xx",boiler,173,pc1rate,PC1 rate,uint8 (>=0<=100),%,false,sensor.boiler_PC1_rate,sensor.boiler_pc1rate,5,0,1,243,1
"Geo 5xx",boiler,173,alternatingop,alternating operation,boolean, ,true,switch.boiler_dhw_alternating_operation,switch.boiler_dhw_alternatingop,5,9,1,15,1
"Geo 5xx",boiler,173,altopprioheat,prioritise heating during dhw,uint8 (>=20<=120),minutes,true,number.boiler_dhw_prioritise_heating_during_dhw,number.boiler_dhw_altopprioheat,5,9,1,16,1
"Geo 5xx",boiler,173,altopprio,prioritise dhw during heating,uint8 (>=30<=120),minutes,true,number.boiler_dhw_prioritise_dhw_during_heating,number.boiler_dhw_altopprio,5,9,1,17,1
"Geo 5xx",boiler,173,comfoff,comfort switch off,uint8 (>=15<=65),C,true,number.boiler_dhw_comfort_switch_off,number.boiler_dhw_comfoff,5,9,1,18,1
"Geo 5xx",boiler,173,ecooff,eco switch off,uint8 (>=15<=65),C,true,number.boiler_dhw_eco_switch_off,number.boiler_dhw_ecooff,5,9,1,19,1
"Geo 5xx",boiler,173,ecoplusoff,eco+ switch off,uint8 (>=48<=63),C,true,number.boiler_dhw_eco+_switch_off,number.boiler_dhw_ecoplusoff,5,9,1,20,1
"Geo 5xx",boiler,173,comfdiff,comfort diff,uint8 (>=6<=12),K,true,number.boiler_dhw_comfort_diff,number.boiler_dhw_comfdiff,5,9,1,21,1
"Geo 5xx",boiler,173,ecodiff,eco diff,uint8 (>=6<=12),K,true,number.boiler_dhw_eco_diff,number.boiler_dhw_ecodiff,5,9,1,22,1
"Geo 5xx",boiler,173,ecoplusdiff,eco+ diff,uint8 (>=6<=12),K,true,number.boiler_dhw_eco+_diff,number.boiler_dhw_ecoplusdiff,5,9,1,23,1
"Geo 5xx",boiler,173,comfstop,comfort stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_comfort_stop_temp,number.boiler_dhw_comfstop,5,9,1,24,1
"Geo 5xx",boiler,173,ecostop,eco stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_eco_stop_temp,number.boiler_dhw_ecostop,5,9,1,25,1
"Geo 5xx",boiler,173,ecoplusstop,eco+ stop temp,uint8 (>=0<=254),C,true,number.boiler_dhw_eco+_stop_temp,number.boiler_dhw_ecoplusstop,5,9,1,26,1
"Geo 5xx",boiler,173,hpcircpump,circulation pump available during dhw,boolean, ,true,switch.boiler_dhw_circulation_pump_available_during_dhw,switch.boiler_dhw_hpcircpump,5,9,1,27,1
"Geo 5xx",boiler,173,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Geo 5xx",boiler,173,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Geo 5xx",boiler,173,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Geo 5xx",boiler,173,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Geo 5xx",boiler,173,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Geo 5xx",boiler,173,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Geo 5xx",boiler,173,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Geo 5xx",boiler,173,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Geo 5xx",boiler,173,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Geo 5xx",boiler,173,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Geo 5xx",boiler,173,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Geo 5xx",boiler,173,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Geo 5xx",boiler,173,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Geo 5xx",boiler,173,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Geo 5xx",boiler,173,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Geo 5xx",boiler,173,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Geo 5xx",boiler,173,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Geo 5xx",boiler,173,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Geo 5xx",boiler,173,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Geo 5xx",boiler,173,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Geo 5xx",boiler,173,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Geo 5xx",boiler,173,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Geo 5xx",boiler,173,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Geo 5xx",boiler,173,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Geo 5xx",boiler,173,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Geo 5xx",boiler,173,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Geo 5xx",boiler,173,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Geo 5xx",boiler,173,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Geo 5xx",boiler,173,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Geo 5xx",boiler,173,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Geo 5xx",boiler,173,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Geo 5xx",boiler,173,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Geo 5xx",boiler,173,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Geo 5xx",boiler,173,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Geo 5xx",boiler,173,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Geo 5xx",boiler,173,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Geo 5xx",boiler,173,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Geo 5xx",boiler,173,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Geo 5xx",boiler,173,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Condens 5000i, Greenstar 8000/GC9800IW, GB192i*2",boiler,195,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logamax U122, Cerapur",boiler,203,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logamax U122, Cerapur",boiler,203,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logamax U122, Cerapur",boiler,203,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logamax U122, Cerapur",boiler,203,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logamax U122, Cerapur",boiler,203,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logamax U122, Cerapur",boiler,203,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logamax U122, Cerapur",boiler,203,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logamax U122, Cerapur",boiler,203,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logamax U122, Cerapur",boiler,203,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logamax U122, Cerapur",boiler,203,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logamax U122, Cerapur",boiler,203,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logamax U122, Cerapur",boiler,203,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logamax U122, Cerapur",boiler,203,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logamax U122, Cerapur",boiler,203,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logamax U122, Cerapur",boiler,203,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logamax U122, Cerapur",boiler,203,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logamax U122, Cerapur",boiler,203,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logamax U122, Cerapur",boiler,203,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logamax U122, Cerapur",boiler,203,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logamax U122, Cerapur",boiler,203,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logamax U122, Cerapur",boiler,203,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logamax U122, Cerapur",boiler,203,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logamax U122, Cerapur",boiler,203,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logamax U122, Cerapur",boiler,203,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logamax U122, Cerapur",boiler,203,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logamax U122, Cerapur",boiler,203,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logamax U122, Cerapur",boiler,203,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logamax U122, Cerapur",boiler,203,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logamax U122, Cerapur",boiler,203,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logamax U122, Cerapur",boiler,203,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logamax U122, Cerapur",boiler,203,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logamax U122, Cerapur",boiler,203,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logamax U122, Cerapur",boiler,203,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logamax U122, Cerapur",boiler,203,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logamax U122, Cerapur",boiler,203,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logamax U122, Cerapur",boiler,203,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logamax U122, Cerapur",boiler,203,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logamax U122, Cerapur",boiler,203,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logamax U122, Cerapur",boiler,203,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logamax U122, Cerapur",boiler,203,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logamax U122, Cerapur",boiler,203,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logamax U122, Cerapur",boiler,203,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logamax U122, Cerapur",boiler,203,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logamax U122, Cerapur",boiler,203,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logamax U122, Cerapur",boiler,203,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logamax U122, Cerapur",boiler,203,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logamax U122, Cerapur",boiler,203,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logamax U122, Cerapur",boiler,203,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logamax U122, Cerapur",boiler,203,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logamax U122, Cerapur",boiler,203,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logamax U122, Cerapur",boiler,203,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logamax U122, Cerapur",boiler,203,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logamax U122, Cerapur",boiler,203,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logamax U122, Cerapur",boiler,203,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logamax U122, Cerapur",boiler,203,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logamax U122, Cerapur",boiler,203,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logamax U122, Cerapur",boiler,203,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logamax U122, Cerapur",boiler,203,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logamax U122, Cerapur",boiler,203,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logamax U122, Cerapur",boiler,203,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logamax U122, Cerapur",boiler,203,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logamax U122, Cerapur",boiler,203,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logamax U122, Cerapur",boiler,203,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logamax U122, Cerapur",boiler,203,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logamax U122, Cerapur",boiler,203,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logamax U122, Cerapur",boiler,203,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logamax U122, Cerapur",boiler,203,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logamax U122, Cerapur",boiler,203,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logamax U122, Cerapur",boiler,203,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logamax U122, Cerapur",boiler,203,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logamax U122, Cerapur",boiler,203,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logamax U122, Cerapur",boiler,203,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logamax U122, Cerapur",boiler,203,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logamax U122, Cerapur",boiler,203,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logamax U122, Cerapur",boiler,203,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logamax U122, Cerapur",boiler,203,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logamax U122, Cerapur",boiler,203,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logamax U122, Cerapur",boiler,203,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logamax U122, Cerapur",boiler,203,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logamax U122, Cerapur",boiler,203,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logamax U122, Cerapur",boiler,203,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logamax U122, Cerapur",boiler,203,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logamax U122, Cerapur",boiler,203,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logamax U122, Cerapur",boiler,203,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logamax U122, Cerapur",boiler,203,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logamax U122, Cerapur",boiler,203,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logamax U122, Cerapur",boiler,203,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logamax U122, Cerapur",boiler,203,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logamax U122, Cerapur",boiler,203,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logamax U122, Cerapur",boiler,203,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logamax U122, Cerapur",boiler,203,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logamax U122, Cerapur",boiler,203,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logamax U122, Cerapur",boiler,203,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logamax U122, Cerapur",boiler,203,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logamax U122, Cerapur",boiler,203,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logamax U122, Cerapur",boiler,203,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logamax U122, Cerapur",boiler,203,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logamax U122, Cerapur",boiler,203,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logamax U122, Cerapur",boiler,203,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logamax U122, Cerapur",boiler,203,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logamax U122, Cerapur",boiler,203,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logamax U122, Cerapur",boiler,203,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logamax U122, Cerapur",boiler,203,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logamax U122, Cerapur",boiler,203,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logamax U122, Cerapur",boiler,203,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logamax U122, Cerapur",boiler,203,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logamax U122, Cerapur",boiler,203,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logamax U122, Cerapur",boiler,203,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logamax U122, Cerapur",boiler,203,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logamax U122, Cerapur",boiler,203,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Ecomline Excellent",boiler,206,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Ecomline Excellent",boiler,206,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Ecomline Excellent",boiler,206,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Ecomline Excellent",boiler,206,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Ecomline Excellent",boiler,206,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Ecomline Excellent",boiler,206,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Ecomline Excellent",boiler,206,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Ecomline Excellent",boiler,206,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Ecomline Excellent",boiler,206,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Ecomline Excellent",boiler,206,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Ecomline Excellent",boiler,206,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Ecomline Excellent",boiler,206,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Ecomline Excellent",boiler,206,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Ecomline Excellent",boiler,206,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Ecomline Excellent",boiler,206,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Ecomline Excellent",boiler,206,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Ecomline Excellent",boiler,206,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Ecomline Excellent",boiler,206,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Ecomline Excellent",boiler,206,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Ecomline Excellent",boiler,206,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Ecomline Excellent",boiler,206,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Ecomline Excellent",boiler,206,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Ecomline Excellent",boiler,206,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Ecomline Excellent",boiler,206,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Ecomline Excellent",boiler,206,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Ecomline Excellent",boiler,206,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Ecomline Excellent",boiler,206,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Ecomline Excellent",boiler,206,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Ecomline Excellent",boiler,206,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Ecomline Excellent",boiler,206,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Ecomline Excellent",boiler,206,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Ecomline Excellent",boiler,206,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Ecomline Excellent",boiler,206,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Ecomline Excellent",boiler,206,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Ecomline Excellent",boiler,206,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Ecomline Excellent",boiler,206,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Ecomline Excellent",boiler,206,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Ecomline Excellent",boiler,206,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Ecomline Excellent",boiler,206,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Ecomline Excellent",boiler,206,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Ecomline Excellent",boiler,206,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Ecomline Excellent",boiler,206,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Ecomline Excellent",boiler,206,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Ecomline Excellent",boiler,206,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Ecomline Excellent",boiler,206,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Ecomline Excellent",boiler,206,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Ecomline Excellent",boiler,206,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Ecomline Excellent",boiler,206,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Ecomline Excellent",boiler,206,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Ecomline Excellent",boiler,206,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Ecomline Excellent",boiler,206,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Ecomline Excellent",boiler,206,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Ecomline Excellent",boiler,206,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Ecomline Excellent",boiler,206,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Ecomline Excellent",boiler,206,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Ecomline Excellent",boiler,206,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Ecomline Excellent",boiler,206,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Ecomline Excellent",boiler,206,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Ecomline Excellent",boiler,206,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Ecomline Excellent",boiler,206,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Ecomline Excellent",boiler,206,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Ecomline Excellent",boiler,206,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Ecomline Excellent",boiler,206,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Ecomline Excellent",boiler,206,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Ecomline Excellent",boiler,206,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Ecomline Excellent",boiler,206,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Ecomline Excellent",boiler,206,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Ecomline Excellent",boiler,206,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Ecomline Excellent",boiler,206,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Ecomline Excellent",boiler,206,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Ecomline Excellent",boiler,206,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Ecomline Excellent",boiler,206,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Ecomline Excellent",boiler,206,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Ecomline Excellent",boiler,206,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Ecomline Excellent",boiler,206,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Ecomline Excellent",boiler,206,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Ecomline Excellent",boiler,206,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Ecomline Excellent",boiler,206,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Ecomline Excellent",boiler,206,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Ecomline Excellent",boiler,206,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Ecomline Excellent",boiler,206,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Ecomline Excellent",boiler,206,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Ecomline Excellent",boiler,206,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Ecomline Excellent",boiler,206,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Ecomline Excellent",boiler,206,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Ecomline Excellent",boiler,206,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Ecomline Excellent",boiler,206,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Ecomline Excellent",boiler,206,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Ecomline Excellent",boiler,206,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Ecomline Excellent",boiler,206,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Ecomline Excellent",boiler,206,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Ecomline Excellent",boiler,206,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Ecomline Excellent",boiler,206,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Ecomline Excellent",boiler,206,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Ecomline Excellent",boiler,206,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Ecomline Excellent",boiler,206,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Ecomline Excellent",boiler,206,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Ecomline Excellent",boiler,206,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Ecomline Excellent",boiler,206,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Ecomline Excellent",boiler,206,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Ecomline Excellent",boiler,206,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Ecomline Excellent",boiler,206,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Ecomline Excellent",boiler,206,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Ecomline Excellent",boiler,206,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Ecomline Excellent",boiler,206,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Ecomline Excellent",boiler,206,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Ecomline Excellent",boiler,206,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Ecomline Excellent",boiler,206,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Ecomline Excellent",boiler,206,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Ecomline Excellent",boiler,206,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logamax Plus, GB192, Condens GC9000, Greenstar ErP",boiler,208,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Cascade MC400",boiler,210,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Cascade MC400",boiler,210,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Cascade MC400",boiler,210,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Cascade MC400",boiler,210,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Cascade MC400",boiler,210,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Cascade MC400",boiler,210,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Cascade MC400",boiler,210,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Cascade MC400",boiler,210,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Cascade MC400",boiler,210,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Cascade MC400",boiler,210,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Cascade MC400",boiler,210,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Cascade MC400",boiler,210,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Cascade MC400",boiler,210,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Cascade MC400",boiler,210,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Cascade MC400",boiler,210,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Cascade MC400",boiler,210,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Cascade MC400",boiler,210,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Cascade MC400",boiler,210,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Cascade MC400",boiler,210,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Cascade MC400",boiler,210,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Cascade MC400",boiler,210,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Cascade MC400",boiler,210,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Cascade MC400",boiler,210,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Cascade MC400",boiler,210,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Cascade MC400",boiler,210,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Cascade MC400",boiler,210,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Cascade MC400",boiler,210,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Cascade MC400",boiler,210,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Cascade MC400",boiler,210,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Cascade MC400",boiler,210,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Cascade MC400",boiler,210,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Cascade MC400",boiler,210,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Cascade MC400",boiler,210,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Cascade MC400",boiler,210,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Cascade MC400",boiler,210,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Cascade MC400",boiler,210,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Cascade MC400",boiler,210,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Cascade MC400",boiler,210,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Cascade MC400",boiler,210,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Cascade MC400",boiler,210,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Cascade MC400",boiler,210,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Cascade MC400",boiler,210,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Cascade MC400",boiler,210,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Cascade MC400",boiler,210,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Cascade MC400",boiler,210,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Cascade MC400",boiler,210,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Cascade MC400",boiler,210,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Cascade MC400",boiler,210,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Cascade MC400",boiler,210,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Cascade MC400",boiler,210,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Cascade MC400",boiler,210,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Cascade MC400",boiler,210,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Cascade MC400",boiler,210,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Cascade MC400",boiler,210,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Cascade MC400",boiler,210,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Cascade MC400",boiler,210,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Cascade MC400",boiler,210,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Cascade MC400",boiler,210,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Cascade MC400",boiler,210,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Cascade MC400",boiler,210,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Cascade MC400",boiler,210,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Cascade MC400",boiler,210,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Cascade MC400",boiler,210,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Cascade MC400",boiler,210,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Cascade MC400",boiler,210,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Cascade MC400",boiler,210,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Cascade MC400",boiler,210,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Cascade MC400",boiler,210,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Cascade MC400",boiler,210,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Cascade MC400",boiler,210,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Cascade MC400",boiler,210,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Cascade MC400",boiler,210,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Cascade MC400",boiler,210,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Cascade MC400",boiler,210,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Cascade MC400",boiler,210,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Cascade MC400",boiler,210,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Cascade MC400",boiler,210,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Cascade MC400",boiler,210,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Cascade MC400",boiler,210,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Cascade MC400",boiler,210,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Cascade MC400",boiler,210,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Cascade MC400",boiler,210,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Cascade MC400",boiler,210,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Cascade MC400",boiler,210,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Cascade MC400",boiler,210,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Cascade MC400",boiler,210,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Cascade MC400",boiler,210,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Cascade MC400",boiler,210,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Cascade MC400",boiler,210,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Cascade MC400",boiler,210,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Cascade MC400",boiler,210,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Cascade MC400",boiler,210,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Cascade MC400",boiler,210,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Cascade MC400",boiler,210,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Cascade MC400",boiler,210,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Cascade MC400",boiler,210,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Cascade MC400",boiler,210,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Cascade MC400",boiler,210,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Cascade MC400",boiler,210,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Cascade MC400",boiler,210,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Cascade MC400",boiler,210,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Cascade MC400",boiler,210,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Cascade MC400",boiler,210,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Cascade MC400",boiler,210,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Cascade MC400",boiler,210,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Cascade MC400",boiler,210,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Cascade MC400",boiler,210,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Cascade MC400",boiler,210,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Cascade MC400",boiler,210,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Cascade MC400",boiler,210,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"EasyControl Adapter",boiler,211,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"EasyControl Adapter",boiler,211,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"EasyControl Adapter",boiler,211,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"EasyControl Adapter",boiler,211,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"EasyControl Adapter",boiler,211,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"EasyControl Adapter",boiler,211,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"EasyControl Adapter",boiler,211,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"EasyControl Adapter",boiler,211,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"EasyControl Adapter",boiler,211,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"EasyControl Adapter",boiler,211,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"EasyControl Adapter",boiler,211,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"EasyControl Adapter",boiler,211,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"EasyControl Adapter",boiler,211,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"EasyControl Adapter",boiler,211,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"EasyControl Adapter",boiler,211,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"EasyControl Adapter",boiler,211,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"EasyControl Adapter",boiler,211,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"EasyControl Adapter",boiler,211,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"EasyControl Adapter",boiler,211,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"EasyControl Adapter",boiler,211,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"EasyControl Adapter",boiler,211,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"EasyControl Adapter",boiler,211,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"EasyControl Adapter",boiler,211,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"EasyControl Adapter",boiler,211,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"EasyControl Adapter",boiler,211,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"EasyControl Adapter",boiler,211,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"EasyControl Adapter",boiler,211,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"EasyControl Adapter",boiler,211,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"EasyControl Adapter",boiler,211,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"EasyControl Adapter",boiler,211,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"EasyControl Adapter",boiler,211,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"EasyControl Adapter",boiler,211,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"EasyControl Adapter",boiler,211,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"EasyControl Adapter",boiler,211,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"EasyControl Adapter",boiler,211,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"EasyControl Adapter",boiler,211,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"EasyControl Adapter",boiler,211,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"EasyControl Adapter",boiler,211,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"EasyControl Adapter",boiler,211,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"EasyControl Adapter",boiler,211,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"EasyControl Adapter",boiler,211,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"EasyControl Adapter",boiler,211,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"EasyControl Adapter",boiler,211,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"EasyControl Adapter",boiler,211,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"EasyControl Adapter",boiler,211,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"EasyControl Adapter",boiler,211,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"EasyControl Adapter",boiler,211,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"EasyControl Adapter",boiler,211,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"EasyControl Adapter",boiler,211,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"EasyControl Adapter",boiler,211,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"EasyControl Adapter",boiler,211,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"EasyControl Adapter",boiler,211,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"EasyControl Adapter",boiler,211,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"EasyControl Adapter",boiler,211,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"EasyControl Adapter",boiler,211,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"EasyControl Adapter",boiler,211,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"EasyControl Adapter",boiler,211,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"EasyControl Adapter",boiler,211,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"EasyControl Adapter",boiler,211,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"EasyControl Adapter",boiler,211,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"EasyControl Adapter",boiler,211,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"EasyControl Adapter",boiler,211,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"EasyControl Adapter",boiler,211,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"EasyControl Adapter",boiler,211,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"EasyControl Adapter",boiler,211,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"EasyControl Adapter",boiler,211,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"EasyControl Adapter",boiler,211,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"EasyControl Adapter",boiler,211,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"EasyControl Adapter",boiler,211,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"EasyControl Adapter",boiler,211,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"EasyControl Adapter",boiler,211,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"EasyControl Adapter",boiler,211,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"EasyControl Adapter",boiler,211,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"EasyControl Adapter",boiler,211,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"EasyControl Adapter",boiler,211,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"EasyControl Adapter",boiler,211,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"EasyControl Adapter",boiler,211,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"EasyControl Adapter",boiler,211,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"EasyControl Adapter",boiler,211,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"EasyControl Adapter",boiler,211,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"EasyControl Adapter",boiler,211,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"EasyControl Adapter",boiler,211,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"EasyControl Adapter",boiler,211,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"EasyControl Adapter",boiler,211,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"EasyControl Adapter",boiler,211,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"EasyControl Adapter",boiler,211,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"EasyControl Adapter",boiler,211,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"EasyControl Adapter",boiler,211,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"EasyControl Adapter",boiler,211,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"EasyControl Adapter",boiler,211,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"EasyControl Adapter",boiler,211,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"EasyControl Adapter",boiler,211,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"EasyControl Adapter",boiler,211,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"EasyControl Adapter",boiler,211,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"EasyControl Adapter",boiler,211,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"EasyControl Adapter",boiler,211,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"EasyControl Adapter",boiler,211,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"EasyControl Adapter",boiler,211,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"EasyControl Adapter",boiler,211,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"EasyControl Adapter",boiler,211,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"EasyControl Adapter",boiler,211,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"EasyControl Adapter",boiler,211,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"EasyControl Adapter",boiler,211,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"EasyControl Adapter",boiler,211,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"EasyControl Adapter",boiler,211,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"EasyControl Adapter",boiler,211,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"EasyControl Adapter",boiler,211,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"EasyControl Adapter",boiler,211,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"EasyControl Adapter",boiler,211,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"EasyControl Adapter",boiler,211,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,netflowtemp,heat network flow temp,uint16 (>=0<=3199),C,false,sensor.boiler_heat_network_flow_temp,sensor.boiler_netflowtemp,5,0,1/10,271,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatvalve,heating valve,uint8 (>=0<=100),%,false,sensor.boiler_heating_valve,sensor.boiler_heatvalve,5,0,1,272,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,dhwvalve,valve,uint8 (>=0<=100),%,false,sensor.boiler_dhw_valve,sensor.boiler_dhw_dhwvalve,5,9,1,73,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,keepwarmtemp,keep warm temperature,uint8 (>=0<=254),C,true,number.boiler_keep_warm_temperature,number.boiler_keepwarmtemp,5,0,1,273,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,setreturntemp,set temp return,uint8 (>=0<=254),C,true,number.boiler_set_temp_return,number.boiler_setreturntemp,5,0,1,274,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heating,heating,boolean, ,false,binary_sensor.boiler_heating,binary_sensor.boiler_heating,5,0,1,275,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Greenstar HIU, Logamax kompakt WS170",boiler,219,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Greenstar HIU, Logamax kompakt WS170",boiler,219,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Greenstar HIU, Logamax kompakt WS170",boiler,219,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Greenstar HIU, Logamax kompakt WS170",boiler,219,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,reset,reset,cmd [-\|maintenance\|error\|history\|message], ,true,sensor.boiler_reset,sensor.boiler_reset,5,0,1,0,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatingoff,force heating off,boolean, ,true,switch.boiler_force_heating_off,switch.boiler_heatingoff,5,0,1,1,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatingactive,heating active,boolean, ,false,binary_sensor.boiler_heating_active,binary_sensor.boiler_heatingactive,5,0,1,2,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,tapwateractive,tapwater active,boolean, ,false,binary_sensor.boiler_tapwater_active,binary_sensor.boiler_tapwateractive,5,0,1,3,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,selflowtemp,selected flow temperature,uint8 (>=0<=90),C,true,number.boiler_selected_flow_temperature,number.boiler_selflowtemp,5,0,1,4,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.boiler_heating_pump_modulation,sensor.boiler_heatingpumpmod,5,0,1,5,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,outdoortemp,outside temperature,int16 (>=-3199<=3199),C,false,sensor.boiler_outside_temperature,sensor.boiler_outdoortemp,5,0,1/10,6,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curflowtemp,current flow temperature,uint16 (>=0<=3199),C,false,sensor.boiler_current_flow_temperature,sensor.boiler_curflowtemp,5,0,1/10,7,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.boiler_return_temperature,sensor.boiler_rettemp,5,0,1/10,8,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,switchtemp,mixing switch temperature,uint16 (>=0<=3199),C,false,sensor.boiler_mixing_switch_temperature,sensor.boiler_switchtemp,5,0,1/10,9,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,syspress,system pressure,uint8 (>=0<=25),bar,false,sensor.boiler_system_pressure,sensor.boiler_syspress,5,0,1/10,10,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,boiltemp,actual boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_actual_boiler_temperature,sensor.boiler_boiltemp,5,0,1/10,11,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,headertemp,low loss header,uint16 (>=0<=3199),C,false,sensor.boiler_low_loss_header,sensor.boiler_headertemp,5,0,1/10,12,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,exhausttemp,exhaust temperature,uint16 (>=0<=3199),C,false,sensor.boiler_exhaust_temperature,sensor.boiler_exhausttemp,5,0,1/10,244,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burngas,gas,boolean, ,false,binary_sensor.boiler_gas,binary_sensor.boiler_burngas,5,0,1,245,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burngas2,gas stage 2,boolean, ,false,binary_sensor.boiler_gas_stage_2,binary_sensor.boiler_burngas2,5,0,1,246,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,flamecurr,flame current,uint16 (>=0<=3199),µA,false,sensor.boiler_flame_current,sensor.boiler_flamecurr,5,0,1/10,247,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,fanwork,fan,boolean, ,false,binary_sensor.boiler_fan,binary_sensor.boiler_fanwork,5,0,1,248,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,ignwork,ignition,boolean, ,false,binary_sensor.boiler_ignition,binary_sensor.boiler_ignwork,5,0,1,249,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,oilpreheat,oil preheating,boolean, ,false,binary_sensor.boiler_oil_preheating,binary_sensor.boiler_oilpreheat,5,0,1,250,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burnminpower,burner min power,uint8 (>=0<=100),%,true,number.boiler_burner_min_power,number.boiler_burnminpower,5,0,1,251,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burnmaxpower,burner max power,uint8 (>=0<=254),%,true,number.boiler_burner_max_power,number.boiler_burnmaxpower,5,0,1,252,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burnminperiod,burner min period,uint8 (>=0<=120),minutes,true,number.boiler_burner_min_period,number.boiler_burnminperiod,5,0,1,253,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,absburnpow,burner current power (absolute),uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power_(absolute),sensor.boiler_absburnpow,5,0,1,254,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatblock,heating block,uint16 (>=0<=3199),C,false,sensor.boiler_heating_block,sensor.boiler_heatblock,5,0,1/10,255,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,boilhyston,hysteresis on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_on_temperature,number.boiler_boilhyston,5,0,1,256,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,boilhystoff,hysteresis off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_off_temperature,number.boiler_boilhystoff,5,0,1,257,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,boil2hyston,hysteresis stage 2 on temperature,int8 (>=-20<=0),C,true,number.boiler_hysteresis_stage_2_on_temperature,number.boiler_boil2hyston,5,0,1,258,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,boil2hystoff,hysteresis stage 2 off temperature,int8 (>=0<=20),C,true,number.boiler_hysteresis_stage_2_off_temperature,number.boiler_boil2hystoff,5,0,1,259,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curveon,heatingcurve on,boolean, ,true,switch.boiler_heatingcurve_on,switch.boiler_curveon,5,0,1,260,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curvebase,heatingcurve base,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_base,number.boiler_curvebase,5,0,1,261,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curveend,heatingcurve end,uint8 (>=20<=90),C,true,number.boiler_heatingcurve_end,number.boiler_curveend,5,0,1,262,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,summertemp,summer temperature,uint8 (>=0<=45),C,true,number.boiler_summer_temperature,number.boiler_summertemp,5,0,1,263,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nofrostmode,nofrost mode,boolean, ,true,switch.boiler_nofrost_mode,switch.boiler_nofrostmode,5,0,1,264,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nofrosttemp,nofrost temperature,uint8 (>=0<=10),C,true,number.boiler_nofrost_temperature,number.boiler_nofrosttemp,5,0,1,265,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatingactivated,heating activated,boolean, ,true,switch.boiler_heating_activated,switch.boiler_heatingactivated,5,0,1,13,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatingtemp,heating temperature,uint8 (>=0<=90),C,true,number.boiler_heating_temperature,number.boiler_heatingtemp,5,0,1,14,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatingpump,heating pump,boolean, ,false,binary_sensor.boiler_heating_pump,binary_sensor.boiler_heatingpump,5,0,1,15,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,pumpmodmax,boiler pump max power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_max_power,number.boiler_pumpmodmax,5,0,1,16,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,pumpmodmin,boiler pump min power,uint8 (>=0<=100),%,true,number.boiler_boiler_pump_min_power,number.boiler_pumpmodmin,5,0,1,17,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,pumpmode,boiler pump mode,enum [proportional\|deltaP-1\|deltaP-2\|deltaP-3\|deltaP-4], ,true,select.boiler_boiler_pump_mode,select.boiler_pumpmode,5,0,1,18,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,pumpcharacter,boiler pump characteristic,enum [proportional\|150mbar\|200mbar\|250mbar\|300mbar\|350mbar\|400mbar], ,true,select.boiler_boiler_pump_characteristic,select.boiler_pumpcharacter,5,0,1,19,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,pumpdelay,pump delay,uint8 (>=0<=60),minutes,true,number.boiler_pump_delay,number.boiler_pumpdelay,5,0,1,20,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,pumpontemp,pump logic temperature,uint8 (>=0<=60),C,true,number.boiler_pump_logic_temperature,number.boiler_pumpontemp,5,0,1,21,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,selburnpow,burner selected max power,uint8 (>=0<=254),%,true,number.boiler_burner_selected_max_power,number.boiler_selburnpow,5,0,1,22,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curburnpow,burner current power,uint8 (>=0<=100),%,false,sensor.boiler_burner_current_power,sensor.boiler_curburnpow,5,0,1,23,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burnstarts,burner starts,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts,sensor.boiler_burnstarts,5,0,1,24,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burnworkmin,total burner operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_burner_operating_time,sensor.boiler_burnworkmin,5,0,1,26,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,burn2workmin,burner stage 2 operating time,time (>=0<=16777213),minutes,false,sensor.boiler_burner_stage_2_operating_time,sensor.boiler_burn2workmin,5,0,1,28,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatworkmin,total heat operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_heat_operating_time,sensor.boiler_heatworkmin,5,0,1,30,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,heatstarts,burner starts heating,uint24 (>=0<=16777213), ,false,sensor.boiler_burner_starts_heating,sensor.boiler_heatstarts,5,0,1,32,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,ubauptime,total UBA operating time,time (>=0<=16777213),minutes,false,sensor.boiler_total_UBA_operating_time,sensor.boiler_ubauptime,5,0,1,34,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,lastcode,last error code,string, ,false,sensor.boiler_last_error_code,sensor.boiler_lastcode,5,0,1,36,28
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,servicecode,service code,string, ,false,sensor.boiler_service_code,sensor.boiler_servicecode,5,0,1,64,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,servicecodenumber,service code number,uint16 (>=0<=31999), ,false,sensor.boiler_service_code_number,sensor.boiler_servicecodenumber,5,0,1,66,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,maintenancemessage,maintenance message,string, ,false,sensor.boiler_maintenance_message,sensor.boiler_maintenancemessage,5,0,1,67,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,maintenance,maintenance scheduled,enum [off\|time\|date\|manual], ,true,select.boiler_maintenance_scheduled,select.boiler_maintenance,5,0,1,69,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,maintenancetime,time to next maintenance,uint16 (>=0<=31999),hours,true,number.boiler_time_to_next_maintenance,number.boiler_maintenancetime,5,0,1,70,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,maintenancedate,next maintenance date,string, ,true,sensor.boiler_next_maintenance_date,sensor.boiler_maintenancedate,5,0,1,71,6
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,emergencyops,emergency operation,boolean, ,true,switch.boiler_emergency_operation,switch.boiler_emergencyops,5,0,1,77,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,emergencytemp,emergency temperature,uint8 (>=15<=70),C,true,number.boiler_emergency_temperature,number.boiler_emergencytemp,5,0,1,78,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,meterheat,meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_meter_heating,sensor.boiler_meterheat,5,0,1/10,91,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,meter,meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_meter,sensor.boiler_dhw_meter,5,9,1/10,2,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,gasmeterheat,gas meter heating,uint24 (>=0<=1677721),kWh,false,sensor.boiler_gas_meter_heating,sensor.boiler_gasmeterheat,5,0,1/10,266,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,gasmeter,gas meter,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_gas_meter,sensor.boiler_dhw_gasmeter,5,9,1/10,69,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nrgheat2,energy heating 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_energy_heating_2,sensor.boiler_nrgheat2,5,0,1/10,268,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nrg2,energy 2,uint24 (>=0<=1677721),kWh,false,sensor.boiler_dhw_energy_2,sensor.boiler_dhw_nrg2,5,9,1/10,71,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,tapactivated,turn on/off,boolean, ,true,switch.boiler_dhw_turn_on/off,switch.boiler_dhw_tapactivated,5,9,1,28,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,settemp,set temperature,uint8 (>=0<=254),C,false,sensor.boiler_dhw_set_temperature,sensor.boiler_dhw_settemp,5,9,1,29,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_temperature,number.boiler_dhw_seltemp,5,9,1,30,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,seltemplow,selected lower temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_lower_temperature,number.boiler_dhw_seltemplow,5,9,1,31,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,tempecoplus,selected eco+ temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_selected_eco+_temperature,number.boiler_dhw_tempecoplus,5,9,1,32,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,seltempoff,selected temperature for off,uint8 (>=0<=254),C,false,sensor.boiler_dhw_selected_temperature_for_off,sensor.boiler_dhw_seltempoff,5,9,1,33,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,seltempsingle,single charge temperature,uint8 (>=0<=254),C,true,number.boiler_dhw_single_charge_temperature,number.boiler_dhw_seltempsingle,5,9,1,34,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,solartemp,solar boiler temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_solar_boiler_temperature,sensor.boiler_dhw_solartemp,5,9,1/10,35,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,type,type,enum [off\|flow\|buffered flow\|buffer\|layered buffer], ,false,sensor.boiler_dhw_type,sensor.boiler_dhw_type,5,9,1,36,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,comfort,comfort,enum [hot\|eco\|intelligent], ,true,select.boiler_dhw_comfort,select.boiler_dhw_comfort,5,9,1,37,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,comfort1,comfort mode,enum [high comfort\|eco], ,true,select.boiler_dhw_comfort_mode,select.boiler_dhw_comfort1,5,9,1,38,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,flowtempoffset,flow temperature offset,uint8 (>=0<=100),C,true,number.boiler_dhw_flow_temperature_offset,number.boiler_dhw_flowtempoffset,5,9,1,39,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,chargeoptimization,charge optimization,boolean, ,true,switch.boiler_dhw_charge_optimization,switch.boiler_dhw_chargeoptimization,5,9,1,40,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,maxpower,max power,uint8 (>=0<=254),%,true,number.boiler_dhw_max_power,number.boiler_dhw_maxpower,5,9,1,41,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,maxtemp,maximum temperature,uint8 (>=0<=80),C,true,number.boiler_dhw_maximum_temperature,number.boiler_dhw_maxtemp,5,9,1,42,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,circpump,circulation pump available,boolean, ,true,switch.boiler_dhw_circulation_pump_available,switch.boiler_dhw_circpump,5,9,1,43,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,chargetype,charging type,enum [chargepump\|3-way valve], ,false,sensor.boiler_dhw_charging_type,sensor.boiler_dhw_chargetype,5,9,1,44,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_on_temperature,number.boiler_dhw_hyston,5,9,1,45,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.boiler_dhw_hysteresis_off_temperature,number.boiler_dhw_hystoff,5,9,1,46,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,disinfectiontemp,disinfection temperature,uint8 (>=60<=80),C,true,number.boiler_dhw_disinfection_temperature,number.boiler_dhw_disinfectiontemp,5,9,1,47,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.boiler_dhw_circulation_pump_mode,select.boiler_dhw_circmode,5,9,1,48,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,circ,circulation active,boolean, ,true,switch.boiler_dhw_circulation_active,switch.boiler_dhw_circ,5,9,1,49,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curtemp,current intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_intern_temperature,sensor.boiler_dhw_curtemp,5,9,1/10,50,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_current_extern_temperature,sensor.boiler_dhw_curtemp2,5,9,1/10,51,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,curflow,current tap water flow,uint8 (>=0<=25),l/min,false,sensor.boiler_dhw_current_tap_water_flow,sensor.boiler_dhw_curflow,5,9,1/10,52,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_intern_temperature,sensor.boiler_dhw_storagetemp1,5,9,1/10,53,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,storagetemp2,storage extern temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_storage_extern_temperature,sensor.boiler_dhw_storagetemp2,5,9,1/10,54,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,activated,activated,boolean, ,true,switch.boiler_dhw_activated,switch.boiler_dhw_activated,5,9,1,55,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,onetime,one time charging,boolean, ,true,switch.boiler_dhw_one_time_charging,switch.boiler_dhw_onetime,5,9,1,56,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,disinfecting,disinfecting,boolean, ,true,switch.boiler_dhw_disinfecting,switch.boiler_dhw_disinfecting,5,9,1,57,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,charging,charging,boolean, ,false,binary_sensor.boiler_dhw_charging,binary_sensor.boiler_dhw_charging,5,9,1,58,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,recharging,recharging,boolean, ,false,binary_sensor.boiler_dhw_recharging,binary_sensor.boiler_dhw_recharging,5,9,1,59,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,tempok,temperature ok,boolean, ,false,binary_sensor.boiler_dhw_temperature_ok,binary_sensor.boiler_dhw_tempok,5,9,1,60,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,active,active,boolean, ,false,binary_sensor.boiler_dhw_active,binary_sensor.boiler_dhw_active,5,9,1,61,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,3wayvalve,3-way valve active,boolean, ,false,binary_sensor.boiler_dhw_3-way_valve_active,binary_sensor.boiler_dhw_3wayvalve,5,9,1,62,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,mixertemp,mixer temperature,uint16 (>=0<=3199),C,false,sensor.boiler_dhw_mixer_temperature,sensor.boiler_dhw_mixertemp,5,9,1/10,63,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,cylmiddletemp,cylinder middle temperature (TS3),uint16 (>=0<=3199),C,false,sensor.boiler_dhw_cylinder_middle_temperature_(TS3),sensor.boiler_dhw_cylmiddletemp,5,9,1/10,64,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,starts,starts,uint24 (>=0<=16777213), ,false,sensor.boiler_dhw_starts,sensor.boiler_dhw_starts,5,9,1,65,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,workm,active time,time (>=0<=16777213),minutes,false,sensor.boiler_dhw_active_time,sensor.boiler_dhw_workm,5,9,1,67,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nompower,nominal Power,uint8 (>=0<=254),kW,true,number.boiler_nominal_Power,number.boiler_nompower,5,0,1,270,1
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.boiler_total_energy,sensor.boiler_nrgtotal,5,0,1/100,79,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nrgheat,energy heating,uint24 (>=0<=10000000),kWh,true,number.boiler_energy_heating,number.boiler_nrgheat,5,0,1/100,81,2
"Logamax Plus GB122, Condense 2300, Junkers Cerapur GC2200W",boiler,234,nrg,energy,uint24 (>=0<=10000000),kWh,true,number.boiler_dhw_energy,number.boiler_dhw_nrg,5,9,1/100,0,2
"Logamatic TC100, Moduline Easy",thermostat,202,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Logamatic TC100, Moduline Easy",thermostat,202,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Logamatic TC100, Moduline Easy",thermostat,202,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"Logamatic TC100, Moduline Easy",thermostat,202,seltemp,selected room temperature,int16 (>=-319<=319),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp,6,1,1/100,0,1
"Logamatic TC100, Moduline Easy",thermostat,202,currtemp,current room temperature,int16 (>=-319<=319),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/100,1,1
"Logamatic TC100, Moduline Easy",thermostat,202,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"EasyControl, CT200",thermostat,203,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"EasyControl, CT200",thermostat,203,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"EasyControl, CT200",thermostat,203,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"EasyControl, CT200",thermostat,203,seltemp,selected room temperature,int16 (>=-319<=319),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp,6,1,1/100,0,1
"EasyControl, CT200",thermostat,203,currtemp,current room temperature,int16 (>=-319<=319),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/100,1,1
"EasyControl, CT200",thermostat,203,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"UI800, BC400",thermostat,4,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"UI800, BC400",thermostat,4,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"UI800, BC400",thermostat,4,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"UI800, BC400",thermostat,4,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"UI800, BC400",thermostat,4,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"UI800, BC400",thermostat,4,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"UI800, BC400",thermostat,4,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"UI800, BC400",thermostat,4,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"UI800, BC400",thermostat,4,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"UI800, BC400",thermostat,4,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"UI800, BC400",thermostat,4,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"UI800, BC400",thermostat,4,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"UI800, BC400",thermostat,4,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"UI800, BC400",thermostat,4,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"UI800, BC400",thermostat,4,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"UI800, BC400",thermostat,4,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"UI800, BC400",thermostat,4,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"UI800, BC400",thermostat,4,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"UI800, BC400",thermostat,4,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"UI800, BC400",thermostat,4,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"UI800, BC400",thermostat,4,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"UI800, BC400",thermostat,4,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"UI800, BC400",thermostat,4,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"UI800, BC400",thermostat,4,mode,operating mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"UI800, BC400",thermostat,4,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"UI800, BC400",thermostat,4,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"UI800, BC400",thermostat,4,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"UI800, BC400",thermostat,4,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"UI800, BC400",thermostat,4,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"UI800, BC400",thermostat,4,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"UI800, BC400",thermostat,4,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"UI800, BC400",thermostat,4,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"UI800, BC400",thermostat,4,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"UI800, BC400",thermostat,4,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"UI800, BC400",thermostat,4,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"UI800, BC400",thermostat,4,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"UI800, BC400",thermostat,4,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"UI800, BC400",thermostat,4,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"UI800, BC400",thermostat,4,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"UI800, BC400",thermostat,4,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"UI800, BC400",thermostat,4,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"UI800, BC400",thermostat,4,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"UI800, BC400",thermostat,4,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"UI800, BC400",thermostat,4,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"UI800, BC400",thermostat,4,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"UI800, BC400",thermostat,4,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"UI800, BC400",thermostat,4,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"UI800, BC400",thermostat,4,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"UI800, BC400",thermostat,4,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"UI800, BC400",thermostat,4,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"UI800, BC400",thermostat,4,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"UI800, BC400",thermostat,4,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"UI800, BC400",thermostat,4,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"UI800, BC400",thermostat,4,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"UI800, BC400",thermostat,4,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"UI800, BC400",thermostat,4,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"UI800, BC400",thermostat,4,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"UI800, BC400",thermostat,4,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"UI800, BC400",thermostat,4,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"UI800, BC400",thermostat,4,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"UI800, BC400",thermostat,4,control,control device,enum [off\|-\|RC100\|RC100H\|-\|RC120RF\|RC220/RT800\|single], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"UI800, BC400",thermostat,4,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"UI800, BC400",thermostat,4,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"UI800, BC400",thermostat,4,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"UI800, BC400",thermostat,4,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"UI800, BC400",thermostat,4,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"UI800, BC400",thermostat,4,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"UI800, BC400",thermostat,4,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"UI800, BC400",thermostat,4,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"UI800, BC400",thermostat,4,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"UI800, BC400",thermostat,4,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"UI800, BC400",thermostat,4,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"UI800, BC400",thermostat,4,mode,operating mode,enum [off\|eco+\|eco\|comfort\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"UI800, BC400",thermostat,4,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"UI800, BC400",thermostat,4,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"UI800, BC400",thermostat,4,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"UI800, BC400",thermostat,4,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"UI800, BC400",thermostat,4,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"UI800, BC400",thermostat,4,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"UI800, BC400",thermostat,4,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"UI800, BC400",thermostat,4,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"UI800, BC400",thermostat,4,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"UI800, BC400",thermostat,4,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"UI800, BC400",thermostat,4,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"RC10",thermostat,65,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC10",thermostat,65,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC10",thermostat,65,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC10",thermostat,65,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC10",thermostat,65,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC10",thermostat,65,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC10",thermostat,65,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC10",thermostat,65,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC10",thermostat,65,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC10",thermostat,65,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"RC10",thermostat,65,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC10",thermostat,65,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC10",thermostat,65,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC10",thermostat,65,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC10",thermostat,65,tempautotemp,temporary set temperature automode,uint8 (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC10",thermostat,65,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC10",thermostat,65,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC10",thermostat,65,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC30",thermostat,67,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC30",thermostat,67,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC30",thermostat,67,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC30",thermostat,67,display,display,enum [internal temperature\|internal setpoint\|external temperature\|burner temperature\|dhw temperature\|functioning mode\|time\|date\|smoke temperature], ,true,select.thermostat_display,select.thermostat_display,6,0,1,63,1
"RC30",thermostat,67,language,language,enum [german\|dutch\|french\|italian], ,false,sensor.thermostat_language,sensor.thermostat_language,6,0,1,64,1
"RC30",thermostat,67,clockoffset,clock offset,int8 (>=-126<=126),seconds,true,number.thermostat_clock_offset,number.thermostat_clockoffset,6,0,1,65,1
"RC30",thermostat,67,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC30",thermostat,67,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC30",thermostat,67,inttemp1,temperature sensor 1,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1,6,0,1/10,66,1
"RC30",thermostat,67,inttemp2,temperature sensor 2,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2,6,0,1/10,67,1
"RC30",thermostat,67,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"RC30",thermostat,67,dampedoutdoortemp,damped outdoor temperature,int8 (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1,48,1
"RC30",thermostat,67,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"RC30",thermostat,67,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC30",thermostat,67,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC30",thermostat,67,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC30",thermostat,67,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC30",thermostat,67,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC30",thermostat,67,daytemp,day temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"RC30",thermostat,67,nighttemp,night temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC30",thermostat,67,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"RC30",thermostat,67,offsettemp,offset temperature,int8 (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1/2,10,1
"RC30",thermostat,67,holidaytemp,holiday temperature,uint8 (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp,6,1,1/2,54,1
"RC30",thermostat,67,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"RC30",thermostat,67,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC30",thermostat,67,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC30",thermostat,67,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode,6,1,1,55,1
"RC30",thermostat,67,nofrosttemp,nofrost temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"RC30",thermostat,67,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"RC30",thermostat,67,roominfluence,room influence,uint8 (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"RC30",thermostat,67,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC30",thermostat,67,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC30",thermostat,67,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset,6,1,1,56,1
"RC30",thermostat,67,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC30",thermostat,67,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"RC30",thermostat,67,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"RC30",thermostat,67,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"RC30",thermostat,67,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays,6,1,1,57,13
"RC30",thermostat,67,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations,6,1,1,70,13
"RC30",thermostat,67,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC30",thermostat,67,pause,pause time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause,6,1,1,83,1
"RC30",thermostat,67,party,party time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party,6,1,1,84,1
"RC30",thermostat,67,tempautotemp,temporary set temperature automode,uint8 (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC30",thermostat,67,noreducetemp,no reduce below temperature,int8 (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"RC30",thermostat,67,reducetemp,off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"RC30",thermostat,67,vacreducetemp,vacations off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp,6,1,1,85,1
"RC30",thermostat,67,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode,6,1,1,86,1
"RC30",thermostat,67,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"RC30",thermostat,67,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"RC30",thermostat,67,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"RC30",thermostat,67,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1,6,1,1,87,8
"RC30",thermostat,67,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2,6,1,1,95,8
"RC30",thermostat,67,mode,operating mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC30",thermostat,67,circmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"RC30",thermostat,67,progmode,program,enum [std prog\|own prog], ,true,select.thermostat_dhw_program,select.thermostat_dhw_progmode,6,9,1,12,1
"RC30",thermostat,67,circprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_dhw_circulation_program,select.thermostat_dhw_circprog,6,9,1,13,1
"RC30",thermostat,67,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"RC30",thermostat,67,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"RC30",thermostat,67,disinfecthour,disinfection hour,uint8 (>=0<=23), ,true,number.thermostat_dhw_disinfection_hour,number.thermostat_dhw_disinfecthour,6,9,1,14,1
"RC30",thermostat,67,maxtemp,maximum temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_maximum_temperature,number.thermostat_dhw_maxtemp,6,9,1,15,1
"RC30",thermostat,67,onetimekey,one time key function,boolean, ,true,switch.thermostat_dhw_one_time_key_function,switch.thermostat_dhw_onetimekey,6,9,1,16,1
"RC30",thermostat,67,switchtimeWW,program switchtime warm water,string, ,true,sensor.thermostat_dhw_program_switchtime_warm_water,sensor.thermostat_dhw_switchtimeWW,6,9,1,17,11
"RC30",thermostat,67,circswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_dhw_circulation_program_switchtime,sensor.thermostat_dhw_circswitchtime,6,9,1,28,8
"RC30",thermostat,67,holidays,holiday dates,string, ,true,sensor.thermostat_dhw_holiday_dates,sensor.thermostat_dhw_holidays,6,9,1,36,13
"RC30",thermostat,67,vacations,vacation dates,string, ,true,sensor.thermostat_dhw_vacation_dates,sensor.thermostat_dhw_vacations,6,9,1,49,13
"RC20, Moduline 300",thermostat,77,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC20, Moduline 300",thermostat,77,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC20, Moduline 300",thermostat,77,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC20, Moduline 300",thermostat,77,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC20, Moduline 300",thermostat,77,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC20, Moduline 300",thermostat,77,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC20, Moduline 300",thermostat,77,mode,operating mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC20, Moduline 300",thermostat,77,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"RC20, Moduline 300",thermostat,77,offtemp,temperature when mode is off,uint8 (>=0<=127),C,true,number.thermostat_hc1_temperature_when_mode_is_off,number.thermostat_hc1_offtemp,6,1,1/2,103,1
"RC20, Moduline 300",thermostat,77,daytemp2,day temperature T2,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T2,number.thermostat_hc1_daytemp2,6,1,1/2,104,1
"RC20, Moduline 300",thermostat,77,daytemp3,day temperature T3,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T3,number.thermostat_hc1_daytemp3,6,1,1/2,105,1
"RC20, Moduline 300",thermostat,77,daytemp4,day temperature T4,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T4,number.thermostat_hc1_daytemp4,6,1,1/2,106,1
"RC20, Moduline 300",thermostat,77,nighttemp,night temperature T1,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature_T1,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC20, Moduline 300",thermostat,77,switchtime,program switchtime,string, ,true,sensor.thermostat_hc1_program_switchtime,sensor.thermostat_hc1_switchtime,6,1,1,107,8
"Moduline 400",thermostat,78,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Moduline 400",thermostat,78,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Moduline 400",thermostat,78,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"Moduline 400",thermostat,78,clockoffset,clock offset,int8 (>=-126<=126),seconds,true,number.thermostat_clock_offset,number.thermostat_clockoffset,6,0,1,65,1
"Moduline 400",thermostat,78,autodst,automatic change daylight saving time,boolean, ,true,switch.thermostat_automatic_change_daylight_saving_time,switch.thermostat_autodst,6,0,1,68,1
"Moduline 400",thermostat,78,language,language,enum [german\|dutch], ,true,select.thermostat_language,select.thermostat_language,6,0,1,64,1
"Moduline 400",thermostat,78,backlight,key backlight,boolean, ,true,switch.thermostat_key_backlight,switch.thermostat_backlight,6,0,1,69,1
"Moduline 400",thermostat,78,brightness,screen brightness,int8 (>=-15<=15), ,true,number.thermostat_screen_brightness,number.thermostat_brightness,6,0,1,70,1
"Moduline 400",thermostat,78,mixingvalves,mixing valves,uint8 (>=0<=2), ,true,number.thermostat_mixing_valves,number.thermostat_mixingvalves,6,0,1,71,1
"Moduline 400",thermostat,78,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"Moduline 400",thermostat,78,heatingpid,heating PID,enum [fast\|medium\|slow], ,true,select.thermostat_heating_PID,select.thermostat_heatingpid,6,0,1,72,1
"Moduline 400",thermostat,78,preheating,preheating in the clock program,boolean, ,true,switch.thermostat_preheating_in_the_clock_program,switch.thermostat_preheating,6,0,1,73,1
"Moduline 400",thermostat,78,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"Moduline 400",thermostat,78,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"Moduline 400",thermostat,78,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"Moduline 400",thermostat,78,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"Moduline 400",thermostat,78,mode,operating mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"Moduline 400",thermostat,78,pause,pause time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause,6,1,1,83,1
"Moduline 400",thermostat,78,party,party time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party,6,1,1,84,1
"Moduline 400",thermostat,78,vacations1,vacation dates 1,string, ,true,sensor.thermostat_hc1_vacation_dates_1,sensor.thermostat_hc1_vacations1,6,1,1,115,11
"Moduline 400",thermostat,78,vacations2,vacation dates 2,string, ,true,sensor.thermostat_hc1_vacation_dates_2,sensor.thermostat_hc1_vacations2,6,1,1,126,11
"Moduline 400",thermostat,78,vacations3,vacation dates 3,string, ,true,sensor.thermostat_hc1_vacation_dates_3,sensor.thermostat_hc1_vacations3,6,1,1,137,11
"Moduline 400",thermostat,78,vacations4,vacation dates 4,string, ,true,sensor.thermostat_hc1_vacation_dates_4,sensor.thermostat_hc1_vacations4,6,1,1,148,11
"Moduline 400",thermostat,78,vacations5,vacation dates 5,string, ,true,sensor.thermostat_hc1_vacation_dates_5,sensor.thermostat_hc1_vacations5,6,1,1,159,11
"Moduline 400",thermostat,78,vacations6,vacation dates 6,string, ,true,sensor.thermostat_hc1_vacation_dates_6,sensor.thermostat_hc1_vacations6,6,1,1,170,11
"Moduline 400",thermostat,78,vacations7,vacation dates 7,string, ,true,sensor.thermostat_hc1_vacation_dates_7,sensor.thermostat_hc1_vacations7,6,1,1,181,11
"Moduline 400",thermostat,78,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"Moduline 400",thermostat,78,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1,6,1,1,87,8
"Moduline 400",thermostat,78,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"Moduline 400",thermostat,78,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"Moduline 400",thermostat,78,holidaytemp,holiday temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp,6,1,1/2,54,1
"Moduline 400",thermostat,78,nighttemp,night temperature T1,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature_T1,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"Moduline 400",thermostat,78,daytemp2,day temperature T2,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T2,number.thermostat_hc1_daytemp2,6,1,1/2,104,1
"Moduline 400",thermostat,78,daytemp3,day temperature T3,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T3,number.thermostat_hc1_daytemp3,6,1,1/2,105,1
"Moduline 400",thermostat,78,daytemp4,day temperature T4,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T4,number.thermostat_hc1_daytemp4,6,1,1/2,106,1
"Moduline 400",thermostat,78,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"Moduline 400",thermostat,78,offtemp,temperature when mode is off,uint8 (>=0<=127),C,true,number.thermostat_hc1_temperature_when_mode_is_off,number.thermostat_hc1_offtemp,6,1,1/2,103,1
"Moduline 400",thermostat,78,mode,operating mode,enum [on\|off\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"Moduline 400",thermostat,78,whenmodeoff,when thermostat mode off,boolean, ,true,switch.thermostat_dhw_when_thermostat_mode_off,switch.thermostat_dhw_whenmodeoff,6,9,1,62,1
"Moduline 400",thermostat,78,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"Moduline 400",thermostat,78,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"Moduline 400",thermostat,78,disinfecthour,disinfection hour,uint8 (>=0<=23), ,true,number.thermostat_dhw_disinfection_hour,number.thermostat_dhw_disinfecthour,6,9,1,14,1
"RC10, Moduline 100",thermostat,79,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC10, Moduline 100",thermostat,79,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC10, Moduline 100",thermostat,79,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC10, Moduline 100",thermostat,79,heatingpid,heating PID,enum [fast\|medium\|slow], ,true,select.thermostat_heating_PID,select.thermostat_heatingpid,6,0,1,72,1
"RC10, Moduline 100",thermostat,79,backlight,key backlight,boolean, ,true,switch.thermostat_key_backlight,switch.thermostat_backlight,6,0,1,69,1
"RC10, Moduline 100",thermostat,79,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC10, Moduline 100",thermostat,79,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC10, Moduline 100",thermostat,79,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC10, Moduline 100",thermostat,79,mode,operating mode,enum [nofrost\|night\|day], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC10, Moduline 100",thermostat,79,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"RC10, Moduline 100",thermostat,79,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC10, Moduline 100",thermostat,79,reducehours,duration for nighttemp,uint8 (>=0<=254),hours,true,number.thermostat_hc1_duration_for_nighttemp,number.thermostat_hc1_reducehours,6,1,1,192,1
"RC10, Moduline 100",thermostat,79,reduceminutes,remaining time for nightmode,uint16 (>=0<=31999),minutes,false,sensor.thermostat_hc1_remaining_time_for_nightmode,sensor.thermostat_hc1_reduceminutes,6,1,1,193,1
"RC10, Moduline 100",thermostat,79,mode,operating mode,enum [on\|off\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"Moduline 200",thermostat,80,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Moduline 200",thermostat,80,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Moduline 200",thermostat,80,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"Moduline 200",thermostat,80,heatingpid,heating PID,enum [fast\|medium\|slow], ,true,select.thermostat_heating_PID,select.thermostat_heatingpid,6,0,1,72,1
"Moduline 200",thermostat,80,backlight,key backlight,boolean, ,true,switch.thermostat_key_backlight,switch.thermostat_backlight,6,0,1,69,1
"Moduline 200",thermostat,80,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"Moduline 200",thermostat,80,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"Moduline 200",thermostat,80,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"Moduline 200",thermostat,80,mode,operating mode,enum [nofrost\|night\|day], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"Moduline 200",thermostat,80,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"Moduline 200",thermostat,80,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"Moduline 200",thermostat,80,reducehours,duration for nighttemp,uint8 (>=0<=254),hours,true,number.thermostat_hc1_duration_for_nighttemp,number.thermostat_hc1_reducehours,6,1,1,192,1
"Moduline 200",thermostat,80,reduceminutes,remaining time for nightmode,uint16 (>=0<=31999),minutes,false,sensor.thermostat_hc1_remaining_time_for_nightmode,sensor.thermostat_hc1_reduceminutes,6,1,1,193,1
"Moduline 200",thermostat,80,mode,operating mode,enum [on\|off\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC35",thermostat,86,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC35",thermostat,86,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC35",thermostat,86,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC35",thermostat,86,intoffset,internal temperature offset,int8 (>=-5<=5),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC35",thermostat,86,minexttemp,minimal external temperature,int8 (>=-30<=0),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC35",thermostat,86,inttemp1,temperature sensor 1,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1,6,0,1/10,66,1
"RC35",thermostat,86,inttemp2,temperature sensor 2,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2,6,0,1/10,67,1
"RC35",thermostat,86,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"RC35",thermostat,86,dampedoutdoortemp,damped outdoor temperature,int8 (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1,48,1
"RC35",thermostat,86,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"RC35",thermostat,86,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC35",thermostat,86,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC35",thermostat,86,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC35",thermostat,86,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC35",thermostat,86,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC35",thermostat,86,daytemp,day temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"RC35",thermostat,86,nighttemp,night temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC35",thermostat,86,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"RC35",thermostat,86,offsettemp,offset temperature,int8 (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1/2,10,1
"RC35",thermostat,86,holidaytemp,holiday temperature,uint8 (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp,6,1,1/2,54,1
"RC35",thermostat,86,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"RC35",thermostat,86,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC35",thermostat,86,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC35",thermostat,86,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode,6,1,1,55,1
"RC35",thermostat,86,nofrosttemp,nofrost temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"RC35",thermostat,86,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"RC35",thermostat,86,roominfluence,room influence,uint8 (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"RC35",thermostat,86,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC35",thermostat,86,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC35",thermostat,86,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset,6,1,1,56,1
"RC35",thermostat,86,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC35",thermostat,86,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"RC35",thermostat,86,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"RC35",thermostat,86,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"RC35",thermostat,86,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays,6,1,1,57,13
"RC35",thermostat,86,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations,6,1,1,70,13
"RC35",thermostat,86,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC35",thermostat,86,pause,pause time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause,6,1,1,83,1
"RC35",thermostat,86,party,party time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party,6,1,1,84,1
"RC35",thermostat,86,tempautotemp,temporary set temperature automode,uint8 (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC35",thermostat,86,noreducetemp,no reduce below temperature,int8 (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"RC35",thermostat,86,reducetemp,off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"RC35",thermostat,86,vacreducetemp,vacations off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp,6,1,1,85,1
"RC35",thermostat,86,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode,6,1,1,86,1
"RC35",thermostat,86,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"RC35",thermostat,86,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"RC35",thermostat,86,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"RC35",thermostat,86,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1,6,1,1,87,8
"RC35",thermostat,86,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2,6,1,1,95,8
"RC35",thermostat,86,mode,operating mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC35",thermostat,86,circmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"RC35",thermostat,86,progmode,program,enum [std prog\|own prog], ,true,select.thermostat_dhw_program,select.thermostat_dhw_progmode,6,9,1,12,1
"RC35",thermostat,86,circprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_dhw_circulation_program,select.thermostat_dhw_circprog,6,9,1,13,1
"RC35",thermostat,86,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"RC35",thermostat,86,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"RC35",thermostat,86,disinfecthour,disinfection hour,uint8 (>=0<=23), ,true,number.thermostat_dhw_disinfection_hour,number.thermostat_dhw_disinfecthour,6,9,1,14,1
"RC35",thermostat,86,maxtemp,maximum temperature,uint8 (>=60<=80),C,true,number.thermostat_dhw_maximum_temperature,number.thermostat_dhw_maxtemp,6,9,1,15,1
"RC35",thermostat,86,onetimekey,one time key function,boolean, ,true,switch.thermostat_dhw_one_time_key_function,switch.thermostat_dhw_onetimekey,6,9,1,16,1
"RC35",thermostat,86,switchtimeWW,program switchtime warm water,string, ,true,sensor.thermostat_dhw_program_switchtime_warm_water,sensor.thermostat_dhw_switchtimeWW,6,9,1,17,11
"RC35",thermostat,86,circswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_dhw_circulation_program_switchtime,sensor.thermostat_dhw_circswitchtime,6,9,1,28,8
"RC35",thermostat,86,holidays,holiday dates,string, ,true,sensor.thermostat_dhw_holiday_dates,sensor.thermostat_dhw_holidays,6,9,1,36,13
"RC35",thermostat,86,vacations,vacation dates,string, ,true,sensor.thermostat_dhw_vacation_dates,sensor.thermostat_dhw_vacations,6,9,1,49,13
"RC10, Moduline 100",thermostat,90,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC10, Moduline 100",thermostat,90,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC10, Moduline 100",thermostat,90,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC10, Moduline 100",thermostat,90,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC10, Moduline 100",thermostat,90,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC10, Moduline 100",thermostat,90,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC10, Moduline 100",thermostat,90,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC10, Moduline 100",thermostat,90,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC10, Moduline 100",thermostat,90,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC10, Moduline 100",thermostat,90,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"RC10, Moduline 100",thermostat,90,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC10, Moduline 100",thermostat,90,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC10, Moduline 100",thermostat,90,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC10, Moduline 100",thermostat,90,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC10, Moduline 100",thermostat,90,tempautotemp,temporary set temperature automode,uint8 (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC10, Moduline 100",thermostat,90,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC10, Moduline 100",thermostat,90,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC10, Moduline 100",thermostat,90,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC20RF",thermostat,93,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC20RF",thermostat,93,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC20RF",thermostat,93,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC20RF",thermostat,93,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC20RF",thermostat,93,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC20RF",thermostat,93,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC20RF",thermostat,93,mode,operating mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC20RF",thermostat,93,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"RC20RF",thermostat,93,offtemp,temperature when mode is off,uint8 (>=0<=127),C,true,number.thermostat_hc1_temperature_when_mode_is_off,number.thermostat_hc1_offtemp,6,1,1/2,103,1
"RC20RF",thermostat,93,daytemp2,day temperature T2,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T2,number.thermostat_hc1_daytemp2,6,1,1/2,104,1
"RC20RF",thermostat,93,daytemp3,day temperature T3,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T3,number.thermostat_hc1_daytemp3,6,1,1/2,105,1
"RC20RF",thermostat,93,daytemp4,day temperature T4,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature_T4,number.thermostat_hc1_daytemp4,6,1,1/2,106,1
"RC20RF",thermostat,93,nighttemp,night temperature T1,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature_T1,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC20RF",thermostat,93,switchtime,program switchtime,string, ,true,sensor.thermostat_hc1_program_switchtime,sensor.thermostat_hc1_switchtime,6,1,1,107,8
"RFM20 Remote",thermostat,94,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RFM20 Remote",thermostat,94,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RFM20 Remote",thermostat,94,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RFM20 Remote",thermostat,94,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RFM20 Remote",thermostat,94,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RFM20 Remote",thermostat,94,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC25",thermostat,151,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC25",thermostat,151,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC25",thermostat,151,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC25",thermostat,151,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC25",thermostat,151,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC25",thermostat,151,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC25",thermostat,151,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC25",thermostat,151,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC25",thermostat,151,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC25",thermostat,151,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"RC25",thermostat,151,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"RC25",thermostat,151,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC25",thermostat,151,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC25",thermostat,151,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC25",thermostat,151,tempautotemp,temporary set temperature automode,uint8 (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC25",thermostat,151,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC25",thermostat,151,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC25",thermostat,151,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC200, CW100, CR120, CR50",thermostat,157,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC200, CW100, CR120, CR50",thermostat,157,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC200, CW100, CR120, CR50",thermostat,157,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC200, CW100, CR120, CR50",thermostat,157,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC200, CW100, CR120, CR50",thermostat,157,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"RC200, CW100, CR120, CR50",thermostat,157,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"RC200, CW100, CR120, CR50",thermostat,157,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"RC200, CW100, CR120, CR50",thermostat,157,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"RC200, CW100, CR120, CR50",thermostat,157,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC200, CW100, CR120, CR50",thermostat,157,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"RC200, CW100, CR120, CR50",thermostat,157,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"RC200, CW100, CR120, CR50",thermostat,157,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"RC200, CW100, CR120, CR50",thermostat,157,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"RC200, CW100, CR120, CR50",thermostat,157,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"RC200, CW100, CR120, CR50",thermostat,157,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"RC200, CW100, CR120, CR50",thermostat,157,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"RC200, CW100, CR120, CR50",thermostat,157,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"RC200, CW100, CR120, CR50",thermostat,157,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"RC200, CW100, CR120, CR50",thermostat,157,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"RC200, CW100, CR120, CR50",thermostat,157,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"RC200, CW100, CR120, CR50",thermostat,157,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC200, CW100, CR120, CR50",thermostat,157,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC200, CW100, CR120, CR50",thermostat,157,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC200, CW100, CR120, CR50",thermostat,157,mode,operating mode,enum [manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC200, CW100, CR120, CR50",thermostat,157,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC200, CW100, CR120, CR50",thermostat,157,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"RC200, CW100, CR120, CR50",thermostat,157,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"RC200, CW100, CR120, CR50",thermostat,157,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"RC200, CW100, CR120, CR50",thermostat,157,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC200, CW100, CR120, CR50",thermostat,157,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"RC200, CW100, CR120, CR50",thermostat,157,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"RC200, CW100, CR120, CR50",thermostat,157,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC200, CW100, CR120, CR50",thermostat,157,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC200, CW100, CR120, CR50",thermostat,157,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"RC200, CW100, CR120, CR50",thermostat,157,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"RC200, CW100, CR120, CR50",thermostat,157,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"RC200, CW100, CR120, CR50",thermostat,157,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"RC200, CW100, CR120, CR50",thermostat,157,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"RC200, CW100, CR120, CR50",thermostat,157,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"RC200, CW100, CR120, CR50",thermostat,157,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC200, CW100, CR120, CR50",thermostat,157,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"RC200, CW100, CR120, CR50",thermostat,157,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"RC200, CW100, CR120, CR50",thermostat,157,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC200, CW100, CR120, CR50",thermostat,157,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"RC200, CW100, CR120, CR50",thermostat,157,controlmode,control mode,enum [optimized\|simple\|n/a\|room\|power], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"RC200, CW100, CR120, CR50",thermostat,157,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC200, CW100, CR120, CR50",thermostat,157,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC200, CW100, CR120, CR50",thermostat,157,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"RC200, CW100, CR120, CR50",thermostat,157,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"RC200, CW100, CR120, CR50",thermostat,157,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"RC200, CW100, CR120, CR50",thermostat,157,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"RC200, CW100, CR120, CR50",thermostat,157,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"RC200, CW100, CR120, CR50",thermostat,157,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"RC200, CW100, CR120, CR50",thermostat,157,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"RC200, CW100, CR120, CR50",thermostat,157,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"RC200, CW100, CR120, CR50",thermostat,157,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"RC200, CW100, CR120, CR50",thermostat,157,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"RC200, CW100, CR120, CR50",thermostat,157,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"RC200, CW100, CR120, CR50",thermostat,157,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"RC200, CW100, CR120, CR50",thermostat,157,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"RC200, CW100, CR120, CR50",thermostat,157,control,control device,enum [RC310\|RC200\|RC100\|RC100H\|TC100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"RC200, CW100, CR120, CR50",thermostat,157,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"RC200, CW100, CR120, CR50",thermostat,157,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"RC200, CW100, CR120, CR50",thermostat,157,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"RC200, CW100, CR120, CR50",thermostat,157,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"RC200, CW100, CR120, CR50",thermostat,157,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"RC200, CW100, CR120, CR50",thermostat,157,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"RC200, CW100, CR120, CR50",thermostat,157,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"RC200, CW100, CR120, CR50",thermostat,157,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"RC200, CW100, CR120, CR50",thermostat,157,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"RC200, CW100, CR120, CR50",thermostat,157,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"RC200, CW100, CR120, CR50",thermostat,157,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"RC200, CW100, CR120, CR50",thermostat,157,mode,operating mode,enum [off\|normal\|comfort\|auto\|own prog], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC200, CW100, CR120, CR50",thermostat,157,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"RC200, CW100, CR120, CR50",thermostat,157,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"RC200, CW100, CR120, CR50",thermostat,157,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"RC200, CW100, CR120, CR50",thermostat,157,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"RC200, CW100, CR120, CR50",thermostat,157,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"RC200, CW100, CR120, CR50",thermostat,157,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"RC200, CW100, CR120, CR50",thermostat,157,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"RC200, CW100, CR120, CR50",thermostat,157,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"RC200, CW100, CR120, CR50",thermostat,157,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"RC200, CW100, CR120, CR50",thermostat,157,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"RC200, CW100, CR120, CR50",thermostat,157,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,mode,operating mode,enum [manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,control,control device,enum [RC310\|RC200\|RC100\|RC100H\|TC100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,mode,operating mode,enum [off\|normal\|comfort\|auto\|own prog], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"RC3*0, Moduline 3000/1010H, CW400, Sense II, HPC410",thermostat,158,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC100, CR10, Moduline 1000/1010",thermostat,165,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC100, CR10, Moduline 1000/1010",thermostat,165,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC100, CR10, Moduline 1000/1010",thermostat,165,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,mode,operating mode,enum [manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,controlmode,control mode,enum [optimized\|simple\|n/a\|room\|power], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,control,control device,enum [RC310\|RC200\|RC100\|RC100H\|TC100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,mode,operating mode,enum [off\|normal\|comfort\|auto\|own prog], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"RC100, CR10, Moduline 1000/1010",thermostat,165,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"Rego 2000/3000",thermostat,172,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Rego 2000/3000",thermostat,172,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Rego 2000/3000",thermostat,172,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"Rego 2000/3000",thermostat,172,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"Rego 2000/3000",thermostat,172,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"Rego 2000/3000",thermostat,172,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"Rego 2000/3000",thermostat,172,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"Rego 2000/3000",thermostat,172,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"Rego 2000/3000",thermostat,172,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"Rego 2000/3000",thermostat,172,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"Rego 2000/3000",thermostat,172,vacations,vacation dates,string, ,true,sensor.thermostat_vacation_dates,sensor.thermostat_vacations,6,0,1,74,13
"Rego 2000/3000",thermostat,172,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"Rego 2000/3000",thermostat,172,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"Rego 2000/3000",thermostat,172,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"Rego 2000/3000",thermostat,172,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"Rego 2000/3000",thermostat,172,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"Rego 2000/3000",thermostat,172,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"Rego 2000/3000",thermostat,172,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"Rego 2000/3000",thermostat,172,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"Rego 2000/3000",thermostat,172,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"Rego 2000/3000",thermostat,172,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"Rego 2000/3000",thermostat,172,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"Rego 2000/3000",thermostat,172,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"Rego 2000/3000",thermostat,172,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"Rego 2000/3000",thermostat,172,mode,operating mode,enum [manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"Rego 2000/3000",thermostat,172,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"Rego 2000/3000",thermostat,172,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"Rego 2000/3000",thermostat,172,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"Rego 2000/3000",thermostat,172,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"Rego 2000/3000",thermostat,172,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"Rego 2000/3000",thermostat,172,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"Rego 2000/3000",thermostat,172,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"Rego 2000/3000",thermostat,172,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"Rego 2000/3000",thermostat,172,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"Rego 2000/3000",thermostat,172,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"Rego 2000/3000",thermostat,172,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"Rego 2000/3000",thermostat,172,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"Rego 2000/3000",thermostat,172,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"Rego 2000/3000",thermostat,172,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"Rego 2000/3000",thermostat,172,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"Rego 2000/3000",thermostat,172,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"Rego 2000/3000",thermostat,172,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"Rego 2000/3000",thermostat,172,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"Rego 2000/3000",thermostat,172,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"Rego 2000/3000",thermostat,172,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"Rego 2000/3000",thermostat,172,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"Rego 2000/3000",thermostat,172,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"Rego 2000/3000",thermostat,172,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"Rego 2000/3000",thermostat,172,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"Rego 2000/3000",thermostat,172,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"Rego 2000/3000",thermostat,172,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"Rego 2000/3000",thermostat,172,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"Rego 2000/3000",thermostat,172,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"Rego 2000/3000",thermostat,172,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"Rego 2000/3000",thermostat,172,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"Rego 2000/3000",thermostat,172,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"Rego 2000/3000",thermostat,172,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"Rego 2000/3000",thermostat,172,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"Rego 2000/3000",thermostat,172,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"Rego 2000/3000",thermostat,172,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"Rego 2000/3000",thermostat,172,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"Rego 2000/3000",thermostat,172,control,control device,enum [RC310\|RC200\|RC100\|RC100H\|TC100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"Rego 2000/3000",thermostat,172,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"Rego 2000/3000",thermostat,172,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"Rego 2000/3000",thermostat,172,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"Rego 2000/3000",thermostat,172,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"Rego 2000/3000",thermostat,172,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"Rego 2000/3000",thermostat,172,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"Rego 2000/3000",thermostat,172,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"Rego 2000/3000",thermostat,172,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"Rego 2000/3000",thermostat,172,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"Rego 2000/3000",thermostat,172,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"Rego 2000/3000",thermostat,172,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"Rego 2000/3000",thermostat,172,mode,operating mode,enum [normal\|comfort\|eco+], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"Rego 2000/3000",thermostat,172,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"Rego 2000/3000",thermostat,172,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"Rego 2000/3000",thermostat,172,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"Rego 2000/3000",thermostat,172,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"Rego 2000/3000",thermostat,172,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"Rego 2000/3000",thermostat,172,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"Rego 2000/3000",thermostat,172,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"Rego 2000/3000",thermostat,172,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"Rego 2000/3000",thermostat,172,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"Rego 2000/3000",thermostat,172,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"Rego 2000/3000",thermostat,172,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"Comfort RF",thermostat,215,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Comfort RF",thermostat,215,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Comfort RF",thermostat,215,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"Comfort RF",thermostat,215,seltemp,selected room temperature,int16 (>=-15999<=15999),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp,6,1,1/2,0,1
"Comfort RF",thermostat,215,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"Comfort RF",thermostat,215,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"Comfort RF",thermostat,215,mode,operating mode,enum [auto\|off], ,false,sensor.thermostat_hc1_operating_mode,sensor.thermostat_hc1_mode,6,1,1,3,1
"Comfort RF",thermostat,215,modetype,mode type,enum [off\|on], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"Comfort RF",thermostat,215,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"CRF200S",thermostat,216,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"CRF200S",thermostat,216,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"CRF200S",thermostat,216,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"CRF200S",thermostat,216,seltemp,selected room temperature,int16 (>=-15999<=15999),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp,6,1,1/2,0,1
"CRF200S",thermostat,216,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"CRF200S",thermostat,216,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"CRF200S",thermostat,216,mode,operating mode,enum [auto\|off], ,false,sensor.thermostat_hc1_operating_mode,sensor.thermostat_hc1_mode,6,1,1,3,1
"CRF200S",thermostat,216,modetype,mode type,enum [off\|on], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"CRF200S",thermostat,216,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"Comfort+2RF",thermostat,246,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Comfort+2RF",thermostat,246,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Comfort+2RF",thermostat,246,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"Comfort+2RF",thermostat,246,seltemp,selected room temperature,int16 (>=-15999<=15999),C,false,sensor.thermostat_hc1_selected_room_temperature,sensor.thermostat_hc1_seltemp,6,1,1/2,0,1
"Comfort+2RF",thermostat,246,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"Comfort+2RF",thermostat,246,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"Comfort+2RF",thermostat,246,mode,operating mode,enum [auto\|off], ,false,sensor.thermostat_hc1_operating_mode,sensor.thermostat_hc1_mode,6,1,1,3,1
"Comfort+2RF",thermostat,246,modetype,mode type,enum [off\|on], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"Comfort+2RF",thermostat,246,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"Rego 3000, UI800, Logamatic BC400",thermostat,253,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"Rego 3000, UI800, Logamatic BC400",thermostat,253,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"Rego 3000, UI800, Logamatic BC400",thermostat,253,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,mode,operating mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,controlmode,control mode,enum [weather compensated\|outside basepoint\|n/a\|room\|power\|constant], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,control,control device,enum [off\|-\|RC100\|RC100H\|-\|RC120RF\|RC220/RT800\|single], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,mode,operating mode,enum [off\|eco+\|eco\|comfort\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"Rego 3000, UI800, Logamatic BC400",thermostat,253,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"ES72, RC20",thermostat,66,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"ES72, RC20",thermostat,66,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"ES72, RC20",thermostat,66,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"ES72, RC20",thermostat,66,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"ES72, RC20",thermostat,66,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"ES72, RC20",thermostat,66,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"ES72, RC20",thermostat,66,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"ES72, RC20",thermostat,66,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"ES72, RC20",thermostat,66,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"ES72, RC20",thermostat,66,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"ES72, RC20",thermostat,66,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"ES72, RC20",thermostat,66,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"ES72, RC20",thermostat,66,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"ES72, RC20",thermostat,66,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"ES72, RC20",thermostat,66,tempautotemp,temporary set temperature automode,uint8 (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"ES72, RC20",thermostat,66,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"ES72, RC20",thermostat,66,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"ES72, RC20",thermostat,66,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"ES73",thermostat,76,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"ES73",thermostat,76,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"ES73",thermostat,76,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"ES73",thermostat,76,display,display,enum [internal temperature\|internal setpoint\|external temperature\|burner temperature\|dhw temperature\|functioning mode\|time\|date\|smoke temperature], ,true,select.thermostat_display,select.thermostat_display,6,0,1,63,1
"ES73",thermostat,76,language,language,enum [german\|dutch\|french\|italian], ,false,sensor.thermostat_language,sensor.thermostat_language,6,0,1,64,1
"ES73",thermostat,76,clockoffset,clock offset,int8 (>=-126<=126),seconds,true,number.thermostat_clock_offset,number.thermostat_clockoffset,6,0,1,65,1
"ES73",thermostat,76,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"ES73",thermostat,76,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"ES73",thermostat,76,inttemp1,temperature sensor 1,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1,6,0,1/10,66,1
"ES73",thermostat,76,inttemp2,temperature sensor 2,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2,6,0,1/10,67,1
"ES73",thermostat,76,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"ES73",thermostat,76,dampedoutdoortemp,damped outdoor temperature,int8 (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1,48,1
"ES73",thermostat,76,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"ES73",thermostat,76,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"ES73",thermostat,76,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"ES73",thermostat,76,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"ES73",thermostat,76,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"ES73",thermostat,76,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"ES73",thermostat,76,daytemp,day temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"ES73",thermostat,76,nighttemp,night temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"ES73",thermostat,76,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"ES73",thermostat,76,offsettemp,offset temperature,int8 (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1/2,10,1
"ES73",thermostat,76,holidaytemp,holiday temperature,uint8 (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp,6,1,1/2,54,1
"ES73",thermostat,76,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"ES73",thermostat,76,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"ES73",thermostat,76,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"ES73",thermostat,76,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode,6,1,1,55,1
"ES73",thermostat,76,nofrosttemp,nofrost temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"ES73",thermostat,76,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"ES73",thermostat,76,roominfluence,room influence,uint8 (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"ES73",thermostat,76,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"ES73",thermostat,76,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"ES73",thermostat,76,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset,6,1,1,56,1
"ES73",thermostat,76,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"ES73",thermostat,76,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"ES73",thermostat,76,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"ES73",thermostat,76,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"ES73",thermostat,76,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays,6,1,1,57,13
"ES73",thermostat,76,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations,6,1,1,70,13
"ES73",thermostat,76,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"ES73",thermostat,76,pause,pause time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause,6,1,1,83,1
"ES73",thermostat,76,party,party time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party,6,1,1,84,1
"ES73",thermostat,76,tempautotemp,temporary set temperature automode,uint8 (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"ES73",thermostat,76,noreducetemp,no reduce below temperature,int8 (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"ES73",thermostat,76,reducetemp,off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"ES73",thermostat,76,vacreducetemp,vacations off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp,6,1,1,85,1
"ES73",thermostat,76,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode,6,1,1,86,1
"ES73",thermostat,76,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"ES73",thermostat,76,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"ES73",thermostat,76,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"ES73",thermostat,76,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1,6,1,1,87,8
"ES73",thermostat,76,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2,6,1,1,95,8
"ES73",thermostat,76,mode,operating mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"ES73",thermostat,76,circmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"ES73",thermostat,76,progmode,program,enum [std prog\|own prog], ,true,select.thermostat_dhw_program,select.thermostat_dhw_progmode,6,9,1,12,1
"ES73",thermostat,76,circprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_dhw_circulation_program,select.thermostat_dhw_circprog,6,9,1,13,1
"ES73",thermostat,76,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"ES73",thermostat,76,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"ES73",thermostat,76,disinfecthour,disinfection hour,uint8 (>=0<=23), ,true,number.thermostat_dhw_disinfection_hour,number.thermostat_dhw_disinfecthour,6,9,1,14,1
"ES73",thermostat,76,maxtemp,maximum temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_maximum_temperature,number.thermostat_dhw_maxtemp,6,9,1,15,1
"ES73",thermostat,76,onetimekey,one time key function,boolean, ,true,switch.thermostat_dhw_one_time_key_function,switch.thermostat_dhw_onetimekey,6,9,1,16,1
"ES73",thermostat,76,switchtimeWW,program switchtime warm water,string, ,true,sensor.thermostat_dhw_program_switchtime_warm_water,sensor.thermostat_dhw_switchtimeWW,6,9,1,17,11
"ES73",thermostat,76,circswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_dhw_circulation_program_switchtime,sensor.thermostat_dhw_circswitchtime,6,9,1,28,8
"ES73",thermostat,76,holidays,holiday dates,string, ,true,sensor.thermostat_dhw_holiday_dates,sensor.thermostat_dhw_holidays,6,9,1,36,13
"ES73",thermostat,76,vacations,vacation dates,string, ,true,sensor.thermostat_dhw_vacation_dates,sensor.thermostat_dhw_vacations,6,9,1,49,13
"ES72, RC20",thermostat,113,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"ES72, RC20",thermostat,113,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"ES72, RC20",thermostat,113,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"ES72, RC20",thermostat,113,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"ES72, RC20",thermostat,113,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"ES72, RC20",thermostat,113,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"ES72, RC20",thermostat,113,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"ES72, RC20",thermostat,113,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"ES72, RC20",thermostat,113,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"ES72, RC20",thermostat,113,daytemp,day temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"ES72, RC20",thermostat,113,nighttemp,night temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"ES72, RC20",thermostat,113,program,program,enum [family\|morning\|evening\|am\|pm\|midday\|singles\|seniors], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"ES72, RC20",thermostat,113,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"ES72, RC20",thermostat,113,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"ES72, RC20",thermostat,113,tempautotemp,temporary set temperature automode,uint8 (>=0<=127),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"ES72, RC20",thermostat,113,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"ES72, RC20",thermostat,113,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"ES72, RC20",thermostat,113,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"ES79",thermostat,156,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"ES79",thermostat,156,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"ES79",thermostat,156,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"ES79",thermostat,156,intoffset,internal temperature offset,int8 (>=-5<=5),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"ES79",thermostat,156,minexttemp,minimal external temperature,int8 (>=-30<=0),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"ES79",thermostat,156,inttemp1,temperature sensor 1,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_1,sensor.thermostat_inttemp1,6,0,1/10,66,1
"ES79",thermostat,156,inttemp2,temperature sensor 2,int16 (>=-3199<=3199),C,false,sensor.thermostat_temperature_sensor_2,sensor.thermostat_inttemp2,6,0,1/10,67,1
"ES79",thermostat,156,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"ES79",thermostat,156,dampedoutdoortemp,damped outdoor temperature,int8 (>=-126<=126),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1,48,1
"ES79",thermostat,156,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"ES79",thermostat,156,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"ES79",thermostat,156,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"ES79",thermostat,156,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"ES79",thermostat,156,mode,operating mode,enum [night\|day\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"ES79",thermostat,156,modetype,mode type,enum [night\|day], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"ES79",thermostat,156,daytemp,day temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_day_temperature,number.thermostat_hc1_daytemp,6,1,1/2,52,1
"ES79",thermostat,156,nighttemp,night temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_night_temperature,number.thermostat_hc1_nighttemp,6,1,1/2,53,1
"ES79",thermostat,156,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"ES79",thermostat,156,offsettemp,offset temperature,int8 (>=-5<=5),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1/2,10,1
"ES79",thermostat,156,holidaytemp,holiday temperature,uint8 (>=5<=30),C,true,number.thermostat_hc1_holiday_temperature,number.thermostat_hc1_holidaytemp,6,1,1/2,54,1
"ES79",thermostat,156,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"ES79",thermostat,156,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"ES79",thermostat,156,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"ES79",thermostat,156,holidaymode,holiday mode,boolean, ,false,binary_sensor.thermostat_hc1_holiday_mode,binary_sensor.thermostat_hc1_holidaymode,6,1,1,55,1
"ES79",thermostat,156,nofrosttemp,nofrost temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"ES79",thermostat,156,nofrostmode,nofrost mode,enum [off\|outdoor\|room], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"ES79",thermostat,156,roominfluence,room influence,uint8 (>=0<=10),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"ES79",thermostat,156,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"ES79",thermostat,156,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"ES79",thermostat,156,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),C,true,number.thermostat_hc1_flow_temperature_offset_for_mixer,number.thermostat_hc1_flowtempoffset,6,1,1,56,1
"ES79",thermostat,156,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"ES79",thermostat,156,reducemode,reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"ES79",thermostat,156,controlmode,control mode,enum [outdoor\|room], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"ES79",thermostat,156,control,control device,enum [off\|RC20\|RC3x], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"ES79",thermostat,156,holidays,holiday dates,string, ,true,sensor.thermostat_hc1_holiday_dates,sensor.thermostat_hc1_holidays,6,1,1,57,13
"ES79",thermostat,156,vacations,vacation dates,string, ,true,sensor.thermostat_hc1_vacation_dates,sensor.thermostat_hc1_vacations,6,1,1,70,13
"ES79",thermostat,156,program,program,enum [own 1\|family\|morning\|evening\|am\|pm\|midday\|singles\|seniors\|new\|own 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"ES79",thermostat,156,pause,pause time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_pause_time,number.thermostat_hc1_pause,6,1,1,83,1
"ES79",thermostat,156,party,party time,uint8 (>=0<=99),hours,true,number.thermostat_hc1_party_time,number.thermostat_hc1_party,6,1,1,84,1
"ES79",thermostat,156,tempautotemp,temporary set temperature automode,uint8 (>=0<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"ES79",thermostat,156,noreducetemp,no reduce below temperature,int8 (>=-31<=10),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"ES79",thermostat,156,reducetemp,off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"ES79",thermostat,156,vacreducetemp,vacations off/reduce switch temperature,int8 (>=-20<=10),C,true,number.thermostat_hc1_vacations_off/reduce_switch_temperature,number.thermostat_hc1_vacreducetemp,6,1,1,85,1
"ES79",thermostat,156,vacreducemode,vacations reduce mode,enum [nofrost\|reduce\|room\|outdoor], ,true,select.thermostat_hc1_vacations_reduce_mode,select.thermostat_hc1_vacreducemode,6,1,1,86,1
"ES79",thermostat,156,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"ES79",thermostat,156,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"ES79",thermostat,156,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"ES79",thermostat,156,switchtime1,own1 program switchtime,string, ,true,sensor.thermostat_hc1_own1_program_switchtime,sensor.thermostat_hc1_switchtime1,6,1,1,87,8
"ES79",thermostat,156,switchtime2,own2 program switchtime,string, ,true,sensor.thermostat_hc1_own2_program_switchtime,sensor.thermostat_hc1_switchtime2,6,1,1,95,8
"ES79",thermostat,156,mode,operating mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"ES79",thermostat,156,circmode,circulation pump mode,enum [off\|on\|auto], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"ES79",thermostat,156,progmode,program,enum [std prog\|own prog], ,true,select.thermostat_dhw_program,select.thermostat_dhw_progmode,6,9,1,12,1
"ES79",thermostat,156,circprog,circulation program,enum [std prog\|own prog], ,true,select.thermostat_dhw_circulation_program,select.thermostat_dhw_circprog,6,9,1,13,1
"ES79",thermostat,156,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"ES79",thermostat,156,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"ES79",thermostat,156,disinfecthour,disinfection hour,uint8 (>=0<=23), ,true,number.thermostat_dhw_disinfection_hour,number.thermostat_dhw_disinfecthour,6,9,1,14,1
"ES79",thermostat,156,maxtemp,maximum temperature,uint8 (>=60<=80),C,true,number.thermostat_dhw_maximum_temperature,number.thermostat_dhw_maxtemp,6,9,1,15,1
"ES79",thermostat,156,onetimekey,one time key function,boolean, ,true,switch.thermostat_dhw_one_time_key_function,switch.thermostat_dhw_onetimekey,6,9,1,16,1
"ES79",thermostat,156,switchtimeWW,program switchtime warm water,string, ,true,sensor.thermostat_dhw_program_switchtime_warm_water,sensor.thermostat_dhw_switchtimeWW,6,9,1,17,11
"ES79",thermostat,156,circswitchtime,circulation program switchtime,string, ,true,sensor.thermostat_dhw_circulation_program_switchtime,sensor.thermostat_dhw_circswitchtime,6,9,1,28,8
"ES79",thermostat,156,holidays,holiday dates,string, ,true,sensor.thermostat_dhw_holiday_dates,sensor.thermostat_dhw_holidays,6,9,1,36,13
"ES79",thermostat,156,vacations,vacation dates,string, ,true,sensor.thermostat_dhw_vacation_dates,sensor.thermostat_dhw_vacations,6,9,1,49,13
"FW100",thermostat,105,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FW100",thermostat,105,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FW100",thermostat,105,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FW100",thermostat,105,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FW100",thermostat,105,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FW100",thermostat,105,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FW100",thermostat,105,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FW100",thermostat,105,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FW100",thermostat,105,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FW100",thermostat,105,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FW100",thermostat,105,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FW100",thermostat,105,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FW100",thermostat,105,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FW100",thermostat,105,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FW100",thermostat,105,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FW100",thermostat,105,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FW100",thermostat,105,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FW100",thermostat,105,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FW100",thermostat,105,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FW100",thermostat,105,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FW100",thermostat,105,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FW100",thermostat,105,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FW100",thermostat,105,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FW100",thermostat,105,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FW100",thermostat,105,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FW100",thermostat,105,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FW100",thermostat,105,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FW100",thermostat,105,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FW100",thermostat,105,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FW100",thermostat,105,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FW100",thermostat,105,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FW100",thermostat,105,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FW100",thermostat,105,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FW100",thermostat,105,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FW100",thermostat,105,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FW200",thermostat,106,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FW200",thermostat,106,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FW200",thermostat,106,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FW200",thermostat,106,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FW200",thermostat,106,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FW200",thermostat,106,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FW200",thermostat,106,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FW200",thermostat,106,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FW200",thermostat,106,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FW200",thermostat,106,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FW200",thermostat,106,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FW200",thermostat,106,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FW200",thermostat,106,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FW200",thermostat,106,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FW200",thermostat,106,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FW200",thermostat,106,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FW200",thermostat,106,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FW200",thermostat,106,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FW200",thermostat,106,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FW200",thermostat,106,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FW200",thermostat,106,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FW200",thermostat,106,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FW200",thermostat,106,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FW200",thermostat,106,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FW200",thermostat,106,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FW200",thermostat,106,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FW200",thermostat,106,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FW200",thermostat,106,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FW200",thermostat,106,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FW200",thermostat,106,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FW200",thermostat,106,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FW200",thermostat,106,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FW200",thermostat,106,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FW200",thermostat,106,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FW200",thermostat,106,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FR100",thermostat,107,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FR100",thermostat,107,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FR100",thermostat,107,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FR100",thermostat,107,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FR100",thermostat,107,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FR100",thermostat,107,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FR100",thermostat,107,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FR100",thermostat,107,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FR100",thermostat,107,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FR100",thermostat,107,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FR100",thermostat,107,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FR100",thermostat,107,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FR100",thermostat,107,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FR100",thermostat,107,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FR100",thermostat,107,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FR100",thermostat,107,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FR100",thermostat,107,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FR100",thermostat,107,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FR100",thermostat,107,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FR100",thermostat,107,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FR100",thermostat,107,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FR100",thermostat,107,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FR100",thermostat,107,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FR100",thermostat,107,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FR100",thermostat,107,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FR100",thermostat,107,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FR100",thermostat,107,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FR100",thermostat,107,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FR100",thermostat,107,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FR100",thermostat,107,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FR100",thermostat,107,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FR100",thermostat,107,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FR100",thermostat,107,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FR100",thermostat,107,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FR100",thermostat,107,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FR110",thermostat,108,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FR110",thermostat,108,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FR110",thermostat,108,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FR110",thermostat,108,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FR110",thermostat,108,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FR110",thermostat,108,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FR110",thermostat,108,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FR110",thermostat,108,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FR110",thermostat,108,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FR110",thermostat,108,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FR110",thermostat,108,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FR110",thermostat,108,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FR110",thermostat,108,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FR110",thermostat,108,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FR110",thermostat,108,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FR110",thermostat,108,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FR110",thermostat,108,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FR110",thermostat,108,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FR110",thermostat,108,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FR110",thermostat,108,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FR110",thermostat,108,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FR110",thermostat,108,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FR110",thermostat,108,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FR110",thermostat,108,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FR110",thermostat,108,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FR110",thermostat,108,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FR110",thermostat,108,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FR110",thermostat,108,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FR110",thermostat,108,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FR110",thermostat,108,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FR110",thermostat,108,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FR110",thermostat,108,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FR110",thermostat,108,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FR110",thermostat,108,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FR110",thermostat,108,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FB10",thermostat,109,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FB10",thermostat,109,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FB10",thermostat,109,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FB10",thermostat,109,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FB10",thermostat,109,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FB10",thermostat,109,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FB10",thermostat,109,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FB10",thermostat,109,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FB10",thermostat,109,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FB10",thermostat,109,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FB10",thermostat,109,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FB10",thermostat,109,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FB10",thermostat,109,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FB10",thermostat,109,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FB10",thermostat,109,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FB10",thermostat,109,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FB10",thermostat,109,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FB10",thermostat,109,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FB10",thermostat,109,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FB10",thermostat,109,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FB10",thermostat,109,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FB10",thermostat,109,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FB10",thermostat,109,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FB10",thermostat,109,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FB10",thermostat,109,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FB10",thermostat,109,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FB10",thermostat,109,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FB10",thermostat,109,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FB10",thermostat,109,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FB10",thermostat,109,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FB10",thermostat,109,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FB10",thermostat,109,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FB10",thermostat,109,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FB10",thermostat,109,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FB10",thermostat,109,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FB100",thermostat,110,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FB100",thermostat,110,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FB100",thermostat,110,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FB100",thermostat,110,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FB100",thermostat,110,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FB100",thermostat,110,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FB100",thermostat,110,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FB100",thermostat,110,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FB100",thermostat,110,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FB100",thermostat,110,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FB100",thermostat,110,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FB100",thermostat,110,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FB100",thermostat,110,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FB100",thermostat,110,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FB100",thermostat,110,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FB100",thermostat,110,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FB100",thermostat,110,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FB100",thermostat,110,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FB100",thermostat,110,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FB100",thermostat,110,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FB100",thermostat,110,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FB100",thermostat,110,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FB100",thermostat,110,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FB100",thermostat,110,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FB100",thermostat,110,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FB100",thermostat,110,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FB100",thermostat,110,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FB100",thermostat,110,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FB100",thermostat,110,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FB100",thermostat,110,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FB100",thermostat,110,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FB100",thermostat,110,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FB100",thermostat,110,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FB100",thermostat,110,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FB100",thermostat,110,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FR10",thermostat,111,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FR10",thermostat,111,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FR10",thermostat,111,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FR10",thermostat,111,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FR10",thermostat,111,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FR10",thermostat,111,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FR10",thermostat,111,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FR10",thermostat,111,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FR10",thermostat,111,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FR10",thermostat,111,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FR10",thermostat,111,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FR10",thermostat,111,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FR10",thermostat,111,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FR10",thermostat,111,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FR10",thermostat,111,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FR10",thermostat,111,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FR10",thermostat,111,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FR10",thermostat,111,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FR10",thermostat,111,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FR10",thermostat,111,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FR10",thermostat,111,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FR10",thermostat,111,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FR10",thermostat,111,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FR10",thermostat,111,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FR10",thermostat,111,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FR10",thermostat,111,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FR10",thermostat,111,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FR10",thermostat,111,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FR10",thermostat,111,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FR10",thermostat,111,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FR10",thermostat,111,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FR10",thermostat,111,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FR10",thermostat,111,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FR10",thermostat,111,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FR10",thermostat,111,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FW500",thermostat,116,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FW500",thermostat,116,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FW500",thermostat,116,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FW500",thermostat,116,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FW500",thermostat,116,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FW500",thermostat,116,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FW500",thermostat,116,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FW500",thermostat,116,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FW500",thermostat,116,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FW500",thermostat,116,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FW500",thermostat,116,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FW500",thermostat,116,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FW500",thermostat,116,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FW500",thermostat,116,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FW500",thermostat,116,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FW500",thermostat,116,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FW500",thermostat,116,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FW500",thermostat,116,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FW500",thermostat,116,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FW500",thermostat,116,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FW500",thermostat,116,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FW500",thermostat,116,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FW500",thermostat,116,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FW500",thermostat,116,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FW500",thermostat,116,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FW500",thermostat,116,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FW500",thermostat,116,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FW500",thermostat,116,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FW500",thermostat,116,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FW500",thermostat,116,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FW500",thermostat,116,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FW500",thermostat,116,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FW500",thermostat,116,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FW500",thermostat,116,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FW500",thermostat,116,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FR50",thermostat,147,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FR50",thermostat,147,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FR50",thermostat,147,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FR50",thermostat,147,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FR50",thermostat,147,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FR50",thermostat,147,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FR50",thermostat,147,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FR50",thermostat,147,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FR50",thermostat,147,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FR50",thermostat,147,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FR50",thermostat,147,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FR50",thermostat,147,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FR50",thermostat,147,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FR50",thermostat,147,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FR50",thermostat,147,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FR50",thermostat,147,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FR50",thermostat,147,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FR50",thermostat,147,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FR50",thermostat,147,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FR50",thermostat,147,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FR50",thermostat,147,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FR50",thermostat,147,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FR50",thermostat,147,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FR50",thermostat,147,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FR50",thermostat,147,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FR50",thermostat,147,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FR50",thermostat,147,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FR50",thermostat,147,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FR50",thermostat,147,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FR50",thermostat,147,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FR50",thermostat,147,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FR50",thermostat,147,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FR50",thermostat,147,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FR50",thermostat,147,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FR50",thermostat,147,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FR120",thermostat,191,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FR120",thermostat,191,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FR120",thermostat,191,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FR120",thermostat,191,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FR120",thermostat,191,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FR120",thermostat,191,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FR120",thermostat,191,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FR120",thermostat,191,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FR120",thermostat,191,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FR120",thermostat,191,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FR120",thermostat,191,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FR120",thermostat,191,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FR120",thermostat,191,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FR120",thermostat,191,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FR120",thermostat,191,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FR120",thermostat,191,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FR120",thermostat,191,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FR120",thermostat,191,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FR120",thermostat,191,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FR120",thermostat,191,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FR120",thermostat,191,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FR120",thermostat,191,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FR120",thermostat,191,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FR120",thermostat,191,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FR120",thermostat,191,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FR120",thermostat,191,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FR120",thermostat,191,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FR120",thermostat,191,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FR120",thermostat,191,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FR120",thermostat,191,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FR120",thermostat,191,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FR120",thermostat,191,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FR120",thermostat,191,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FR120",thermostat,191,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FR120",thermostat,191,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"FW120",thermostat,192,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"FW120",thermostat,192,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"FW120",thermostat,192,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"FW120",thermostat,192,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"FW120",thermostat,192,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"FW120",thermostat,192,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"FW120",thermostat,192,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"FW120",thermostat,192,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"FW120",thermostat,192,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"FW120",thermostat,192,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"FW120",thermostat,192,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/10,0,1
"FW120",thermostat,192,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"FW120",thermostat,192,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"FW120",thermostat,192,mode,operating mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"FW120",thermostat,192,modetype,mode type,enum [nofrost\|eco\|heat], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"FW120",thermostat,192,heattemp,heat temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_heat_temperature,number.thermostat_hc1_heattemp,6,1,1/2,194,1
"FW120",thermostat,192,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"FW120",thermostat,192,nofrosttemp,nofrost temperature,int8 (>=-63<=63),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1/2,17,1
"FW120",thermostat,192,control,control device,enum [off\|FB10\|FB100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"FW120",thermostat,192,program,program,enum [prog a\|prog b\|prog c\|prog d\|prog e\|prog f], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"FW120",thermostat,192,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"FW120",thermostat,192,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"FW120",thermostat,192,summertemp,summer temperature,uint8 (>=9<=25),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1/2,8,1
"FW120",thermostat,192,roomsensor,room sensor,enum [extern\|intern\|auto], ,true,select.thermostat_hc1_room_sensor,select.thermostat_hc1_roomsensor,6,1,1,195,1
"FW120",thermostat,192,holidaymode,holiday mode,enum [nofrost\|eco\|heat\|auto], ,true,select.thermostat_hc1_holiday_mode,select.thermostat_hc1_holidaymode,6,1,1,55,1
"FW120",thermostat,192,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"FW120",thermostat,192,heatup,heatup,enum [slow\|medium\|fast], ,true,select.thermostat_hc1_heatup,select.thermostat_hc1_heatup,6,1,1,196,1
"FW120",thermostat,192,minflowtemp,min flow temperature,uint8 (>=5<=70),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"FW120",thermostat,192,maxflowtemp,max flow temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"FW120",thermostat,192,designtemp,design temperature,uint8 (>=30<=90),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"FW120",thermostat,192,roominfluence,room influence,enum [off\|intern\|extern\|auto], ,true,select.thermostat_hc1_room_influence,select.thermostat_hc1_roominfluence,6,1,1,13,1
"FW120",thermostat,192,roominflfactor,room influence factor,uint8 (>=0<=100),%,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,10,14,1
"FW120",thermostat,192,heatingtype,heating type,enum [off\|heatingcurve\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"FW120",thermostat,192,controlmode,control mode,enum [off\|unmixed\|unmixed IPM\|mixed IPM], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"FW120",thermostat,192,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"RT800, RC220",thermostat,3,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RT800, RC220",thermostat,3,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RT800, RC220",thermostat,3,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RT800, RC220",thermostat,3,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RT800, RC220",thermostat,3,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RT800, RC220",thermostat,3,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC100H, CR10H",thermostat,200,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC100H, CR10H",thermostat,200,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC100H, CR10H",thermostat,200,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC100H, CR10H",thermostat,200,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC100H, CR10H",thermostat,200,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC100H, CR10H",thermostat,200,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"TR120RF, CR20RF",thermostat,249,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"TR120RF, CR20RF",thermostat,249,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"TR120RF, CR20RF",thermostat,249,datetime,date/time,string, ,false,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"TR120RF, CR20RF",thermostat,249,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"TR120RF, CR20RF",thermostat,249,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"TR120RF, CR20RF",thermostat,249,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC120",thermostat,157,errorcode,error code,string, ,false,sensor.thermostat_error_code,sensor.thermostat_errorcode,6,0,1,0,8
"RC120",thermostat,157,lastcode,last error code,string, ,false,sensor.thermostat_last_error_code,sensor.thermostat_lastcode,6,0,1,8,25
"RC120",thermostat,157,datetime,date/time,string, ,true,sensor.thermostat_date/time,sensor.thermostat_datetime,6,0,1,33,13
"RC120",thermostat,157,intoffset,internal temperature offset,int8 (>=-12<=12),C,true,number.thermostat_internal_temperature_offset,number.thermostat_intoffset,6,0,1/10,46,1
"RC120",thermostat,157,floordry,floor drying,enum [off\|start\|heat\|hold\|cool\|end], ,false,sensor.thermostat_floor_drying,sensor.thermostat_floordry,6,0,1,47,1
"RC120",thermostat,157,dampedoutdoortemp,damped outdoor temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_damped_outdoor_temperature,sensor.thermostat_dampedoutdoortemp,6,0,1/10,48,1
"RC120",thermostat,157,floordrytemp,floor drying temperature,uint8 (>=0<=254),C,false,sensor.thermostat_floor_drying_temperature,sensor.thermostat_floordrytemp,6,0,1,49,1
"RC120",thermostat,157,building,building type,enum [light\|medium\|heavy], ,true,select.thermostat_building_type,select.thermostat_building,6,0,1,50,1
"RC120",thermostat,157,minexttemp,minimal external temperature,int8 (>=-126<=126),C,true,number.thermostat_minimal_external_temperature,number.thermostat_minexttemp,6,0,1,51,1
"RC120",thermostat,157,damping,damping outdoor temperature,boolean, ,true,switch.thermostat_damping_outdoor_temperature,switch.thermostat_damping,6,0,1,52,1
"RC120",thermostat,157,hybridstrategy,hybrid control strategy,enum [co2 optimized\|cost optimized\|outside temp switched\|co2 cost mix], ,true,select.thermostat_hybrid_control_strategy,select.thermostat_hybridstrategy,6,0,1,53,1
"RC120",thermostat,157,switchovertemp,outside switchover temperature,int8 (>=-20<=20),C,true,number.thermostat_outside_switchover_temperature,number.thermostat_switchovertemp,6,0,1,54,1
"RC120",thermostat,157,energycostratio,energy cost ratio,uint8 (>=0<=20), ,true,number.thermostat_energy_cost_ratio,number.thermostat_energycostratio,6,0,1/10,55,1
"RC120",thermostat,157,fossilefactor,fossile energy factor,uint8 (>=0<=5), ,true,number.thermostat_fossile_energy_factor,number.thermostat_fossilefactor,6,0,1/10,56,1
"RC120",thermostat,157,electricfactor,electric energy factor,uint8 (>=0<=5), ,true,number.thermostat_electric_energy_factor,number.thermostat_electricfactor,6,0,1/10,57,1
"RC120",thermostat,157,delayboiler,delay boiler support,uint8 (>=5<=120),minutes,true,number.thermostat_delay_boiler_support,number.thermostat_delayboiler,6,0,1,58,1
"RC120",thermostat,157,tempdiffboiler,temp diff boiler support,uint8 (>=1<=99),C,true,number.thermostat_temp_diff_boiler_support,number.thermostat_tempdiffboiler,6,0,1,59,1
"RC120",thermostat,157,pvenabledhw,enable raise dhw,boolean, ,true,switch.thermostat_enable_raise_dhw,switch.thermostat_pvenabledhw,6,0,1,60,1
"RC120",thermostat,157,pvraiseheat,raise heating with PV,int8 (>=0<=5),K,true,number.thermostat_raise_heating_with_PV,number.thermostat_pvraiseheat,6,0,1,61,1
"RC120",thermostat,157,pvlowercool,lower cooling with PV,int8 (>=-5<=0),K,true,number.thermostat_lower_cooling_with_PV,number.thermostat_pvlowercool,6,0,1,62,1
"RC120",thermostat,157,seltemp,selected room temperature,int16 (>=0<=30),C,true,number.thermostat_hc1_selected_room_temperature,number.thermostat_hc1_seltemp,6,1,1/2,0,1
"RC120",thermostat,157,currtemp,current room temperature,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_temperature,sensor.thermostat_hc1_currtemp,6,1,1/10,1,1
"RC120",thermostat,157,haclimate,mqtt discovery current room temperature,enum [selTemp\|roomTemp] (>=5<=30), ,false,sensor.thermostat_hc1_mqtt_discovery_current_room_temperature,sensor.thermostat_hc1_haclimate,6,1,1,2,1
"RC120",thermostat,157,mode,operating mode,enum [off\|manual\|auto], ,true,select.thermostat_hc1_operating_mode,select.thermostat_hc1_mode,6,1,1,3,1
"RC120",thermostat,157,modetype,mode type,enum [eco\|comfort], ,false,sensor.thermostat_hc1_mode_type,sensor.thermostat_hc1_modetype,6,1,1,4,1
"RC120",thermostat,157,ecotemp,eco temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_eco_temperature,number.thermostat_hc1_ecotemp,6,1,1/2,5,1
"RC120",thermostat,157,manualtemp,manual temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_manual_temperature,number.thermostat_hc1_manualtemp,6,1,1/2,6,1
"RC120",thermostat,157,comforttemp,comfort temperature,uint8 (>=0<=127),C,true,number.thermostat_hc1_comfort_temperature,number.thermostat_hc1_comforttemp,6,1,1/2,7,1
"RC120",thermostat,157,summertemp,summer temperature,uint8 (>=10<=30),C,true,number.thermostat_hc1_summer_temperature,number.thermostat_hc1_summertemp,6,1,1,8,1
"RC120",thermostat,157,designtemp,design temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_design_temperature,number.thermostat_hc1_designtemp,6,1,1,9,1
"RC120",thermostat,157,offsettemp,offset temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_offset_temperature,number.thermostat_hc1_offsettemp,6,1,1,10,1
"RC120",thermostat,157,minflowtemp,min flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_min_flow_temperature,number.thermostat_hc1_minflowtemp,6,1,1,11,1
"RC120",thermostat,157,maxflowtemp,max flow temperature,uint8 (>=0<=254),C,true,number.thermostat_hc1_max_flow_temperature,number.thermostat_hc1_maxflowtemp,6,1,1,12,1
"RC120",thermostat,157,roominfluence,room influence,uint8 (>=0<=254),C,true,number.thermostat_hc1_room_influence,number.thermostat_hc1_roominfluence,6,1,1,13,1
"RC120",thermostat,157,roominflfactor,room influence factor,uint8 (>=0<=25), ,true,number.thermostat_hc1_room_influence_factor,number.thermostat_hc1_roominflfactor,6,1,1/10,14,1
"RC120",thermostat,157,curroominfl,current room influence,int16 (>=-3199<=3199),C,false,sensor.thermostat_hc1_current_room_influence,sensor.thermostat_hc1_curroominfl,6,1,1/10,15,1
"RC120",thermostat,157,nofrostmode,nofrost mode,enum [room\|outdoor\|room outdoor], ,true,select.thermostat_hc1_nofrost_mode,select.thermostat_hc1_nofrostmode,6,1,1,16,1
"RC120",thermostat,157,nofrosttemp,nofrost temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_nofrost_temperature,number.thermostat_hc1_nofrosttemp,6,1,1,17,1
"RC120",thermostat,157,targetflowtemp,target flow temperature,uint8 (>=0<=254),C,false,sensor.thermostat_hc1_target_flow_temperature,sensor.thermostat_hc1_targetflowtemp,6,1,1,18,1
"RC120",thermostat,157,heatingtype,heating type,enum [off\|radiator\|convector\|floor], ,true,select.thermostat_hc1_heating_type,select.thermostat_hc1_heatingtype,6,1,1,19,1
"RC120",thermostat,157,summersetmode,set summer mode,enum [summer\|auto\|winter], ,true,select.thermostat_hc1_set_summer_mode,select.thermostat_hc1_summersetmode,6,1,1,20,1
"RC120",thermostat,157,hpoperatingmode,heatpump operating mode,enum [off\|auto\|heating\|cooling], ,true,select.thermostat_hc1_heatpump_operating_mode,select.thermostat_hc1_hpoperatingmode,6,1,1,21,1
"RC120",thermostat,157,summermode,summer mode,enum [winter\|summer], ,false,sensor.thermostat_hc1_summer_mode,sensor.thermostat_hc1_summermode,6,1,1,22,1
"RC120",thermostat,157,hpoperatingstate,heatpump operating state,enum [heating\|off\|cooling], ,false,sensor.thermostat_hc1_heatpump_operating_state,sensor.thermostat_hc1_hpoperatingstate,6,1,1,23,1
"RC120",thermostat,157,controlmode,control mode,enum [optimized\|simple\|n/a\|room\|power], ,true,select.thermostat_hc1_control_mode,select.thermostat_hc1_controlmode,6,1,1,24,1
"RC120",thermostat,157,program,program,enum [prog 1\|prog 2], ,true,select.thermostat_hc1_program,select.thermostat_hc1_program,6,1,1,25,1
"RC120",thermostat,157,tempautotemp,temporary set temperature automode,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_automode,number.thermostat_hc1_tempautotemp,6,1,1/2,26,1
"RC120",thermostat,157,remoteseltemp,temporary set temperature from remote,int8 (>=-1<=30),C,true,number.thermostat_hc1_temporary_set_temperature_from_remote,number.thermostat_hc1_remoteseltemp,6,1,1/2,27,1
"RC120",thermostat,157,fastheatup,fast heatup,uint8 (>=0<=100),%,true,number.thermostat_hc1_fast_heatup,number.thermostat_hc1_fastheatup,6,1,1,28,1
"RC120",thermostat,157,switchonoptimization,switch-on optimization,boolean, ,true,switch.thermostat_hc1_switch-on_optimization,switch.thermostat_hc1_switchonoptimization,6,1,1,29,1
"RC120",thermostat,157,reducemode,reduce mode,enum [outdoor\|room\|reduce], ,true,select.thermostat_hc1_reduce_mode,select.thermostat_hc1_reducemode,6,1,1,30,1
"RC120",thermostat,157,noreducetemp,no reduce below temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_no_reduce_below_temperature,number.thermostat_hc1_noreducetemp,6,1,1,31,1
"RC120",thermostat,157,reducetemp,off/reduce switch temperature,int8 (>=-126<=126),C,true,number.thermostat_hc1_off/reduce_switch_temperature,number.thermostat_hc1_reducetemp,6,1,1,32,1
"RC120",thermostat,157,dhwprio,dhw priority,boolean, ,true,switch.thermostat_hc1_dhw_priority,switch.thermostat_hc1_dhwprio,6,1,1,33,1
"RC120",thermostat,157,hpcooling,hp cooling,boolean, ,true,switch.thermostat_hc1_hp_cooling,switch.thermostat_hc1_hpcooling,6,1,1,34,1
"RC120",thermostat,157,coolingon,cooling on,boolean, ,false,binary_sensor.thermostat_hc1_cooling_on,binary_sensor.thermostat_hc1_coolingon,6,1,1,35,1
"RC120",thermostat,157,hpmode,HP Mode,enum [heating\|cooling\|heating & cooling], ,true,select.thermostat_hc1_HP_Mode,select.thermostat_hc1_hpmode,6,1,1,36,1
"RC120",thermostat,157,dewoffset,dew point offset,uint8 (>=2<=10),K,true,number.thermostat_hc1_dew_point_offset,number.thermostat_hc1_dewoffset,6,1,1,37,1
"RC120",thermostat,157,roomtempdiff,room temp difference,uint8 (>=0<=254),K,true,number.thermostat_hc1_room_temp_difference,number.thermostat_hc1_roomtempdiff,6,1,1,38,1
"RC120",thermostat,157,hpminflowtemp,HP min. flow temp.,uint8 (>=0<=254),C,true,number.thermostat_hc1_HP_min._flow_temp.,number.thermostat_hc1_hpminflowtemp,6,1,1,39,1
"RC120",thermostat,157,control,control device,enum [RC310\|RC200\|RC100\|RC100H\|TC100], ,true,select.thermostat_hc1_control_device,select.thermostat_hc1_control,6,1,1,40,1
"RC120",thermostat,157,remotetemp,room temperature from remote,cmd [] (>=-1<=101),C,true,sensor.thermostat_hc1_room_temperature_from_remote,sensor.thermostat_hc1_remotetemp,6,1,1/10,41,1
"RC120",thermostat,157,remotehum,room humidity from remote,cmd [] (>=-1<=101),%,true,sensor.thermostat_hc1_room_humidity_from_remote,sensor.thermostat_hc1_remotehum,6,1,1,42,1
"RC120",thermostat,157,heatondelay,heat-on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-on_delay,number.thermostat_hc1_heatondelay,6,1,1,43,1
"RC120",thermostat,157,heatoffdelay,heat-off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_heat-off_delay,number.thermostat_hc1_heatoffdelay,6,1,1,44,1
"RC120",thermostat,157,instantstart,instant start,uint8 (>=1<=10),K,true,number.thermostat_hc1_instant_start,number.thermostat_hc1_instantstart,6,1,1,45,1
"RC120",thermostat,157,boost,boost mode,boolean, ,true,switch.thermostat_hc1_boost_mode,switch.thermostat_hc1_boost,6,1,1,46,1
"RC120",thermostat,157,boosttime,boost time,uint8 (>=0<=254),hours,true,number.thermostat_hc1_boost_time,number.thermostat_hc1_boosttime,6,1,1,47,1
"RC120",thermostat,157,coolstart,cooling starttemp,uint8 (>=20<=35),C,true,number.thermostat_hc1_cooling_starttemp,number.thermostat_hc1_coolstart,6,1,1,48,1
"RC120",thermostat,157,coolondelay,cooling on delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_on_delay,number.thermostat_hc1_coolondelay,6,1,1,49,1
"RC120",thermostat,157,cooloffdelay,cooling off delay,uint8 (>=1<=48),hours,true,number.thermostat_hc1_cooling_off_delay,number.thermostat_hc1_cooloffdelay,6,1,1,50,1
"RC120",thermostat,157,switchprogmode,switch program mode,enum [level\|absolute], ,true,select.thermostat_hc1_switch_program_mode,select.thermostat_hc1_switchprogmode,6,1,1,51,1
"RC120",thermostat,157,mode,operating mode,enum [off\|comfort\|auto], ,true,select.thermostat_dhw_operating_mode,select.thermostat_dhw_mode,6,9,1,0,1
"RC120",thermostat,157,settemp,set temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_temperature,number.thermostat_dhw_settemp,6,9,1,1,1
"RC120",thermostat,157,settemplow,set low temperature,uint8 (>=0<=254),C,true,number.thermostat_dhw_set_low_temperature,number.thermostat_dhw_settemplow,6,9,1,2,1
"RC120",thermostat,157,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.thermostat_dhw_circulation_pump_mode,select.thermostat_dhw_circmode,6,9,1,3,1
"RC120",thermostat,157,chargeduration,charge duration,uint8 (>=0<=3810),minutes,true,number.thermostat_dhw_charge_duration,number.thermostat_dhw_chargeduration,6,9,15,4,1
"RC120",thermostat,157,charge,charge,boolean, ,true,switch.thermostat_dhw_charge,switch.thermostat_dhw_charge,6,9,1,5,1
"RC120",thermostat,157,extra,extra,boolean, ,false,binary_sensor.thermostat_dhw_extra,binary_sensor.thermostat_dhw_extra,6,9,1,6,1
"RC120",thermostat,157,disinfecting,disinfecting,boolean, ,true,switch.thermostat_dhw_disinfecting,switch.thermostat_dhw_disinfecting,6,9,1,7,1
"RC120",thermostat,157,disinfectday,disinfection day,enum [mo\|tu\|we\|th\|fr\|sa\|su\|all], ,true,select.thermostat_dhw_disinfection_day,select.thermostat_dhw_disinfectday,6,9,1,8,1
"RC120",thermostat,157,disinfecttime,disinfection time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_disinfection_time,number.thermostat_dhw_disinfecttime,6,9,15,9,1
"RC120",thermostat,157,dailyheating,daily heating,boolean, ,true,switch.thermostat_dhw_daily_heating,switch.thermostat_dhw_dailyheating,6,9,1,10,1
"RC120",thermostat,157,dailyheattime,daily heating time,uint8 (>=0<=1431),minutes,true,number.thermostat_dhw_daily_heating_time,number.thermostat_dhw_dailyheattime,6,9,15,11,1
"MM10",mixer,69,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"MM10",mixer,69,valvestatus,mixing valve actuator (VC1),int8 (>=-100<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"MM10",mixer,69,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"MM10",mixer,69,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"MM10",mixer,69,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated,7,1,1,4,1
"MM10",mixer,69,valvesettime,time to set valve,uint8 (>=10<=600),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime,7,1,10,5,1
"IPM",mixer,100,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"IPM",mixer,100,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"IPM",mixer,100,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"IPM",mixer,100,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"IPM",mixer,100,flowtempvf,flow temperature in header (T0/Vf),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_in_header_(T0/Vf),sensor.mixer_hc1_flowtempvf,7,1,1/10,6,1
"IPM2",mixer,102,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"IPM2",mixer,102,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"IPM2",mixer,102,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"IPM2",mixer,102,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"IPM2",mixer,102,flowtempvf,flow temperature in header (T0/Vf),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_in_header_(T0/Vf),sensor.mixer_hc1_flowtempvf,7,1,1/10,6,1
"MM50",mixer,159,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"MM50",mixer,159,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"MM50",mixer,159,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"MM50",mixer,159,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"MM50",mixer,159,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated,7,1,1,4,1
"MM50",mixer,159,valvesettime,time to set valve,uint8 (>=10<=600),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime,7,1,10,5,1
"MM50",mixer,159,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),K,true,number.mixer_hc1_flow_temperature_offset_for_mixer,number.mixer_hc1_flowtempoffset,7,1,1,7,1
"MM100",mixer,160,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"MM100",mixer,160,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"MM100",mixer,160,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"MM100",mixer,160,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"MM100",mixer,160,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated,7,1,1,4,1
"MM100",mixer,160,valvesettime,time to set valve,uint8 (>=10<=600),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime,7,1,10,5,1
"MM100",mixer,160,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),K,true,number.mixer_hc1_flow_temperature_offset_for_mixer,number.mixer_hc1_flowtempoffset,7,1,1,7,1
"MM200",mixer,161,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"MM200",mixer,161,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"MM200",mixer,161,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"MM200",mixer,161,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"MM200",mixer,161,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated,7,1,1,4,1
"MM200",mixer,161,valvesettime,time to set valve,uint8 (>=10<=600),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime,7,1,10,5,1
"MM200",mixer,161,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),K,true,number.mixer_hc1_flow_temperature_offset_for_mixer,number.mixer_hc1_flowtempoffset,7,1,1,7,1
"MZ100",mixer,193,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"MZ100",mixer,193,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"MZ100",mixer,193,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"MZ100",mixer,193,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"MZ100",mixer,193,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated,7,1,1,4,1
"MZ100",mixer,193,valvesettime,time to set valve,uint8 (>=10<=600),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime,7,1,10,5,1
"MZ100",mixer,193,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),K,true,number.mixer_hc1_flow_temperature_offset_for_mixer,number.mixer_hc1_flowtempoffset,7,1,1,7,1
"HM210",mixer,248,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.mixer_hc1_flow_temperature_(TC1),sensor.mixer_hc1_flowtemphc,7,1,1/10,0,1
"HM210",mixer,248,valvestatus,mixing valve actuator (VC1),uint8 (>=0<=100),%,false,sensor.mixer_hc1_mixing_valve_actuator_(VC1),sensor.mixer_hc1_valvestatus,7,1,1,1,1
"HM210",mixer,248,flowsettemp,setpoint flow temperature,uint8 (>=0<=254),C,true,number.mixer_hc1_setpoint_flow_temperature,number.mixer_hc1_flowsettemp,7,1,1,2,1
"HM210",mixer,248,pumpstatus,pump status (PC1),boolean, ,true,switch.mixer_hc1_pump_status_(PC1),switch.mixer_hc1_pumpstatus,7,1,1,3,1
"HM210",mixer,248,activated,activated,boolean, ,true,switch.mixer_hc1_activated,switch.mixer_hc1_activated,7,1,1,4,1
"HM210",mixer,248,valvesettime,time to set valve,uint8 (>=10<=600),seconds,true,number.mixer_hc1_time_to_set_valve,number.mixer_hc1_valvesettime,7,1,10,5,1
"HM210",mixer,248,flowtempoffset,flow temperature offset for mixer,uint8 (>=0<=20),K,true,number.mixer_hc1_flow_temperature_offset_for_mixer,number.mixer_hc1_flowtempoffset,7,1,1,7,1
"SM10",solar,73,collectortemp,collector temperature (TS1),int16 (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp,8,0,1/10,0,1
"SM10",solar,73,cylbottomtemp,cylinder bottom temperature (TS2),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp,8,0,1/10,1,1
"SM10",solar,73,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump,8,0,1,2,1
"SM10",solar,73,pumpworktime,pump working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime,8,0,1,3,2
"SM10",solar,73,cylmaxtemp,maximum cylinder temperature,uint8 (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp,8,0,1,5,1
"SM10",solar,73,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown,8,0,1,6,1
"SM10",solar,73,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated,8,0,1,7,1
"SM10",solar,73,solarpumpmod,pump modulation (PS1),uint8 (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod,8,0,1,8,1
"SM10",solar,73,pumpminmod,minimum pump modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod,8,0,1,9,1
"SM10",solar,73,turnondiff,pump turn on difference,uint8 (>=0<=254),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff,8,0,1,10,1
"SM10",solar,73,turnoffdiff,pump turn off difference,uint8 (>=0<=254),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff,8,0,1,11,1
"SM10",solar,73,solarpower,actual solar power,int16 (>=-31999<=31999),W,false,sensor.solar_actual_solar_power,sensor.solar_solarpower,8,0,1,12,1
"SM10",solar,73,energylasthour,energy last hour,uint24 (>=0<=1677721),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour,8,0,1/10,13,2
"SM10",solar,73,maxflow,maximum solar flow,uint8 (>=0<=25),l/min,true,number.solar_maximum_solar_flow,number.solar_maxflow,8,0,1/10,15,1
"SM10",solar,73,mintemp,minimum temperature,uint8 (>=0<=254),C,true,number.solar_dhw_minimum_temperature,number.solar_dhw_mintemp,8,9,1,0,1
"SM10",solar,73,solarenabled,solarmodule enabled,boolean, ,true,switch.solar_solarmodule_enabled,switch.solar_solarenabled,8,0,1,16,1
"ISM1",solar,101,collectortemp,collector temperature (TS1),int16 (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp,8,0,1/10,0,1
"ISM1",solar,101,cylbottomtemp,cylinder bottom temperature (TS2),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp,8,0,1/10,1,1
"ISM1",solar,101,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump,8,0,1,2,1
"ISM1",solar,101,pumpworktime,pump working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime,8,0,1,3,2
"ISM1",solar,101,cylmaxtemp,maximum cylinder temperature,uint8 (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp,8,0,1,5,1
"ISM1",solar,101,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown,8,0,1,6,1
"ISM1",solar,101,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated,8,0,1,7,1
"ISM1",solar,101,cylmiddletemp,cylinder middle temperature (TS3),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp,8,0,1/10,17,1
"ISM1",solar,101,retheatassist,return temperature heat assistance (TS4),int16 (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist,8,0,1/10,18,1
"ISM1",solar,101,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve,8,0,1,19,1
"ISM1",solar,101,energylasthour,energy last hour,uint24 (>=0<=1677721),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour,8,0,1/10,13,2
"ISM2",solar,103,collectortemp,collector temperature (TS1),int16 (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp,8,0,1/10,0,1
"ISM2",solar,103,cylbottomtemp,cylinder bottom temperature (TS2),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp,8,0,1/10,1,1
"ISM2",solar,103,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump,8,0,1,2,1
"ISM2",solar,103,pumpworktime,pump working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime,8,0,1,3,2
"ISM2",solar,103,cylmaxtemp,maximum cylinder temperature,uint8 (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp,8,0,1,5,1
"ISM2",solar,103,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown,8,0,1,6,1
"ISM2",solar,103,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated,8,0,1,7,1
"ISM2",solar,103,cylmiddletemp,cylinder middle temperature (TS3),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp,8,0,1/10,17,1
"ISM2",solar,103,retheatassist,return temperature heat assistance (TS4),int16 (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist,8,0,1/10,18,1
"ISM2",solar,103,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve,8,0,1,19,1
"ISM2",solar,103,energylasthour,energy last hour,uint24 (>=0<=1677721),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour,8,0,1/10,13,2
"SM50",solar,162,collectortemp,collector temperature (TS1),int16 (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp,8,0,1/10,0,1
"SM50",solar,162,cylbottomtemp,cylinder bottom temperature (TS2),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp,8,0,1/10,1,1
"SM50",solar,162,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump,8,0,1,2,1
"SM50",solar,162,pumpworktime,pump working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime,8,0,1,3,2
"SM50",solar,162,cylmaxtemp,maximum cylinder temperature,uint8 (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp,8,0,1,5,1
"SM50",solar,162,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown,8,0,1,6,1
"SM50",solar,162,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated,8,0,1,7,1
"SM50",solar,162,solarpumpmod,pump modulation (PS1),uint8 (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod,8,0,1,8,1
"SM50",solar,162,pumpminmod,minimum pump modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod,8,0,5,9,1
"SM50",solar,162,turnondiff,pump turn on difference,uint8 (>=0<=25),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff,8,0,1/10,10,1
"SM50",solar,162,turnoffdiff,pump turn off difference,uint8 (>=0<=25),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff,8,0,1/10,11,1
"SM50",solar,162,collector2temp,collector 2 temperature (TS7),int16 (>=-3199<=3199),C,false,sensor.solar_collector_2_temperature_(TS7),sensor.solar_collector2temp,8,0,1/10,20,1
"SM50",solar,162,cylmiddletemp,cylinder middle temperature (TS3),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp,8,0,1/10,17,1
"SM50",solar,162,retheatassist,return temperature heat assistance (TS4),int16 (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist,8,0,1/10,18,1
"SM50",solar,162,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve,8,0,1,19,1
"SM50",solar,162,heatassistpower,heat assistance valve power (M1),uint8 (>=0<=100),%,false,sensor.solar_heat_assistance_valve_power_(M1),sensor.solar_heatassistpower,8,0,1,21,1
"SM50",solar,162,solarpump2,pump 2 (PS4),boolean, ,false,binary_sensor.solar_pump_2_(PS4),binary_sensor.solar_solarpump2,8,0,1,22,1
"SM50",solar,162,solarpump2mod,pump 2 modulation (PS4),uint8 (>=0<=100),%,false,sensor.solar_pump_2_modulation_(PS4),sensor.solar_solarpump2mod,8,0,1,23,1
"SM50",solar,162,cyl2bottomtemp,second cylinder bottom temperature (TS5),int16 (>=-3199<=3199),C,false,sensor.solar_second_cylinder_bottom_temperature_(TS5),sensor.solar_cyl2bottomtemp,8,0,1/10,24,1
"SM50",solar,162,cyl3bottomtemp,third cylinder bottom temperature (TS11),int16 (>=-3199<=3199),C,false,sensor.solar_third_cylinder_bottom_temperature_(TS11),sensor.solar_cyl3bottomtemp,8,0,1/10,25,1
"SM50",solar,162,cyltoptemp,cylinder top temperature (TS10),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_top_temperature_(TS10),sensor.solar_cyltoptemp,8,0,1/10,26,1
"SM50",solar,162,heatexchangertemp,heat exchanger temperature (TS6),int16 (>=-3199<=3199),C,false,sensor.solar_heat_exchanger_temperature_(TS6),sensor.solar_heatexchangertemp,8,0,1/10,27,1
"SM50",solar,162,cylpumpmod,cylinder pump modulation (PS5),uint8 (>=0<=100),%,false,sensor.solar_cylinder_pump_modulation_(PS5),sensor.solar_cylpumpmod,8,0,1,28,1
"SM50",solar,162,valvestatus,valve status,boolean, ,false,binary_sensor.solar_valve_status,binary_sensor.solar_valvestatus,8,0,1,29,1
"SM50",solar,162,vs1status,valve status VS1,boolean, ,false,binary_sensor.solar_valve_status_VS1,binary_sensor.solar_vs1status,8,0,1,30,1
"SM50",solar,162,vs3status,valve status VS3,boolean, ,false,binary_sensor.solar_valve_status_VS3,binary_sensor.solar_vs3status,8,0,1,31,1
"SM50",solar,162,transferpump,transfer pump,boolean, ,false,binary_sensor.solar_transfer_pump,binary_sensor.solar_transferpump,8,0,1,32,1
"SM50",solar,162,transferpumpmod,transfer pump modulation,uint8 (>=0<=100),%,false,sensor.solar_transfer_pump_modulation,sensor.solar_transferpumpmod,8,0,1,33,1
"SM50",solar,162,collectormaxtemp,maximum collector temperature,uint8 (>=0<=254),C,true,number.solar_maximum_collector_temperature,number.solar_collectormaxtemp,8,0,1,34,1
"SM50",solar,162,collectormintemp,minimum collector temperature,uint8 (>=0<=254),C,true,number.solar_minimum_collector_temperature,number.solar_collectormintemp,8,0,1,35,1
"SM50",solar,162,energylasthour,energy last hour,uint24 (>=0<=1677721),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour,8,0,1/10,13,2
"SM50",solar,162,energytoday,total energy today,uint24 (>=0<=16777213),Wh,false,sensor.solar_total_energy_today,sensor.solar_energytoday,8,0,1,36,2
"SM50",solar,162,energytotal,total energy,uint24 (>=0<=1677721),kWh,false,sensor.solar_total_energy,sensor.solar_energytotal,8,0,1/10,38,2
"SM50",solar,162,pump2worktime,pump 2 working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_2_working_time,sensor.solar_pump2worktime,8,0,1,40,2
"SM50",solar,162,m1worktime,differential control working time,time (>=0<=16777213),minutes,false,sensor.solar_differential_control_working_time,sensor.solar_m1worktime,8,0,1,42,2
"SM50",solar,162,heattransfersystem,heattransfer system,boolean, ,true,switch.solar_heattransfer_system,switch.solar_heattransfersystem,8,0,1,44,1
"SM50",solar,162,externalcyl,external cylinder,boolean, ,true,switch.solar_external_cylinder,switch.solar_externalcyl,8,0,1,45,1
"SM50",solar,162,thermaldisinfect,thermal disinfection,boolean, ,true,switch.solar_thermal_disinfection,switch.solar_thermaldisinfect,8,0,1,46,1
"SM50",solar,162,heatmetering,heatmetering,boolean, ,true,switch.solar_heatmetering,switch.solar_heatmetering,8,0,1,47,1
"SM50",solar,162,activated,activated,boolean, ,true,switch.solar_activated,switch.solar_activated,8,0,1,48,1
"SM50",solar,162,solarpumpmode,solar pump mode,enum [constant\|pwm\|analog], ,true,select.solar_solar_pump_mode,select.solar_solarpumpmode,8,0,1,49,1
"SM50",solar,162,solarpumpkick,solar pump kick,boolean, ,true,switch.solar_solar_pump_kick,switch.solar_solarpumpkick,8,0,1,50,1
"SM50",solar,162,plainwatermode,plain water mode,boolean, ,true,switch.solar_plain_water_mode,switch.solar_plainwatermode,8,0,1,51,1
"SM50",solar,162,doublematchflow,doublematchflow,boolean, ,true,switch.solar_doublematchflow,switch.solar_doublematchflow,8,0,1,52,1
"SM50",solar,162,pump2minmod,minimum pump 2 modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_2_modulation,number.solar_pump2minmod,8,0,1,53,1
"SM50",solar,162,turnondiff2,pump 2 turn on difference,uint8 (>=0<=25),C,true,number.solar_pump_2_turn_on_difference,number.solar_turnondiff2,8,0,1/10,54,1
"SM50",solar,162,turnoffdiff2,pump 2 turn off difference,uint8 (>=0<=25),C,true,number.solar_pump_2_turn_off_difference,number.solar_turnoffdiff2,8,0,1/10,55,1
"SM50",solar,162,pump2kick,pump kick 2,boolean, ,true,switch.solar_pump_kick_2,switch.solar_pump2kick,8,0,1,56,1
"SM50",solar,162,climatezone,climate zone,uint8 (>=0<=254), ,true,number.solar_climate_zone,number.solar_climatezone,8,0,1,57,1
"SM50",solar,162,collector1area,collector 1 area,uint16 (>=0<=3199),m²,true,number.solar_collector_1_area,number.solar_collector1area,8,0,1/10,58,1
"SM50",solar,162,collector1type,collector 1 type,enum [flat\|vacuum], ,true,select.solar_collector_1_type,select.solar_collector1type,8,0,1,59,1
"SM50",solar,162,collector2area,collector 2 area,uint16 (>=0<=3199),m²,true,number.solar_collector_2_area,number.solar_collector2area,8,0,1/10,60,1
"SM50",solar,162,collector2type,collector 2 type,enum [flat\|vacuum], ,true,select.solar_collector_2_type,select.solar_collector2type,8,0,1,61,1
"SM50",solar,162,cylpriority,cylinder priority,enum [cyl 1\|cyl 2], ,true,select.solar_cylinder_priority,select.solar_cylpriority,8,0,1,62,1
"SM50",solar,162,heatcntflowtemp,heat counter flow temperature,uint16 (>=0<=3199),C,false,sensor.solar_heat_counter_flow_temperature,sensor.solar_heatcntflowtemp,8,0,1/10,63,1
"SM50",solar,162,heatcntrettemp,heat counter return temperature,uint16 (>=0<=3199),C,false,sensor.solar_heat_counter_return_temperature,sensor.solar_heatcntrettemp,8,0,1/10,64,1
"SM50",solar,162,heatcnt,heat counter impulses,uint8 (>=0<=254), ,false,sensor.solar_heat_counter_impulses,sensor.solar_heatcnt,8,0,1,65,1
"SM50",solar,162,swapflowtemp,swap flow temperature (TS14),uint16 (>=0<=3199),C,false,sensor.solar_swap_flow_temperature_(TS14),sensor.solar_swapflowtemp,8,0,1/10,66,1
"SM50",solar,162,swaprettemp,swap return temperature (TS15),uint16 (>=0<=3199),C,false,sensor.solar_swap_return_temperature_(TS15),sensor.solar_swaprettemp,8,0,1/10,67,1
"SM100, MS100",solar,163,collectortemp,collector temperature (TS1),int16 (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp,8,0,1/10,0,1
"SM100, MS100",solar,163,cylbottomtemp,cylinder bottom temperature (TS2),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp,8,0,1/10,1,1
"SM100, MS100",solar,163,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump,8,0,1,2,1
"SM100, MS100",solar,163,pumpworktime,pump working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime,8,0,1,3,2
"SM100, MS100",solar,163,cylmaxtemp,maximum cylinder temperature,uint8 (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp,8,0,1,5,1
"SM100, MS100",solar,163,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown,8,0,1,6,1
"SM100, MS100",solar,163,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated,8,0,1,7,1
"SM100, MS100",solar,163,solarpumpmod,pump modulation (PS1),uint8 (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod,8,0,1,8,1
"SM100, MS100",solar,163,pumpminmod,minimum pump modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod,8,0,5,9,1
"SM100, MS100",solar,163,turnondiff,pump turn on difference,uint8 (>=0<=25),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff,8,0,1/10,10,1
"SM100, MS100",solar,163,turnoffdiff,pump turn off difference,uint8 (>=0<=25),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff,8,0,1/10,11,1
"SM100, MS100",solar,163,collector2temp,collector 2 temperature (TS7),int16 (>=-3199<=3199),C,false,sensor.solar_collector_2_temperature_(TS7),sensor.solar_collector2temp,8,0,1/10,20,1
"SM100, MS100",solar,163,cylmiddletemp,cylinder middle temperature (TS3),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp,8,0,1/10,17,1
"SM100, MS100",solar,163,retheatassist,return temperature heat assistance (TS4),int16 (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist,8,0,1/10,18,1
"SM100, MS100",solar,163,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve,8,0,1,19,1
"SM100, MS100",solar,163,heatassistpower,heat assistance valve power (M1),uint8 (>=0<=100),%,false,sensor.solar_heat_assistance_valve_power_(M1),sensor.solar_heatassistpower,8,0,1,21,1
"SM100, MS100",solar,163,solarpump2,pump 2 (PS4),boolean, ,false,binary_sensor.solar_pump_2_(PS4),binary_sensor.solar_solarpump2,8,0,1,22,1
"SM100, MS100",solar,163,solarpump2mod,pump 2 modulation (PS4),uint8 (>=0<=100),%,false,sensor.solar_pump_2_modulation_(PS4),sensor.solar_solarpump2mod,8,0,1,23,1
"SM100, MS100",solar,163,cyl2bottomtemp,second cylinder bottom temperature (TS5),int16 (>=-3199<=3199),C,false,sensor.solar_second_cylinder_bottom_temperature_(TS5),sensor.solar_cyl2bottomtemp,8,0,1/10,24,1
"SM100, MS100",solar,163,cyl3bottomtemp,third cylinder bottom temperature (TS11),int16 (>=-3199<=3199),C,false,sensor.solar_third_cylinder_bottom_temperature_(TS11),sensor.solar_cyl3bottomtemp,8,0,1/10,25,1
"SM100, MS100",solar,163,cyltoptemp,cylinder top temperature (TS10),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_top_temperature_(TS10),sensor.solar_cyltoptemp,8,0,1/10,26,1
"SM100, MS100",solar,163,heatexchangertemp,heat exchanger temperature (TS6),int16 (>=-3199<=3199),C,false,sensor.solar_heat_exchanger_temperature_(TS6),sensor.solar_heatexchangertemp,8,0,1/10,27,1
"SM100, MS100",solar,163,cylpumpmod,cylinder pump modulation (PS5),uint8 (>=0<=100),%,false,sensor.solar_cylinder_pump_modulation_(PS5),sensor.solar_cylpumpmod,8,0,1,28,1
"SM100, MS100",solar,163,valvestatus,valve status,boolean, ,false,binary_sensor.solar_valve_status,binary_sensor.solar_valvestatus,8,0,1,29,1
"SM100, MS100",solar,163,vs1status,valve status VS1,boolean, ,false,binary_sensor.solar_valve_status_VS1,binary_sensor.solar_vs1status,8,0,1,30,1
"SM100, MS100",solar,163,vs3status,valve status VS3,boolean, ,false,binary_sensor.solar_valve_status_VS3,binary_sensor.solar_vs3status,8,0,1,31,1
"SM100, MS100",solar,163,transferpump,transfer pump,boolean, ,false,binary_sensor.solar_transfer_pump,binary_sensor.solar_transferpump,8,0,1,32,1
"SM100, MS100",solar,163,transferpumpmod,transfer pump modulation,uint8 (>=0<=100),%,false,sensor.solar_transfer_pump_modulation,sensor.solar_transferpumpmod,8,0,1,33,1
"SM100, MS100",solar,163,collectormaxtemp,maximum collector temperature,uint8 (>=0<=254),C,true,number.solar_maximum_collector_temperature,number.solar_collectormaxtemp,8,0,1,34,1
"SM100, MS100",solar,163,collectormintemp,minimum collector temperature,uint8 (>=0<=254),C,true,number.solar_minimum_collector_temperature,number.solar_collectormintemp,8,0,1,35,1
"SM100, MS100",solar,163,energylasthour,energy last hour,uint24 (>=0<=1677721),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour,8,0,1/10,13,2
"SM100, MS100",solar,163,energytoday,total energy today,uint24 (>=0<=16777213),Wh,false,sensor.solar_total_energy_today,sensor.solar_energytoday,8,0,1,36,2
"SM100, MS100",solar,163,energytotal,total energy,uint24 (>=0<=1677721),kWh,false,sensor.solar_total_energy,sensor.solar_energytotal,8,0,1/10,38,2
"SM100, MS100",solar,163,pump2worktime,pump 2 working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_2_working_time,sensor.solar_pump2worktime,8,0,1,40,2
"SM100, MS100",solar,163,m1worktime,differential control working time,time (>=0<=16777213),minutes,false,sensor.solar_differential_control_working_time,sensor.solar_m1worktime,8,0,1,42,2
"SM100, MS100",solar,163,heattransfersystem,heattransfer system,boolean, ,true,switch.solar_heattransfer_system,switch.solar_heattransfersystem,8,0,1,44,1
"SM100, MS100",solar,163,externalcyl,external cylinder,boolean, ,true,switch.solar_external_cylinder,switch.solar_externalcyl,8,0,1,45,1
"SM100, MS100",solar,163,thermaldisinfect,thermal disinfection,boolean, ,true,switch.solar_thermal_disinfection,switch.solar_thermaldisinfect,8,0,1,46,1
"SM100, MS100",solar,163,heatmetering,heatmetering,boolean, ,true,switch.solar_heatmetering,switch.solar_heatmetering,8,0,1,47,1
"SM100, MS100",solar,163,activated,activated,boolean, ,true,switch.solar_activated,switch.solar_activated,8,0,1,48,1
"SM100, MS100",solar,163,solarpumpmode,solar pump mode,enum [constant\|pwm\|analog], ,true,select.solar_solar_pump_mode,select.solar_solarpumpmode,8,0,1,49,1
"SM100, MS100",solar,163,solarpumpkick,solar pump kick,boolean, ,true,switch.solar_solar_pump_kick,switch.solar_solarpumpkick,8,0,1,50,1
"SM100, MS100",solar,163,plainwatermode,plain water mode,boolean, ,true,switch.solar_plain_water_mode,switch.solar_plainwatermode,8,0,1,51,1
"SM100, MS100",solar,163,doublematchflow,doublematchflow,boolean, ,true,switch.solar_doublematchflow,switch.solar_doublematchflow,8,0,1,52,1
"SM100, MS100",solar,163,pump2minmod,minimum pump 2 modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_2_modulation,number.solar_pump2minmod,8,0,1,53,1
"SM100, MS100",solar,163,turnondiff2,pump 2 turn on difference,uint8 (>=0<=25),C,true,number.solar_pump_2_turn_on_difference,number.solar_turnondiff2,8,0,1/10,54,1
"SM100, MS100",solar,163,turnoffdiff2,pump 2 turn off difference,uint8 (>=0<=25),C,true,number.solar_pump_2_turn_off_difference,number.solar_turnoffdiff2,8,0,1/10,55,1
"SM100, MS100",solar,163,pump2kick,pump kick 2,boolean, ,true,switch.solar_pump_kick_2,switch.solar_pump2kick,8,0,1,56,1
"SM100, MS100",solar,163,climatezone,climate zone,uint8 (>=0<=254), ,true,number.solar_climate_zone,number.solar_climatezone,8,0,1,57,1
"SM100, MS100",solar,163,collector1area,collector 1 area,uint16 (>=0<=3199),m²,true,number.solar_collector_1_area,number.solar_collector1area,8,0,1/10,58,1
"SM100, MS100",solar,163,collector1type,collector 1 type,enum [flat\|vacuum], ,true,select.solar_collector_1_type,select.solar_collector1type,8,0,1,59,1
"SM100, MS100",solar,163,collector2area,collector 2 area,uint16 (>=0<=3199),m²,true,number.solar_collector_2_area,number.solar_collector2area,8,0,1/10,60,1
"SM100, MS100",solar,163,collector2type,collector 2 type,enum [flat\|vacuum], ,true,select.solar_collector_2_type,select.solar_collector2type,8,0,1,61,1
"SM100, MS100",solar,163,cylpriority,cylinder priority,enum [cyl 1\|cyl 2], ,true,select.solar_cylinder_priority,select.solar_cylpriority,8,0,1,62,1
"SM100, MS100",solar,163,heatcntflowtemp,heat counter flow temperature,uint16 (>=0<=3199),C,false,sensor.solar_heat_counter_flow_temperature,sensor.solar_heatcntflowtemp,8,0,1/10,63,1
"SM100, MS100",solar,163,heatcntrettemp,heat counter return temperature,uint16 (>=0<=3199),C,false,sensor.solar_heat_counter_return_temperature,sensor.solar_heatcntrettemp,8,0,1/10,64,1
"SM100, MS100",solar,163,heatcnt,heat counter impulses,uint8 (>=0<=254), ,false,sensor.solar_heat_counter_impulses,sensor.solar_heatcnt,8,0,1,65,1
"SM100, MS100",solar,163,swapflowtemp,swap flow temperature (TS14),uint16 (>=0<=3199),C,false,sensor.solar_swap_flow_temperature_(TS14),sensor.solar_swapflowtemp,8,0,1/10,66,1
"SM100, MS100",solar,163,swaprettemp,swap return temperature (TS15),uint16 (>=0<=3199),C,false,sensor.solar_swap_return_temperature_(TS15),sensor.solar_swaprettemp,8,0,1/10,67,1
"SM200, MS200",solar,164,collectortemp,collector temperature (TS1),int16 (>=-3199<=3199),C,false,sensor.solar_collector_temperature_(TS1),sensor.solar_collectortemp,8,0,1/10,0,1
"SM200, MS200",solar,164,cylbottomtemp,cylinder bottom temperature (TS2),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_bottom_temperature_(TS2),sensor.solar_cylbottomtemp,8,0,1/10,1,1
"SM200, MS200",solar,164,solarpump,pump (PS1),boolean, ,false,binary_sensor.solar_pump_(PS1),binary_sensor.solar_solarpump,8,0,1,2,1
"SM200, MS200",solar,164,pumpworktime,pump working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_working_time,sensor.solar_pumpworktime,8,0,1,3,2
"SM200, MS200",solar,164,cylmaxtemp,maximum cylinder temperature,uint8 (>=0<=254),C,true,number.solar_maximum_cylinder_temperature,number.solar_cylmaxtemp,8,0,1,5,1
"SM200, MS200",solar,164,collectorshutdown,collector shutdown,boolean, ,false,binary_sensor.solar_collector_shutdown,binary_sensor.solar_collectorshutdown,8,0,1,6,1
"SM200, MS200",solar,164,cylheated,cyl heated,boolean, ,false,binary_sensor.solar_cyl_heated,binary_sensor.solar_cylheated,8,0,1,7,1
"SM200, MS200",solar,164,solarpumpmod,pump modulation (PS1),uint8 (>=0<=100),%,false,sensor.solar_pump_modulation_(PS1),sensor.solar_solarpumpmod,8,0,1,8,1
"SM200, MS200",solar,164,pumpminmod,minimum pump modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_modulation,number.solar_pumpminmod,8,0,5,9,1
"SM200, MS200",solar,164,turnondiff,pump turn on difference,uint8 (>=0<=25),C,true,number.solar_pump_turn_on_difference,number.solar_turnondiff,8,0,1/10,10,1
"SM200, MS200",solar,164,turnoffdiff,pump turn off difference,uint8 (>=0<=25),C,true,number.solar_pump_turn_off_difference,number.solar_turnoffdiff,8,0,1/10,11,1
"SM200, MS200",solar,164,collector2temp,collector 2 temperature (TS7),int16 (>=-3199<=3199),C,false,sensor.solar_collector_2_temperature_(TS7),sensor.solar_collector2temp,8,0,1/10,20,1
"SM200, MS200",solar,164,cylmiddletemp,cylinder middle temperature (TS3),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_middle_temperature_(TS3),sensor.solar_cylmiddletemp,8,0,1/10,17,1
"SM200, MS200",solar,164,retheatassist,return temperature heat assistance (TS4),int16 (>=-3199<=3199),C,false,sensor.solar_return_temperature_heat_assistance_(TS4),sensor.solar_retheatassist,8,0,1/10,18,1
"SM200, MS200",solar,164,heatassistvalve,heat assistance valve (M1),boolean, ,false,binary_sensor.solar_heat_assistance_valve_(M1),binary_sensor.solar_heatassistvalve,8,0,1,19,1
"SM200, MS200",solar,164,heatassistpower,heat assistance valve power (M1),uint8 (>=0<=100),%,false,sensor.solar_heat_assistance_valve_power_(M1),sensor.solar_heatassistpower,8,0,1,21,1
"SM200, MS200",solar,164,solarpump2,pump 2 (PS4),boolean, ,false,binary_sensor.solar_pump_2_(PS4),binary_sensor.solar_solarpump2,8,0,1,22,1
"SM200, MS200",solar,164,solarpump2mod,pump 2 modulation (PS4),uint8 (>=0<=100),%,false,sensor.solar_pump_2_modulation_(PS4),sensor.solar_solarpump2mod,8,0,1,23,1
"SM200, MS200",solar,164,cyl2bottomtemp,second cylinder bottom temperature (TS5),int16 (>=-3199<=3199),C,false,sensor.solar_second_cylinder_bottom_temperature_(TS5),sensor.solar_cyl2bottomtemp,8,0,1/10,24,1
"SM200, MS200",solar,164,cyl3bottomtemp,third cylinder bottom temperature (TS11),int16 (>=-3199<=3199),C,false,sensor.solar_third_cylinder_bottom_temperature_(TS11),sensor.solar_cyl3bottomtemp,8,0,1/10,25,1
"SM200, MS200",solar,164,cyltoptemp,cylinder top temperature (TS10),int16 (>=-3199<=3199),C,false,sensor.solar_cylinder_top_temperature_(TS10),sensor.solar_cyltoptemp,8,0,1/10,26,1
"SM200, MS200",solar,164,heatexchangertemp,heat exchanger temperature (TS6),int16 (>=-3199<=3199),C,false,sensor.solar_heat_exchanger_temperature_(TS6),sensor.solar_heatexchangertemp,8,0,1/10,27,1
"SM200, MS200",solar,164,cylpumpmod,cylinder pump modulation (PS5),uint8 (>=0<=100),%,false,sensor.solar_cylinder_pump_modulation_(PS5),sensor.solar_cylpumpmod,8,0,1,28,1
"SM200, MS200",solar,164,valvestatus,valve status,boolean, ,false,binary_sensor.solar_valve_status,binary_sensor.solar_valvestatus,8,0,1,29,1
"SM200, MS200",solar,164,vs1status,valve status VS1,boolean, ,false,binary_sensor.solar_valve_status_VS1,binary_sensor.solar_vs1status,8,0,1,30,1
"SM200, MS200",solar,164,vs3status,valve status VS3,boolean, ,false,binary_sensor.solar_valve_status_VS3,binary_sensor.solar_vs3status,8,0,1,31,1
"SM200, MS200",solar,164,transferpump,transfer pump,boolean, ,false,binary_sensor.solar_transfer_pump,binary_sensor.solar_transferpump,8,0,1,32,1
"SM200, MS200",solar,164,transferpumpmod,transfer pump modulation,uint8 (>=0<=100),%,false,sensor.solar_transfer_pump_modulation,sensor.solar_transferpumpmod,8,0,1,33,1
"SM200, MS200",solar,164,collectormaxtemp,maximum collector temperature,uint8 (>=0<=254),C,true,number.solar_maximum_collector_temperature,number.solar_collectormaxtemp,8,0,1,34,1
"SM200, MS200",solar,164,collectormintemp,minimum collector temperature,uint8 (>=0<=254),C,true,number.solar_minimum_collector_temperature,number.solar_collectormintemp,8,0,1,35,1
"SM200, MS200",solar,164,energylasthour,energy last hour,uint24 (>=0<=1677721),Wh,false,sensor.solar_energy_last_hour,sensor.solar_energylasthour,8,0,1/10,13,2
"SM200, MS200",solar,164,energytoday,total energy today,uint24 (>=0<=16777213),Wh,false,sensor.solar_total_energy_today,sensor.solar_energytoday,8,0,1,36,2
"SM200, MS200",solar,164,energytotal,total energy,uint24 (>=0<=1677721),kWh,false,sensor.solar_total_energy,sensor.solar_energytotal,8,0,1/10,38,2
"SM200, MS200",solar,164,pump2worktime,pump 2 working time,time (>=0<=16777213),minutes,false,sensor.solar_pump_2_working_time,sensor.solar_pump2worktime,8,0,1,40,2
"SM200, MS200",solar,164,m1worktime,differential control working time,time (>=0<=16777213),minutes,false,sensor.solar_differential_control_working_time,sensor.solar_m1worktime,8,0,1,42,2
"SM200, MS200",solar,164,heattransfersystem,heattransfer system,boolean, ,true,switch.solar_heattransfer_system,switch.solar_heattransfersystem,8,0,1,44,1
"SM200, MS200",solar,164,externalcyl,external cylinder,boolean, ,true,switch.solar_external_cylinder,switch.solar_externalcyl,8,0,1,45,1
"SM200, MS200",solar,164,thermaldisinfect,thermal disinfection,boolean, ,true,switch.solar_thermal_disinfection,switch.solar_thermaldisinfect,8,0,1,46,1
"SM200, MS200",solar,164,heatmetering,heatmetering,boolean, ,true,switch.solar_heatmetering,switch.solar_heatmetering,8,0,1,47,1
"SM200, MS200",solar,164,activated,activated,boolean, ,true,switch.solar_activated,switch.solar_activated,8,0,1,48,1
"SM200, MS200",solar,164,solarpumpmode,solar pump mode,enum [constant\|pwm\|analog], ,true,select.solar_solar_pump_mode,select.solar_solarpumpmode,8,0,1,49,1
"SM200, MS200",solar,164,solarpumpkick,solar pump kick,boolean, ,true,switch.solar_solar_pump_kick,switch.solar_solarpumpkick,8,0,1,50,1
"SM200, MS200",solar,164,plainwatermode,plain water mode,boolean, ,true,switch.solar_plain_water_mode,switch.solar_plainwatermode,8,0,1,51,1
"SM200, MS200",solar,164,doublematchflow,doublematchflow,boolean, ,true,switch.solar_doublematchflow,switch.solar_doublematchflow,8,0,1,52,1
"SM200, MS200",solar,164,pump2minmod,minimum pump 2 modulation,uint8 (>=0<=100),%,true,number.solar_minimum_pump_2_modulation,number.solar_pump2minmod,8,0,1,53,1
"SM200, MS200",solar,164,turnondiff2,pump 2 turn on difference,uint8 (>=0<=25),C,true,number.solar_pump_2_turn_on_difference,number.solar_turnondiff2,8,0,1/10,54,1
"SM200, MS200",solar,164,turnoffdiff2,pump 2 turn off difference,uint8 (>=0<=25),C,true,number.solar_pump_2_turn_off_difference,number.solar_turnoffdiff2,8,0,1/10,55,1
"SM200, MS200",solar,164,pump2kick,pump kick 2,boolean, ,true,switch.solar_pump_kick_2,switch.solar_pump2kick,8,0,1,56,1
"SM200, MS200",solar,164,climatezone,climate zone,uint8 (>=0<=254), ,true,number.solar_climate_zone,number.solar_climatezone,8,0,1,57,1
"SM200, MS200",solar,164,collector1area,collector 1 area,uint16 (>=0<=3199),m²,true,number.solar_collector_1_area,number.solar_collector1area,8,0,1/10,58,1
"SM200, MS200",solar,164,collector1type,collector 1 type,enum [flat\|vacuum], ,true,select.solar_collector_1_type,select.solar_collector1type,8,0,1,59,1
"SM200, MS200",solar,164,collector2area,collector 2 area,uint16 (>=0<=3199),m²,true,number.solar_collector_2_area,number.solar_collector2area,8,0,1/10,60,1
"SM200, MS200",solar,164,collector2type,collector 2 type,enum [flat\|vacuum], ,true,select.solar_collector_2_type,select.solar_collector2type,8,0,1,61,1
"SM200, MS200",solar,164,cylpriority,cylinder priority,enum [cyl 1\|cyl 2], ,true,select.solar_cylinder_priority,select.solar_cylpriority,8,0,1,62,1
"SM200, MS200",solar,164,heatcntflowtemp,heat counter flow temperature,uint16 (>=0<=3199),C,false,sensor.solar_heat_counter_flow_temperature,sensor.solar_heatcntflowtemp,8,0,1/10,63,1
"SM200, MS200",solar,164,heatcntrettemp,heat counter return temperature,uint16 (>=0<=3199),C,false,sensor.solar_heat_counter_return_temperature,sensor.solar_heatcntrettemp,8,0,1/10,64,1
"SM200, MS200",solar,164,heatcnt,heat counter impulses,uint8 (>=0<=254), ,false,sensor.solar_heat_counter_impulses,sensor.solar_heatcnt,8,0,1,65,1
"SM200, MS200",solar,164,swapflowtemp,swap flow temperature (TS14),uint16 (>=0<=3199),C,false,sensor.solar_swap_flow_temperature_(TS14),sensor.solar_swapflowtemp,8,0,1/10,66,1
"SM200, MS200",solar,164,swaprettemp,swap return temperature (TS15),uint16 (>=0<=3199),C,false,sensor.solar_swap_return_temperature_(TS15),sensor.solar_swaprettemp,8,0,1/10,67,1
"HP Module",heatpump,252,airhumidity,relative air humidity,uint8 (>=0<=100),%,false,sensor.heatpump_relative_air_humidity,sensor.heatpump_airhumidity,9,0,1,0,1
"HP Module",heatpump,252,dewtemperature,dew point temperature,uint8 (>=0<=254),C,false,sensor.heatpump_dew_point_temperature,sensor.heatpump_dewtemperature,9,0,1,1,1
"HP Module",heatpump,252,curflowtemp,current flow temperature,int16 (>=-3199<=3199),C,false,sensor.heatpump_current_flow_temperature,sensor.heatpump_curflowtemp,9,0,1/10,2,1
"HP Module",heatpump,252,rettemp,return temperature,int16 (>=-3199<=3199),C,false,sensor.heatpump_return_temperature,sensor.heatpump_rettemp,9,0,1/10,3,1
"HP Module",heatpump,252,sysrettemp,system return temperature,int16 (>=-3199<=3199),C,false,sensor.heatpump_system_return_temperature,sensor.heatpump_sysrettemp,9,0,1/10,4,1
"HP Module",heatpump,252,hpta4,drain pan temp (TA4),int16 (>=-3199<=3199),C,false,sensor.heatpump_drain_pan_temp_(TA4),sensor.heatpump_hpta4,9,0,1/10,5,1
"HP Module",heatpump,252,hptr1,compressor temperature (TR1),int16 (>=-3199<=3199),C,false,sensor.heatpump_compressor_temperature_(TR1),sensor.heatpump_hptr1,9,0,1/10,6,1
"HP Module",heatpump,252,hptr3,refrigerant temperature liquid side (condenser output) (TR3),int16 (>=-3199<=3199),C,false,sensor.heatpump_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.heatpump_hptr3,9,0,1/10,7,1
"HP Module",heatpump,252,hptr4,evaporator inlet temperature (TR4),int16 (>=-3199<=3199),C,false,sensor.heatpump_evaporator_inlet_temperature_(TR4),sensor.heatpump_hptr4,9,0,1/10,8,1
"HP Module",heatpump,252,hptr5,compressor inlet temperature (TR5),int16 (>=-3199<=3199),C,false,sensor.heatpump_compressor_inlet_temperature_(TR5),sensor.heatpump_hptr5,9,0,1/10,9,1
"HP Module",heatpump,252,hptr6,compressor outlet temperature (TR6),int16 (>=-3199<=3199),C,false,sensor.heatpump_compressor_outlet_temperature_(TR6),sensor.heatpump_hptr6,9,0,1/10,10,1
"HP Module",heatpump,252,hptl2,air inlet temperature (TL2),int16 (>=-3199<=3199),C,false,sensor.heatpump_air_inlet_temperature_(TL2),sensor.heatpump_hptl2,9,0,1/10,11,1
"HP Module",heatpump,252,hppl1,low pressure side temperature (PL1),int16 (>=-3199<=3199),C,false,sensor.heatpump_low_pressure_side_temperature_(PL1),sensor.heatpump_hppl1,9,0,1/10,12,1
"HP Module",heatpump,252,hpph1,high pressure side temperature (PH1),int16 (>=-3199<=3199),C,false,sensor.heatpump_high_pressure_side_temperature_(PH1),sensor.heatpump_hpph1,9,0,1/10,13,1
"HP Module",heatpump,252,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.heatpump_heating_pump_modulation,sensor.heatpump_heatingpumpmod,9,0,1,14,1
"HP Module",heatpump,252,hpcompspd,compressor speed,uint8 (>=0<=100),%,false,sensor.heatpump_compressor_speed,sensor.heatpump_hpcompspd,9,0,1,15,1
"HP Module",heatpump,252,hybridstrategy,hybrid control strategy,enum [cost optimized\|co2 optimized\|outside temperature alt.\|outside temperature parallel\|heatpump preferred\|boiler only], ,true,select.heatpump_hybrid_control_strategy,select.heatpump_hybridstrategy,9,0,1,16,1
"HP Module",heatpump,252,lownoisemode,low noise mode,enum [off\|reduced output\|switch off hp\|perm. reduced], ,true,select.heatpump_low_noise_mode,select.heatpump_lownoisemode,9,0,1,17,1
"HP Module",heatpump,252,lownoisestart,low noise starttime,uint8 (>=0<=23),hours,true,number.heatpump_low_noise_starttime,number.heatpump_lownoisestart,9,0,1,18,1
"HP Module",heatpump,252,lownoisestop,low noise stoptime,uint8 (>=0<=23),hours,true,number.heatpump_low_noise_stoptime,number.heatpump_lownoisestop,9,0,1,19,1
"HP Module",heatpump,252,hybriddhw,hybrid DHW,enum [eco\|high comfort], ,true,select.heatpump_dhw_hybrid_DHW,select.heatpump_dhw_hybriddhw,9,9,1,0,1
"HP Module",heatpump,252,energypricegas,energy price gas,uint8 (>=0<=254),ct/kWh,true,number.heatpump_energy_price_gas,number.heatpump_energypricegas,9,0,1,20,1
"HP Module",heatpump,252,energypriceel,energy price electric,uint8 (>=0<=254),ct/kWh,true,number.heatpump_energy_price_electric,number.heatpump_energypriceel,9,0,1,21,1
"HP Module",heatpump,252,energyfeedpv,feed in PV,uint8 (>=0<=254),ct/kWh,true,number.heatpump_feed_in_PV,number.heatpump_energyfeedpv,9,0,1,22,1
"HP Module",heatpump,252,switchovertemp,outside switchover temperature,int8 (>=-126<=126),C,true,number.heatpump_outside_switchover_temperature,number.heatpump_switchovertemp,9,0,1,23,1
"HP Module",heatpump,252,airpurgemode,air purge mode,boolean, ,true,switch.heatpump_air_purge_mode,switch.heatpump_airpurgemode,9,0,1,24,1
"HP Module",heatpump,252,heatpumpoutput,heatpump output,uint8 (>=0<=100),%,true,number.heatpump_heatpump_output,number.heatpump_heatpumpoutput,9,0,1,25,1
"HP Module",heatpump,252,coolingcircuit,cooling circuit,boolean, ,true,switch.heatpump_cooling_circuit,switch.heatpump_coolingcircuit,9,0,1,26,1
"HP Module",heatpump,252,compstartmod,compressor start modulation,uint8 (>=0<=100),%,true,number.heatpump_compressor_start_modulation,number.heatpump_compstartmod,9,0,1,27,1
"HP Module",heatpump,252,heatdrainpan,heat drain pan,boolean, ,true,switch.heatpump_heat_drain_pan,switch.heatpump_heatdrainpan,9,0,1,28,1
"HP Module",heatpump,252,heatcable,heating cable,boolean, ,true,switch.heatpump_heating_cable,switch.heatpump_heatcable,9,0,1,29,1
"HP Module",heatpump,252,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.heatpump_total_energy,sensor.heatpump_nrgtotal,9,0,1/100,30,2
"HP Module",heatpump,252,nrg,energy,uint24 (>=0<=167772),kWh,false,sensor.heatpump_dhw_energy,sensor.heatpump_dhw_nrg,9,9,1/100,1,2
"HP Module",heatpump,252,nrgheat,energy heating,uint24 (>=0<=167772),kWh,false,sensor.heatpump_energy_heating,sensor.heatpump_nrgheat,9,0,1/100,32,2
"HP Module",heatpump,252,metertotal,meter total,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_total,sensor.heatpump_metertotal,9,0,1/100,34,2
"HP Module",heatpump,252,metercomp,meter compressor,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_compressor,sensor.heatpump_metercomp,9,0,1/100,36,2
"HP Module",heatpump,252,metereheat,meter e-heater,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_e-heater,sensor.heatpump_metereheat,9,0,1/100,38,2
"HP Module",heatpump,252,meterheat,meter heating,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_heating,sensor.heatpump_meterheat,9,0,1/100,40,2
"HP Module",heatpump,252,meter,meter,uint24 (>=0<=167772),kWh,false,sensor.heatpump_dhw_meter,sensor.heatpump_dhw_meter,9,9,1/100,3,2
"HP Module",heatpump,252,heatingstarts,heating control starts,uint24 (>=0<=16777213), ,false,sensor.heatpump_heating_control_starts,sensor.heatpump_heatingstarts,9,0,1,42,2
"HP Module",heatpump,252,startshp,starts hp,uint24 (>=0<=16777213), ,false,sensor.heatpump_dhw_starts_hp,sensor.heatpump_dhw_startshp,9,9,1,5,2
"HP Module",heatpump,252,fuelheat,fuel consuption heating,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_fuel_consuption_heating,sensor.heatpump_fuelheat,9,0,1/10,44,2
"HP Module",heatpump,252,fueldhw,fuel consuption,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_dhw_fuel_consuption,sensor.heatpump_dhw_fueldhw,9,9,1/10,7,2
"HP Module",heatpump,252,elheat,el. consuption heating,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_el._consuption_heating,sensor.heatpump_elheat,9,0,1/10,46,2
"HP Module",heatpump,252,eldhw,el consuption,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_dhw_el_consuption,sensor.heatpump_dhw_eldhw,9,9,1/10,9,2
"HP Module",heatpump,252,elgenheat,el. generation heating,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_el._generation_heating,sensor.heatpump_elgenheat,9,0,1/10,48,2
"HP Module",heatpump,252,elgendhw,el generation,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_dhw_el_generation,sensor.heatpump_dhw_elgendhw,9,9,1/10,11,2
"Hybrid Manager HM200",heatpump,248,airhumidity,relative air humidity,uint8 (>=0<=100),%,false,sensor.heatpump_relative_air_humidity,sensor.heatpump_airhumidity,9,0,1,0,1
"Hybrid Manager HM200",heatpump,248,dewtemperature,dew point temperature,uint8 (>=0<=254),C,false,sensor.heatpump_dew_point_temperature,sensor.heatpump_dewtemperature,9,0,1,1,1
"Hybrid Manager HM200",heatpump,248,curflowtemp,current flow temperature,int16 (>=-3199<=3199),C,false,sensor.heatpump_current_flow_temperature,sensor.heatpump_curflowtemp,9,0,1/10,2,1
"Hybrid Manager HM200",heatpump,248,rettemp,return temperature,int16 (>=-3199<=3199),C,false,sensor.heatpump_return_temperature,sensor.heatpump_rettemp,9,0,1/10,3,1
"Hybrid Manager HM200",heatpump,248,sysrettemp,system return temperature,int16 (>=-3199<=3199),C,false,sensor.heatpump_system_return_temperature,sensor.heatpump_sysrettemp,9,0,1/10,4,1
"Hybrid Manager HM200",heatpump,248,hpta4,drain pan temp (TA4),int16 (>=-3199<=3199),C,false,sensor.heatpump_drain_pan_temp_(TA4),sensor.heatpump_hpta4,9,0,1/10,5,1
"Hybrid Manager HM200",heatpump,248,hptr1,compressor temperature (TR1),int16 (>=-3199<=3199),C,false,sensor.heatpump_compressor_temperature_(TR1),sensor.heatpump_hptr1,9,0,1/10,6,1
"Hybrid Manager HM200",heatpump,248,hptr3,refrigerant temperature liquid side (condenser output) (TR3),int16 (>=-3199<=3199),C,false,sensor.heatpump_refrigerant_temperature_liquid_side_(condenser_output)_(TR3),sensor.heatpump_hptr3,9,0,1/10,7,1
"Hybrid Manager HM200",heatpump,248,hptr4,evaporator inlet temperature (TR4),int16 (>=-3199<=3199),C,false,sensor.heatpump_evaporator_inlet_temperature_(TR4),sensor.heatpump_hptr4,9,0,1/10,8,1
"Hybrid Manager HM200",heatpump,248,hptr5,compressor inlet temperature (TR5),int16 (>=-3199<=3199),C,false,sensor.heatpump_compressor_inlet_temperature_(TR5),sensor.heatpump_hptr5,9,0,1/10,9,1
"Hybrid Manager HM200",heatpump,248,hptr6,compressor outlet temperature (TR6),int16 (>=-3199<=3199),C,false,sensor.heatpump_compressor_outlet_temperature_(TR6),sensor.heatpump_hptr6,9,0,1/10,10,1
"Hybrid Manager HM200",heatpump,248,hptl2,air inlet temperature (TL2),int16 (>=-3199<=3199),C,false,sensor.heatpump_air_inlet_temperature_(TL2),sensor.heatpump_hptl2,9,0,1/10,11,1
"Hybrid Manager HM200",heatpump,248,hppl1,low pressure side temperature (PL1),int16 (>=-3199<=3199),C,false,sensor.heatpump_low_pressure_side_temperature_(PL1),sensor.heatpump_hppl1,9,0,1/10,12,1
"Hybrid Manager HM200",heatpump,248,hpph1,high pressure side temperature (PH1),int16 (>=-3199<=3199),C,false,sensor.heatpump_high_pressure_side_temperature_(PH1),sensor.heatpump_hpph1,9,0,1/10,13,1
"Hybrid Manager HM200",heatpump,248,heatingpumpmod,heating pump modulation,uint8 (>=0<=100),%,false,sensor.heatpump_heating_pump_modulation,sensor.heatpump_heatingpumpmod,9,0,1,14,1
"Hybrid Manager HM200",heatpump,248,hpcompspd,compressor speed,uint8 (>=0<=100),%,false,sensor.heatpump_compressor_speed,sensor.heatpump_hpcompspd,9,0,1,15,1
"Hybrid Manager HM200",heatpump,248,hybridstrategy,hybrid control strategy,enum [cost optimized\|co2 optimized\|outside temperature alt.\|outside temperature parallel\|heatpump preferred\|boiler only], ,true,select.heatpump_hybrid_control_strategy,select.heatpump_hybridstrategy,9,0,1,16,1
"Hybrid Manager HM200",heatpump,248,lownoisemode,low noise mode,enum [off\|reduced output\|switch off hp\|perm. reduced], ,true,select.heatpump_low_noise_mode,select.heatpump_lownoisemode,9,0,1,17,1
"Hybrid Manager HM200",heatpump,248,lownoisestart,low noise starttime,uint8 (>=0<=23),hours,true,number.heatpump_low_noise_starttime,number.heatpump_lownoisestart,9,0,1,18,1
"Hybrid Manager HM200",heatpump,248,lownoisestop,low noise stoptime,uint8 (>=0<=23),hours,true,number.heatpump_low_noise_stoptime,number.heatpump_lownoisestop,9,0,1,19,1
"Hybrid Manager HM200",heatpump,248,hybriddhw,hybrid DHW,enum [eco\|high comfort], ,true,select.heatpump_dhw_hybrid_DHW,select.heatpump_dhw_hybriddhw,9,9,1,0,1
"Hybrid Manager HM200",heatpump,248,energypricegas,energy price gas,uint8 (>=0<=254),ct/kWh,true,number.heatpump_energy_price_gas,number.heatpump_energypricegas,9,0,1,20,1
"Hybrid Manager HM200",heatpump,248,energypriceel,energy price electric,uint8 (>=0<=254),ct/kWh,true,number.heatpump_energy_price_electric,number.heatpump_energypriceel,9,0,1,21,1
"Hybrid Manager HM200",heatpump,248,energyfeedpv,feed in PV,uint8 (>=0<=254),ct/kWh,true,number.heatpump_feed_in_PV,number.heatpump_energyfeedpv,9,0,1,22,1
"Hybrid Manager HM200",heatpump,248,switchovertemp,outside switchover temperature,int8 (>=-126<=126),C,true,number.heatpump_outside_switchover_temperature,number.heatpump_switchovertemp,9,0,1,23,1
"Hybrid Manager HM200",heatpump,248,airpurgemode,air purge mode,boolean, ,true,switch.heatpump_air_purge_mode,switch.heatpump_airpurgemode,9,0,1,24,1
"Hybrid Manager HM200",heatpump,248,heatpumpoutput,heatpump output,uint8 (>=0<=100),%,true,number.heatpump_heatpump_output,number.heatpump_heatpumpoutput,9,0,1,25,1
"Hybrid Manager HM200",heatpump,248,coolingcircuit,cooling circuit,boolean, ,true,switch.heatpump_cooling_circuit,switch.heatpump_coolingcircuit,9,0,1,26,1
"Hybrid Manager HM200",heatpump,248,compstartmod,compressor start modulation,uint8 (>=0<=100),%,true,number.heatpump_compressor_start_modulation,number.heatpump_compstartmod,9,0,1,27,1
"Hybrid Manager HM200",heatpump,248,heatdrainpan,heat drain pan,boolean, ,true,switch.heatpump_heat_drain_pan,switch.heatpump_heatdrainpan,9,0,1,28,1
"Hybrid Manager HM200",heatpump,248,heatcable,heating cable,boolean, ,true,switch.heatpump_heating_cable,switch.heatpump_heatcable,9,0,1,29,1
"Hybrid Manager HM200",heatpump,248,nrgtotal,total energy,uint24 (>=0<=167772),kWh,false,sensor.heatpump_total_energy,sensor.heatpump_nrgtotal,9,0,1/100,30,2
"Hybrid Manager HM200",heatpump,248,nrg,energy,uint24 (>=0<=167772),kWh,false,sensor.heatpump_dhw_energy,sensor.heatpump_dhw_nrg,9,9,1/100,1,2
"Hybrid Manager HM200",heatpump,248,nrgheat,energy heating,uint24 (>=0<=167772),kWh,false,sensor.heatpump_energy_heating,sensor.heatpump_nrgheat,9,0,1/100,32,2
"Hybrid Manager HM200",heatpump,248,metertotal,meter total,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_total,sensor.heatpump_metertotal,9,0,1/100,34,2
"Hybrid Manager HM200",heatpump,248,metercomp,meter compressor,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_compressor,sensor.heatpump_metercomp,9,0,1/100,36,2
"Hybrid Manager HM200",heatpump,248,metereheat,meter e-heater,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_e-heater,sensor.heatpump_metereheat,9,0,1/100,38,2
"Hybrid Manager HM200",heatpump,248,meterheat,meter heating,uint24 (>=0<=167772),kWh,false,sensor.heatpump_meter_heating,sensor.heatpump_meterheat,9,0,1/100,40,2
"Hybrid Manager HM200",heatpump,248,meter,meter,uint24 (>=0<=167772),kWh,false,sensor.heatpump_dhw_meter,sensor.heatpump_dhw_meter,9,9,1/100,3,2
"Hybrid Manager HM200",heatpump,248,heatingstarts,heating control starts,uint24 (>=0<=16777213), ,false,sensor.heatpump_heating_control_starts,sensor.heatpump_heatingstarts,9,0,1,42,2
"Hybrid Manager HM200",heatpump,248,startshp,starts hp,uint24 (>=0<=16777213), ,false,sensor.heatpump_dhw_starts_hp,sensor.heatpump_dhw_startshp,9,9,1,5,2
"Hybrid Manager HM200",heatpump,248,fuelheat,fuel consuption heating,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_fuel_consuption_heating,sensor.heatpump_fuelheat,9,0,1/10,44,2
"Hybrid Manager HM200",heatpump,248,fueldhw,fuel consuption,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_dhw_fuel_consuption,sensor.heatpump_dhw_fueldhw,9,9,1/10,7,2
"Hybrid Manager HM200",heatpump,248,elheat,el. consuption heating,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_el._consuption_heating,sensor.heatpump_elheat,9,0,1/10,46,2
"Hybrid Manager HM200",heatpump,248,eldhw,el consuption,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_dhw_el_consuption,sensor.heatpump_dhw_eldhw,9,9,1/10,9,2
"Hybrid Manager HM200",heatpump,248,elgenheat,el. generation heating,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_el._generation_heating,sensor.heatpump_elgenheat,9,0,1/10,48,2
"Hybrid Manager HM200",heatpump,248,elgendhw,el generation,uint32 (>=0<=1677721),kWh,false,sensor.heatpump_dhw_el_generation,sensor.heatpump_dhw_elgendhw,9,9,1/10,11,2
"WM10",switch,71,activated,activated,boolean, ,false,binary_sensor.switch_activated,binary_sensor.switch_activated,11,0,1,0,1
"WM10",switch,71,flowtemphc,flow temperature (TC1),uint16 (>=0<=3199),C,false,sensor.switch_flow_temperature_(TC1),sensor.switch_flowtemphc,11,0,1/10,1,1
"WM10",switch,71,status,status,int8 (>=-126<=126), ,false,sensor.switch_status,sensor.switch_status,11,0,1,2,1
"Rego 3000",controller,240,datetime,date/time,string, ,false,sensor.controller_date/time,sensor.controller_datetime,12,0,1,0,13
"EM10",alert,74,setflowtemp,set flow temperature,uint8 (>=0<=254),C,false,sensor.alert_set_flow_temperature,sensor.alert_setflowtemp,14,0,1,0,1
"EM10",alert,74,setburnpow,burner set power,uint8 (>=0<=100),%,false,sensor.alert_burner_set_power,sensor.alert_setburnpow,14,0,1,1,1
"EM10, EM100",extension,243,flowtempvf,flow temperature in header (T0/Vf),int16 (>=-3199<=3199),C,false,sensor.extension_flow_temperature_in_header_(T0/Vf),sensor.extension_flowtempvf,15,0,1/10,0,1
"EM10, EM100",extension,243,input,input,uint8 (>=0<=25),V,false,sensor.extension_input,sensor.extension_input,15,0,1/10,1,1
"EM10, EM100",extension,243,outpow,output IO1,uint8 (>=0<=100),%,false,sensor.extension_output_IO1,sensor.extension_outpow,15,0,1,2,1
"EM10, EM100",extension,243,setpower,request power,uint8 (>=0<=100),%,false,sensor.extension_request_power,sensor.extension_setpower,15,0,1,3,1
"EM10, EM100",extension,243,setpoint,set temp.,uint8 (>=0<=254),C,false,sensor.extension_set_temp.,sensor.extension_setpoint,15,0,1,4,1
"EM10, EM100",extension,243,minv,min volt.,uint8 (>=0<=25),V,true,number.extension_min_volt.,number.extension_minv,15,0,1/10,5,1
"EM10, EM100",extension,243,maxv,max volt.,uint8 (>=0<=25),V,true,number.extension_max_volt.,number.extension_maxv,15,0,1/10,6,1
"EM10, EM100",extension,243,mint,min temp.,uint8 (>=0<=254),C,true,number.extension_min_temp.,number.extension_mint,15,0,1,7,1
"EM10, EM100",extension,243,maxt,max temp.,uint8 (>=0<=254),C,true,number.extension_max_temp.,number.extension_maxt,15,0,1,8,1
"EM10, EM100",extension,243,mode,operating mode,uint8 (>=0<=254), ,false,sensor.extension_operating_mode,sensor.extension_mode,15,0,1,9,1
"T1RF",extension,220,flowtempvf,flow temperature in header (T0/Vf),int16 (>=-3199<=3199),C,false,sensor.extension_flow_temperature_in_header_(T0/Vf),sensor.extension_flowtempvf,15,0,1/10,0,1
"T1RF",extension,220,input,input,uint8 (>=0<=25),V,false,sensor.extension_input,sensor.extension_input,15,0,1/10,1,1
"T1RF",extension,220,outpow,output IO1,uint8 (>=0<=100),%,false,sensor.extension_output_IO1,sensor.extension_outpow,15,0,1,2,1
"T1RF",extension,220,setpower,request power,uint8 (>=0<=100),%,false,sensor.extension_request_power,sensor.extension_setpower,15,0,1,3,1
"T1RF",extension,220,setpoint,set temp.,uint8 (>=0<=254),C,false,sensor.extension_set_temp.,sensor.extension_setpoint,15,0,1,4,1
"T1RF",extension,220,minv,min volt.,uint8 (>=0<=25),V,true,number.extension_min_volt.,number.extension_minv,15,0,1/10,5,1
"T1RF",extension,220,maxv,max volt.,uint8 (>=0<=25),V,true,number.extension_max_volt.,number.extension_maxv,15,0,1/10,6,1
"T1RF",extension,220,mint,min temp.,uint8 (>=0<=254),C,true,number.extension_min_temp.,number.extension_mint,15,0,1,7,1
"T1RF",extension,220,maxt,max temp.,uint8 (>=0<=254),C,true,number.extension_max_temp.,number.extension_maxt,15,0,1,8,1
"T1RF",extension,220,mode,operating mode,uint8 (>=0<=254), ,false,sensor.extension_operating_mode,sensor.extension_mode,15,0,1,9,1
"Logavent HRV176",ventilation,231,outfresh,outdoor fresh air,int16 (>=-3199<=3199),C,false,sensor.ventilation_outdoor_fresh_air,sensor.ventilation_outfresh,18,0,1/10,0,1
"Logavent HRV176",ventilation,231,infresh,indoor fresh air,int16 (>=-3199<=3199),C,false,sensor.ventilation_indoor_fresh_air,sensor.ventilation_infresh,18,0,1/10,1,1
"Logavent HRV176",ventilation,231,outexhaust,outdoor exhaust air,int16 (>=-3199<=3199),C,false,sensor.ventilation_outdoor_exhaust_air,sensor.ventilation_outexhaust,18,0,1/10,2,1
"Logavent HRV176",ventilation,231,inexhaust,indoor exhaust air,int16 (>=-3199<=3199),C,false,sensor.ventilation_indoor_exhaust_air,sensor.ventilation_inexhaust,18,0,1/10,3,1
"Logavent HRV176",ventilation,231,ventinspeed,in blower speed,uint8 (>=0<=100),%,false,sensor.ventilation_in_blower_speed,sensor.ventilation_ventinspeed,18,0,1,4,1
"Logavent HRV176",ventilation,231,ventoutspeed,out blower speed,uint8 (>=0<=100),%,false,sensor.ventilation_out_blower_speed,sensor.ventilation_ventoutspeed,18,0,1,5,1
"Logavent HRV176",ventilation,231,ventmode,ventilation mode,enum [auto\|off\|L1\|L2\|L3\|L4\|demand\|sleep\|intense\|bypass\|party\|fireplace], ,true,select.ventilation_ventilation_mode,select.ventilation_ventmode,18,0,1,6,1
"Logavent HRV176",ventilation,231,airquality,air quality (voc),uint16 (>=0<=31999), ,false,sensor.ventilation_air_quality_(voc),sensor.ventilation_airquality,18,0,1,7,1
"Logavent HRV176",ventilation,231,airhumidity,relative air humidity,uint8 (>=0<=100),%,false,sensor.ventilation_relative_air_humidity,sensor.ventilation_airhumidity,18,0,1,8,1
"IPM",water,100,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.water_dhw_selected_temperature,number.water_dhw_seltemp,19,9,1,0,1
"IPM",water,100,temp,current temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_temperature,sensor.water_dhw_temp,19,9,1/10,1,1
"IPM",water,100,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_extern_temperature,sensor.water_dhw_curtemp2,19,9,1/10,2,1
"IPM",water,100,hydrTemp,hydraulic header temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_hydraulic_header_temperature,sensor.water_dhw_hydrTemp,19,9,1/10,3,1
"IPM",water,100,pump,pump,boolean, ,false,binary_sensor.water_dhw_pump,binary_sensor.water_dhw_pump,19,9,1,4,1
"IPM",water,100,flowtempoffset,flow temperature offset,uint8 (>=0<=254),C,true,number.water_dhw_flow_temperature_offset,number.water_dhw_flowtempoffset,19,9,1,5,1
"IPM",water,100,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.water_dhw_hysteresis_on_temperature,number.water_dhw_hyston,19,9,1,6,1
"IPM",water,100,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.water_dhw_hysteresis_off_temperature,number.water_dhw_hystoff,19,9,1,7,1
"IPM",water,100,disinfectiontemp,disinfection temperature,uint8 (>=0<=254),C,true,number.water_dhw_disinfection_temperature,number.water_dhw_disinfectiontemp,19,9,1,8,1
"IPM",water,100,circ,circulation active,boolean, ,true,switch.water_dhw_circulation_active,switch.water_dhw_circ,19,9,1,9,1
"IPM",water,100,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.water_dhw_circulation_pump_mode,select.water_dhw_circmode,19,9,1,10,1
"IPM2",water,102,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.water_dhw_selected_temperature,number.water_dhw_seltemp,19,9,1,0,1
"IPM2",water,102,temp,current temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_temperature,sensor.water_dhw_temp,19,9,1/10,1,1
"IPM2",water,102,curtemp2,current extern temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_extern_temperature,sensor.water_dhw_curtemp2,19,9,1/10,2,1
"IPM2",water,102,hydrTemp,hydraulic header temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_hydraulic_header_temperature,sensor.water_dhw_hydrTemp,19,9,1/10,3,1
"IPM2",water,102,pump,pump,boolean, ,false,binary_sensor.water_dhw_pump,binary_sensor.water_dhw_pump,19,9,1,4,1
"IPM2",water,102,flowtempoffset,flow temperature offset,uint8 (>=0<=254),C,true,number.water_dhw_flow_temperature_offset,number.water_dhw_flowtempoffset,19,9,1,5,1
"IPM2",water,102,hyston,hysteresis on temperature,int8 (>=-126<=126),C,true,number.water_dhw_hysteresis_on_temperature,number.water_dhw_hyston,19,9,1,6,1
"IPM2",water,102,hystoff,hysteresis off temperature,int8 (>=-126<=126),C,true,number.water_dhw_hysteresis_off_temperature,number.water_dhw_hystoff,19,9,1,7,1
"IPM2",water,102,disinfectiontemp,disinfection temperature,uint8 (>=0<=254),C,true,number.water_dhw_disinfection_temperature,number.water_dhw_disinfectiontemp,19,9,1,8,1
"IPM2",water,102,circ,circulation active,boolean, ,true,switch.water_dhw_circulation_active,switch.water_dhw_circ,19,9,1,9,1
"IPM2",water,102,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.water_dhw_circulation_pump_mode,select.water_dhw_circmode,19,9,1,10,1
"MM100",water,160,temp,current temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_temperature,sensor.water_dhw_temp,19,9,1/10,1,1
"MM100",water,160,tempstatus,temperature switch in assigned dhw (MC1),int8 (>=-126<=126), ,false,sensor.water_dhw_temperature_switch_in_assigned_dhw_(MC1),sensor.water_dhw_tempstatus,19,9,1,11,1
"MM100",water,160,pump,pump,boolean, ,false,binary_sensor.water_dhw_pump,binary_sensor.water_dhw_pump,19,9,1,4,1
"MM100",water,160,maxtemp,maximum temperature,uint8 (>=0<=254),C,true,number.water_dhw_maximum_temperature,number.water_dhw_maxtemp,19,9,1,12,1
"MM100",water,160,difftemp,start differential temperature,int8 (>=-126<=126),C,true,number.water_dhw_start_differential_temperature,number.water_dhw_difftemp,19,9,1,13,1
"MM100",water,160,disinfectiontemp,disinfection temperature,uint8 (>=0<=254),C,true,number.water_dhw_disinfection_temperature,number.water_dhw_disinfectiontemp,19,9,1,8,1
"MM100",water,160,redtemp,reduced temperature,uint8 (>=0<=254),C,true,number.water_dhw_reduced_temperature,number.water_dhw_redtemp,19,9,1,14,1
"MM100",water,160,requiredtemp,required temperature,uint8 (>=0<=254),C,true,number.water_dhw_required_temperature,number.water_dhw_requiredtemp,19,9,1,15,1
"MM100",water,160,circ,circulation active,boolean, ,true,switch.water_dhw_circulation_active,switch.water_dhw_circ,19,9,1,9,1
"MM100",water,160,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.water_dhw_circulation_pump_mode,select.water_dhw_circmode,19,9,1,10,1
"MM200",water,161,temp,current temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_temperature,sensor.water_dhw_temp,19,9,1/10,1,1
"MM200",water,161,tempstatus,temperature switch in assigned dhw (MC1),int8 (>=-126<=126), ,false,sensor.water_dhw_temperature_switch_in_assigned_dhw_(MC1),sensor.water_dhw_tempstatus,19,9,1,11,1
"MM200",water,161,pump,pump,boolean, ,false,binary_sensor.water_dhw_pump,binary_sensor.water_dhw_pump,19,9,1,4,1
"MM200",water,161,maxtemp,maximum temperature,uint8 (>=0<=254),C,true,number.water_dhw_maximum_temperature,number.water_dhw_maxtemp,19,9,1,12,1
"MM200",water,161,difftemp,start differential temperature,int8 (>=-126<=126),C,true,number.water_dhw_start_differential_temperature,number.water_dhw_difftemp,19,9,1,13,1
"MM200",water,161,disinfectiontemp,disinfection temperature,uint8 (>=0<=254),C,true,number.water_dhw_disinfection_temperature,number.water_dhw_disinfectiontemp,19,9,1,8,1
"MM200",water,161,redtemp,reduced temperature,uint8 (>=0<=254),C,true,number.water_dhw_reduced_temperature,number.water_dhw_redtemp,19,9,1,14,1
"MM200",water,161,requiredtemp,required temperature,uint8 (>=0<=254),C,true,number.water_dhw_required_temperature,number.water_dhw_requiredtemp,19,9,1,15,1
"MM200",water,161,circ,circulation active,boolean, ,true,switch.water_dhw_circulation_active,switch.water_dhw_circ,19,9,1,9,1
"MM200",water,161,circmode,circulation pump mode,enum [off\|on\|auto\|own prog], ,true,select.water_dhw_circulation_pump_mode,select.water_dhw_circmode,19,9,1,10,1
"SM100, MS100",water,163,temp,current temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_temperature,sensor.water_dhw_temp,19,9,1/10,1,1
"SM100, MS100",water,163,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_storage_intern_temperature,sensor.water_dhw_storagetemp1,19,9,1/10,16,1
"SM100, MS100",water,163,coldtemp,cold water,uint16 (>=0<=3199),C,false,sensor.water_dhw_cold_water,sensor.water_dhw_coldtemp,19,9,1/10,17,1
"SM100, MS100",water,163,temp5,temperature 5,uint16 (>=0<=3199),C,false,sensor.water_dhw_temperature_5,sensor.water_dhw_temp5,19,9,1/10,18,1
"SM100, MS100",water,163,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_return_temperature,sensor.water_dhw_rettemp,19,9,1/10,19,1
"SM100, MS100",water,163,pump,pump,boolean, ,false,binary_sensor.water_dhw_pump,binary_sensor.water_dhw_pump,19,9,1,4,1
"SM100, MS100",water,163,maxtemp,maximum temperature,uint8 (>=0<=254),C,true,number.water_dhw_maximum_temperature,number.water_dhw_maxtemp,19,9,1,12,1
"SM100, MS100",water,163,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.water_dhw_selected_temperature,number.water_dhw_seltemp,19,9,1,0,1
"SM100, MS100",water,163,redtemp,reduced temperature,uint8 (>=0<=254),C,true,number.water_dhw_reduced_temperature,number.water_dhw_redtemp,19,9,1,14,1
"SM100, MS100",water,163,hottemp,extra hot temperature,uint8 (>=0<=254),C,true,number.water_dhw_extra_hot_temperature,number.water_dhw_hottemp,19,9,1,20,1
"SM100, MS100",water,163,dailytemp,daily temperature,uint8 (>=0<=254),C,true,number.water_dhw_daily_temperature,number.water_dhw_dailytemp,19,9,1,21,1
"SM100, MS100",water,163,disinfectiontemp,disinfection temperature,uint8 (>=0<=254),C,true,number.water_dhw_disinfection_temperature,number.water_dhw_disinfectiontemp,19,9,1,8,1
"SM100, MS100",water,163,circ,circulation active,boolean, ,true,switch.water_dhw_circulation_active,switch.water_dhw_circ,19,9,1,9,1
"SM100, MS100",water,163,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.water_dhw_circulation_pump_mode,select.water_dhw_circmode,19,9,1,10,1
"SM100, MS100",water,163,circtc,circulation time controled,boolean, ,true,switch.water_dhw_circulation_time_controled,switch.water_dhw_circtc,19,9,1,22,1
"SM100, MS100",water,163,keepwarm,keep warm,boolean, ,true,switch.water_dhw_keep_warm,switch.water_dhw_keepwarm,19,9,1,23,1
"SM100, MS100",water,163,status2,status 2,enum [\|\|\|no heat\|\|\|heat request\|\|disinfecting\|hold], ,false,sensor.water_dhw_status_2,sensor.water_dhw_status2,19,9,1,24,1
"SM100, MS100",water,163,pumpmod,pump modulation,uint8 (>=0<=100),%,false,sensor.water_dhw_pump_modulation,sensor.water_dhw_pumpmod,19,9,1,25,1
"SM100, MS100",water,163,flow,flow rate,uint16 (>=0<=3199),l/min,false,sensor.water_dhw_flow_rate,sensor.water_dhw_flow,19,9,1/10,26,1
"SM100, MS100",water,163,valvereturn,return valve,uint8 (>=0<=100),%,true,number.water_dhw_return_valve,number.water_dhw_valvereturn,19,9,1,27,1
"SM100, MS100",water,163,deltatret,temp. diff. return valve,uint8 (>=0<=254),K,true,number.water_dhw_temp._diff._return_valve,number.water_dhw_deltatret,19,9,1,28,1
"SM100, MS100",water,163,errordisp,error display,enum [off\|normal\|inverted], ,true,select.water_dhw_error_display,select.water_dhw_errordisp,19,9,1,29,1
"SM200, MS200",water,164,temp,current temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_current_temperature,sensor.water_dhw_temp,19,9,1/10,1,1
"SM200, MS200",water,164,storagetemp1,storage intern temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_storage_intern_temperature,sensor.water_dhw_storagetemp1,19,9,1/10,16,1
"SM200, MS200",water,164,coldtemp,cold water,uint16 (>=0<=3199),C,false,sensor.water_dhw_cold_water,sensor.water_dhw_coldtemp,19,9,1/10,17,1
"SM200, MS200",water,164,temp5,temperature 5,uint16 (>=0<=3199),C,false,sensor.water_dhw_temperature_5,sensor.water_dhw_temp5,19,9,1/10,18,1
"SM200, MS200",water,164,rettemp,return temperature,uint16 (>=0<=3199),C,false,sensor.water_dhw_return_temperature,sensor.water_dhw_rettemp,19,9,1/10,19,1
"SM200, MS200",water,164,pump,pump,boolean, ,false,binary_sensor.water_dhw_pump,binary_sensor.water_dhw_pump,19,9,1,4,1
"SM200, MS200",water,164,maxtemp,maximum temperature,uint8 (>=0<=254),C,true,number.water_dhw_maximum_temperature,number.water_dhw_maxtemp,19,9,1,12,1
"SM200, MS200",water,164,seltemp,selected temperature,uint8 (>=0<=254),C,true,number.water_dhw_selected_temperature,number.water_dhw_seltemp,19,9,1,0,1
"SM200, MS200",water,164,redtemp,reduced temperature,uint8 (>=0<=254),C,true,number.water_dhw_reduced_temperature,number.water_dhw_redtemp,19,9,1,14,1
"SM200, MS200",water,164,hottemp,extra hot temperature,uint8 (>=0<=254),C,true,number.water_dhw_extra_hot_temperature,number.water_dhw_hottemp,19,9,1,20,1
"SM200, MS200",water,164,dailytemp,daily temperature,uint8 (>=0<=254),C,true,number.water_dhw_daily_temperature,number.water_dhw_dailytemp,19,9,1,21,1
"SM200, MS200",water,164,disinfectiontemp,disinfection temperature,uint8 (>=0<=254),C,true,number.water_dhw_disinfection_temperature,number.water_dhw_disinfectiontemp,19,9,1,8,1
"SM200, MS200",water,164,circ,circulation active,boolean, ,true,switch.water_dhw_circulation_active,switch.water_dhw_circ,19,9,1,9,1
"SM200, MS200",water,164,circmode,circulation pump mode,enum [off\|1x3min\|2x3min\|3x3min\|4x3min\|5x3min\|6x3min\|continuous], ,true,select.water_dhw_circulation_pump_mode,select.water_dhw_circmode,19,9,1,10,1
"SM200, MS200",water,164,circtc,circulation time controled,boolean, ,true,switch.water_dhw_circulation_time_controled,switch.water_dhw_circtc,19,9,1,22,1
"SM200, MS200",water,164,keepwarm,keep warm,boolean, ,true,switch.water_dhw_keep_warm,switch.water_dhw_keepwarm,19,9,1,23,1
"SM200, MS200",water,164,status2,status 2,enum [\|\|\|no heat\|\|\|heat request\|\|disinfecting\|hold], ,false,sensor.water_dhw_status_2,sensor.water_dhw_status2,19,9,1,24,1
"SM200, MS200",water,164,pumpmod,pump modulation,uint8 (>=0<=100),%,false,sensor.water_dhw_pump_modulation,sensor.water_dhw_pumpmod,19,9,1,25,1
"SM200, MS200",water,164,flow,flow rate,uint16 (>=0<=3199),l/min,false,sensor.water_dhw_flow_rate,sensor.water_dhw_flow,19,9,1/10,26,1
"SM200, MS200",water,164,valvereturn,return valve,uint8 (>=0<=100),%,true,number.water_dhw_return_valve,number.water_dhw_valvereturn,19,9,1,27,1
"SM200, MS200",water,164,deltatret,temp. diff. return valve,uint8 (>=0<=254),K,true,number.water_dhw_temp._diff._return_valve,number.water_dhw_deltatret,19,9,1,28,1
"SM200, MS200",water,164,errordisp,error display,enum [off\|normal\|inverted], ,true,select.water_dhw_error_display,select.water_dhw_errordisp,19,9,1,29,1
"MP100",pool,204,pooltemp,pool temperature,int16 (>=-3199<=3199),C,false,sensor.pool_pool_temperature,sensor.pool_pooltemp,20,0,1/10,-1,1
"MP100",pool,204,poolshuntstatus,pool shunt status opening/closing,enum [stopped\|opening\|closing\|open\|close], ,false,sensor.pool_pool_shunt_status_opening/closing,sensor.pool_poolshuntstatus,20,0,1,-1,1
"MP100",pool,204,poolshunt,pool shunt open/close (0% = pool / 100% = heat),uint8 (>=0<=100),%,false,sensor.pool_pool_shunt_open/close_(0%_=_pool_/_100%_=_heat),sensor.pool_poolshunt,20,0,1,-1,1
